[Federal Register Volume 85, Number 192 (Friday, October 2, 2020)]
[Proposed Rules]
[Pages 62234-62239]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2020-21506]


 ========================================================================
 Proposed Rules
                                                 Federal Register
 ________________________________________________________________________
 
 This section of the FEDERAL REGISTER contains notices to the public of 
 the proposed issuance of rules and regulations. The purpose of these 
 notices is to give interested persons an opportunity to participate in 
 the rule making prior to the adoption of the final rules.
 
 ========================================================================
 

  Federal Register / Vol. 85, No. 192 / Friday, October 2, 2020 / 
Proposed Rules  

[[Page 62234]]



NUCLEAR REGULATORY COMMISSION

10 CFR Part 50

[NRC-2017-0151]
RIN 3150-AK07


Reactor Vessel Material Surveillance Program

AGENCY: Nuclear Regulatory Commission.

ACTION: Proposed rule.

-----------------------------------------------------------------------

SUMMARY: The U.S. Nuclear Regulatory Commission (NRC) is proposing to 
amend the reactor vessel material surveillance program requirements for 
commercial light-water power reactors. This action would amend the 
requirements associated with the testing of specimens contained within 
surveillance capsules and reporting the surveillance test results. This 
action would also clarify the requirements for the design of 
surveillance programs and the capsule withdrawal schedules for 
surveillance capsules in reactor vessels purchased after 1982. These 
changes would reduce regulatory burden, with no effect on public health 
and safety.

DATES: Submit comments by November 2, 2020. Comments received after 
this date will be considered if it is practical to do so, but the NRC 
is able to ensure consideration only for comments received on or before 
this date.

ADDRESSES: You may submit comments by any of the following methods:
     Federal Rulemaking website: Go to https://www.regulations.gov and search for Docket ID NRC-2017-0151. Address 
questions about NRC dockets to Carol Gallagher; telephone: 301-415-
3463; email: [email protected]. For technical questions contact 
the individuals listed in the FOR FURTHER INFORMATION CONTACT section 
of this document.
     Email comments to: [email protected]. If you do 
not receive an automatic email reply confirming receipt, then contact 
us at 301-415-1677.
     Mail comments to: Secretary, U.S. Nuclear Regulatory 
Commission, Washington, DC 20555-0001, ATTN: Rulemakings and 
Adjudications Staff.
    For additional direction on obtaining information and submitting 
comments, see ``Obtaining Information and Submitting Comments'' in the 
SUPPLEMENTARY INFORMATION section of this document.

FOR FURTHER INFORMATION CONTACT: Stewart Schneider, Office of Nuclear 
Material Safety and Safeguards, 301-415-4123, email: 
[email protected], or On Yee, Office of Nuclear Reactor 
Regulation, telephone: 301-415-1905, email: [email protected]. Both are 
staff of the U.S. Nuclear Regulatory Commission, Washington, DC 20555-
0001.

SUPPLEMENTARY INFORMATION:

Table of Contents

I. Obtaining Information and Submitting Comments
II. Rulemaking Procedure
III. Background
IV. Plain Writing
V. Paperwork Reduction Act Statement
VI. Voluntary Consensus Standards
VII. Availability of Documents

I. Obtaining Information and Submitting Comments

A. Obtaining Information

    Please refer to Docket ID NRC-2017-0151 when contacting the NRC 
about the availability of information for this action. You may obtain 
publicly-available information related to this action by any of the 
following methods:
     Federal Rulemaking website: Go to https://www.regulations.gov and search for Docket ID NRC-2017-0151.
     NRC's Agencywide Documents Access and Management System 
(ADAMS): You may obtain publicly-available documents online in the 
ADAMS Public Documents collection at https://www.nrc.gov/reading-rm/adams.html. To begin the search, select ``ADAMS Public Documents'' and 
then select ``Begin Web-based ADAMS Search.'' For problems with ADAMS, 
please contact the NRC's Public Document Room (PDR) reference staff at 
1-800-397-4209, at 301-415-4737, or by email to [email protected]. 
For the convenience of the reader, instructions about obtaining 
materials referenced in this document are provided in the 
``Availability of Documents'' section.
     Attention: The Public Document Room (PDR), where you may 
examine and order copies of public documents is currently closed. You 
may submit your request to the PDR via email at [email protected] or 
call 1-800-397-4209 between 8:00 a.m. and 4:00 p.m. (EST), Monday 
through Friday, except Federal holidays.

