[Federal Register Volume 89, Number 170 (Tuesday, September 3, 2024)]
[Notices]
[Pages 71433-71443]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2024-19687]


-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION

[NRC-2024-0150]


Monthly Notice; Applications and Amendments to Facility Operating 
Licenses and Combined Licenses Involving No Significant Hazards 
Considerations

AGENCY: Nuclear Regulatory Commission.

ACTION: Monthly notice.

-----------------------------------------------------------------------

SUMMARY: Pursuant to section 189a.(2) of the Atomic Energy Act of 1954, 
as amended (the Act), the U.S. Nuclear Regulatory Commission (NRC) is 
publishing this regular monthly notice. The Act requires the Commission 
to publish notice of any amendments issued, or proposed to be issued, 
and grants the Commission the authority to issue and make immediately 
effective any amendment to an operating license or combined license, as 
applicable, upon a determination by the Commission that such amendment 
involves no significant hazards consideration (NSHC), notwithstanding 
the pendency before the Commission of a request for a hearing from any 
person.

DATES: Comments must be filed by October 3, 2024. A request for a 
hearing or petitions for leave to intervene must be filed by November 
4, 2024. This monthly notice includes all amendments issued, or 
proposed to be issued, from July 19, 2024, to August 15, 2024. The last 
monthly notice was published on August 6, 2024.

ADDRESSES: You may submit comments by any of the following methods; 
however, the NRC encourages electronic comment submission through the 
Federal rulemaking website.
     Federal rulemaking website: Go to https://www.regulations.gov and search for Docket ID NRC-2024-0150. Address 
questions about Docket IDs in Regulations.gov to Stacy Schumann; 
telephone: 301-415-0624; email: [email protected]. For technical 
questions, contact the individual listed in the For Further Information 
Contact section of this document.
     Mail comments to: Office of Administration, Mail Stop: 
TWFN-7-A60M, U.S. Nuclear Regulatory Commission, Washington, DC 20555-
0001, ATTN: Program Management, Announcements and Editing Staff.
    For additional direction on obtaining information and submitting 
comments, see ``Obtaining Information and Submitting Comments'' in the 
SUPPLEMENTARY INFORMATION section of this document.

FOR FURTHER INFORMATION CONTACT: Karen Zeleznock, Office of Nuclear 
Reactor Regulation, U.S. Nuclear Regulatory Commission, Washington, DC 
20555-0001; telephone: 301-415-1118; email: [email protected].

SUPPLEMENTARY INFORMATION:

I. Obtaining Information and Submitting Comments

A. Obtaining Information

    Please refer to Docket ID NRC-2024-0150, facility name, unit 
number(s), docket number(s), application date, and subject when 
contacting the NRC about the availability of information for this 
action. You may obtain publicly available information related to this 
action by any of the following methods:
     Federal Rulemaking Website: Go to https://www.regulations.gov and search for Docket ID NRC-2024-0150.
     NRC's Agencywide Documents Access and Management System 
(ADAMS): You may obtain publicly available documents online in the 
ADAMS Public Documents collection at https://www.nrc.gov/reading-rm/adams.html. To begin the search, select ``Begin Web-based ADAMS 
Search.'' For problems with ADAMS, please contact the NRC's Public 
Document Room (PDR) reference staff at 1-800-397-4209, at 301-415-4737, 
or by email to [email protected]. The ADAMS accession number for 
each document referenced (if it is available in ADAMS) is provided the 
first time that it is mentioned in this document.
     NRC's PDR: The PDR, where you may examine and order copies 
of publicly available documents, is open by appointment. To make an 
appointment to visit the PDR, please send an email to 
[email protected]

[[Page 71434]]

or call 1-800-397-4209 or 301-415-4737, between 8 a.m. and 4 p.m. 
eastern time (ET), Monday through Friday, except Federal holidays.

B. Submitting Comments

    The NRC encourages electronic comment submission through the 
Federal rulemaking website (https://www.regulations.gov). Please 
include Docket ID NRC-2024-0150, facility name, unit number(s), docket 
number(s), application date, and subject, in your comment submission.
    The NRC cautions you not to include identifying or contact 
information that you do not want to be publicly disclosed in your 
comment submission. The NRC will post all comment submissions at 
https://www.regulations.gov as well as enter the comment submissions 
into ADAMS. The NRC does not routinely edit comment submissions to 
remove identifying or contact information.
    If you are requesting or aggregating comments from other persons 
for submission to the NRC, then you should inform those persons not to 
include identifying or contact information that they do not want to be 
publicly disclosed in their comment submission. Your request should 
state that the NRC does not routinely edit comment submissions to 
remove such information before making the comment submissions available 
to the public or entering the comment into ADAMS.

II. Notice of Consideration of Issuance of Amendments to Facility 
Operating Licenses and Combined Licenses and Proposed No Significant 
Hazards Consideration Determination

    For the facility-specific amendment requests shown in this notice, 
the Commission finds that the licensees' analyses provided, consistent 
with section 50.91 of title 10 of the Code of Federal Regulations (10 
CFR) ``Notice for public comment; State consultation,'' are sufficient 
to support the proposed determinations that these amendment requests 
involve NSHC. Under the Commission's regulations in 10 CFR 50.92, 
operation of the facilities in accordance with the proposed amendments 
would not (1) involve a significant increase in the probability or 
consequences of an accident previously evaluated; or (2) create the 
possibility of a new or different kind of accident from any accident 
previously evaluated; or (3) involve a significant reduction in a 
margin of safety.
    The Commission is seeking public comments on these proposed 
determinations. Any comments received within 30 days after the date of 
publication of this notice will be considered in making any final 
determinations.
    Normally, the Commission will not issue the amendments until the 
expiration of 60 days after the date of publication of this notice. The 
Commission may issue any of these license amendments before expiration 
of the 60-day period provided that its final determination is that the 
amendment involves NSHC. In addition, the Commission may issue any of 
these amendments prior to the expiration of the 30-day comment period 
if circumstances change during the 30-day comment period such that 
failure to act in a timely way would result, for example in derating or 
shutdown of the facility. If the Commission takes action on any of 
these amendments prior to the expiration of either the comment period 
or the notice period, it will publish in the Federal Register a notice 
of issuance. If the Commission makes a final NSHC determination for any 
of these amendments, any hearing will take place after issuance. The 
Commission expects that the need to take action on any amendment before 
60 days have elapsed will occur very infrequently.

