[Federal Register Volume 86, Number 131 (Tuesday, July 13, 2021)]
[Notices]
[Pages 36776-36785]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2021-14642]


=======================================================================
-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION

[NRC-2021-0136]


Monthly Notice; Applications and Amendments to Facility Operating 
Licenses and Combined Licenses Involving No Significant Hazards 
Considerations

AGENCY: Nuclear Regulatory Commission.

ACTION: Monthly notice.

-----------------------------------------------------------------------

SUMMARY: Pursuant to section 189.a.(2) of the Atomic Energy Act of 
1954, as amended (the Act), the U.S. Nuclear Regulatory Commission 
(NRC) is publishing this regular monthly notice. The Act requires the 
Commission to publish notice of any amendments issued, or proposed to 
be issued, and grants the Commission the authority to issue and make 
immediately effective any amendment to an operating license or combined 
license, as applicable, upon a determination by the Commission that 
such amendment involves no significant hazards consideration (NSHC), 
notwithstanding the pendency before the Commission of a request for a 
hearing from any person. This monthly notice includes all amendments 
issued, or proposed to be

[[Page 36777]]

issued, from May 27, 2021, to June 24, 2021. The last monthly notice 
was published on June 15, 2021.

DATES: Comments must be filed by August 12, 2021. A request for a 
hearing or petitions for leave to intervene must be filed by September 
13, 2021.

ADDRESSES: You may submit comments by any of the following methods; 
however, the NRC encourages electronic comment submission through the 
Federal Rulemaking website:
     Federal Rulemaking Website: Go to https://www.regulations.gov and search for Docket ID NRC-2021-0136. Address 
questions about Docket IDs in Regulations.gov to Stacy Schumann; 
telephone: 301-415-0624; email: [email protected]. For technical 
questions, contact the individual listed in the FOR FURTHER INFORMATION 
CONTACT section of this document.
     Mail comments to: Office of Administration, Mail Stop: 
TWFN-7-A60M, U.S. Nuclear Regulatory Commission, Washington, DC 20555-
0001, ATTN: Program Management, Announcements and Editing Staff.
    For additional direction on obtaining information and submitting 
comments, see ``Obtaining Information and Submitting Comments'' in the 
SUPPLEMENTARY INFORMATION section of this document.

FOR FURTHER INFORMATION CONTACT: Paula Blechman, Office of Nuclear 
Reactor Regulation, U.S. Nuclear Regulatory Commission, Washington, DC 
20555-0001, telephone: 301-415-2242, email: [email protected].

SUPPLEMENTARY INFORMATION:

I. Obtaining Information and Submitting Comments

A. Obtaining Information

    Please refer to Docket ID NRC-2021-0136, facility name, unit 
number(s), docket number(s), application date, and subject when 
contacting the NRC about the availability of information for this 
action. You may obtain publicly available information related to this 
action by any of the following methods:
     Federal Rulemaking Website: Go to https://www.regulations.gov and search for Docket ID NRC-2021-0136.
     NRC's Agencywide Documents Access and Management System 
(ADAMS): You may obtain publicly available documents online in the 
ADAMS Public Documents collection at https://www.nrc.gov/reading-rm/adams.html. To begin the search, select ``Begin Web-based ADAMS 
Search.'' For problems with ADAMS, please contact the NRC's Public 
Document Room (PDR) reference staff at 1-800-397-4209, 301-415-4737, or 
by email to [email protected]. The ADAMS accession number for each 
document referenced (if it is available in ADAMS) is provided the first 
time that it is mentioned in this document.
     Attention: The PDR, where you may examine and order copies 
of public documents, is currently closed. You may submit your request 
to the PDR via email at [email protected] or call 1-800-397-4209 or 
301-415-4737, between 8:00 a.m. and 4:00 p.m. (EST), Monday through 
Friday, except Federal holidays.

B. Submitting Comments

    The NRC encourages electronic comment submission through the 
Federal Rulemaking website (https://www.regulations.gov). Please 
include Docket ID NRC-2021-0136, facility name, unit number(s), docket 
number(s), application date, and subject, in your comment submission.
    The NRC cautions you not to include identifying or contact 
information that you do not want to be publicly disclosed in your 
comment submission. The NRC will post all comment submissions at 
https://www.regulations.gov as well as enter the comment submissions 
into ADAMS. The NRC does not routinely edit comment submissions to 
remove identifying or contact information.
    If you are requesting or aggregating comments from other persons 
for submission to the NRC, then you should inform those persons not to 
include identifying or contact information that they do not want to be 
publicly disclosed in their comment submission. Your request should 
state that the NRC does not routinely edit comment submissions to 
remove such information before making the comment submissions available 
to the public or entering the comment into ADAMS.

II. Notice of Consideration of Issuance of Amendments to Facility 
Operating Licenses and Combined Licenses and Proposed No Significant 
Hazards Consideration Determination

    For the facility-specific amendment requests shown below, the 
Commission finds that the licensees' analyses provided, consistent with 
title 10 of the Code of Federal Regulations (10 CFR) section 50.91, are 
sufficient to support the proposed determinations that these amendment 
requests involve NSHC. Under the Commission's regulations in 10 CFR 
50.92, operation of the facilities in accordance with the proposed 
amendments would not (1) involve a significant increase in the 
probability or consequences of an accident previously evaluated; or (2) 
create the possibility of a new or different kind of accident from any 
accident previously evaluated; or (3) involve a significant reduction 
in a margin of safety.
    The Commission is seeking public comments on these proposed 
determinations. Any comments received within 30 days after the date of 
publication of this notice will be considered in making any final 
determinations.
    Normally, the Commission will not issue the amendments until the 
expiration of 60 days after the date of publication of this notice. The 
Commission may issue any of these license amendments before expiration 
of the 60-day period provided that its final determination is that the 
amendment involves NSHC. In addition, the Commission may issue any of 
these amendments prior to the expiration of the 30-day comment period 
if circumstances change during the 30-day comment period such that 
failure to act in a timely way would result, for example in derating or 
shutdown of the facility. If the Commission takes action on any of 
these amendments prior to the expiration of either the comment period 
or the notice period, it will publish in the Federal Register a notice 
of issuance. If the Commission makes a final NSHC determination for any 
of these amendments, any hearing will take place after issuance. The 
Commission expects that the need to take action on any amendment before 
60 days have elapsed will occur very infrequently.