B. Submitting Comments

    Please include Docket ID NRC-2017-0151 in your comment submission.
    The NRC cautions you not to include identifying or contact 
information that you do not want to be publicly disclosed in your 
comment submission. The NRC will post all comment submissions at 
https://www.regulations.gov as well as enter the comment submissions 
into ADAMS. The NRC does not routinely edit comment submissions to 
remove identifying or contact information.
    If you are requesting or aggregating comments from other persons 
for submission to the NRC, then you should inform those persons not to 
include identifying or contact information that they do not want to be 
publicly disclosed in their comment submission. Your request should 
state that the NRC does not routinely edit comment submissions to 
remove such information before making the comment submissions available 
to the public or entering the comment into ADAMS.

II. Rulemaking Procedure

    Because the NRC anticipates that this action will be non-
controversial, the NRC is publishing this proposed rule concurrently 
with a direct final rule in the Rules and Regulations section of this 
issue of the Federal Register. The direct final rule will become 
effective on February 1, 2021. However, if the NRC receives significant 
adverse comments on this proposed rule by November 2, 2020, then the 
NRC will publish a document that withdraws the direct final rule. If 
the direct final rule is withdrawn, the NRC will address the comments 
received in response to these proposed revisions in a subsequent final 
rule. Absent significant modifications to the proposed revisions 
requiring republication, the NRC will not initiate a second comment 
period on this action in the event the direct final rule is withdrawn.

[[Page 62235]]

    A significant adverse comment is a comment where the commenter 
explains why the rule would be inappropriate, including challenges to 
the rule's underlying premise or approach, or would be ineffective or 
unacceptable without a change. A comment is adverse and significant if:
    (1) The comment opposes the rule and provides a reason sufficient 
to require a substantive response in a notice-and-comment process. For 
example, a substantive response is required when:
    (a) The comment causes the NRC to reevaluate (or reconsider) its 
position or conduct additional analysis;
    (b) The comment raises an issue serious enough to warrant a 
substantive response to clarify or complete the record; or
    (c) The comment raises a relevant issue that was not previously 
addressed or considered by the NRC.
    (2) The comment proposes a change or an addition to the rule, and 
it is apparent that the rule would be ineffective or unacceptable 
without incorporation of the change or addition.
    (3) The comment causes the NRC to make a change (other than 
editorial) to the rule.
    For procedural information and the regulatory analysis, see the 
direct final rule published in the Rules and Regulations section of 
this issue of the Federal Register.

III. Background

A. Description of a Reactor Vessel Material Surveillance Program

    The reactor vessel and its internal components support and align 
the fuel assemblies that make up the reactor core and provide a flow 
path to ensure adequate heat removal from the fuel assemblies. The 
reactor vessel also provides containment and a floodable volume to 
maintain core cooling in the event of an accident causing loss of the 
primary coolant. It is a cylindrical shell with a welded hemispherical 
bottom head and a removable hemispherical upper head. Some vessel 
shells were fabricated from curved plates that were joined by 
longitudinal and circumferential welds. Others were manufactured using 
forged rings and, therefore, only have circumferential welds that join 
the rings. These plate and forging materials are referred to as base 
metals. Maintenance of the structural integrity of the reactor vessel 
is essential in ensuring plant safety, because there is no redundant 
system to maintain core cooling in the event of a vessel failure.
    One characteristic of reactor vessel steels is that their material 
properties change as a function of temperature and neutron irradiation. 
The primary material property of interest for the purposes of reactor 
vessel integrity is the fracture toughness of the reactor vessel 
material. Extensive experimental work determined that Charpy impact 
energy tests, which measure the amount of energy required to fail a 
small material specimen, can be correlated to changes in fracture 
toughness of a material. Thus, the Charpy impact specimens \1\ from the 
beltline \2\ materials (i.e., base metal, weld metal, and heat-affected 
zone) became the standard to assess the change in fracture toughness in 
ferritic steels.
---------------------------------------------------------------------------