A. Opportunity To Request a Hearing and Petition for Leave To Intervene

    Within 60 days after the date of publication of this notice, any 
person (petitioner) whose interest may be affected by any of these 
actions may file a request for a hearing and petition for leave to 
intervene (petition) with respect to that action. Petitions shall be 
filed in accordance with the Commission's ``Agency Rules of Practice 
and Procedure'' in 10 CFR part 2. Interested persons should consult a 
current copy of 10 CFR 2.309. If a petition is filed, the Commission or 
a presiding officer will rule on the petition and, if appropriate, a 
notice of a hearing will be issued.
    Petitions must be filed no later than 60 days from the date of 
publication of this notice in accordance with the filing instructions 
in the ``Electronic Submissions (E-Filing)'' section of this document. 
Petitions and motions for leave to file new or amended contentions that 
are filed after the deadline will not be entertained absent a 
determination by the presiding officer that the filing demonstrates 
good cause by satisfying the three factors in 10 CFR 2.309(c)(1)(i) 
through (iii).
    If a hearing is requested, and the Commission has not made a final 
determination on the issue of no significant hazards consideration, the 
Commission will make a final determination on the issue of no 
significant hazards consideration, which will serve to establish when 
the hearing is held. If the final determination is that the amendment 
request involves no significant hazards consideration, the Commission 
may issue the amendment and make it immediately effective, 
notwithstanding the request for a hearing. Any hearing would take place 
after issuance of the amendment. If the final determination is that the 
amendment request involves a significant hazards consideration, then 
any hearing held would take place before the issuance of the amendment 
unless the Commission finds an imminent danger to the health or safety 
of the public, in which case it will issue an appropriate order or rule 
under 10 CFR part 2.
    A State, local governmental body, Federally recognized Indian 
Tribe, or designated agency thereof, may submit a petition to the 
Commission to participate as a party under 10 CFR 2.309(h) no later 
than 60 days from the date of publication of this notice. 
Alternatively, a State, local governmental body, Federally recognized 
Indian Tribe, or agency thereof may participate as a non-party under 10 
CFR 2.315(c).
    For information about filing a petition and about participation by 
a person not a party under 10 CFR 2.315, see ADAMS Accession No. 
ML20340A053 (https://adamswebsearch2.nrc.gov/webSearch2/main.jsp?AccessionNumber=ML20340A053) and on the NRC's public website 
at https://www.nrc.gov/about-nrc/regulatory/adjudicatory/hearing.html#participate.

B. Electronic Submissions (E-Filing)

    All documents filed in NRC adjudicatory proceedings, including 
documents filed by an interested State, local governmental body, 
Federally recognized Indian Tribe, or designated agency thereof that 
requests to participate under 10 CFR 2.315(c), must be filed in 
accordance with 10 CFR 2.302. The E-Filing process requires 
participants to submit and serve all adjudicatory documents over the 
internet, or in some cases, to mail copies on electronic storage media, 
unless an exemption permitting an alternative filing method, as further 
discussed, is granted. Detailed guidance on electronic submissions is 
located in the ``Guidance for Electronic Submissions to the NRC'' 
(ADAMS Accession No. ML13031A056) and on the NRC's public website at 
https://www.nrc.gov/site-help/e-submittals.html.
    To comply with the procedural requirements of E-Filing, at least 10 
days prior to the filing deadline, the

[[Page 71435]]

participant should contact the Office of the Secretary by email at 
[email protected], or by telephone at 301-415-1677, to (1) request 
a digital identification (ID) certificate, which allows the participant 
(or its counsel or representative) to digitally sign submissions and 
access the E-Filing system for any proceeding in which it is 
participating; and (2) advise the Secretary that the participant will 
be submitting a petition or other adjudicatory document (even in 
instances in which the participant, or its counsel or representative, 
already holds an NRC-issued digital ID certificate). Based upon this 
information, the Secretary will establish an electronic docket for the 
proceeding if the Secretary has not already established an electronic 
docket.
    Information about applying for a digital ID certificate is 
available on the NRC's public website at https://www.nrc.gov/site-help/e-submittals/getting-started.html. After a digital ID certificate is 
obtained and a docket created, the participant must submit adjudicatory 
documents in Portable Document Format. Guidance on submissions is 
available on the NRC's public website at https://www.nrc.gov/site-help/electronic-sub-ref-mat.html. A filing is considered complete at the 
time the document is submitted through the NRC's E-Filing system. To be 
timely, an electronic filing must be submitted to the E-Filing system 
no later than 11:59 p.m. ET on the due date. Upon receipt of a 
transmission, the E-Filing system time-stamps the document and sends 
the submitter an email confirming receipt of the document. The E-Filing 
system also distributes an email that provides access to the document 
to the NRC's Office of the General Counsel and any others who have 
advised the Office of the Secretary that they wish to participate in 
the proceeding, so that the filer need not serve the document on those 
participants separately. Therefore, applicants and other participants 
(or their counsel or representative) must apply for and receive a 
digital ID certificate before adjudicatory documents are filed to 
obtain access to the documents via the E-Filing system.
    A person filing electronically using the NRC's adjudicatory E-
Filing system may seek assistance by contacting the NRC's Electronic 
Filing Help Desk through the ``Contact Us'' link located on the NRC's 
public website at https://www.nrc.gov/site-help/e-submittals.html, by 
email to [email protected], or by a toll-free call at 1-866-672-
7640. The NRC Electronic Filing Help Desk is available between 9 a.m. 
and 6 p.m., ET, Monday through Friday, except Federal holidays.
    Participants who believe that they have good cause for not 
submitting documents electronically must file an exemption request, in 
accordance with 10 CFR 2.302(g), with their initial paper filing 
stating why there is good cause for not filing electronically and 
requesting authorization to continue to submit documents in paper 
format. Such filings must be submitted in accordance with 10 CFR 
2.302(b)-(d). Participants filing adjudicatory documents in this manner 
are responsible for serving their documents on all other participants. 
Participants granted an exemption under 10 CFR 2.302(g)(2) must still 
meet the electronic formatting requirement in 10 CFR 2.302(g)(1), 
unless the participant also seeks and is granted an exemption from 10 
CFR 2.302(g)(1).
    Documents submitted in adjudicatory proceedings will appear in the 
NRC's electronic hearing docket, which is publicly available at https://adams.nrc.gov/ehd, unless excluded pursuant to an order of the 
presiding officer. If you do not have an NRC-issued digital ID 
certificate as previously described, click ``cancel'' when the link 
requests certificates and you will be automatically directed to the 
NRC's electronic hearing docket where you will be able to access any 
publicly available documents in a particular hearing docket. 
Participants are requested not to include personal privacy information 
such as social security numbers, home addresses, or personal phone 
numbers in their filings unless an NRC regulation or other law requires 
submission of such information. With respect to copyrighted works, 
except for limited excerpts that serve the purpose of the adjudicatory 
filings and would constitute a Fair Use application, participants 
should not include copyrighted materials in their submission.
    The following table provides the plant name, docket number, date of 
application, ADAMS accession number, and location in the application of 
the licensees' proposed NSHC determinations. For further details with 
respect to these license amendment applications, see the applications 
for amendment, which are available for public inspection in ADAMS. For 
additional direction on accessing information related to this document, 
see the ``Obtaining Information and Submitting Comments'' section of 
this document.