A. Opportunity To Request a Hearing and Petition for Leave To Intervene

    Within 60 days after the date of publication of this notice, any 
persons (petitioner) whose interest may be affected by any of these 
actions may file a request for a hearing and petition for leave to 
intervene (petition) with respect to that action. Petitions shall be 
filed in accordance with the Commission's ``Agency Rules of Practice 
and Procedure'' in 10 CFR part 2. Interested persons should consult a 
current copy of 10 CFR 2.309. The NRC's regulations are accessible 
electronically from the NRC Library on the NRC's website at https://www.nrc.gov/reading-rm/doc-collections/cfr/. If a petition is filed, 
the Commission or a presiding officer will rule on the petition and, if 
appropriate, a notice of a hearing will be issued.
    As required by 10 CFR 2.309(d) the petition should specifically 
explain the reasons why intervention should be permitted with 
particular reference to the following general requirements for 
standing: (1) The name, address, and

[[Page 36778]]

telephone number of the petitioner; (2) the nature of the petitioner's 
right to be made a party to the proceeding; (3) the nature and extent 
of the petitioner's property, financial, or other interest in the 
proceeding; and (4) the possible effect of any decision or order which 
may be entered in the proceeding on the petitioner's interest.
    In accordance with 10 CFR 2.309(f), the petition must also set 
forth the specific contentions that the petitioner seeks to have 
litigated in the proceeding. Each contention must consist of a specific 
statement of the issue of law or fact to be raised or controverted. In 
addition, the petitioner must provide a brief explanation of the bases 
for the contention and a concise statement of the alleged facts or 
expert opinion that support the contention and on which the petitioner 
intends to rely in proving the contention at the hearing. The 
petitioner must also provide references to the specific sources and 
documents on which the petitioner intends to rely to support its 
position on the issue. The petition must include sufficient information 
to show that a genuine dispute exists with the applicant or licensee on 
a material issue of law or fact. Contentions must be limited to matters 
within the scope of the proceeding. The contention must be one that, if 
proven, would entitle the petitioner to relief. A petitioner who fails 
to satisfy the requirements at 10 CFR 2.309(f) with respect to at least 
one contention will not be permitted to participate as a party.
    Those permitted to intervene become parties to the proceeding, 
subject to any limitations in the order granting leave to intervene. 
Parties have the opportunity to participate fully in the conduct of the 
hearing with respect to resolution of that party's admitted 
contentions, including the opportunity to present evidence, consistent 
with the NRC's regulations, policies, and procedures.
    Petitions must be filed no later than 60 days from the date of 
publication of this notice. Petitions and motions for leave to file new 
or amended contentions that are filed after the deadline will not be 
entertained absent a determination by the presiding officer that the 
filing demonstrates good cause by satisfying the three factors in 10 
CFR 2.309(c)(1)(i) through (iii). The petition must be filed in 
accordance with the filing instructions in the ``Electronic Submissions 
(E-Filing)'' section of this document.
    If a hearing is requested, and the Commission has not made a final 
determination on the issue of NSHC, the Commission will make a final 
determination on the issue of NSHC. The final determination will serve 
to establish when the hearing is held. If the final determination is 
that the amendment request involves NSHC, the Commission may issue the 
amendment and make it immediately effective, notwithstanding the 
request for a hearing. Any hearing would take place after issuance of 
the amendment. If the final determination is that the amendment request 
involves a significant hazards consideration, then any hearing held 
would take place before the issuance of the amendment unless the 
Commission finds an imminent danger to the health or safety of the 
public, in which case it will issue an appropriate order or rule under 
10 CFR part 2.
    A State, local governmental body, Federally recognized Indian 
Tribe, or agency thereof, may submit a petition to the Commission to 
participate as a party under 10 CFR 2.309(h)(1). The petition should 
state the nature and extent of the petitioner's interest in the 
proceeding. The petition should be submitted to the Commission no later 
than 60 days from the date of publication of this notice. The petition 
must be filed in accordance with the filing instructions in the 
``Electronic Submissions (E-Filing)'' section of this document, and 
should meet the requirements for petitions set forth in this section, 
except that under 10 CFR 2.309(h)(2) a State, local governmental body, 
or Federally recognized Indian Tribe, or agency thereof does not need 
to address the standing requirements in 10 CFR 2.309(d) if the facility 
is located within its boundaries. Alternatively, a State, local 
governmental body, Federally recognized Indian Tribe, or agency thereof 
may participate as a non-party under 10 CFR 2.315(c).
    If a petition is submitted, any person who is not a party to the 
proceeding and is not affiliated with or represented by a party may, at 
the discretion of the presiding officer, be permitted to make a limited 
appearance pursuant to the provisions of 10 CFR 2.315(a). A person 
making a limited appearance may make an oral or written statement of 
his or her position on the issues but may not otherwise participate in 
the proceeding. A limited appearance may be made at any session of the 
hearing or at any prehearing conference, subject to the limits and 
conditions as may be imposed by the presiding officer. Details 
regarding the opportunity to make a limited appearance will be provided 
by the presiding officer if such sessions are scheduled.

B. Electronic Submissions (E-Filing)

    All documents filed in NRC adjudicatory proceedings including 
documents filed by an interested State, local governmental body, 
Federally recognized Indian Tribe, or designated agency thereof that 
requests to participate under 10 CFR 2.315(c), must be filed in 
accordance with 10 CFR 2.302. The E-Filing process requires 
participants to submit and serve all adjudicatory documents over the 
internet, or in some cases, to mail copies on electronic storage media, 
unless an exemption permitting an alternative filing method, as 
discussed below, is granted. Detailed guidance on electronic 
submissions is located in the Guidance for Electronic Submissions to 
the NRC (ADAMS Accession No. ML13031A056) and on the NRC website at 
https://www.nrc.gov/site-help/e-submittals.html.
    To comply with the procedural requirements of E-Filing, at least 10 
days prior to the filing deadline, the participant should contact the 
Office of the Secretary by email at [email protected], or by 
telephone at 301-415-1677, to (1) request a digital identification (ID) 
certificate, which allows the participant (or its counsel or 
representative) to digitally sign submissions and access the E-Filing 
system for any proceeding in which it is participating; and (2) advise 
the Secretary that the participant will be submitting a petition or 
other adjudicatory document (even in instances in which the 
participant, or its counsel or representative, already holds an NRC-
issued digital ID certificate). Based upon this information, the 
Secretary will establish an electronic docket for the proceeding if the 
Secretary has not already established an electronic docket.
    Information about applying for a digital ID certificate is 
available on the NRC's public website at https://www.nrc.gov/site-help/e-submittals/getting-started.html. After a digital ID certificate is 
obtained and a docket created, the participant must submit adjudicatory 
documents in Portable Document Format. Guidance on submissions is 
available on the NRC's public website at https://www.nrc.gov/site-help/electronic-sub-ref-mat.html. A filing is considered complete at the 
time the document is submitted through the NRC's E-Filing system. To be 
timely, an electronic filing must be submitted to the E-Filing system 
no later than 11:59 p.m. Eastern Time on the due date. Upon receipt of 
a transmission, the E-Filing system timestamps the document and sends 
the submitter an email