    \1\ A Charpy impact specimen is a bar of metal, or other 
material, having a V-groove notch machined across the 10 mm 
thickness dimension.
    \2\ A definition of the beltline or beltline region is provided 
in appendix G to 10 CFR part 50.
---------------------------------------------------------------------------

    The fracture toughness of reactor vessel materials decreases with 
decreasing temperature and with increasing irradiation from the 
reactor. The decrease in fracture toughness due to neutron irradiation 
is referred to as ``neutron embrittlement.'' The fracture toughness of 
reactor vessel materials is determined by using fracture toughness 
curves in the American Society of Mechanical Engineers (ASME) Code, 
which are indexed to the reference temperature for nil-ductility 
transition (RTNDT), as specified in ASME Boiler and Pressure 
Vessel Code, Section II, ``Materials.'' To account for the effects of 
neutron irradiation, the increase in RTNDT is equated to the 
increase in the 30 ft-lb index temperature from tests of Charpy-V notch 
impact specimens irradiated in capsules as a part of the surveillance 
program. The surveillance program includes Charpy impact specimens of 
the base and weld metals for the reactor vessel in each surveillance 
capsule. These surveillance capsules are exposed to the same operating 
conditions as the reactor vessel, and because the capsules are located 
closer to the reactor core than the reactor vessel inner diameter, the 
surveillance specimens are generally exposed to higher neutron 
irradiation levels than those experienced by the reactor vessel at any 
given time.
    As a result of the surveillance capsule's location within the 
reactor vessel, the test specimens generally reflect changes in 
fracture toughness due to neutron embrittlement in advance of what the 
reactor vessel experiences and provide insight to the future condition 
of the reactor vessel. Therefore, the NRC instituted reactor vessel 
material surveillance programs as a requirement of appendix H, 
``Reactor Vessel Material Surveillance Program Requirements'' (appendix 
H), to part 50 of title 10 of the Code of Federal Regulations (10 CFR), 
``Domestic Licensing of Production and Utilization Facilities,'' so 
that the placement and testing of Charpy impact specimens in capsules 
between the inner diameter vessel wall and the core can provide data 
for assessing and projecting the change in fracture toughness of the 
reactor vessel.
    The purpose for requiring a reactor vessel material surveillance 
program is to monitor changes in the fracture toughness properties in 
the beltline region \3\ of the reactor vessel and to use this 
information to analyze the reactor vessel integrity. Surveillance 
programs are designed not only to examine the current status of reactor 
vessel material properties but also to predict the changes in these 
properties resulting from the cumulative effects of neutron 
irradiation.
---------------------------------------------------------------------------

    \3\ NRC Regulatory Issue Summary 2014-11, ``Information on 
Licensing Applications for Fracture Toughness Requirements for 
Ferric Reactor Coolant Pressure Boundary Components,'' includes a 
definition of reactor vessel beltline.
---------------------------------------------------------------------------

    The determination as to whether a commercial nuclear power reactor 
vessel requires a material surveillance program under appendix H to 10 
CFR part 50 is made at the time of plant licensing under 10 CFR part 50 
or 10 CFR part 52, ``Licenses, Certifications, and Approvals for 
Nuclear Power Plants.'' If this surveillance program is required, it is 
designed and implemented at that time using the existing requirements. 
Certain aspects of the program, such as the specific materials to be 
monitored, the number of required surveillance capsules to be inserted 
in the reactor vessel, and the initial capsule withdrawal schedule were 
designed for the original licensed period of operation (i.e., 40 
years). The editions of the ASTM International (ASTM) E 185 which are 
incorporated by reference in appendix H to 10 CFR part 50 recommend 
three, four, or five surveillance capsules to be included in the design 
of the reactor vessel material surveillance programs for the original 
licensed period of operation, based on the irradiation sensitivity of 
the material used to fabricate the reactor vessel.\4\

[[Page 62236]]