                       License Amendment Requests
------------------------------------------------------------------------
 
------------------------------------------------------------------------
Duke Energy Carolinas, LLC; Catawba Nuclear Station, Units 1 and 2; York
                               County, SC
------------------------------------------------------------------------
Docket Nos...................  50-413, 50-414.
Application date.............  June 18, 2024.
ADAMS Accession No...........  ML24170A696.
Location in Application of     Pages 7-8 of the Enclosure.
 NSHC.
Brief Description of           The proposed amendments would revise
 Amendments.                    Catawba's Units 1 and 2 Technical
                                Specification (TS) 3.4.3, ``RCS Pressure
                                and Temperature (P/T) Limits,'' to
                                reflect an update to the P/T limit
                                curves in Figures 3.4.3-1 (Unit 2 only)
                                and 3.4.3-2 (Unit 2 only). The proposed
                                amendments will also reflect that the
                                revised Catawba Unit 2 P/T limit curves
                                in TS 3.4.3 are applicable until 54
                                effective full power years.
Proposed Determination.......  NSHC.
Name of Attorney for           Tracey Mitchell LeRoy, Deputy General
 Licensee, Mailing Address.     Counsel, Duke Energy Corporation, 525 S
                                Tryon Street, Charlotte, NC 28210.
NRC Project Manager,           Jack Minzer Bryant, 301-415-0610.
 Telephone Number.
------------------------------------------------------------------------
 Entergy Operations, Inc.; Waterford Steam Electric Station, Unit 3; St.
                           Charles Parish, LA
------------------------------------------------------------------------
Docket No....................  50-382.
Application date.............  May 8, 2024.
ADAMS Accession No...........  ML24129A039.
Location in Application of     Pages 13-14 of the Enclosure.
 NSHC.

[[Page 71436]]

 
Brief Description of           The proposed amendment would change four
 Amendment.                     surveillance frequencies associated with
                                specific Waterford Steam Electric
                                Station, Unit 3 (Waterford 3), technical
                                specifications surveillances, to instead
                                be performed in accordance with the
                                Surveillance Frequency Control Program.
                                These changes were originally intended
                                to have been addressed in the Waterford
                                3 license amendment request for TSTF-
                                425, ``Relocate Surveillance Frequencies
                                to Licensee Control--Risk-Informed
                                Technical Specification Task Force
                                (RITSTF) Initiative 5b'' (ADAMS Package
                                Accession No. ML15170A121), dated June
                                17, 2015.
Proposed Determination.......  NSHC.
Name of Attorney for           Susan Raimo, Associate General Counsel--
 Licensee, Mailing Address.     Nuclear, 101 Constitution Avenue NW,
                                Washington, DC 20001.
NRC Project Manager,           Jason Drake, 301-415-8378.
 Telephone Number.
------------------------------------------------------------------------
 NextEra Energy Point Beach, LLC; Point Beach Nuclear Plant, Units 1 and
                         2; Manitowoc County, WI
------------------------------------------------------------------------
Docket Nos...................  50-266, 50-301.
Application date.............  July 24, 2024.
ADAMS Accession No...........  ML24206A109.
Location in Application of     Pages 2-3 of Enclosure.
 NSHC.
Brief Description of           The proposed amendments would request
 Amendments.                    adoption of Technical Specifications
                                Task Force (TSTF) Traveler, TSTF-577,
                                Revision 1, ``Revised Frequencies for
                                Steam Generator Tube Inspections.''
Proposed Determination.......  NSHC.
Name of Attorney for           Steven Hamrick, Senior Attorney, 801
 Licensee, Mailing Address.     Pennsylvania Ave. NW, Suite 220,
                                Washington, DC 20004.
NRC Project Manager,           Scott Wall, 301-415-2855.
 Telephone Number.
------------------------------------------------------------------------
      Nine Mile Point Nuclear Station, LLC and Constellation Energy
Generation, LLC; Nine Mile Point Nuclear Station, Unit 1; Oswego County,
                                   NY
------------------------------------------------------------------------
Docket No....................  50-220.
Application date.............  June 13, 2024.
ADAMS Accession No...........  ML24165A223.
Location in Application of     Pages 4-5 of Attachment 1.
 NSHC.
Brief Description of           The proposed amendment would modify the
 Amendment.                     Nine Mile Point Nuclear Station, Unit 1
                                (NMP1) technical specifications (TSs) by
                                adopting Technical Specification Task
                                Force (TSTF)-230, Revision 1, ``Add New
                                Condition B to LCO [Limiting Condition
                                for Operation] 3.6.2.3, RHR Suppression
                                Pool Cooling.'' The TSTF modifies
                                improved TS (ITS) 3.6.2.3, ``Residual
                                Heat Removal (RHR) Suppression Pool
                                Cooling,'' to allow two RHR suppression
                                pool cooling subsystems to be inoperable
                                for eight hours. NMP1 does not have
                                ITSs; therefore, the applicable LCO for
                                NMP1 is TS LCO 3.3.7, ``Containment
                                Spray System.'' Additionally, a new
                                specification is proposed to be added
                                that will direct operators to place the
                                unit in ``Shutdown Condition--Hot''
                                within 12 hours and ``Shutdown
                                Condition--Cold'' in 36 hours if
                                applicable specifications are not met.
Proposed Determination.......  NSHC.
Name of Attorney for           Jason Zorn, Associate General Counsel,
 Licensee, Mailing Address.     Constellation Energy Generation, LLC,
                                101 Constitution Ave. NW, Suite 400
                                East, Washington, DC 20001.
NRC Project Manager,           Richard Guzman, 301-415-1030.
 Telephone Number.
------------------------------------------------------------------------
   Southern Nuclear Operating Company, Inc.; Joseph M. Farley Nuclear
                Plant, Units 1 and 2; Houston County, AL
------------------------------------------------------------------------
Docket Nos...................  50-348, 50-364.
Application date.............  June 28, 2024.
ADAMS Accession No...........  ML24180A204.
Location in Application of     Pages E-14 to E-16 of Enclosure.
 NSHC.
Brief Description of           The proposed amendments would modify
 Amendments.                    Joseph M. Farley Nuclear Plant, Units 1
                                and 2, technical specification
                                requirements related to direct current
                                (DC) electrical systems in accordance
                                with Technical Specifications Task Force
                                (TSTF) Traveler TSTF-500, Revision 2,
                                ``DC Electrical Rewrite-Update to TSTF-
                                360.''
Proposed Determination.......  NSHC.
Name of Attorney for           Millicent Ronnlund, Vice President and
 Licensee, Mailing Address.     General Counsel, Southern Nuclear
                                Operating Co., Inc., P.O. Box 1295,
                                Birmingham, AL 35201-1295.
NRC Project Manager,           Zachary Turner 415-6303.
 Telephone Number.
------------------------------------------------------------------------
  Southern Nuclear Operating Company, Inc.; Vogtle Electric Generating
                 Plant, Units 3 and 4; Burke County, GA
------------------------------------------------------------------------
Docket Nos...................  52-025, 52-026.
Application date.............  June 21, 2024.
ADAMS Accession No...........  ML24173A220.
Location in Application of     Pages E-9 and E-11 of Enclosure.
 NSHC.
Brief Description of           The proposed amendments would revise the
 Amendments.                    Combined License, Technical
                                Specifications (TS) 3.7.6, ``Main
                                Control Room Emergency Habitability
                                System (VES),'' Action E and
                                Surveillance Requirement 3.7.6.5, and
                                the Updated Final Safety Analysis Report
                                subsection 6.4.5.3, Air Quality Testing
                                for Vogtle Electric Generating Plant,
                                Units 3 and 4.
Proposed Determination.......  NSHC.

