[Federal Register Volume 89, Number 34 (Tuesday, February 20, 2024)]
[Notices]
[Pages 12873-12880]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2024-03243]



[[Page 12873]]

=======================================================================
-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION

[NRC-2024-0042]


Monthly Notice; Applications and Amendments to Facility Operating 
Licenses and Combined Licenses Involving No Significant Hazards 
Considerations

AGENCY: Nuclear Regulatory Commission.

ACTION: Monthly notice.

-----------------------------------------------------------------------

SUMMARY: Pursuant to section 189.a.(2) of the Atomic Energy Act of 
1954, as amended (the Act), the U.S. Nuclear Regulatory Commission 
(NRC) is publishing this regular monthly notice. The Act requires the 
Commission to publish notice of any amendments issued, or proposed to 
be issued, and grants the Commission the authority to issue and make 
immediately effective any amendment to an operating license or combined 
license, as applicable, upon a determination by the Commission that 
such amendment involves no significant hazards consideration (NSHC), 
notwithstanding the pendency before the Commission of a request for a 
hearing from any person.

DATES: Comments must be filed by March 21, 2024. A request for a 
hearing or petitions for leave to intervene must be filed by April 22, 
2024. This monthly notice includes all amendments issued, or proposed 
to be issued, from January 5, 2024, to February 1, 2024. The last 
monthly notice was published on January 23, 2024.

ADDRESSES: You may submit comments by any of the following methods; 
however, the NRC encourages electronic comment submission through the 
Federal rulemaking website:
     Federal rulemaking website: Go to https://www.regulations.gov and search for Docket ID NRC-2024-0042. Address 
questions about Docket IDs in Regulations.gov to Stacy Schumann; 
telephone: 301-415-0624; email: [email protected]. For technical 
questions, contact the individual listed in the ``For Further 
Information Contact'' section of this document.
     Mail comments to: Office of Administration, Mail Stop: 
TWFN-7-A60M, U.S. Nuclear Regulatory Commission, Washington, DC 20555-
0001, ATTN: Program Management, Announcements and Editing Staff.
    For additional direction on obtaining information and submitting 
comments, see ``Obtaining Information and Submitting Comments'' in the 
SUPPLEMENTARY INFORMATION section of this document.

FOR FURTHER INFORMATION CONTACT: Karen Zeleznock, Office of Nuclear 
Reactor Regulation, U.S. Nuclear Regulatory Commission, Washington, DC 
20555-0001, telephone: 301-415-1118; email: [email protected].

SUPPLEMENTARY INFORMATION:

I. Obtaining Information and Submitting Comments

A. Obtaining Information

    Please refer to Docket ID NRC-2024-0042, facility name, unit 
number(s), docket number(s), application date, and subject when 
contacting the NRC about the availability of information for this 
action. You may obtain publicly available information related to this 
action by any of the following methods:
     Federal Rulemaking Website: Go to https://www.regulations.gov and search for Docket ID NRC-2024-0042.
     NRC's Agencywide Documents Access and Management System 
(ADAMS): You may obtain publicly available documents online in the 
ADAMS Public Documents collection at https://www.nrc.gov/reading-rm/adams.html. To begin the search, select ``Begin Web-based ADAMS 
Search.'' For problems with ADAMS, please contact the NRC's Public 
Document Room (PDR) reference staff at 1-800-397-4209, at 301-415-4737, 
or by email to [email protected]. The ADAMS accession number for 
each document referenced (if it is available in ADAMS) is provided the 
first time that it is mentioned in this document.
     NRC's PDR: The PDR, where you may examine and order copies 
of publicly available documents, is open by appointment. To make an 
appointment to visit the PDR, please send an email to 
[email protected] or call 1-800-397-4209 or 301-415-4737, between 8 
a.m. and 4 p.m. eastern time (ET), Monday through Friday, except 
Federal holidays.

B. Submitting Comments

    The NRC encourages electronic comment submission through the 
Federal rulemaking website (https://www.regulations.gov). Please 
include Docket ID NRC-2024-0042, facility name, unit number(s), docket 
number(s), application date, and subject, in your comment submission.
    The NRC cautions you not to include identifying or contact 
information that you do not want to be publicly disclosed in your 
comment submission. The NRC will post all comment submissions at 
https://www.regulations.gov as well as enter the comment submissions 
into ADAMS. The NRC does not routinely edit comment submissions to 
remove identifying or contact information.
    If you are requesting or aggregating comments from other persons 
for submission to the NRC, then you should inform those persons not to 
include identifying or contact information that they do not want to be 
publicly disclosed in their comment submission. Your request should 
state that the NRC does not routinely edit comment submissions to 
remove such information before making the comment submissions available 
to the public or entering the comment into ADAMS.