Most plants have included several additional surveillance capsules 
beyond the number recommended by ASTM E 185. These capsules are 
referred to as ``standby capsules.'' The surveillance program for each 
reactor vessel provides assurance that the plant's operating limits 
(e.g., the pressure-temperature limits) continue to meet the provisions 
in Appendix G of ASME Boiler and Pressure Vessel Code, Section XI, 
``Rules for Inservice Inspection of Nuclear Power Plant Components,'' 
as required by appendix G, ``Fracture Toughness Requirements,'' to 10 
CFR part 50. The program also provides assurance that the reactor 
vessel material upper shelf energy meets the requirements of appendix G 
to 10 CFR part 50. These assessments are used to ensure the integrity 
of the reactor vessel.
---------------------------------------------------------------------------

    \4\ The requirements in appendix H to 10 CFR part 50 are based, 
in part, on the information contained within ASTM E 185-73, 
``Standard Recommended Practice for Surveillance Tests for Nuclear 
Reactor Vessels;'' ASTM E 185-79, ``Standard Practice for Conducting 
Surveillance Tests for Light-Water Cooled Nuclear Power Reactor 
Vessels;'' and ASTM E 185-82, ``Standard Practice for Conducting 
Surveillance Tests for Light-Water Cooled Nuclear Power Reactor 
Vessels,'' which are incorporated by reference.
---------------------------------------------------------------------------

    In addition to the Charpy impact specimens for determining the 
embrittlement in the reactor vessel, the surveillance capsules 
typically contain neutron dosimeters, thermal monitors, and tension 
specimens.\5\ Surveillance capsules may also contain correlation 
monitor material, which is a material with composition, properties, and 
response to radiation that have been well-characterized. The overall 
accuracy of neutron fluence measurements is dependent upon knowledge of 
the neutron spectrum. Therefore, a variety of neutron detector 
materials (dosimetry wires) are included in each surveillance capsule 
and used in the determination of neutron fluence for the vessel. The 
thermal monitors that are placed in the capsules (e.g., low melting 
point elements or eutectic alloys) are used to identify the irradiated 
specimen's maximum exposure temperature.
---------------------------------------------------------------------------

    \5\ Tension specimens have a standardized sample cross-section, 
with two shoulders and a gage (section) in between.
---------------------------------------------------------------------------

B. Current Requirements Under Appendix H to 10 CFR part 50

    Appendix H to 10 CFR part 50 requires light-water nuclear power 
reactor licensees to have a reactor vessel material surveillance 
program to monitor changes in the fracture toughness properties of the 
reactor vessel materials adjacent to the reactor core in the beltline 
region. Unless it can be shown that the end of design life neutron 
fluence is below certain criteria, the NRC requires licensees to 
implement a materials surveillance program that tests irradiated 
material specimens that are located in surveillance test capsules in 
the reactor vessels. The program evaluates changes in material fracture 
toughness and thereby assesses the integrity of the reactor vessel. For 
each capsule withdrawal, the test procedures and reporting requirements 
must meet the requirements of ASTM E 185-82, ``Standard Practice for 
Conducting Surveillance Tests for Light-Water Cooled Reactor Vessels,'' 
to the extent practicable for the configuration of the specimens in the 
capsule.
    The design of the surveillance program and the withdrawal schedule 
must meet the requirements of the edition of ASTM E 185 that is current 
on the issue date of the ASME Code to which the reactor vessel was 
purchased. Later editions of ASTM E 185, up to and including those 
editions through 1982, may be used. Appendix H to 10 CFR part 50 
specifically incorporates by reference ASTM E 185-73, ``Standard 
Recommended Practice for Surveillance Tests for Nuclear Reactor 
Vessels;'' ASTM E 185-79, ``Standard Practice for Conducting 
Surveillance Tests for Light-Water Cooled Nuclear Power Reactor 
Vessels,'' and ASTM E 185-82. In sum, the surveillance program must 
comply with ASTM E 185, as modified by appendix H to 10 CFR part 50. 
The number, design, and location of these surveillance capsules within 
the reactor vessel are established during the design of the program, 
before initial plant operation.
    Appendix H to 10 CFR part 50 also specifies that each capsule 
withdrawal and subsequent test results must be the subject of a summary 
technical report to be submitted to the NRC within one year of the date 
of capsule withdrawal, unless an extension is granted by the Director, 
Office of Nuclear Reactor Regulation. The NRC uses the results from the 
surveillance program to assess licensee submittals related to pressure-
temperature limits under appendix G to 10 CFR part 50 and to assess 
pressurized water reactor licensee's compliance with either Sec.  
50.61, ``Fracture toughness requirements for protection against 
pressurized thermal shock events,'' or Sec.  50.61a, ``Alternate 
fracture toughness requirements for protection against pressurized 
thermal shock events.''