[[Page 36779]]

confirming receipt of the document. The E-Filing system also 
distributes an email that provides access to the document to the NRC's 
Office of the General Counsel and any others who have advised the 
Office of the Secretary that they wish to participate in the 
proceeding, so that the filer need not serve the document on those 
participants separately. Therefore, applicants and other participants 
(or their counsel or representative) must apply for and receive a 
digital ID certificate before adjudicatory documents are filed to 
obtain access to the documents via the E-Filing system.
    A person filing electronically using the NRC's adjudicatory E-
Filing system may seek assistance by contacting the NRC's Electronic 
Filing Help Desk through the ``Contact Us'' link located on the NRC's 
public website at https://www.nrc.gov/site-help/e-submittals.html, by 
email to [email protected], or by a toll-free call at 1-866-672-
7640. The NRC Electronic Filing Help Desk is available between 9 a.m. 
and 6 p.m., Eastern Time, Monday through Friday, excluding government 
holidays.
    Participants who believe that they have good cause for not 
submitting documents electronically must file an exemption request, in 
accordance with 10 CFR 2.302(g), with their initial paper filing 
stating why there is good cause for not filing electronically and 
requesting authorization to continue to submit documents in paper 
format. Such filings must be submitted in accordance with 10 CFR 
2.302(b)-(d). Participants filing adjudicatory documents in this manner 
are responsible for serving their documents on all other participants. 
Participants granted an exemption under 10 CFR 2.302(g)(2) must still 
meet the electronic formatting requirement in 10 CFR 2.302(g)(1), 
unless the participant also seeks and is granted an exemption from 10 
CFR 2.302(g)(1).
    Documents submitted in adjudicatory proceedings will appear in the 
NRC's electronic hearing docket, which is publicly available at https://adams.nrc.gov/ehd, unless excluded pursuant to an order of the 
presiding officer. If you do not have an NRC-issued digital ID 
certificate as described above, click ``cancel'' when the link requests 
certificates and you will be automatically directed to the NRC's 
electronic hearing dockets where you will be able to access any 
publicly available documents in a particular hearing docket. 
Participants are requested not to include personal privacy information 
such as social security numbers, home addresses, or personal phone 
numbers in their filings unless an NRC regulation or other law requires 
submission of such information. With respect to copyrighted works, 
except for limited excerpts that serve the purpose of the adjudicatory 
filings and would constitute a Fair Use application, participants 
should not include copyrighted materials in their submission.
    The table below provides the plant name, docket number, date of 
application, ADAMS accession number, and location in the application of 
the licensees' proposed NSHC determinations. For further details with 
respect to these license amendment applications, see the applications 
for amendment, which are available for public inspection in ADAMS. For 
additional direction on accessing information related to this document, 
see the ``Obtaining Information and Submitting Comments'' section of 
this document.

                      License Amendment Request(s)
------------------------------------------------------------------------
 
------------------------------------------------------------------------
 Dominion Energy South Carolina, Inc.; Virgil C. Summer Nuclear Station,
                      Unit 1, Fairfield County, SC
------------------------------------------------------------------------
Docket No(s)......................  50-395.
Application date..................  May 27, 2021.
ADAMS Accession No................  ML21147A377.
Location in Application of NSHC...  Pages 1-2 of Attachment 4.
Brief Description of Amendment(s).  The proposed amendment would revise
                                     the Virgil C. Summer Nuclear
                                     Station, Unit 1, Technical
                                     Specification 6.3, ``Unit Staff
                                     Qualifications,'' by relocating the
                                     unit staff qualifications to the
                                     Dominion Energy Nuclear Facility
                                     Quality Assurance Program
                                     Description consistent with
                                     guidance contained in the NRC
                                     Administrative Letter (AL) 95-06,
                                     ``Relocation of Technical
                                     Specification Administrative
                                     Controls to Quality Assurance.''
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      W. S. Blair, Senior Counsel,
 Mailing Address.                    Dominion Resource Services, Inc.,
                                     120 Tredegar St., RS-2, Richmond,
                                     VA 23219.
NRC Project Manager, Telephone      Stephanie Devlin-Gill, 301-415-5301.
 Number.
------------------------------------------------------------------------
    Energy Northwest; Columbia Generating Station; Benton County, WA
------------------------------------------------------------------------
Docket No(s)......................  50-397.
Application date..................  April 28, 2021.
ADAMS Accession No................  ML21118A812.
Location in Application of NSHC...  Pages 9-10 of Enclosure 1.
Brief Description of Amendment(s).  The proposed amendment would remove
                                     License Condition (LC) 2.C.(34) and
                                     revise LC 2.C.(35) for Columbia
                                     Generating Station (Columbia). LC
                                     2.C.(34) is no longer applicable as
                                     the Columbia Final Safety Analysis
                                     Report has been updated to include
                                     the License Renewal (LR)
                                     commitments set forth in NUREG-
                                     2123, ``Safety Evaluation Report
                                     Related to the License Renewal of
                                     Columbia Generating Station,''
                                     published May 2012. The revision to
                                     LC 2.C.(35) would clarify that
                                     future changes to the LR
                                     commitments, as dictated by
                                     operating experience, would be made
                                     under the provisions of 10 CFR
                                     50.59, ``Changes, tests, and
                                     experiments.''
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Kathleen Galioto, Assistant General
 Mailing Address.                    Counsel, Energy Northwest, MD PE13,
                                     P.O. Box 968, Richland, WA 99352.
NRC Project Manager, Telephone      Mahesh Chawla, 301-415-8371.
 Number.
------------------------------------------------------------------------
    Energy Northwest; Columbia Generating Station; Benton County, WA
------------------------------------------------------------------------
Docket No(s)......................  50-397.