[[Page 71437]]

 
Name of Attorney for           Millicent Ronnlund, Vice President and
 Licensee, Mailing Address.     General Counsel, Southern Nuclear
                                Operating Co., Inc., P.O. Box 1295,
                                Birmingham, AL 35201-1295.
NRC Project Manager,           John Lamb, 301-415-3100.
 Telephone Number.
------------------------------------------------------------------------
  Southern Nuclear Operating Company, Inc.; Vogtle Electric Generating
                 Plant, Units 3 and 4; Burke County, GA
------------------------------------------------------------------------
Docket Nos...................  52-025, 52-026.
Application date.............  July 25, 2024.
ADAMS Accession No...........  ML24207A252.
Location in Application of     Pages E-7 to E-9 of Enclosure.
 NSHC.
Brief Description of           The proposed amendments would revise the
 Amendments.                    Vogtle Electric Generating Plant, Units
                                3 and 4, Combined License Appendix A
                                Technical Specification 3.7.6, ``Main
                                Control Room Emergency Habitability
                                System (VES),'' Action A and
                                Surveillance Requirement 3.7.6.6 related
                                to inoperable valves and/or dampers.
Proposed Determination.......  NSHC.
Name of Attorney for           Millicent Ronnlund, Vice President and
 Licensee, Mailing Address.     General Counsel, Southern Nuclear
                                Operating Co., Inc., P.O. Box 1295,
                                Birmingham, AL 35201-1295.
NRC Project Manager,           John Lamb, 301-415-3100.
 Telephone Number.
------------------------------------------------------------------------
Tennessee Valley Authority; Watts Bar Nuclear Plant, Units 1 and 2; Rhea
                               County, TN
------------------------------------------------------------------------
Docket Nos...................  50-390, 50-391.
Application date.............  June 25, 2024.
ADAMS Accession No...........  ML24178A413.
Location in Application of     Pages E8-E9 of the Enclosure.
 NSHC.
Brief Description of           The proposed amendments would revise
 Amendments.                    Watts Bar, Units 1 and 2, Technical
                                Specification (TS) 3.8.1, ``AC
                                [alternating current] Sources--
                                Operating,'' by adopting Technical
                                Specification Task Force (TSTF) Traveler
                                TSTF-276-A, Revision 2, ``Revise DG
                                [diesel generator] full load rejection
                                test.'' Specifically, the proposed
                                amendments would revise the notes to
                                Surveillance Requirement (SR) 3.8.1.9,
                                for the DG single largest load rejection
                                test, SR 3.8.1.10, for the DG full load
                                rejection test, and SR 3.8.1.14, for the
                                DG endurance and margin test, to require
                                that these SRs be performed at a
                                specified power factor of <=0.9 with
                                clarifications addressing situations
                                when the power factor cannot be
                                achieved. The proposed amendments would
                                also revise SR 3.8.1.10 and SR 3.8.1.14
                                to remove the surveillance kVAR ranges
                                and modify the note to SR 3.8.1.18 to
                                allow for the surveillance to be
                                performed in Modes 1, 2, 3, or 4 to
                                reestablish operability provided an
                                assessment of plant safety is performed.
Proposed Determination.......  NSHC.
Name of Attorney for           David Fountain, Executive VP and General
 Licensee, Mailing Address.     Counsel, Tennessee Valley Authority, 6A
                                West Tower, 400 West Summit Hill Drive,
                                Knoxville, TN 37902.
NRC Project Manager,           Kimberly Green, 301-415-1627.
 Telephone Number.
------------------------------------------------------------------------
   Union Electric Company; Callaway Plant, Unit 1; Callaway County, MO
------------------------------------------------------------------------
Docket No....................  50-483.
Application date.............  June 6, 2024.
ADAMS Package Accession No...  ML24158A521 (Package).
Location in Application of     Pages 2-4 of the Enclosure.
 NSHC.
Brief Description of           The proposed amendment would adopt
 Amendment.                     Technical Specifications Task Force
                                (TSTF) Traveler TSTF-569, Revision 2,
                                ``Revise Response Time Testing
                                Definition,'' which is an approved
                                change to the Standard Technical
                                Specifications for Westinghouse
                                pressurized-water reactor nuclear power
                                plants. The proposed changes are related
                                to the purpose and past use of several
                                related topical reports, including WCAP-
                                13632-P-A, Revision 2, ``Elimination of
                                Pressure Sensor Response Time Testing
                                Requirements,'' and WCAP-14036-P-A,
                                ``Elimination of Periodic Protection
                                Channel Response Time Tests,'' as
                                applicable to the Callaway Plant, Unit
                                1. Together, these topical reports
                                justify eliminating response time
                                testing for applicable instrument loops/
                                channels, for all applicable devices/
                                components in the loops/channels, within
                                the reactor trip system and engineered
                                safety features actuation system. The
                                topical reports provided detailed
                                information that forms the basis for the
                                methodology contained in TSTF-569,
                                Revision 2 (ADAMS Accession No.
                                ML19176A034), which provides a means for
                                allowing use of bounding response times
                                (in lieu of being measured) for newer/
                                redesigned components in the applicable
                                instrument loops/channels.
Proposed Determination.......  NSHC.
Name of Attorney for           Jay E. Silberg, Pillsbury Winthrop Shaw
 Licensee, Mailing Address.     Pittman LLP, 1200 17th St. NW,
                                Washington, DC 20036.
NRC Project Manager,           Mahesh Chawla, 301-415-8371.
 Telephone Number.
------------------------------------------------------------------------
 Vistra Operations Company LLC; Davis-Besse Nuclear Power Station, Unit
                          1; Ottawa County, OH
------------------------------------------------------------------------
Docket No....................  50-346.
Application date.............  July 8, 2024.
ADAMS Accession No...........  ML24191A432.
Location in Application of     Pages 4-5 of Attachment 1.
 NSHC.
Brief Description of           The proposed amendment would remove the
 Amendment.                     table of contents from technical
                                specification and place it under
                                licensee control.