C. The Need for Rulemaking

    When appendix H to 10 CFR part 50 was established as a requirement 
(38 FR 19012; July 17, 1973), limited information and data were 
available on the subject of reactor vessel embrittlement. Thus, 
appendix H to 10 CFR part 50 required the inclusion of a comprehensive 
collection of specimen types representing the reactor vessel beltline 
materials in each surveillance capsule. Since 1973, a significant 
number of surveillance capsules have been withdrawn and tested. 
Analyses of these results support reconsidering the specimen types 
required for testing, and the required time for reporting the results 
from surveillance capsule testing. One outcome of this effort was that 
some specimen types were found to contribute to the characterization of 
reactor vessel embrittlement, while others did not. Therefore, the NRC 
determined that these latter types were unnecessary to meet the 
objectives of appendix H to 10 CFR part 50 and should no longer be 
required. Revising appendix H to 10 CFR part 50 to address this 
situation would reduce the regulatory burden on licensees for data 
collection, with no effect on public health and safety.
    In 1983, appendix H to 10 CFR part 50 was revised to require 
licensees to submit test results to the NRC within one year of the date 
of capsule withdrawal, unless an extension is granted by the Director, 
Office of Nuclear Reactor Regulation (48 FR 24008; May 27, 1983). As 
stated in the 1983 rulemaking, the reason for the requirement was the 
need for timely reporting of test results and notification of any 
problems. At that time, there was a limited amount of data from 
irradiated materials from which to estimate embrittlement trends of 
reactor vessels at nuclear power plants, making it important to receive 
timely reporting of test results.
    Licensees that participate in an integrated surveillance program 
have found it challenging to meet this one-year requirement. This is 
related to the fact that an integrated surveillance program requires 
coordination among the multiple licensees participating in the 
program.\6\ A significant number of test specimens have been analyzed 
since 1983, the results of which support a reduced need for prompt 
reporting of the test results. Therefore, there is a reduced need for 
prompt reporting of the test results. Based on this, the NRC has 
determined that the reporting requirement in appendix H to 10 CFR part 
50 should be revised. Extending the reporting period allows for more 
time for licensee coordination and should eliminate the need for 
licensees to prepare and submit extension requests and for the NRC to 
review such

[[Page 62237]]

requests. This revision would have no effect on public health and 
safety.
---------------------------------------------------------------------------

    \6\ Appendix H to 10 CFR part 50 permits the use of an 
integrated surveillance program (ISP) as an alternative to a plant-
specific surveillance program. In an ISP, the representative 
materials chosen for surveillance of a reactor vessel are irradiated 
in one or more other reactor vessel vessels that have similar design 
and operating features. The data obtained from these test specimens 
may then be used in the analysis of other plants participating in 
the program.
---------------------------------------------------------------------------

D. Regulatory Basis To Support Rulemaking

    In January 2019, the Commission issued Staff Requirements 
Memorandum (SRM)-COMSECY-18-0016, ``Request Commission Approval to Use 
the Direct Final Rule Process to Revise the Testing and Reporting 
Requirements in 10 CFR part 50, Appendix H, Reactor Vessel Material 
Surveillance Program Requirements (RIN 3150-AK07),'' approving 
publication of the supporting regulatory basis and use of the direct 
final rule process. On April 3, 2019, the NRC issued the regulatory 
basis which provides an in-depth discussion on the technical merits of 
this rulemaking (84 FR 12876).\7\ The regulatory basis includes 
additional information on the regulatory framework, types of reactor 
vessel material surveillance programs, regulatory topics that initiated 
this rulemaking effort, and options to address these topics. The 
regulatory basis shows that there is sufficient justification to 
proceed with rulemaking to amend appendix H to 10 CFR part 50 to 
eliminate and reduce certain test specimens and extend the period to 
submit surveillance capsule reports to the NRC. In addition, in SRM-
COMSECY-18-0016, the Commission directed the staff to clarify the 
requirements for the design of surveillance programs and the withdrawal 
schedules for reactor vessels purchased after 1982. These revisions 
would not establish any additional requirements for the current fleet 
of operating reactors.
---------------------------------------------------------------------------