[[Page 36780]]

 
Application date..................  May 8, 2021.
ADAMS Accession No................  ML21130A573.
Location in Application of NSHC...  Pages 3-4 of Enclosure 1.
Brief Description of Amendment(s).  The proposed amendment would alter
                                     Surveillance Requirement (SR)
                                     3.3.1.1.2 of Technical
                                     Specification (TS) 3.3.1.1,
                                     ``Reactor Protection System (RPS)
                                     Instrumentation.'' This proposed
                                     change would revise the SR to
                                     verify that calculated (i.e.,
                                     calorimetric heat balance) power is
                                     no more than 2 percent greater than
                                     the average power range monitor
                                     (APRM) channel output. The SR
                                     requires the APRM channel to be
                                     adjusted such that calibrated power
                                     is no more than 2 percent greater
                                     than the APRM indicated power when
                                     operating at greater than or equal
                                     to 25 percent of rated thermal
                                     power. The proposed change is
                                     consistent with Technical
                                     Specifications Task Force (TSTF)
                                     Traveler TSTF-546, Revision 0,
                                     ``Revise APRM Channel Adjustment
                                     Surveillance Requirement.''
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Kathleen Galioto, Assistant General
 Mailing Address.                    Counsel, Energy Northwest, MD PE13,
                                     P.O. Box 968, Richland, WA 99352.
NRC Project Manager, Telephone      Mahesh Chawla, 301-415-8371.
 Number.
------------------------------------------------------------------------
 Entergy Operations, Inc.; Waterford Steam Electric Station, Unit 3; St.
                           Charles Parish, LA
------------------------------------------------------------------------
Docket No(s)......................  50-382.
Application date..................  May 28, 2021.
ADAMS Accession No................  ML21148A104.
Location in Application of NSHC...  Pages 4-5 of the Enclosure.
Brief Description of Amendment(s).  The proposed amendment would revise
                                     the technical specifications (TSs)
                                     in accordance with Technical
                                     Specifications Task Force (TSTF)
                                     Traveler TSTF-563, Revision 0,
                                     ``Revise Instrument Testing
                                     Definitions to Incorporate the
                                     Surveillance Frequency Control
                                     Program,'' dated May 10, 2017
                                     (ADAMS Accession No. ML17130A819).
                                     TSTF-563 revises the TS definitions
                                     of Channel Calibration and Channel
                                     Functional Test, which currently
                                     permit performance by any series of
                                     sequential, overlapping, or total
                                     channel steps, to allow the
                                     required frequency for testing the
                                     components or devices in each step
                                     to be determined in accordance with
                                     the TS Surveillance Frequency
                                     Control Program. The NRC issued a
                                     final safety evaluation approving
                                     TSTF-563, Revision 0, on December
                                     4, 2018 (ADAMS Accession No.
                                     ML18333A152).
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Anna Vinson Jones, Senior Counsel,
 Mailing Address.                    Entergy Services, Inc., 101
                                     Constitution Avenue NW, Suite 200
                                     East, Washington, DC 20001.
NRC Project Manager, Telephone      Perry Buckberg, 301-415-1383.
 Number.
------------------------------------------------------------------------
   Exelon FitzPatrick, LLC and Exelon Generation Company, LLC; James A
           FitzPatrick Nuclear Power Plant; Oswego County, NY,
------------------------------------------------------------------------
Docket No(s)......................  50-333.
Application date..................  April 16, 2021.
ADAMS Accession No................  ML21109A113.
Location in Application of NSHC...  Pages 5-7 of the Enclosure.
Brief Description of Amendment(s).  The proposed amendment would revise
                                     certain technical specification
                                     (TS) requirements related to the
                                     reactor pressure vessel (RPV) water
                                     inventory control (WIC) for James
                                     A. FitzPatrick Nuclear Power Plant.
                                     The proposed changes are based on
                                     Technical Specifications Task Force
                                     (TSTF) Traveler TSTF-582, Revision
                                     0, ``RPV WIC Enhancements'' (ADAMS
                                     Accession No. ML19240A260). The
                                     proposed changes also include other
                                     administrative changes to the TSs.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Donald P. Ferraro, Assistant General
 Mailing Address.                    Counsel, Exelon Generation Company,
                                     LLC, 200 Exelon Way, Suite 305,
                                     Kennett Square, PA 19348.
NRC Project Manager, Telephone      Justin Poole, 301-415-2048.
 Number.
------------------------------------------------------------------------
 Nebraska Public Power District; Cooper Nuclear Station; Nemaha County,
                                   NE
------------------------------------------------------------------------
Docket No(s)......................  50-298.
Application date..................  May 11, 2021.
ADAMS Accession No................  ML21132A062.
Location in Application of NSHC...  Pages 7-9 of Attachment 1.
Brief Description of Amendment(s).  The proposed amendment would adopt
                                     Technical Specifications Task Force
                                     (TSTF) Traveler TSTF-582, ``RPV WIC
                                     [Reactor Pressure Vessel Water
                                     Inventory Control] Enhancements,''
                                     at the Cooper Nuclear Station. The
                                     Technical Specifications related to
                                     RPV WIC would be revised to
                                     incorporate operating experience
                                     and to correct errors and omissions
                                     in TSTF-542, Revision 2, ``Reactor
                                     Pressure Vessel Water Inventory
                                     Control.''
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      John C. McClure, Nebraska Public
 Mailing Address.                    Power District, P.O. Box 499,
                                     Columbus, NE 68602-0499.
NRC Project Manager, Telephone      Thomas Wengert, 301-415-4037.
 Number.
------------------------------------------------------------------------
Nine Mile Point Nuclear Station, LLC and Exelon Generation Company, LLC;
       Nine Mile Point Nuclear Station, Unit 2; Oswego County, NY
------------------------------------------------------------------------
Docket No(s)......................  50-410.
Application date..................  May 26, 2021.

