[Federal Register Volume 85, Number 184 (Tuesday, September 22, 2020)]
[Notices]
[Pages 59559-59565]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2020-20720]


=======================================================================
-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION

[NRC-2020-0216]


Biweekly Notice; Applications and Amendments to Facility 
Operating Licenses and Combined Licenses Involving No Significant 
Hazards Considerations

AGENCY: Nuclear Regulatory Commission.

ACTION: Biweekly notice.

-----------------------------------------------------------------------

SUMMARY: Pursuant to section 189.a.(2) of the Atomic Energy Act of 
1954, as amended (the Act), the U.S. Nuclear Regulatory Commission 
(NRC) is publishing this regular biweekly notice. The Act requires the 
Commission to publish notice of any amendments issued, or proposed to 
be issued, and grants the Commission the authority to issue and make 
immediately effective any amendment to an operating license or combined 
license, as applicable, upon a determination by the Commission that 
such amendment involves no significant hazards consideration (NSHC), 
notwithstanding the pendency before the Commission of a request for a 
hearing from any person. This biweekly notice includes all amendments 
issued, or proposed to be issued, from August 25, 2020, to September 7, 
2020. The last biweekly notice was published on September 8, 2020.

DATES: Comments must be filed by October 22, 2020. A request for a 
hearing or petitions for leave to intervene must be filed by November 
23, 2020.

ADDRESSES: You may submit comments by any of the following methods:

[[Page 59560]]

     Federal Rulemaking Website: Go to https://www.regulations.gov and search for Docket ID NRC-2020-0216. Address 
questions about NRC Docket IDs in Regulations.gov to Jennifer Borges; 
telephone: 301-287-9127; email: [email protected]. For technical 
questions, contact the individual(s) listed in the FOR FURTHER 
INFORMATION CONTACT section of this document.
     Mail comments to: Office of Administration, Mail Stop: 
TWFN-7-A60M, U.S. Nuclear Regulatory Commission, Washington, DC 20555-
0001, ATTN: Program Management, Announcements and Editing Staff.
    For additional direction on obtaining information and submitting 
comments, see ``Obtaining Information and Submitting Comments'' in the 
SUPPLEMENTARY INFORMATION section of this document.

FOR FURTHER INFORMATION CONTACT: Lynn Ronewicz, Office of Nuclear 
Reactor Regulation, telephone: 301-415-1927, email: 
[email protected], U.S. Nuclear Regulatory Commission, Washington, 
DC 20555-0001.

SUPPLEMENTARY INFORMATION:

I. Obtaining Information and Submitting Comments

A. Obtaining Information

    Please refer to Docket ID NRC-2020-0216, facility name, unit 
number(s), docket number(s), application date, and subject when 
contacting the NRC about the availability of information for this 
action. You may obtain publicly-available information related to this 
action by any of the following methods:
     Federal Rulemaking Website: Go to https://www.regulations.gov and search for Docket ID NRC-2020-0216.
     NRC's Agencywide Documents Access and Management System 
(ADAMS): You may obtain publicly-available documents online in the 
ADAMS Public Documents collection at https://www.nrc.gov/reading-rm/adams.html. To begin the search, select ``Begin Web-based ADAMS 
Search.'' For problems with ADAMS, please contact the NRC's Public 
Document Room reference staff at 1-800-397-4209, 301-415-4737, or by 
email to [email protected]. The ADAMS accession number for each 
document referenced (if it is available in ADAMS) is provided the first 
time that it is mentioned in this document.

B. Submitting Comments

    Please include Docket ID NRC-2020-0216, facility name, unit 
number(s), docket number(s), application date, and subject in your 
comment submission.
    The NRC cautions you not to include identifying or contact 
information that you do not want to be publicly disclosed in your 
comment submission. The NRC will post all comment submissions at 
https://www.regulations.gov as well as enter the comment submissions 
into ADAMS. The NRC does not routinely edit comment submissions to 
remove identifying or contact information.
    If you are requesting or aggregating comments from other persons 
for submission to the NRC, then you should inform those persons not to 
include identifying or contact information that they do not want to be 
publicly disclosed in their comment submission. Your request should 
state that the NRC does not routinely edit comment submissions to 
remove such information before making the comment submissions available 
to the public or entering the comment into ADAMS.