II. Notice of Consideration of Issuance of Amendments to Facility 
Operating Licenses and Combined Licenses and Proposed No Significant 
Hazards Consideration Determination

    For the facility-specific amendment requests shown in this notice, 
the Commission finds that the licensees' analyses provided, consistent 
with section 50.91 of title 10 of the Code of Federal Regulations (10 
CFR) ``Notice for public comment; State consultation,'' are sufficient 
to support the proposed determinations that these amendment requests 
involve NSHC. Under the Commission's regulations in 10 CFR 50.92, 
operation of the facilities in accordance with the proposed amendments 
would not (1) involve a significant increase in the probability or 
consequences of an accident previously evaluated; or (2) create the 
possibility of a new or different kind of accident from any accident 
previously evaluated; or (3) involve a significant reduction in a 
margin of safety.
    The Commission is seeking public comments on these proposed 
determinations. Any comments received within 30 days after the date of 
publication of this notice will be considered in making any final 
determinations.
    Normally, the Commission will not issue the amendments until the 
expiration of 60 days after the date of publication of this notice. The 
Commission may issue any of these license amendments before expiration 
of the 60-day period provided that its final determination is that the 
amendment involves NSHC. In addition, the Commission may issue any of 
these amendments prior to the expiration of the 30-day comment period 
if circumstances change during the 30-day comment period such that 
failure to act in a timely way would result, for example in derating or 
shutdown of the facility. If the Commission takes action on any of 
these amendments prior to the expiration of either the comment period 
or the notice period, it will publish in

[[Page 12874]]

the Federal Register a notice of issuance. If the Commission makes a 
final NSHC determination for any of these amendments, any hearing will 
take place after issuance. The Commission expects that the need to take 
action on any amendment before 60 days have elapsed will occur very 
infrequently.

A. Opportunity To Request a Hearing and Petition for Leave To Intervene

    Within 60 days after the date of publication of this notice, any 
person (petitioner) whose interest may be affected by any of these 
actions may file a request for a hearing and petition for leave to 
intervene (petition) with respect to that action. Petitions shall be 
filed in accordance with the Commission's ``Agency Rules of Practice 
and Procedure'' in 10 CFR part 2. Interested persons should consult a 
current copy of 10 CFR 2.309. If a petition is filed, the Commission or 
a presiding officer will rule on the petition and, if appropriate, a 
notice of a hearing will be issued.
    Petitions must be filed no later than 60 days from the date of 
publication of this notice in accordance with the filing instructions 
in the ``Electronic Submissions (E-Filing)'' section of this document. 
Petitions and motions for leave to file new or amended contentions that 
are filed after the deadline will not be entertained absent a 
determination by the presiding officer that the filing demonstrates 
good cause by satisfying the three factors in 10 CFR 2.309(c)(1)(i) 
through (iii).
    If a hearing is requested, and the Commission has not made a final 
determination on the issue of no significant hazards consideration, the 
Commission will make a final determination on the issue of no 
significant hazards consideration, which will serve to establish when 
the hearing is held. If the final determination is that the amendment 
request involves no significant hazards consideration, the Commission 
may issue the amendment and make it immediately effective, 
notwithstanding the request for a hearing. Any hearing would take place 
after issuance of the amendment. If the final determination is that the 
amendment request involves a significant hazards consideration, then 
any hearing held would take place before the issuance of the amendment 
unless the Commission finds an imminent danger to the health or safety 
of the public, in which case it will issue an appropriate order or rule 
under 10 CFR part 2.
    A State, local governmental body, Federally recognized Indian 
Tribe, or designated agency thereof, may submit a petition to the 
Commission to participate as a party under 10 CFR 2.309(h) no later 
than 60 days from the date of publication of this notice. 
Alternatively, a State, local governmental body, Federally recognized 
Indian Tribe, or agency thereof may participate as a non-party under 10 
CFR 2.315(c).
    For information about filing a petition and about participation by 
a person not a party under 10 CFR 2.315, see ADAMS Accession No. 
ML20340A053 (https://adamswebsearch2.nrc.gov/webSearch2/main.jsp?AccessionNumber=ML20340A053) and on the NRC's public website 
at https://www.nrc.gov/about-nrc/regulatory/adjudicatory/hearing.html#participate.