[[Page 36781]]

 
ADAMS Accession No................  ML21146A045.
Location in Application of NSHC...  Attachment 1, pages 4-6.
Brief Description of Amendment(s).  The proposed amendment would revise
                                     Technical Specification (TS) 3.8.3,
                                     ``Diesel Fuel Oil, Lube Oil, and
                                     Starting Air,'' by relocating the
                                     current stored diesel fuel oil and
                                     lube oil numerical volume
                                     requirements from the TS to a
                                     licensee controlled document. The
                                     TS would be modified so that the
                                     stored diesel fuel oil and lube oil
                                     inventory will require that a 7-day
                                     supply be available for each diesel
                                     generator. Condition A and
                                     Condition B in the Action table for
                                     TS 3.8.3 and Surveillance
                                     Requirements 3.8.3.1 and 3.8.3.2
                                     would be revised to reflect the
                                     above change.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Tamra Domeyer, Associate General
 Mailing Address.                    Counsel, Exelon Generation Company,
                                     LLC, 4300 Winfield Road,
                                     Warrenville, IL 60555.
NRC Project Manager, Telephone      Michael Marshall, 301-415-2871.
 Number.
------------------------------------------------------------------------
    PSEG Nuclear LLC; Hope Creek Generating Station; Salem County, NJ
------------------------------------------------------------------------
Docket No(s)......................  50-354.
Application date..................  May 7, 2021.
ADAMS Accession No................  ML21127A085.
Location in Application of NSHC...  Pages 10-11 of the Enclosure.
Brief Description of Amendment(s).  The proposed amendment would revise
                                     Technical Specification 3/4.7.1.3,
                                     ``Ultimate Heat Sink'' (UHS), to
                                     modify the limiting condition for
                                     operation river temperature,
                                     increase the temperature in the
                                     action statement for opening the
                                     emergency discharge valves, add a
                                     new 72-hour allowed outage time for
                                     one station service water system
                                     pump or one safety auxiliary
                                     cooling system pump or one
                                     emergency diesel generator
                                     inoperable with UHS temperature
                                     above 88 degrees Fahrenheit, and
                                     revise the UHS average temperature
                                     limit and maximum temperature.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Steven Fleischer, PSEG Services
 Mailing Address.                    Corporation, 80 Park Plaza, T-5,
                                     Newark, NJ 07102.
NRC Project Manager, Telephone      James Kim, 301-415-4125.
 Number.
------------------------------------------------------------------------
 Southern Nuclear Operating Company, Inc.; Edwin I Hatch Nuclear Plant,
 Units 1 and 2; Appling County, GA; Southern Nuclear Operating Company,
 Inc.; Joseph M Farley Nuclear Plant, Units 1 and 2; Houston County, AL;
  Southern Nuclear Operating Company, Inc.; Vogtle Electric Generating
                 Plant, Units 1 and 2; Burke County, GA
------------------------------------------------------------------------
Docket No(s)......................  50-321, 50-348, 50-364, 50-366, 50-
                                     424, 50-425.
Application date..................  June 22, 2021.
ADAMS Accession No................  ML21173A064.
Location in Application of NSHC...  Pages E-2 through E-4 of the
                                     Enclosure.
Brief Description of Amendment(s).  The proposed amendments would revise
                                     the technical specifications to
                                     remove the table of contents from
                                     the Joseph M. Farley Nuclear Plant,
                                     Units 1 and 2; Edwin I. Hatch
                                     Nuclear Plant (Hatch), Units, 1 and
                                     2; and Vogtle Electric Generating
                                     Plant, Units 1 and 2, as well as
                                     remove the effective page list from
                                     the Hatch, Units 1 and 2, technical
                                     specifications, to be put under the
                                     licensee's control.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      Millicent Ronnlund, Vice President
 Mailing Address.                    and General Counsel, Southern
                                     Nuclear Operating Co., Inc., P. O.
                                     Box 1295, Birmingham, AL 35201-
                                     1295.
NRC Project Manager, Telephone      John Lamb, 301-415-3100.
 Number.
------------------------------------------------------------------------
    Tennessee Valley Authority; Watts Bar Nuclear Plant, Unit 2; Rhea
                               County, TN
------------------------------------------------------------------------
Docket No(s)......................  50-391.
Application date..................  March 11, 2021.
ADAMS Accession No................  ML21070A432.
Location in Application of NSHC...  Pages E-5-E-7 of the Enclosure.
Brief Description of Amendment(s).  The proposed amendments would delete
                                     Watts Bar, Unit 2, technical
                                     specification (TS) requirements
                                     that will no longer apply following
                                     installation of the replacement
                                     steam generators (SGs) including:
                                     the F* SG tube inspection
                                     methodology, the voltage-based
                                     alternate repair criteria SG tube
                                     inspection methodology, and the
                                     provision allowing the use of SG
                                     tube sleeving as an SG tube repair
                                     methodology. The proposed amendment
                                     would also revise TS 5.7.2.12.d.2
                                     to reflect the Technical
                                     Specifications Task Force (TSTF)
                                     Traveler TSTF-510, ``Revision to
                                     Steam Generator Program Inspection
                                     Frequencies and Tube Sample
                                     Selection,'' Revision 2, TS
                                     requirements for Alloy 690
                                     thermally treated tubing that will
                                     apply to the replacement SGs.
                                     Lastly, the proposed amendment
                                     would revise Facility Operating
                                     License Condition 2.C.(4) to delete
                                     the reference to PAD4TCD, which
                                     will not apply to the replacement
                                     SGs.
Proposed Determination............  NSHC.
Name of Attorney for Licensee,      David Fountain, Executive VP and
 Mailing Address.                    General Counsel, Tennessee Valley
                                     Authority, 400 West Summit Hill
                                     Drive, WT 6A, Knoxville, TN 37902.
NRC Project Manager, Telephone      Kimberly Green, 301-415-1627.
 Number.
------------------------------------------------------------------------


[[Page 36782]]