[[Page 71438]]

 
Proposed Determination.......  NSHC.
Name of Attorney for           Roland Backhaus, Senior lead Counsel-
 Licensee, Mailing Address.     Nuclear, Vistra Corp., 325 7th Street
                                NW, Suite 520, Washington, DC 20004.
NRC Project Manager,           Scott Wall, 301-415-2855.
 Telephone Number.
------------------------------------------------------------------------

III. Notice of Issuance of Amendments to Facility Operating Licenses 
and Combined Licenses

    During the period since publication of the last monthly notice, the 
Commission has issued the following amendments. The Commission has 
determined for each of these amendments that the application complies 
with the standards and requirements of the Atomic Energy Act of 1954, 
as amended (the Act), and the Commission's rules and regulations. The 
Commission has made appropriate findings as required by the Act and the 
Commission's rules and regulations in 10 CFR chapter I, which are set 
forth in the license amendment.
    A notice of consideration of issuance of amendment to facility 
operating license or combined license, as applicable, proposed NSHC 
determination, and opportunity for a hearing in connection with these 
actions, were published in the Federal Register as indicated in the 
safety evaluation for each amendment.
    Unless otherwise indicated, the Commission has determined that 
these amendments satisfy the criteria for categorical exclusion in 
accordance with 10 CFR 51.22. Therefore, pursuant to 10 CFR 51.22(b), 
no environmental impact statement or environmental assessment need be 
prepared for these amendments. If the Commission has prepared an 
environmental assessment under the special circumstances provision in 
10 CFR 51.22(b) and has made a determination based on that assessment, 
it is so indicated in the safety evaluation for the amendment.
    For further details with respect to each action, see the amendment 
and associated documents such as the Commission's letter and safety 
evaluation, which may be obtained using the ADAMS accession numbers 
indicated in the following table. The safety evaluation will provide 
the ADAMS accession numbers for the application for amendment and the 
Federal Register citation for any environmental assessment. All of 
these items can be accessed as described in the ``Obtaining Information 
and Submitting Comments'' section of this document.

                       License Amendment Issuances
------------------------------------------------------------------------
 
------------------------------------------------------------------------
Constellation Energy Generation, LLC; Limerick Generating Station, Units
                     1 and 2; Montgomery County, PA
------------------------------------------------------------------------
Docket Nos...................  50-352, 50-353.
Amendment Date...............  July 29, 2024.
ADAMS Accession No...........  ML24204A071.
Amendment Nos................  263 (Unit1), 225 (Unit 2).
Brief Description of           The amendments revised the technical
 Amendments.                    specifications by replacing automatic
                                main steam isolation valve isolation
                                requirements with a monitoring
                                requirement and a manual shutdown if the
                                turbine enclosure main steam line tunnel
                                temperature exceeds a certain value and
                                main steam line pressure boundary
                                leakage is detected.
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
Constellation Energy Generation, LLC; Quad Cities Nuclear Power Station,
                  Units 1 and 2; Rock Island County, IL
------------------------------------------------------------------------
Docket Nos...................  50-254, 50-265.
Amendment Date...............  August 8, 2024.
ADAMS Accession No...........  ML24183A108.
Amendment Nos................  302 (Unit 1), 298 (Unit 2).
Brief Description of           The amendments adopted Technical
 Amendments.                    Specification Task Force (TSTF)
                                Travelers 505 (TSTF-505), Revision 2,
                                ``Provide Risk Informed Extended
                                Completion Times--RITSTF Initiative 4b''
                                and TSTF-591, Revision 0, ``Revise Risk
                                Informed Completion Time (RICT)
                                Program.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Dominion Energy South Carolina, Inc.; Virgil C. Summer Nuclear Station,
                       Unit 1,Fairfield County, SC
------------------------------------------------------------------------
Docket No....................  50-395.
Amendment Date...............  July 31, 2024.
ADAMS Accession No...........  ML24158A388.
Amendment No.................  226.
Brief Description of           The amendment modified the Virgil C.
 Amendment.                     Summer Nuclear Station (VCSNS) emergency
                                plan by extending emergency response
                                augmentation times; relocating the
                                Emergency Operations Facility and Joint
                                Information Center; defining ``Facility
                                Activation'' criteria; revising the
                                minimum staffing definition for the
                                Emergency Response Facilities; extending
                                facility activation requirements after
                                declaration of an Alert of higher
                                classification; reorganizing the VCSNS
                                Emergency Plan based on emergency
                                preparedness functions and removing
                                references to chemistry, firefighting,
                                first aid/rescue, and site access
                                control functions while being on shift;
                                and reducing the level at which the
                                dispatch of Offsite Survey Teams are
                                required.
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------

[[Page 71439]]