    \7\ A subsequent notification was published on April 12, 2019 
(84 FR 14845), to correct the ADAMS accession number for the 
regulatory basis.
---------------------------------------------------------------------------

IV. Plain Writing

    The Plain Writing Act of 2010 (Pub. L. 111-274) requires Federal 
agencies to write documents in a clear, concise, well-organized manner 
that also follows other best practices appropriate to the subject or 
field and the intended audience. The NRC has written this document to 
be consistent with the Plain Writing Act as well as the Presidential 
Memorandum, ``Plain Language in Government Writing,'' published June 
10, 1998 (63 FR 31883). The NRC requests comment on the proposed rule 
with respect to clarity and effectiveness of the language used.

V. Paperwork Reduction Act

    This proposed rule contains new or amended information collection 
requirements that are subject to the Paperwork Reduction Act of 1995 
(44 U.S.C. 3501 et seq). This proposed rule has been submitted to the 
Office of Management and Budget (OMB) for review and approval of the 
information collection requirements
    Type of submission, new or revision: Revision.
    The title of the information collection: Reactor Vessel Material 
Surveillance Program.
    The form number if applicable: NA.
    How often the collection is required or requested: On occasion.
    Who will be required or asked to respond: Holders of an operating 
license for commercial light-water power reactors.
    An estimate of the number of annual responses: A reduction of 1 
response.
    The estimated number of annual respondents: A reduction of 1 
respondent.
    An estimate of the total number of hours needed annually to comply 
with the information collection requirement or request: An annual 
reduction of 78 hours of reporting burden.
    Abstract: The requirements for a reactor vessel material 
surveillance program are specified under appendix H to 10 CFR part 50. 
The NRC requires light-water nuclear power reactor licensees to 
implement this program when it cannot be shown that the end of design 
life neutron fluence for the reactor vessel is below certain criteria. 
This program monitors changes in the fracture toughness properties of 
the reactor vessel materials adjacent to the reactor core. It involves 
the testing of irradiated material specimens that are located in 
surveillance capsules in the reactor vessel. The surveillance test 
results are used to evaluate the changes in material fracture toughness 
and thereby assesses the integrity of the reactor vessel.
    Appendix H to 10 CFR part 50 requires that within one year of the 
date of the surveillance capsule withdrawal, a summary technical report 
be submitted to the NRC that contains the data required by ASTM E 185, 
and the results of all fracture toughness tests conducted on the 
beltline materials in the irradiated and unirradiated conditions, 
unless an extension is granted by the Director, Office of Nuclear 
Reactor Regulation. At the time this requirement became effective (48 
FR 24008; July 26, 1983), there was a limited amount of data from 
irradiated materials from which to estimate embrittlement trends of 
reactor vessels at nuclear power plants, making it important to receive 
timely reporting of test results.
    Licensees that participate in an integrated surveillance program 
have found it challenging to meet this one-year requirement, due to the 
time needed for coordination among the multiple licensees participating 
in the program. A significant number of test specimens have been 
analyzed since 1983, the results of which support the reduced need for 
prompt reporting of the test results. Based on this finding, the NRC 
determined that the reporting requirement in appendix H to 10 CFR part 
50 should be revised. The NRC is proposing to extend the reporting 
period from 1 year to 18 months, with the objectives of eliminating the 
need for licensees to prepare and submit extension requests and for the 
NRC to review such requests. This revision would have no effect on 
public health and safety.
    Licensees must maintain records and prepare reports to demonstrate 
their fulfillment of the regulatory requirements related to a reactor 
vessel material surveillance program. The information collection 
requirements under this program include:
     Maintenance of records of the test results from this 
program throughout the life of the reactor vessel.
     Reports of the information specified in ASTM E 185-82.
    The NRC published a Federal Register notice with a 60-day comment 
period on this information collection on January 13, 2020, 85 FR 
1825.\8\ No comments were received.
---------------------------------------------------------------------------