B. Electronic Submissions (E-Filing)

    All documents filed in NRC adjudicatory proceedings, including 
documents filed by an interested State, local governmental body, 
Federally recognized Indian Tribe, or designated agency thereof that 
requests to participate under 10 CFR 2.315(c), must be filed in 
accordance with 10 CFR 2.302. The E-Filing process requires 
participants to submit and serve all adjudicatory documents over the 
internet, or in some cases, to mail copies on electronic storage media, 
unless an exemption permitting an alternative filing method, as further 
discussed, is granted. Detailed guidance on electronic submissions is 
located in the ``Guidance for Electronic Submissions to the NRC'' 
(ADAMS Accession No. ML13031A056) and on the NRC's public website at 
https://www.nrc.gov/site-help/e-submittals.html.
    To comply with the procedural requirements of E-Filing, at least 10 
days prior to the filing deadline, the participant should contact the 
Office of the Secretary by email at [email protected], or by 
telephone at 301-415-1677, to (1) request a digital identification (ID) 
certificate, which allows the participant (or its counsel or 
representative) to digitally sign submissions and access the E-Filing 
system for any proceeding in which it is participating; and (2) advise 
the Secretary that the participant will be submitting a petition or 
other adjudicatory document (even in instances in which the 
participant, or its counsel or representative, already holds an NRC-
issued digital ID certificate). Based upon this information, the 
Secretary will establish an electronic docket for the proceeding if the 
Secretary has not already established an electronic docket.
    Information about applying for a digital ID certificate is 
available on the NRC's public website at https://www.nrc.gov/site-help/e-submittals/getting-started.html. After a digital ID certificate is 
obtained and a docket created, the participant must submit adjudicatory 
documents in Portable Document Format. Guidance on submissions is 
available on the NRC's public website at https://www.nrc.gov/site-help/electronic-sub-ref-mat.html. A filing is considered complete at the 
time the document is submitted through the NRC's E-Filing system. To be 
timely, an electronic filing must be submitted to the E-Filing system 
no later than 11:59 p.m. ET on the due date. Upon receipt of a 
transmission, the E-Filing system time-stamps the document and sends 
the submitter an email confirming receipt of the document. The E-Filing 
system also distributes an email that provides access to the document 
to the NRC's Office of the General Counsel and any others who have 
advised the Office of the Secretary that they wish to participate in 
the proceeding, so that the filer need not serve the document on those 
participants separately. Therefore, applicants and other participants 
(or their counsel or representative) must apply for and receive a 
digital ID certificate before adjudicatory documents are filed to 
obtain access to the documents via the E-Filing system.
    A person filing electronically using the NRC's adjudicatory E-
Filing system may seek assistance by contacting the NRC's Electronic 
Filing Help Desk through the ``Contact Us'' link located on the NRC's 
public website at https://www.nrc.gov/site-help/e-submittals.html, by 
email to [email protected], or by a toll-free call at 1-866-672-
7640. The NRC Electronic Filing Help Desk is available between 9 a.m. 
and 6 p.m., ET, Monday through Friday, except Federal holidays.
    Participants who believe that they have good cause for not 
submitting documents electronically must file an exemption request, in 
accordance with 10 CFR 2.302(g), with their initial paper filing 
stating why there is good cause for not filing electronically and 
requesting authorization to continue to submit documents in paper 
format. Such filings must be submitted in accordance with 10 CFR 
2.302(b)-(d). Participants filing adjudicatory documents in this manner 
are responsible for serving their documents on all other participants. 
Participants granted an exemption under 10 CFR 2.302(g)(2) must still 
meet the electronic formatting requirement in 10 CFR 2.302(g)(1), 
unless the participant also seeks and is granted an exemption from 10 
CFR 2.302(g)(1).
    Documents submitted in adjudicatory proceedings will appear in the 
NRC's

[[Page 12875]]

electronic hearing docket, which is publicly available at https://adams.nrc.gov/ehd, unless excluded pursuant to an order of the 
presiding officer. If you do not have an NRC-issued digital ID 
certificate as previously described, click ``cancel'' when the link 
requests certificates and you will be automatically directed to the 
NRC's electronic hearing dockets where you will be able to access any 
publicly available documents in a particular hearing docket. 
Participants are requested not to include personal privacy information 
such as Social Security numbers, home addresses, or personal phone 
numbers in their filings unless an NRC regulation or other law requires 
submission of such information. With respect to copyrighted works, 
except for limited excerpts that serve the purpose of the adjudicatory 
filings and would constitute a Fair Use application, participants 
should not include copyrighted materials in their submission.
    The following table provides the plant name, docket number, date of 
application, ADAMS accession number, and location in the application of 
the licensees' proposed NSHC determinations. For further details with 
respect to these license amendment applications, see the applications 
for amendment, which are available for public inspection in ADAMS. For 
additional direction on accessing information related to this document, 
see the ``Obtaining Information and Submitting Comments'' section of 
this document.

                       License Amendment Requests
------------------------------------------------------------------------
 
------------------------------------------------------------------------
Constellation Energy Generation, LLC; Peach Bottom Atomic Power Station,
                         Unit 1; York County, PA
------------------------------------------------------------------------
Docket No.........................  50-171.
Application date..................  September 22, 2023.
ADAMS Accession No................  ML23265A150.
Location in Application of NSHC...  Pages 7-9 of Attachment 1.
Brief Description of Amendment....  The proposed amendment would modify
                                     License Condition 2.C(1) and
                                     Technical Specifications (TSs)
                                     Sections 1.0, 2.1(b)1, 2.1(b)6,
                                     2.3(b)1, and 2.3(b)2 to remove
                                     restrictions that currently
                                     preclude certain decommissioning
                                     activities without prior NRC
                                     approval. The proposed changes
                                     would amend the applicable License
                                     Condition and TSs to eliminate
                                     legacy restrictions and adopt
                                     requirements that more closely
                                     align with the current standards
                                     and guidance that govern
                                     decommissioning activities/efforts
                                     as specified in 10 CFR 50.82.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Donald P. Ferraro, Assistant General
 Mailing Address.                    Counsel, Constellation Energy
                                     Generation, LLC, 200 Exelon Way,
                                     Suite 305, Kennett Square, PA
                                     19348.
NRC Project Manager, Telephone      Tanya Hood, 301-415-1387.
 Number.
------------------------------------------------------------------------
Constellation FitzPatrick, LLC and Constellation Energy Generation, LLC;
       James A. FitzPatrick Nuclear Power Plant; Oswego County, NY
------------------------------------------------------------------------
Docket No.........................  50-333.
Application date..................  December 14, 2023.
ADAMS Accession No................  ML23348A154.
Location in Application of NSHC...  Pages 7-8 of Attachment 1.
Brief Description of Amendment(s).  The proposed amendment would modify
                                     Technical Specification (TS)
                                     requirements in Section 1.3
                                     regarding Completion Times and
                                     Section 3.0 regarding Limiting
                                     Condition for Operation and
                                     Surveillance Requirement usage.
                                     These changes are consistent with
                                     the NRC-approved Technical
                                     Specification Task Force (TSTF)
                                     Traveler TSTF-529, Revision 4,
                                     ``Clarify Use and Application
                                     Rules.'' Additionally, the proposed
                                     amendment makes several
                                     administrative changes to the TS.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Jason Zorn, Associate General
 Mailing Address.                    Counsel, Constellation Energy
                                     Generation, 101 Constitution Ave.
                                     NW, Suite 400 East, Washington, DC
                                     20001.
NRC Project Manager, Telephone      James Kim, 301-415-4125.
 Number.
------------------------------------------------------------------------
    Energy Northwest; Columbia Generating Station; Benton County, WA
------------------------------------------------------------------------
Docket No.........................  50-397.
Application date..................  December 5, 2023.
ADAMS Accession No................  ML23339A124.
Location in Application of NSHC...  Pages 2-3 of the Enclosure.
Brief Description of Amendment....  The proposed amendment would modify
                                     Technical Specification (TS)
                                     3.3.6.1, ``Primary Containment
                                     Isolation Instrumentation,'' to
                                     remove the requirement that the
                                     Reactor Water Cleanup (RWCU) System
                                     automatically isolate on manual
                                     initiation of the Standby Liquid
                                     Control (SLC) System. This change
                                     to the TS facilitates a future
                                     change to the plant design and
                                     procedures to require manually
                                     isolating the RWCU System when
                                     manually initiating the SLC System.
                                     The proposed change is consistent
                                     with NRC-approved Technical
                                     Specification Task Force (TSTF)
                                     Traveler TSTF-584, Revision 0,
                                     ``Eliminate Automatic RWCU System
                                     Isolation on SLC Initiation.''
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Ryan Lukson, Assistant General
 Mailing Address.                    Counsel, Energy Northwest, MD 1020,
                                     P.O. Box 968, Richland, WA 99352.
NRC Project Manager, Telephone      Mahesh Chawla, 301-415-8371.
 Number.
------------------------------------------------------------------------
 Florida Power & Light Company; Turkey Point Nuclear Generating Units 3
                      and 4; Miami-Dade County, FL
------------------------------------------------------------------------
Docket Nos........................  50-250, 50-251.