 
 Dominion Energy South Carolina, Inc.; Virgil C. Summer Nuclear Station,
                      Unit 1, Fairfield County, SC
------------------------------------------------------------------------
Docket No....................  50-395.
Amendment Date...............  August 5, 2024.
ADAMS Accession No...........  ML24180A006.
Amendment No.................  227.
Brief Description of           The amendment modified the Virgil C.
 Amendment.                     Summer Nuclear Station (VCSNS) Technical
                                Specification (TS) Limiting Condition
                                for Operation (LCO) 3.8.3.1, Action C,
                                concerning inoperable Alternating
                                Current Inverters of TS 3/4.8.3. The
                                amendment extends the Allowed Outage
                                Time for VCSNS's TS LCO 3.8.3.1 Action C
                                in the case of an inoperable inverter.
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
Duke Energy Progress, LLC; H. B. Robinson Steam Electric Plant, Unit No.
                        2; Darlington County, SC
------------------------------------------------------------------------
Docket No....................  50-261.
Amendment Date...............  August 14, 2024.
ADAMS Accession No...........  ML24169A271.
Amendment No.................  280.
Brief Description of           The amendment revised Technical
 Amendment.                     Specification (TS) Section 5.7, ``High
                                Radiation Area,'' consistent with NRC-
                                approved TS Task Force (TSTF) Traveler
                                258 (TSTF-258-A), Revision 4, ``Changes
                                to Section 5.0, Administrative
                                Controls.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Duke Energy Progress, LLC; Shearon Harris Nuclear Power Plant, Unit 1;
                      Wake and Chatham Counties, NC
------------------------------------------------------------------------
Docket No....................  50-400.
Amendment Date...............  August 14, 2024.
ADAMS Accession No...........  ML24059A425.
Amendment No.................  202.
Brief Description of           The amendment modified the Technical
 Amendment.                     Specification (TS) Surveillance
                                Requirement (SR) 4.6.1.1 to eliminate
                                the requirement to perform periodic
                                position verification for containment
                                penetrations that are maintained locked,
                                sealed, or otherwise secured closed, and
                                adopted Technical Specifications Task
                                Force (TSTF) Improved Standard TS (ISTS)
                                Change Traveler No. 45 (TSTF-45-A),
                                Revision 2, ``Exempt Verification of
                                Containment Isolation Valves that are
                                Not Locked, Sealed, or Other-wise
                                Secured.'' The amendment also revised TS
                                3.3.3.5, ``Remote Shutdown System,'' to
                                increase the completion time for
                                inoperable Remote Shut-down System
                                components to a time that is more
                                consistent with their safety
                                significance and removed the requirement
                                to submit a Special Report. It also
                                relocated the content in Table 3.3-9,
                                ``Remote Shutdown System,'' and Table
                                4.3-6, ``Remote Shutdown Monitoring
                                Instrumentation Surveillance
                                Requirements,'' in accordance with TSTF-
                                266-A, Revision 3, ``Eliminate the
                                Remote Shutdown System Table of
                                Instrumentation and Controls.''
                                Additionally, the amendment updated SR
                                4.3.1.1, Table 4.3-1, ``Reactor Trip
                                System Instrumentation Surveillance
                                Requirements,'' to address the
                                application of the Surveillance
                                Frequency Control Program to establish
                                the frequency for performance of the
                                Analog Channel Operational Test of
                                select Reactor Trip System
                                instrumentation. Changes were made to
                                the administrative controls section of
                                the TS to reflect current organizational
                                titles as well as remove reporting
                                requirements that were redundant to
                                existing regulations. The changes
                                reflect requirements consistent with
                                those in NUREG-1431, Revision 5,
                                ``Standard Technical Specifications-
                                Westinghouse Plants.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Duke Energy Progress, LLC; Shearon Harris Nuclear Power Plant, Unit 1;
                      Wake and Chatham Counties, NC
------------------------------------------------------------------------
Docket No....................  50-400.
Amendment Date...............  August 2, 2024.
ADAMS Accession No...........  ML24213A052.
Amendment No(s)..............  201.
Brief Description of           The amendment extended the completion
 Amendment.                     time of Action a of Technical
                                Specification 3/4.5.1, ``Accumulators,''
                                from 1 hour to 24 hours to restore a
                                reactor coolant system accumulator to
                                operable status when declared inoperable
                                due to any reason except not being
                                within the required boron concentration
                                range. The change is consistent with NRC-
                                approved Industry/Technical
                                Specification Task Force (TSTF) Standard
                                Technical Specification Change Traveler
                                TSTF-370, ``Risk-Informed Evaluation of
                                an Extension to Accumulator Completion
                                Times for Westinghouse Plants.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------

[[Page 71440]]