III. Notice of Issuance of Amendments to Facility Operating Licenses 
and Combined Licenses

    During the period since publication of the last monthly notice, the 
Commission has issued the following amendments. The Commission has 
determined for each of these amendments that the application complies 
with the standards and requirements of the Atomic Energy Act of 1954, 
as amended (the Act), and the Commission's rules and regulations. The 
Commission has made appropriate findings as required by the Act and the 
Commission's rules and regulations in 10 CFR chapter I, which are set 
forth in the license amendment.
    A notice of consideration of issuance of amendment to facility 
operating license or combined license, as applicable, proposed NSHC 
determination, and opportunity for a hearing in connection with these 
actions, was published in the Federal Register as indicated in the 
safety evaluation for each amendment.
    Unless otherwise indicated, the Commission has determined that 
these amendments satisfy the criteria for categorical exclusion in 
accordance with 10 CFR 51.22. Therefore, pursuant to 10 CFR 51.22(b), 
no environmental impact statement or environmental assessment need be 
prepared for these amendments. If the Commission has prepared an 
environmental assessment under the special circumstances provision in 
10 CFR 51.22(b) and has made a determination based on that assessment, 
it is so indicated in the safety evaluation for the amendment.
    For further details with respect to each action, see the amendment 
and associated documents such as the Commission's letter and safety 
evaluation, which may be obtained using the ADAMS accession numbers 
indicated in the table below. The safety evaluation will provide the 
ADAMS accession numbers for the application for amendment and the 
Federal Register citation for any environmental assessment. All of 
these items can be accessed as described in the ``Obtaining Information 
and Submitting Comments'' section of this document.

                      License Amendment Issuance(s)
------------------------------------------------------------------------
 
------------------------------------------------------------------------
         DTE Electric Company; Fermi, Unit 2; Monroe County, MI
------------------------------------------------------------------------
Docket No(s)......................  50-341.
Amendment Date....................  June 11, 2021.
ADAMS Accession No................  ML21147A167.
Amendment No(s)...................  221.
Brief Description of Amendment(s).  The amendment revised the Fermi 2
                                     technical specifications (TSs) to
                                     adopt Technical Specifications Task
                                     Force (TSTF) Traveler TSTF-563,
                                     Revision 0, ``Revise Instrument
                                     Testing Definitions to Incorporate
                                     the Surveillance Frequency Control
                                     Program.'' Specifically, the
                                     amendment revised TS Section 1.1,
                                     ``Definitions,'' to modify
                                     definitions for Channel Calibration
                                     and Channel Functional Test to
                                     allow the frequency for testing the
                                     components and devices in each step
                                     to be determined in accordance with
                                     the TS Surveillance Frequency
                                     Control Program.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
Duke Energy Carolinas, LLC; Catawba Nuclear Station, Units 1 and 2; York
County, SC; Duke Energy Carolinas, LLC; McGuire Nuclear Station, Units 1
                      and 2; Mecklenburg County, NC
------------------------------------------------------------------------
Docket No(s)......................  50-413, 50-414, 50-369, 50-370.
Amendment Date....................  June 23, 2021.
ADAMS Accession No................  ML21131A026.
Amendment No(s)...................  Catawba--308 (Unit 1) and 304 (Unit
                                     2); McGuire--318 (Unit 1) and 297
                                     (Unit 2).
Brief Description of Amendment(s).  The amendments revised Catawba
                                     Nuclear Station, Units 1 and 2 and
                                     McGuire Nuclear Station, Units 1
                                     and 2 Technical Specification 3.8.1
                                     regarding the emergency diesel
                                     generators to reduce the maximum
                                     steady state voltage specified in
                                     the associated surveillances.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
    Entergy Louisiana, LLC, and Entergy Operations, Inc.; River Bend
  Station, Unit 1; West Feliciana Parish, LA; Entergy Operations, Inc.,
    System Energy Resources, Inc., Cooperative Energy, A Mississippi
 Electric Cooperative, and Entergy Mississippi, LLC; Grand Gulf Nuclear
                  Station, Unit 1; Claiborne County, MS
------------------------------------------------------------------------
Docket No(s)......................  50-416, 50-458.
Amendment Date....................  June 8, 2021.
ADAMS Accession No................  ML21146A018.
Amendment No(s)...................  Grand Gulf--229 and River Bend--207.
Brief Description of Amendment(s).  The amendments changed the technical
                                     specifications to revise the
                                     current instrumentation testing
                                     definitions of Channel Calibration
                                     and Channel Functional Test to
                                     permit determination of the
                                     appropriate frequency to perform
                                     the surveillance requirement based
                                     on the devices being tested in each
                                     step. The changes are based on
                                     Technical Specifications Task Force
                                     (TSTF) Traveler TSTF-563, Revision
                                     0, ``Revise Instrument Testing
                                     Definitions to Incorporate the
                                     Surveillance Frequency Control
                                     Program.''
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Entergy Nuclear Operations, Inc., Entergy Nuclear Indian Point 2, LLC;
Indian Point Nuclear Generating Station, Unit No. 2; Westchester County,
  NY; Entergy Nuclear Operations, Inc., Entergy Nuclear Indian Point 3,
  LLC; Indian Point Nuclear Generating Station, Unit No. 3; Westchester
   County, NY; Entergy Nuclear Operations, Inc.; Indian Point Nuclear
         Generating Station, Unit No. 1; Westchester County, NY
------------------------------------------------------------------------
Docket No(s)......................  50-003, 50-247, 50-286.

[[Page 36783]]