[[Page 12876]]

 
Application date..................  November 15, 2023.
ADAMS Accession No................  ML23320A028.
Location in Application of NSHC...  Page 42-46 of Enclosure 1.
Brief Description of Amendments...  The proposed amendments would revise
                                     the Turkey Point Nuclear Generating
                                     Units 3 and 4 licensing basis by
                                     incorporating advanced fuel
                                     features (e.g., AXIOM[supreg]
                                     cladding, ADOPTTM fuel pellets, and
                                     a PRIMETM fuel skeleton), extend
                                     Technical Specification (TS)
                                     surveillance intervals, modify TS
                                     Allowable Values, and make
                                     conforming changes to the Updated
                                     Final Safety Analysis Report to
                                     facilitate a transition to 24-month
                                     fuel cycles.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Steven Hamrick, Senior Attorney 801
 Mailing Address.                    Pennsylvania Ave. NW, Suite 220
                                     Washington, DC 20004.
NRC Project Manager, Telephone      Michael Mahoney, 301-415-3867.
 Number.
------------------------------------------------------------------------
 Southern Nuclear Operating Company, Inc.; Edwin I. Hatch Nuclear Plant,
                    Units 1 and 2; Appling County, GA
------------------------------------------------------------------------
Docket Nos........................  50-321, 50-366.
Application date..................  August 19, 2022, as supplemented by
                                     letters dated January 20, 2023;
                                     October 20, 2023; January 30, 2024.
ADAMS Accession Nos...............  ML22231B055, ML23020A902,
                                     ML23293A235, ML24030A895.
Location in Application of NSHC...  Pages E1-11 to E1-12 of Attachment 3
                                     in supplement dated January 30,
                                     2024.
Brief Description of Amendments...  The proposed amendments would revise
                                     the renewed facility operating
                                     licenses and Technical
                                     Specifications Table 1.1-1,
                                     ``MODES,'' to relax the required
                                     number of fully tensioned reactor
                                     pressure vessel closure studs.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Millicent Ronnlund, Vice President
 Mailing Address.                    and General Counsel, Southern
                                     Nuclear Operating Co., Inc., P.O.
                                     Box 1295, Birmingham, AL 35201-
                                     1295.
NRC Project Manager, Telephone      Andrea Johnson 301-415-2890.
 Number.
------------------------------------------------------------------------
 Southern Nuclear Operating Company, Inc.; Edwin I. Hatch Nuclear Plant,
                    Units 1 and 2; Appling County, GA
------------------------------------------------------------------------
Docket Nos........................  50-321, 50-366.
Application date..................  December 6, 2023.
ADAMS Accession No................  ML23340A223.
Location in Application of NSHC...  Pages A1-4 to A1-5 of Attachment 1.
Brief Description of Amendments...  The proposed amendments would modify
                                     the Edwin I. Hatch Nuclear Plant,
                                     Units 1 and 2, Technical
                                     Specification (TS) requirements
                                     related to Completion Times (CTs)
                                     for Required Actions to provide the
                                     option to calculate a longer, risk-
                                     informed CT for the condition of
                                     one pump inoperable for TS 3.7.1,
                                     ``Residual Heat Removal Service
                                     Water (RHRSW) System,'' and for TS
                                     3.7.2, ``Plant Service Water (PSW)
                                     System and Ultimate Heat Sink
                                     (UHS).'' The proposed amendments
                                     would also make corresponding
                                     changes to TS 5.5.16, ``Risk
                                     Informed Completion Time Program,''
                                     and to TS 1.3, ``Completion
                                     Times,'' Example 1.3-8.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Millicent Ronnlund, Vice President
 Mailing Address.                    and General Counsel, Southern
                                     Nuclear Operating Co., Inc., P.O.
                                     Box 1295, Birmingham, AL 35201-
                                     1295.
NRC Project Manager, Telephone      John Lamb, 301-415-3100.
 Number.
------------------------------------------------------------------------
    Tennessee Valley Authority; Watts Bar Nuclear Plant, Unit 1; Rhea
                               County, TN
------------------------------------------------------------------------
Docket No.........................  50-390.
Application date..................  January 8, 2024.
ADAMS Accession No................  ML24009A165.
Location in Application of NSHC...  Pages E6 and E7 of the Enclosure.
Brief Description of Amendment....  The proposed amendment would revise
                                     Watts Bar Nuclear Plant, Unit 1,
                                     Technical Specification 3.8.2, ``AC
                                     Sources-Shutdown,'' Limiting
                                     Condition for Operation to remove
                                     the note regarding the C-S diesel
                                     generator.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      David Fountain, Executive VP and
 Mailing Address.                    General Counsel, Tennessee Valley
                                     Authority, 6A West Tower, 400 West
                                     Summit Hill Drive, Knoxville, TN
                                     37902.
NRC Project Manager, Telephone      Kimberly Green, 301-415-1627.
 Number.
------------------------------------------------------------------------
Tennessee Valley Authority; Watts Bar Nuclear Plant, Units 1 and 2; Rhea
                               County, TN
------------------------------------------------------------------------
Docket Nos........................  50-390, 50-391.
Application date..................  December 13, 2023.
ADAMS Accession No................  ML23347A161.
Location in Application of NSHC...  TSTF-5: pages E-5 and E-6; TSTF-9:
                                     pages E-9 and E-10; TSTF-12: pages
                                     E-12 and E-13; TSTF-13: pages E-15
                                     and E-16; TSTF-14: pages E-18 and E-
                                     19; TSTF-109: pages E-21 and E-22;
                                     TSTF-110: pages E-25 and E-26; TSTF-
                                     135: pages E-30 and E-31; TSTF-136:
                                     pages E-33 and E-34; TSTF-142:
                                     pages E-36 and E-37; TSTF-241:
                                     pages E-41 and E-42; TSTF-256:
                                     pages E-44 and E-45; TSTF-339:
                                     pages E-47 and E-48.