 
    Entergy Louisiana, LLC, and Entergy Operations, Inc.; River Bend
  Station, Unit 1; West Feliciana Parish, LA; Entergy Operations, Inc.,
    System Energy Resources, Inc., Cooperative Energy, A Mississippi
 Electric Cooperative, and Entergy Mississippi, LLC; Grand Gulf Nuclear
    Station, Unit 1; Claiborne County, MS; Entergy Operations, Inc.;
              Arkansas Nuclear One, Unit 2; Pope County, AR
------------------------------------------------------------------------
Docket Nos...................  50-368, 50-416, 50-458.
Amendment Date...............  August 13, 2024.
ADAMS Accession No...........  ML24185A152.
Amendment Nos................  334 (ANO-2), 235 (Grand Gulf), and 215
                                (River Bend).
Brief Description of           The amendments revised Arkansas Nuclear
 Amendments.                    One, Unit 2 (ANO-2) Technical
                                Specification (TS) Definitions 1.9, and
                                1.11 for Channel Calibration and Channel
                                Functional Test, respectively; Grand
                                Gulf Nuclear Station, Unit 1 (Grand
                                Gulf) TS Definition 1.1 for Channel
                                Calibration, Channel Functional Test,
                                and Logic System Functional Test; and
                                River Bend Station, Unit 1 (River Bend)
                                TS Definition 1.1 for Channel
                                Calibration, Channel Functional Test,
                                and Logic System Functional Test. The
                                proposed changes aligned the ANO-2,
                                Grand Gulf, and River Bend TS
                                definitions with the definitions in
                                Technical Specifications Task Force
                                (TSTF) Traveler TSTF-205-A, Revision 3,
                                ``Revision of Channel Calibration,
                                Channel Functional Test, and Related
                                Definitions.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
  Entergy Operations, Inc., System Energy Resources, Inc., Cooperative
  Energy, A Mississippi Electric Cooperative, and Entergy Mississippi,
      LLC; Grand Gulf Nuclear Station, Unit 1; Claiborne County, MS
------------------------------------------------------------------------
Docket No....................  50-416.
Amendment Date...............  July 29, 2024.
ADAMS Accession No...........  ML24172A250.
Amendment No.................  233.
Brief Description of           The amendment revised the Grand Gulf
 Amendment.                     Nuclear Station, Unit 1, Renewed
                                Facility Operating License No. NPF-29 to
                                add a new license condition to allow for
                                the implementation of 10 CFR 50.69,
                                ``Risk-informed categorization and
                                treatment of structures, systems and
                                components for nuclear power reactors.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
  Entergy Operations, Inc., System Energy Resources, Inc., Cooperative
  Energy, A Mississippi Electric Cooperative, and Entergy Mississippi,
      LLC; Grand Gulf Nuclear Station, Unit 1; Claiborne County, MS
------------------------------------------------------------------------
Docket No....................  50-416.
Amendment Date...............  July 29, 2024.
ADAMS Accession No...........  ML24176A120.
Amendment No.................  234.
Brief Description of           The amendment modified the Grand Gulf
 Amendment.                     Nuclear Station, Unit 1, technical
                                specification requirements to permit the
                                use of risk-informed completion times in
                                accordance with Technical Specifications
                                Task Force (TSTF) Traveler TSTF-505,
                                Revision 2, ``Provide Risk-Informed
                                Extended Completion Times--RITSTF [Risk-
                                Informed TSTF] Initiative 4b.'' The NRC
                                staff issued a final model safety
                                evaluation TSTF-505, Revision 2, on
                                November 21, 2018.
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Entergy Operations, Inc.; Waterford Steam Electric Station, Unit 3; St.
                           Charles Parish, LA
------------------------------------------------------------------------
Docket No....................  50-382.
Amendment Date...............  August 7, 2024.
ADAMS Accession No...........  ML24164A251.
Amendment No.................  271.
Brief Description of           The amendment revised Surveillance
 Amendment.                     Requirement (SR) 4.3.1.3, listed in
                                Technical Specification (TS) 3.3.1,
                                ``Reactor Protective Instrumentation,''
                                and SR 4.3.2.3, listed in TS 3.3.2,
                                ``Engineered Safety Features Actuation
                                System Instrumentation,'' to remove
                                conflicting language that should have
                                been removed as part of the Waterford
                                Steam Electric Station, Unit 3 license
                                amendment request to adopt Technical
                                Specifications Task Force (TSTF)
                                Traveler TSTF-425 (ADAMS Accession No.
                                ML15170A121), which relocated specific
                                surveillance frequencies to the
                                surveillance frequency control program.
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
  Indiana Michigan Power Company; Donald C. Cook Nuclear Plant, Unit 1;
                           Berrien County, MI
------------------------------------------------------------------------
Docket No....................  50-315.
Amendment Date...............  July 25, 2024.
ADAMS Accession No...........  ML24169A214.
Amendment No.................  362.
Brief Description of           The amendment revised the technical
 Amendment.                     specifications (TSs) by adding the
                                Completion Time requirement
                                ``Immediately'' to TS 3.4.12, ``Low
                                Temperature Overpressure Protection
                                (LTOP) System,'' Actions Table to
                                Condition F, Required Action F.2.

[[Page 71441]]

 
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
  TMI-2 Solutions, LLC; Three Mile Island Unit 2; Londonderry Township,
                           Dauphin County, PA
------------------------------------------------------------------------
Docket No(s).................  50-320.
Amendment Date...............  August 9, 2024.
ADAMS Accession No...........  ML24135A327 (Package).
Amendment No.................  68.
Brief Description of           The NRC issued TMI-2 Solutions, LLC (TMI-
 Amendment.                     2S) Amendment No. 68 to Possession-Only
                                License Demonstration Power Reactor
                                (DPR) -73. The amendment allows TMI-2S
                                to conduct certain decommissioning
                                activities at TMI-2 that were not
                                previously addressed in the staff's
                                environmental reviews (site-specific
                                impacts to historic and cultural
                                resources).
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
  Virginia Electric and Power Company; Surry Power Station, Unit Nos. 1
                         and 2; Surry County, VA
------------------------------------------------------------------------
Docket Nos...................  50-280, 50-281.
Amendment Date...............  July 17, 2024.
ADAMS Accession No...........  ML24165A278.
Amendment Nos................  318 (Unit 1), 318 (Unit 2).
Brief Description of           The amendments revised technical
 Amendments.                    specifications (TSs) to add low head
                                safety injection (LHSI) flow indication
                                as required accident monitoring
                                instrumentation. The addition of LHSI
                                flow instrumentation to the TSs is due
                                to reclassification of the variable from
                                a Type D Category 2 variable to a Type A
                                Category 1 variable per Regulatory Guide
                                1.97, Revision 3, ``Criteria for
                                Accident Monitoring Instrumentation for
                                Nuclear Power Plants.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Vistra Operations Company LLC; Comanche Peak Nuclear Power Plant, Unit
                   Nos. 1 and 2; Somervell County, TX
------------------------------------------------------------------------
Docket Nos...................  50-445, 50-446.
Amendment Date...............  August 7, 2024.
ADAMS Accession No...........  ML24177A269.
Amendment Nos................  188 (Unit 1),188 (Unit 2).
Brief Description of           The amendments revised technical
 Amendments.                    specifications to adopt Technical
                                Specifications Task Force (TSTF)
                                Traveler TSTF-591, ``Revise Risk
                                Informed Completion Time (RICT)
                                Program.''
Public Comments Received as    No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------

IV. Notice of Issuance of Amendment to Facility Operating Licenses and 
Combined Licenses and Final Determination of No Significant Hazards 
Consideration and Opportunity for a Hearing (Exigent Circumstances or 
Emergency Situation)