    \8\ A subsequent notice was published on January 21, 2020 (85 FR 
3432), to correct the Docket ID listed in the body of the notice
---------------------------------------------------------------------------

    The NRC is providing the public a second opportunity to comment on 
the potential impact of the information collections contained in this 
proposed rule and on the following issues:
    1. Is the proposed information collection necessary for the proper 
performance of the functions of the NRC, including whether the 
information will have practical utility?
    2. Is the estimate of burden accurate?
    3. Is there a way to enhance the quality, utility, and clarity of 
the information to be collected?
    4. How can the burden of the information collection be minimized, 
including the use of automated collection techniques?
    A copy of the OMB clearance package and proposed rule is available 
in ADAMS under Accession Nos. ML20041B864 and ML19184A621, 
respectively, or may be viewed free of charge at the NRC's PDR, One 
White Flint North, 11555 Rockville Pike, Room O1-F21, Rockville, MD 
20852. You may

[[Page 62238]]

obtain information and comment submissions related to the OMB clearance 
package by searching on https://www.regulations.gov under Docket ID 
NRC-2017-0151.
    Send comments on any aspect of these proposed information 
collections, including suggestions for reducing the burden and on the 
above previously stated issues, by November 2, 2020 to the Information 
Services Branch (T6-A10M), U.S. Nuclear Regulatory Commission, 
Washington, DC 20555-0001, or by email to [email protected] 
and to the OMB reviewer at: OMB Office of Information and Regulatory 
Affairs (3150-0011), Attn: Desk Officer for the Nuclear Regulatory 
Commission, 725 17th Street NW, Washington, DC 20503; email: 
[email protected]. Comments received after this date will be 
considered if it is practical to do so, but assurance of consideration 
cannot be given to comments received after this date.

Public Protection Notification

    The NRC may not conduct or sponsor, and a person is not required to 
respond to, a collection of information unless the document requesting 
or requiring the collection displays a currently valid OMB control 
number.

VI. Voluntary Consensus Standards

    The National Technology Transfer and Advancement Act of 1995 (Pub. 
L. 104-113) requires that Federal agencies use technical standards that 
are developed or adopted by voluntary consensus standards bodies unless 
using such a standard is inconsistent with applicable law or otherwise 
impractical. In this proposed rule, the NRC would amend the reactor 
vessel materials surveillance program requirements to reduce the 
regulatory burden for non-safety-significant issues associated with the 
testing of surveillance capsule specimens and reporting the 
surveillance test results. It would also clarify the requirements for 
the design of surveillance programs and the withdrawal schedules for 
reactor vessels purchased after 1982. Specifically, this proposed rule 
allows licensees to reduce the testing of some specimens and eliminates 
the testing of other specimens that were found not to provide 
meaningful information to assess the integrity of the reactor vessel. 
It would also extend by 6 months the period for licensees to submit the 
report of test results to the NRC. The increase in neutron fluence over 
6 months is very small, and therefore the projected increase in 
embrittlement over this period would also be very small. This small 
impact, in conjunction with the margin of safety which is inherent in 
the pressure-temperature limit curves, minimizes any impact due to the 
6 month increase. This action would not constitute the establishment of 
new conditions on the ASTM standards that are currently incorporated by 
reference in appendix H to 10 CFR part 50 nor a standard that contains 
generally applicable requirements. This action would maintain the use 
of the ASTM standards that are currently incorporated by reference in 
appendix H to 10 CFR part 50 but would make optional certain aspects of 
the ASTM standards that have been determined not to be necessary for 
safe operation of nuclear power plants.

VII. Availability of Documents

    The documents identified in the following table are available to 
interested persons through one or more of the following methods, as 
indicated.