[[Page 12877]]

 
Brief Description of Amendments...  The proposed amendments would revise
                                     various technical specifications
                                     (TS) in Watts Bar Nuclear Plant,
                                     Units 1 and 2 TS 2.0, 3.0, 3.1,
                                     3.2, 3.3, 3.4, and 5.9.5 by
                                     adopting the following Technical
                                     Specifications Task Force (TSTF)
                                     Travelers: TSTF-5-A, Revision 1,
                                     ``Delete Safety Limit Violation
                                     Notification Requirements,'' TSTF-9-
                                     A, Revision 1, ``Relocate Value for
                                     Shutdown Margin to COLR [core
                                     operating limit report],'' TSTF-12-
                                     A, Revision 1, ``Delete LCO
                                     [limiting condition for operation]
                                     3.1.9 and 3.1.11 (Physics Tests
                                     Exceptions),'' TSTF-13-A, Revision
                                     1, ``Move SR [surveillance
                                     requirement] For 300 ppm MTC
                                     [moderator temperature coefficient]
                                     Measurement to Frequency Note of SR
                                     3.1.4.3,'' TSTF-14-A, Revision 4,
                                     ``Add an LCO Item and SR to Mode 2
                                     Physics Tests Exceptions To Verify
                                     That Thermal Power <= 5% RTP [rated
                                     thermal power],'' TSTF-109-A,
                                     ``Clarify the QPTR [quadrant power
                                     tilt ratio] Surveillances,'' TSTF-
                                     110-A, Revision 2, ``Delete SR
                                     Frequencies Based on Inoperable
                                     Alarms,'' TSTF-135-A, Revision 3,
                                     ``RPS [reactor protection system]
                                     and ESFAS [engineered safety
                                     features actuation signals]
                                     Instrumentation,'' TSTF-136-A,
                                     ``Combine LCO 3.1.1 and 3.1.2,''
                                     TSTF-142-A, ``Increase the
                                     Completion Time When the Core
                                     Reactivity Balance is Not Within
                                     Limit,'' TSTF-241-A, Revision 4,
                                     ``Allow Time for Stabilization
                                     After Reducing Power Due to QPTR
                                     Out-of-Limit,'' TSTF-256-A,
                                     ``Modify MODE 2 STE [special test
                                     exemption] Applicability,'' and
                                     TSTF-339-A, Revision 2, ``Relocate
                                     TS Parameters to COLR.'' The
                                     amendments would also delete one-
                                     time historical information from TS
                                     Surveillance Requirements 3.1.3.1
                                     and 3.1.4.1, and make editorial
                                     changes for items that are not
                                     consistent with Standard Technical
                                     Specifications.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      David Fountain, Executive VP and
 Mailing Address.                    General Counsel, Tennessee Valley
                                     Authority, 6A West Tower, 400 West
                                     Summit Hill Drive, Knoxville, TN
                                     37902.
NRC Project Manager, Telephone      Tony Sierra, 301-287-9531.
 Number.
------------------------------------------------------------------------