    Since publication of the last monthly notice, the Commission has 
issued the following amendment. The Commission has determined for this 
amendment that the application for the amendment complies with the 
standards and requirements of the Atomic Energy Act of 1954, as amended 
(the Act), and the Commission's rules and regulations. The Commission 
has made appropriate findings as required by the Act and the 
Commission's rules and regulations in 10 CFR chapter I, which are set 
forth in the license amendment.
    Because of exigent circumstances or emergency situation associated 
with the date the amendment was needed, there was not time for the 
Commission to publish, for public comment before issuance, its usual 
notice of consideration of issuance of amendment, proposed NSHC 
determination, and opportunity for a hearing.
    In circumstances where failure to act in a timely way would have 
resulted, for example, in derating or shutdown of a nuclear power plant 
or in prevention of either resumption of operation or of increase in 
power output up to the plant's licensed power level (an emergency 
situation), the Commission may not have had an opportunity to provide 
for public comment on its NSHC determination. In such case, the license 
amendment has been issued without opportunity for comment prior to 
issuance. Nonetheless, the State has been consulted by telephone 
whenever possible.
    Under its regulations, the Commission may issue and make an 
amendment immediately effective, notwithstanding the pendency before it 
of a request for a hearing from any person, in advance of the holding 
and completion of any required hearing, where it has determined that 
NSHC is involved. The Commission has applied the standards of 10 CFR 
50.92 and has made a final determination that the amendments involve 
NSHC. The basis for this determination is contained in the NRC staff 
safety evaluation related to each action. Accordingly, the amendment 
has been issued and made effective as indicated.
    For those amendments that involve an emergency situation, the 
Commission is now providing an opportunity to comment on the final NSHC 
determination for each action; comments should be submitted in 
accordance with Section I of this notice within 30 days of the date of 
this notice. Any comments received within 30 days of the date of 
publication this notice will be considered.
    For those amendments that have not been previously noticed in the 
Federal Register, within 60 days after the date of publication of this 
notice, any persons (petitioner) whose interest may be affected by this 
action may file a request for a hearing and petition for leave to 
intervene (petition) with respect to the action. Petitions shall be 
filed in

[[Page 71442]]

accordance with the guidance concerning the Commission's ``Agency Rules 
of Practice and Procedure'' in 10 CFR part 2 as discussed in section 
II.A of this document.
    Unless otherwise indicated, the Commission has determined that the 
amendment satisfies the criteria for categorical exclusion in 
accordance with 10 CFR 51.22. Therefore, pursuant to 10 CFR 51.22(b), 
no environmental impact statement or environmental assessment need be 
prepared for this amendment. If the Commission has prepared an 
environmental assessment under the special circumstances provision in 
10 CFR 51.12(b) and has made a determination based on that assessment, 
it is so indicated in the safety evaluation for the amendment.
    For further details with respect to these actions, see the 
amendment and associated documents such as the Commission's letter and 
safety evaluation, which may be obtained using the ADAMS accession 
numbers indicated in the following table. The safety evaluation will 
provide the ADAMS accession number(s) for the application for amendment 
and the Federal Register citation for any environmental assessment. All 
of these items can be accessed as described in the ``Obtaining 
Information and Submitting Comments'' section of this document.

           License Amendment Issuance--Emergency Circumstances
------------------------------------------------------------------------
 
------------------------------------------------------------------------
  Southern Nuclear Operating Company, Inc.; Vogtle Electric Generating
                     Plant, Unit 1; Burke County, GA
------------------------------------------------------------------------
Docket No....................  50-424.
Amendment Date...............  July 23, 2024.
ADAMS Accession No...........  ML24204A072.
Amendment No.................  225.
Brief Description of           The amendment revised Technical
 Amendment.                     Specification (TS) 3.7.9, ``Ultimate
                                Heat Sink,'' to allow a 92-day
                                Completion Time for Required Action D.2
                                for an inoperable Nuclear Service
                                Cooling Water (NSCW) basin transfer
                                pump. The TS changes would be a one-time
                                change and in effect only until
                                September 9, 2024, during Vogtle Unit 1
                                Cycle 25 (1R25). The change also
                                includes a Required Action D.2 Note
                                which prevents Application of limiting
                                conditions for operation 3.0.4.a and b
                                for entry into MODE 4 following 1R25
                                unless repairs to the 1A NSCW transfer
                                pump have been completed. The license
                                amendment is issued under emergency
                                circumstances as described in the
                                provisions of 10 CFR 50.91(a)(5) due to
                                the time critical nature of the
                                amendment.
Local Media Notice (Yes/No)..  No.
Public Comments Requested as   No.
 to Proposed NSHC (Yes/No).
------------------------------------------------------------------------

V. Previously Published Notice of Consideration of Issuance of 
Amendments to Facility Operating Licenses and Combined Licenses, 
Proposed No Significant Hazards Consideration Determination, and 
Opportunity for a Hearing

    The following notice was previously published as separate 
individual notice. It was published as an individual notice either 
because time did not allow the Commission to wait for this monthly 
notice or because the action involved exigent circumstances. It is 
repeated here because the monthly notice lists all amendments issued or 
proposed to be issued involving NSHC.
    For details, including the applicable notice period, see the 
individual notice in the Federal Register on the day and page cited.

   License Amendment Request(s)--Repeat of Individual Federal Register
                                 Notice
------------------------------------------------------------------------
 
------------------------------------------------------------------------
   Southern Nuclear Operating Company, Inc.; Joseph M. Farley Nuclear
                Plant, Units 1 and 2; Houston County, AL
------------------------------------------------------------------------
Docket Nos...................  50-364, 50-348.
Application Date.............  July 18, 2024.
ADAMS Accession No...........  ML24201A108.
Brief Description of           The NRC is considering issuance of an
 Amendments.                    amendment to Facility Operating License
                                No. NPF-2 and NPF-8, issued to Southern
                                Nuclear Operating Company, Inc. (SNC,
                                the licensee), for operation of the
                                Joseph M. Farley Nuclear Plant, (Farley)
                                Units 1 and 2. The requested amendment
                                would revise the operating license,
                                Appendix A, Technical Specification (TS)
                                3.6.5, ``Containment Air Temperature,''
                                actions upon exceeding the containment
                                average air temperature limit of 120
                                degrees Fahrenheit ([deg]F) and remove
                                an expired Note provision. Specifically,
                                the proposed amendment would revise TS
                                3.6.5 Required Actions and Completion
                                Time A.1, add Required Actions and
                                Completion Times A.2 and A.3, as well as
                                remove an expired Note in TS 3.6.5
                                Limiting Conditions for Operation.
Date and Citation of Federal   July 29, 2024; 89 FR 60930.
 Register Individual Notice.
Expiration Dates for Public    August 28, 2024 (Public Comments) and
 Comments & Hearing Requests.   September 27, 2024 (Hearing Requests).
------------------------------------------------------------------------



[[Page 71443]]

    Dated: August 27, 2024.

    For the Nuclear Regulatory Commission.
Aida Rivera-Varona,
Deputy Director, Division of Operating Reactor Licensing, Office of 
Nuclear Reactor Regulation.
[FR Doc. 2024-19687 Filed 8-30-24; 8:45 am]
BILLING CODE 7590-01-P