 
Amendment Date....................  May 28, 2021.
ADAMS Accession No................  ML21126A004.
Amendment No(s)...................  64 (Unit 1), 295 (Unit 2), and 271
                                     (Unit 3).
Brief Description of Amendment(s).  On November 23, 2020, the NRC issued
                                     an order approving the transfer of
                                     the licenses for Indian Point from
                                     Entergy to Holtec International
                                     (Holtec) subsidiaries, Holtec
                                     Indian Point 2, LLC and Holtec
                                     Indian Point 3, LLC. The order also
                                     approved the transfer of Entergy
                                     Nuclear Operations, Inc.'s (ENOI)
                                     operating authority for conducting
                                     license activities at the Indian
                                     Point Energy Center to Holtec
                                     Decommissioning International, LLC
                                     (HDI). The order also approved
                                     conforming administrative
                                     amendments to reflect the proposed
                                     transfer and to delete certain
                                     license conditions to reflect the
                                     satisfaction and termination of
                                     certain obligations after the
                                     license transfer. On May 28, 2021,
                                     Entergy and HDI informed the NRC
                                     that the transaction closed on May
                                     28, 2021. Accordingly, the NRC
                                     issued Amendment No. 64 to
                                     Provisional License No. DPR-5,
                                     Amendment No. 295 to Renewed
                                     Facility License No. DPR-26 , and
                                     Amendment No. 271 to Renewed
                                     Facility License No. DPR-64. A copy
                                     of the related Safety Evaluation
                                     (ADAMS Accession No. ML20297A333)
                                     was provided with the Order dated
                                     November 23, 2020, approving the
                                     license transfer and the conforming
                                     amendment.
Public Comments Received as to      Yes.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Entergy Operations, Inc.; Waterford Steam Electric Station, Unit 3; St.
                           Charles Parish, LA
------------------------------------------------------------------------
Docket No(s)......................  50-382.
Amendment Date....................  May 19, 2021.
ADAMS Accession No................  ML21082A302.
Amendment No(s)...................  259.
Brief Description of Amendment(s).  The amendment revised the current
                                     emergency action level scheme to
                                     one based on Nuclear Energy
                                     Institute (NEI) guidance in NEI 99-
                                     01, Revision 6, ``Development of
                                     Emergency Action Levels for Non-
                                     Passive Reactors,'' dated November
                                     2012, which was endorsed by the NRC
                                     in a letter dated March 26, 2013.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Exelon Generation Company, LLC; LaSalle County Station, Units 1 and 2;
                           LaSalle County, IL
------------------------------------------------------------------------
Docket No(s)......................  50-373, 50-374.
Amendment Date....................  May 27, 2021.
ADAMS Accession No................  ML21082A422.
Amendment No(s)...................  249 (Unit 1) and 235 (Unit 2).
Brief Description of Amendment(s).  The amendments modified the
                                     licensing basis by the addition of
                                     a license condition to allow for
                                     the implementation of the
                                     provisions of 10 CFR 50.69, ``Risk-
                                     informed categorization and
                                     treatment of structures, systems
                                     and components for nuclear power
                                     reactors.''
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
   Pacific Gas and Electric Company; Humboldt Bay Power Plant Unit 3;
                           Humboldt County, CA
------------------------------------------------------------------------
Docket No(s)......................  50-133.
Amendment Date....................  June 24, 2021.
ADAMS Accession No................  ML21158A123.
Amendment Nos.....................  46.
Brief Description of Amendment(s).  The amendment revised the Humboldt
                                     Bay Power Plant, Unit 3 (HBPP)
                                     license by revising License
                                     Condition 2.C.5. This license
                                     condition incorporates the revised
                                     License Termination Plan into the
                                     HBPP license. All other aspects of
                                     the license remain the same.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
    Tennessee Valley Authority; Watts Bar Nuclear Plant, Unit 2; Rhea
                               County, TN
------------------------------------------------------------------------
Docket No(s)......................  50-391.
Amendment Date....................  June 17, 2021.
ADAMS Accession No................  ML21148A100.
Amendment No(s)...................  53.
Brief Description of Amendment(s).  The amendment revised Technical
                                     Specification 5.9.6, ``Reactor
                                     Coolant System (RCS) Pressure and
                                     Temperature Limits Report (PTLR),''
                                     to add WCAP-18124-NP-A, Revision 0,
                                     ``Fluence Determination with RAPTOR-
                                     M3G and FERRET,'' as a neutron
                                     fluence calculational methodology
                                     for the evaluation of reactor
                                     vessel specimens to support the
                                     determination of reactor coolant
                                     system pressure and temperature
                                     limits.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Vistra Operations Company LLC; Comanche Peak Nuclear Power Plant, Unit
                   Nos. 1 and 2; Somervell County, TX
------------------------------------------------------------------------
Docket No(s)......................  50-445, 50-446.
Amendment Date....................  May 19, 2021.

[[Page 36784]]

 
ADAMS Accession No................  ML21061A217.
Amendment No(s)...................  180 (Unit 1) and 180 (Unit 2).
Brief Description of Amendment(s).  The amendments authorized changes
                                     and clarifications to specific
                                     emergency action levels of the
                                     Emergency Plan, and supporting
                                     bases discussions, for the Comanche
                                     Peak Nuclear Power Plant, Unit Nos.
                                     1 and 2.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------
 Vistra Operations Company LLC; Comanche Peak Nuclear Power Plant, Unit
                   Nos. 1 and 2; Somervell County, TX
------------------------------------------------------------------------
Docket No(s)......................  50-445, 50-446.
Amendment Date....................  June 9, 2021.
ADAMS Accession No................  ML21132A089.
Amendment No(s)...................  181 (Unit 1) and 181 (Unit 2).
Brief Description of Amendment(s).  The amendments adopted Technical
                                     Specifications Task Force (TSTF)
                                     Traveler TSTF-567, Revision 1,
                                     ``Containment Sump TS [Technical
                                     Specification] to Address GSI
                                     [Generic Safety Issue]-191
                                     Issues.'' The amendments revised
                                     the TSs to address the condition of
                                     the containment sump made
                                     inoperable due to containment
                                     accident generated and transported
                                     debris exceeding the analyzed
                                     limits.
Public Comments Received as to      No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------

IV. Notice of Issuance of Amendment to Facility Operating Licenses and 
Combined Licenses and Final Determination of No Significant Hazards 
Consideration and Opportunity for a Hearing (Exigent Circumstances or 
Emergency Situation)