III. Notice of Issuance of Amendments to Facility Operating Licenses 
and Combined Licenses

    During the period since publication of the last monthly notice, the 
Commission has issued the following amendments. The Commission has 
determined for each of these amendments that the application complies 
with the standards and requirements of the Atomic Energy Act of 1954, 
as amended (the Act), and the Commission's rules and regulations. The 
Commission has made appropriate findings as required by the Act and the 
Commission's rules and regulations in 10 CFR chapter I, which are set 
forth in the license amendment.
    A notice of consideration of issuance of amendment to facility 
operating license or combined license, as applicable, proposed NSHC 
determination, and opportunity for a hearing in connection with these 
actions, were published in the Federal Register as indicated in the 
safety evaluation for each amendment.
    Unless otherwise indicated, the Commission has determined that 
these amendments satisfy the criteria for categorical exclusion in 
accordance with 10 CFR 51.22. Therefore, pursuant to 10 CFR 51.22(b), 
no environmental impact statement or environmental assessment need be 
prepared for these amendments. If the Commission has prepared an 
environmental assessment under the special circumstances provision in 
10 CFR 51.22(b) and has made a determination based on that assessment, 
it is so indicated in the safety evaluation for the amendment.
    For further details with respect to each action, see the amendment 
and associated documents such as the Commission's letter and safety 
evaluation, which may be obtained using the ADAMS accession numbers 
indicated in the following table. The safety evaluation will provide 
the ADAMS accession numbers for the application for amendment and the 
Federal Register citation for any environmental assessment. All of 
these items can be accessed as described in the ``Obtaining Information 
and Submitting Comments'' section of this document.

                       License Amendment Issuances
------------------------------------------------------------------------
 
------------------------------------------------------------------------
Dominion Energy Nuclear Connecticut, Inc.; Millstone Power Station, Unit
                      No. 3; New London County, CT
------------------------------------------------------------------------
Docket No.........................  50-423.
Amendment Date....................  January 12, 2024.
ADAMS Accession No................  ML23341A017.
Amendment No......................  288.
Brief Description of Amendment....  The amendment revised the Millstone
                                     Power Station, Unit No. 3 Technical
                                     Specification 3.4.9.1, ``Reactor
                                     Coolant System Pressure/Temperature
                                     Limits,'' to reflect that the
                                     existing pressure-temperature limit
                                     curves for 32 effective full power
                                     years (EFPY) in Figures 3.4-2 and
                                     3.4-3 of TS 3.4.9.1 are applicable
                                     up to 54 EFPY.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Entergy Operations, Inc.; Arkansas Nuclear One, Unit 1; Pope County, AR
------------------------------------------------------------------------
Docket No.........................  50-313.
Amendment Date....................  January 24, 2024.
ADAMS Accession No................  ML23326A039.
Amendment No......................  281.

[[Page 12878]]

 
Brief Description of Amendment....  The amendment revised the technical
                                     specifications to permit the use of
                                     risk-informed completion times for
                                     actions to be taken when limiting
                                     conditions for operation are not
                                     met. The changes are based on
                                     Technical Specifications Task Force
                                     (TSTF) Traveler TSTF-505, Revision
                                     2, ``Provide Risk-informed Extended
                                     Completion Times--RITSTF [Risk-
                                     Informed TSTF] Initiative 4b,''
                                     dated July 2, 2018 (ML18183A493).
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
Florida Power & Light Company; Turkey Point Nuclear Generating Unit Nos.
                     3 and 4; Miami-Dade County, FL
------------------------------------------------------------------------
Docket No.........................  50-250, 50-251.
Amendment Date....................  January 22, 2024.
ADAMS Accession No................  ML23320A306.
Amendment Nos.....................  298 (Unit 3), 291 (Unit 4).
Brief Description of Amendments...  The amendments revised the Fire
                                     Protection Program in support of
                                     reactor coolant pump (RCP) seal
                                     replacements. The amendments were
                                     requested in accordance with the
                                     units' operating licenses,
                                     paragraph 3.D, ``Fire Protection,''
                                     for Fire Protection Program changes
                                     that may be made without prior NRC
                                     approval. One of the criteria for
                                     such a change is that the risk
                                     increase resulting from the change
                                     is less than 1 x 10-7/year (yr) for
                                     core damage frequency and less than
                                     1 x 10-8/yr for large early release
                                     frequency. The change is to support
                                     replacement of the currently
                                     installed RCP seals with the
                                     Framatome RCP hydrostatic seal
                                     package equipped with the passive
                                     shutdown seal.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 NextEra Energy Point Beach, LLC; Point Beach Nuclear Plant, Units 1 and
                         2; Manitowoc County, WI
------------------------------------------------------------------------
Docket Nos........................  50-266, 50-301.
Amendment Date....................  January 23, 2024.
ADAMS Accession No................  ML23352A275.
Amendment Nos.....................  274 (Unit 1), 276 (Unit 2).
Brief Description of Amendments...  The amendments revised Technical
                                     Specification (TS) 5.5.17, ``Pre-
                                     Stressed Concrete Containment
                                     Tendon Surveillance Program,'' to
                                     replace the reference to Regulatory
                                     Guide 1.35, ``Inservice Inspection
                                     of Ungrouted Tendons in Prestressed
                                     Concrete Containments,'' with a
                                     reference to Section XI, Subsection
                                     IWL of the American Society of
                                     Mechanical Engineers Boiler and
                                     Pressure Vessel Code. Additionally,
                                     the provisions of Surveillance
                                     Requirement 3.0.2 in TS 5.5.17 were
                                     also deleted by the license
                                     amendment.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
    Northern States Power Company--Minnesota; Prairie Island Nuclear
           Generating Plant, Units 1 and 2; Goodhue County, MN
------------------------------------------------------------------------
Docket Nos........................  50-282, 50-306.
Amendment Date....................  January 17, 2024.
ADAMS Accession No................  ML23356A003.
Amendment Nos.....................  243 (Unit 1), 231 (Unit 2).
Brief Description of Amendments...  The amendments revised Technical
                                     Specification 5.6.6, ``Reactor
                                     Coolant System (RCS) Pressure and
                                     Temperature Limits Report (PTLR),''
                                     to replace the current PTLR method
                                     with more recent analytical methods
                                     and remove a reference to an
                                     American Society of Mechanical
                                     Engineers Code Case.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
    PSEG Nuclear LLC; Hope Creek Generating Station; Salem County, NJ
------------------------------------------------------------------------
Docket No.........................  50-354.
Amendment Date....................  January 16, 2024.
ADAMS Accession No................  ML23341A137.
Amendment No......................  235.
Brief Description of Amendment....  The amendment modified the operation
                                     of safety-related heating,
                                     ventilation, and air conditioning
                                     (HVAC) trains as described in the
                                     updated final safety analysis
                                     report for Hope Creek. The change
                                     modified a portion of the trip and
                                     standby start logic for the safety-
                                     related HVAC trains from an
                                     automatic function to a manual
                                     operator action.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
  Southern Nuclear Operating Company, Inc.; Vogtle Electric Generating
                     Plant, Unit 4; Burke County, GA
------------------------------------------------------------------------
Docket No.........................  52-026.
Amendment Date....................  January 17, 2024.
ADAMS Accession No................  ML23279A004.
Amendment No......................  194.