----------------------------------------------------------------------------------------------------------------
                        Document                          Adams Accession No./Web Link/Federal Register Citaton
----------------------------------------------------------------------------------------------------------------
ASME Boiler and Pressure Vessel Code, Section II,        https://www.asme.org.
 ``Materials''.
NRC Regulatory Issue Summary 2014-11, ``Information on   ML14149A165.
 Licensing Applications for Fracture Toughness
 Requirements for Ferric Reactor Coolant Pressure
 Boundary Components,'' October 14, 2014.
ASTM E 185[dash]73, ``Standard Recommended Practice for  https://www.astm.org.
 Surveillance Tests for Nuclear Reactor Vessels''.
ASTM 185[dash]79, ``Standard Practice for Conducting     https://www.astm.org.
 Surveillance Tests for Light-Water Cooled Nuclear
 Power Reactor Vessels''.
ASTM E 185[dash]82, ``Standard Practice for Conducting   https://www.astm.org.
 Surveillance Tests for Light[dash]Water Cooled Nuclear
 Power Reactor Vessels''.
ASME Boiler and Pressure Vessel Code, Section XI,        https://www.asme.org.
 Appendix G, ``Rules for Inservice Inspection of
 Nuclear Power Plant Components''.
Federal Register notification--``Part 50 Final Rule-     38 FR 19012.
 Licensing of Production and Utilization Facilities;
 Fracture Toughness and Surveillance Program
 Requirements,'' July 17, 1973.
Federal Register notification--``10 CFR Part 50 Final    48 FR 24008.
 Rule, Fracture Toughness Requirements for Light-Water
 Nuclear Power Reactors,'' May 27, 1983.
Rulemaking for Appendix H to 10 CFR Part 50, ``Reactor   ML19038A477.
 Vessel Material Surveillance Program Requirements--
 Regulatory Basis,'' April 2019.
Federal Register notification--``10 CFR Part 50,         84 FR 12876.
 Reactor Vessel Material Surveillance Program:
 Regulatory Basis; Availability,'' April 3, 2019.
Federal Register notification--``10 CFR Part 50,         84 FR 14845.
 Reactor Vessel Material Surveillance Program:
 Regulatory Basis; Availability; Correction,'' April
 12, 2019.
Staff Requirements Memorandum                            ML19009A517.
 (SRM)[dash]COMSECY[dash]18[dash]0016, ``Request
 Commission Approval to Use the Direct Final Rule
 Process to Revise the Testing and Reporting
 Requirements in 10 CFR Part 50, Appendix H, Reactor
 Vessel Material Surveillance Program Requirements (RIN
 3150[dash]AK07),'' January 9, 2019.
Federal Register notice--``Information Collection:       85 FR 1825.
 Domestic Licensing of Production and Utilization
 Facilities; Revision of Existing Information
 Collection; Request for Comment,'' January 13, 2020.
Federal Register notice--``Information Collection:       85 FR 3432.
 Domestic Licensing of Production and Utilization
 Facilities; Correction; Revision of Existing
 Information Collection; Request for Comment;
 Correction,'' January 21, 2020.
OMB Supporting Statement for Information Collections     ML20041B864.
 Contained in the Appendix H to 10 CFR Part 50,
 ``Reactor Vessel Material Surveillance Program
 Requirements, Proposed Rule''.
----------------------------------------------------------------------------------------------------------------

    The NRC may post materials related to this document, including 
public comments, on the Federal Rulemaking website at https://www.regulations.gov under Docket ID NRC-2017-0151. The Federal 
Rulemaking website allows you to receive alerts when changes or 
additions occur in a docket folder. To subscribe: (1) Navigate to the 
docket

[[Page 62239]]

folder (NRC-2017-0151); (2) click the ``Sign up for Email Alerts'' 
link; and (3) enter your email address and select how frequently you 
would like to receive emails (daily, weekly, or monthly).

List of Subjects in 10 CFR Part 50

    Administrative practice and procedure, Antitrust, Backfitting, 
Classified information, Criminal penalties, Education, Fire prevention, 
Fire protection, Incorporation by reference, Intergovernmental 
relations, Nuclear power plants and reactors, Penalties, Radiation 
protection, Reactor siting criteria, Reporting and recordkeeping 
requirements, Whistleblowing.

    Dated at Rockville, Maryland, this 24th day of September, 2020.

    For the Nuclear Regulatory Commission.
Annette Vietti-Cook,
Secretary for the Commission.
[FR Doc. 2020-21506 Filed 10-1-20; 8:45 am]
BILLING CODE 7590-01-P