    Since publication of the last monthly notice, the Commission has 
issued the following amendment. The Commission has determined for this 
amendment that the application for the amendment complies with the 
standards and requirements of the Atomic Energy Act of 1954, as amended 
(the Act), and the Commission's rules and regulations. The Commission 
has made appropriate findings as required by the Act and the 
Commission's rules and regulations in 10 CFR chapter I, which are set 
forth in the license amendment.
    Because of exigent circumstances or emergency situation associated 
with the date the amendment was needed, there was not time for the 
Commission to publish, for public comment before issuance, its usual 
notice of consideration of issuance of amendment, proposed NSHC 
determination, and opportunity for a hearing.
    For exigent circumstances, the Commission has either issued a 
Federal Register notice providing opportunity for public comment or has 
used local media to provide notice to the public in the area 
surrounding a licensee's facility of the licensee's application and of 
the Commission's proposed determination of NSHC. The Commission has 
provided a reasonable opportunity for the public to comment, using its 
best efforts to make available to the public means of communication for 
the public to respond quickly, and in the case of telephone comments, 
the comments have been recorded or transcribed as appropriate and the 
licensee has been informed of the public comments.
    In circumstances where failure to act in a timely way would have 
resulted, for example, in derating or shutdown of a nuclear power plant 
or in prevention of either resumption of operation or of increase in 
power output up to the plant's licensed power level, the Commission may 
not have had an opportunity to provide for public comment on its NSHC 
determination. In such case, the license amendment has been issued 
without opportunity for comment prior to issuance. If there has been 
some time for public comment but less than 30 days, the Commission may 
provide an opportunity for public comment. If comments have been 
requested, it is so stated. In either event, the State has been 
consulted by telephone whenever possible.
    Under its regulations, the Commission may issue and make an 
amendment immediately effective, notwithstanding the pendency before it 
of a request for a hearing from any person, in advance of the holding 
and completion of any required hearing, where it has determined that 
NSHC is involved.
    The Commission has applied the standards of 10 CFR 50.92 and has 
made a final determination that the amendments involve NSHC. The basis 
for this determination is contained in the documents related to each 
action. Accordingly, the amendment has been issued and made effective 
as indicated. For those amendments that have not been previously 
noticed in the Federal Register, within 60 days after the date of 
publication of this notice, any persons (petitioner) whose interest may 
be affected by this action may file a request for a hearing and 
petition for leave to intervene (petition) with respect to the action. 
Petitions shall be filed in accordance with the guidance concerning the 
Commission's ``Agency Rules of Practice and Procedure'' in 10 CFR part 
2 as discussed in section II.A of this document.
    Unless otherwise indicated, the Commission has determined that the 
amendment satisfies the criteria for categorical exclusion in 
accordance with 10 CFR 51.22. Therefore, pursuant to 10 CFR 51.22(b), 
no environmental impact statement or environmental assessment need be 
prepared for this amendment. If the Commission has prepared an 
environmental assessment under the special circumstances provision in 
10 CFR 51.12(b) and has made a determination based on that assessment, 
it is so indicated in the safety evaluation for the amendment.
    For further details with respect to these actions, see the 
amendment and associated documents such as the Commission's letter and 
safety evaluation, which may be obtained using the ADAMS accession 
numbers indicated in the table below. The safety evaluation will 
provide the ADAMS accession number(s) for the application for amendment 
and the Federal Register citation for any environmental assessment. All 
of these items can be accessed as described in the ``Obtaining 
Information and Submitting Comments'' section of this document.

[[Page 36785]]



     License Amendment Issuance(s)--Exigent/Emergency Circumstances
------------------------------------------------------------------------
 
------------------------------------------------------------------------
   Exelon FitzPatrick, LLC and Exelon Generation Company, LLC; James A
           FitzPatrick Nuclear Power Plant; Oswego County, NY
------------------------------------------------------------------------
Docket No(s)......................  50-333.
Amendment Date....................  June 14, 2021.
ADAMS Accession No................  ML21162A042.
Amendment No(s)...................  342.
Brief Description of Amendment(s).  The amendment modified Technical
                                     Specification (TS) 3.5.1, ``ECCS
                                     [Emergency Core Cooling System]--
                                     Operating,'' Condition A; TS
                                     3.6.4.1, ``Secondary Containment,''
                                     Condition A; and TS 3.6.1.9
                                     Residual Heat Removal (RHR)
                                     Containment Spray System,'' as well
                                     as certain Surveillance
                                     Requirements to support emergent
                                     repair of the ``A'' RHR pump motor.
                                     Specifically, the amendment revised
                                     the completion time from 7 days to
                                     34 days for the ``A'' RHR pump, the
                                     completion time from 4 hours to 30
                                     hours for restoring secondary
                                     containment, and the completion
                                     time from 7 days to 27 days for
                                     restoring one containment spray
                                     subsystem to operable status.
                                     Additionally, the amendment allowed
                                     extending the completion of several
                                     surveillance requirements of
                                     equipment being protected during
                                     the replacement of the ``A'' RHR
                                     pump motor.
Local Media Notice (Yes/No).......  No.
Public Comments Requested as to     No.
 Proposed NSHC (Yes/No).
------------------------------------------------------------------------

V. Previously Published Notice of Consideration of Issuance of 
Amendment to Facility Operating Licenses and Combined Licenses, 
Proposed No Significant Hazards Consideration Determination, and 
Opportunity for a Hearing

    The following notice was previously published as separate 
individual notice. It was published as an individual notice either 
because time did not allow the Commission to wait for this monthly 
notice or because the action involved exigent circumstances. It is 
repeated here because the monthly notice lists all amendments issued or 
proposed to be issued involving NSHC.
    For details, including the applicable notice period, see the 
individual notice in the Federal Register on the day and page cited.

   License Amendment Request(s)--Repeat of Individual Federal Register
                                 Notice
------------------------------------------------------------------------
 
------------------------------------------------------------------------
 Exelon Generation Company, LLC; Braidwood Station, Units 1 and 2; Will
                               County, IL
------------------------------------------------------------------------
Docket No(s)......................  50-456, 50-457.
Application Date..................  May 27, 2021.
ADAMS Accession No................  ML21147A543.
Brief Description of Amendment(s).  The proposed amendment would revise
                                     Technical Specification
                                     Surveillance Requirement 3.7.9.2 to
                                     allow an ultimate heat sink
                                     temperature of less than or equal
                                     to 102.8 degrees Fahrenheit through
                                     September 30, 2021.
Date & Cite of Federal Register     June 10, 2021 (86 FR 30991).
 Individual Notice.
Expiration Dates for Public         July 12, 2021 (Public Comments);
 Comments & Hearing Requests.        August 9, 2021 (Hearing Requests).
------------------------------------------------------------------------


    Dated: July 3, 2021.

    For the Nuclear Regulatory Commission.
Jennifer L. Dixon-Herrity,
Acting Deputy, Director, Division of Operating Reactor, Licensing, 
Office of Nuclear Reactor Regulation.
[FR Doc. 2021-14642 Filed 7-12-21; 8:45 am]
BILLING CODE 7590-01-P