[[Page 12879]]

 
Brief Description of Amendment....  The amendment removed Appendix C,
                                     ``Inspections, Tests, Analyses, and
                                     Acceptance Criteria'' (ITAAC) in
                                     its entirety from the Combined
                                     Operating License (COL) along with
                                     specific references to Appendix C
                                     within license conditions contained
                                     in the COL. In addition, the
                                     amendment deleted license
                                     conditions 2.D(2)(d) and 2.D(3)(b)
                                     that reference Appendix C. The
                                     staff made its 10 CFR 52.103(g)
                                     finding for Vogtle Unit 4 on July
                                     28, 2023. The regulations in 10 CFR
                                     52.103(h) and 10 CFR part 52,
                                     appendix D, IX.B.3 state that ITAAC
                                     are no longer requirements
                                     following the 10 CFR 52.103(g)
                                     finding. No ITAAC listed in
                                     Appendix C to COL NPF-92 are the
                                     subject of a Sec.   52.103(a)
                                     hearing. Thus, all Vogtle Unit 4
                                     ITAAC expired upon the making of
                                     the 10 CFR 52.103(g) finding.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Tennessee Valley Authority; Browns Ferry Nuclear Plant, Units 1, 2, and
                         3; Limestone County, AL
------------------------------------------------------------------------
Docket Nos........................  50-259, 50-260, 50-296.
Amendment Date....................  January 3, 2024.
ADAMS Accession No................  ML23319A199.
Amendment Nos.....................  333 (Unit 1), 356 (Unit 2), 316
                                     (Unit 3).
Brief Description of Amendments...  The amendments revised Browns Ferry
                                     Nuclear Plant, Units 1, 2, and 3
                                     Technical Specification
                                     Surveillance Requirements 3.4.3.2
                                     and 3.5.1.11 by supplementing the
                                     current requirement to verify the
                                     safety relief valves and automatic
                                     depressurization valves,
                                     respectively, open when manually
                                     actuated with an alternate
                                     requirement that demonstrates the
                                     valves are capable of being opened
                                     in accordance with the inservice
                                     testing program (IST) and revising
                                     the frequency to conform with the
                                     IST.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
   Tennessee Valley Authority; Sequoyah Nuclear Plant, Units 1 and 2;
   Hamilton County, TN; Tennessee Valley Authority; Watts Bar Nuclear
                  Plant, Units 1 and 2; Rhea County, TN
------------------------------------------------------------------------
Docket Nos........................  50-327, 50-328, 50-390, 50-391.
Amendment Date....................  January 31, 2024.
ADAMS Accession No................  ML23319A245.
Amendment Nos.....................  Sequoyah 366 (Unit 1), 360 (Unit 2);
                                     Watts Bar 164 (Unit 1), 71 (Unit
                                     2).
Brief Description of Amendments...  The amendments revised Sequoyah
                                     Nuclear Plant, Units 1 and 2, and
                                     the Watts Bar Nuclear Plant, Units
                                     1 and 2 technical specifications
                                     (TSs) to adopt Technical
                                     Specifications Task Force (TSTF)
                                     Traveler TSTF-567-A, Revision 1,
                                     ``Add Containment Sump TS to
                                     Address GSI [Generic Safety Issue]--
                                     191 Issues,'' by adding a new TS
                                     3.6.16, ``Containment Sump,'' and
                                     adding an Action to address the
                                     condition of the containment sump
                                     made inoperable due to containment
                                     accident generated and transported
                                     debris exceeding the analyzed
                                     limits. The action provided time to
                                     correct or evaluate the condition
                                     in lieu of an immediate plant
                                     shutdown.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Union Electric Company; Callaway Plant, Unit No. 1; Callaway County, MO
------------------------------------------------------------------------
Docket No.........................  50-483.
Amendment Date....................  January 18, 2024.
ADAMS Accession No................  ML23353A171.
Amendment No......................  237.
Brief Description of Amendment....  The amendment revised the Callaway
                                     Plant Licensing Basis (i.e., the
                                     final safety analysis report and
                                     technical specifications (TSs)), to
                                     allow use of one train of the
                                     normal, non-safety-related service
                                     water system to solely provide
                                     cooling water support for one of
                                     two redundant trains of TS-required
                                     equipment when both equipment
                                     trains are required to be operable
                                     during cold shutdown/refueling
                                     conditions. The supported equipment/
                                     systems affected by the proposed
                                     change are the residual heat
                                     removal system and control room air
                                     conditioning system, as applicable
                                     during Modes 5 and 6. The
                                     applicable/affected TS limiting
                                     conditions for operation are TS
                                     3.4.8, ``RCS [Reactor Coolant
                                     System] Loops--Mode 5, Loops Not
                                     Filled''; TS 3.7.11, ``Control Room
                                     Air Conditioning System (CRACS)'';
                                     and TS 3.9.6, ``Residual Heat
                                     Removal (RHR) and Coolant
                                     Circulation--Low Water Level.''
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Union Electric Company; Callaway Plant, Unit No. 1; Callaway County, MO
------------------------------------------------------------------------
Docket No.........................  50-483.
Amendment Date....................  January 11, 2024.
ADAMS Accession No................  ML23347A121.
Amendment No......................  236.

[[Page 12880]]

 
Brief Description of Amendment....  The amendment revised Technical
                                     Specification (TS) 3.8.3, ``Diesel
                                     Fuel Oil, Lube Oil, and Starting
                                     Air,'' Surveillance Requirement
                                     (SR) 3.8.3.1 (verification of fuel
                                     oil storage tank volume), and SR
                                     3.8.3.2 (verification of lube oil
                                     inventory volume), by removing the
                                     current stored diesel fuel oil and
                                     lube oil numerical volume
                                     requirements and replacing them
                                     with duration-based diesel
                                     operating time requirements,
                                     consistent with Technical
                                     Specifications Task Force (TSTF)
                                     Traveler TSTF-501, Revision 1,
                                     ``Relocate Stored Fuel Oil and Lube
                                     Oil Volume Values to Licensee
                                     Control,'' dated February 20, 2009
                                     (ML090510686).
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
Virginia Electric and Power Company; Surry Power Station, Units 1 and 2;
                            Surry County, VA
------------------------------------------------------------------------
Docket Nos........................  50-280, 50-281.
Amendment Date....................  January 18, 2024.
ADAMS Accession No................  ML23312A192.
Amendment Nos.....................  316 (Unit 1), 316 (Unit 2).
Brief Description of Amendments...  The amendments applied a risk-
                                     informed approach to demonstrate
                                     the fuel handling trolley support
                                     structure, as designed, meets the
                                     intent of a tornado resistant
                                     structure under Surry Power
                                     Station's current licensing basis
                                     considering a maximum tornado wind
                                     speed.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------

IV. Previously Published Notice of Consideration of Issuance of 
Amendments to Facility Operating Licenses and Combined Licenses, 
Proposed No Significant Hazards Consideration Determination, and 
Opportunity for a Hearing

    The following notice was previously published as separate 
individual notice. It was published as an individual notice either 
because time did not allow the Commission to wait for this monthly 
notice or because the action involved exigent circumstances. It is 
repeated here because the monthly notice lists all amendments issued or 
proposed to be issued involving NSHC.
    For details, including the applicable notice period, see the 
individual notice in the Federal Register on the day and page cited.

 License Amendment Request--Repeat of Individual Federal Register Notice
------------------------------------------------------------------------
 
------------------------------------------------------------------------
Wolf Creek Nuclear Operating Corporation; Wolf Creek Generating Station,
                        Unit 1; Coffey County, KS
------------------------------------------------------------------------
Docket No.........................  50-482.
Application Date..................  January 18, 2024.
ADAMS Accession No................  ML24018A248.
Brief Description of Amendment....  The proposed amendment would modify
                                     the implementation date of License
                                     Amendment No. 238 for Wolf Creek
                                     Generating Station, Unit 1.
Date & Cite of Federal Register     Published January 26, 2024; 89 FR
 Individual Notice.                  5267.
Expiration Dates for Public         February 26, 2024 (Public Comments);
 Comments & Hearing Requests.        March 26, 2024 (Hearing Requests).
------------------------------------------------------------------------


    Dated: February 12, 2024.

    For the Nuclear Regulatory Commission.
Bo M. Pham,
Director, Division of Operating Reactor Licensing, Office of Nuclear 
Reactor Regulation.
[FR Doc. 2024-03243 Filed 2-16-24; 8:45 am]
BILLING CODE 7590-01-P