II. Notice of Consideration of Issuance of Amendments to Facility 
Operating Licenses and Combined Licenses and Proposed No Significant 
Hazards Consideration Determination

    For the facility-specific amendment requests shown below, the 
Commission finds that the licensee's analyses provided, consistent with 
title 10 of the Code of Federal Regulations (10 CFR) section 50.91, is 
sufficient to support the proposed determination that these amendment 
requests involve NSHC. Under the Commission's regulations in 10 CFR 
50.92, operation of the facility in accordance with the proposed 
amendment would not (1) involve a significant increase in the 
probability or consequences of an accident previously evaluated; or (2) 
create the possibility of a new or different kind of accident from any 
accident previously evaluated; or (3) involve a significant reduction 
in a margin of safety.
    The Commission is seeking public comments on this proposed 
determination. Any comments received within 30 days after the date of 
publication of this notice will be considered in making any final 
determination.
    Normally, the Commission will not issue the amendment until the 
expiration of 60 days after the date of publication of this notice. The 
Commission may issue the license amendment before expiration of the 60-
day period provided that its final determination is that the amendment 
involves NSHC. In addition, the Commission may issue the amendment 
prior to the expiration of the 30-day comment period if circumstances 
change during the 30-day comment period such that failure to act in a 
timely way would result, for example in derating or shutdown of the 
facility. If the Commission takes action prior to the expiration of 
either the comment period or the notice period, it will publish in the 
Federal Register a notice of issuance. If the Commission makes a final 
NSHC determination, any hearing will take place after issuance. The 
Commission expects that the need to take action on an amendment before 
60 days have elapsed will occur very infrequently.

A. Opportunity To Request a Hearing and Petition for Leave To Intervene

    Within 60 days after the date of publication of this notice, any 
persons (petitioner) whose interest may be affected by this action may 
file a request for a hearing and petition for leave to intervene 
(petition) with respect to the action. Petitions shall be filed in 
accordance with the Commission's ``Agency Rules of Practice and 
Procedure'' in 10 CFR part 2. Interested persons should consult a 
current copy of 10 CFR 2.309. The NRC's regulations are accessible 
electronically from the NRC Library on the NRC's website at https://www.nrc.gov/reading-rm/doc-collections/cfr/. If a petition is filed, 
the Commission or a presiding officer will rule on the petition and, if 
appropriate, a notice of a hearing will be issued.
    As required by 10 CFR 2.309(d) the petition should specifically 
explain the reasons why intervention should be permitted with 
particular reference to the following general requirements for 
standing: (1) The name, address, and telephone number of the 
petitioner; (2) the nature of the petitioner's right to be made a party 
to the proceeding; (3) the nature and extent of the petitioner's 
property, financial, or other interest in the proceeding; and (4) the 
possible effect of any decision or order which may be entered in the 
proceeding on the petitioner's interest.
    In accordance with 10 CFR 2.309(f), the petition must also set 
forth the specific contentions which the petitioner seeks to have 
litigated in the proceeding. Each contention must consist of a specific 
statement of the issue of law or fact to be raised or controverted. In 
addition, the petitioner must provide a brief explanation of the bases 
for the contention and a concise statement of the alleged facts or 
expert opinion which support the contention and on which the petitioner 
intends to rely in proving the contention at the hearing. The 
petitioner must also provide references to the specific sources and 
documents on which the petitioner intends to rely to support its

[[Page 59561]]

position on the issue. The petition must include sufficient information 
to show that a genuine dispute exists with the applicant or licensee on 
a material issue of law or fact. Contentions must be limited to matters 
within the scope of the proceeding. The contention must be one which, 
if proven, would entitle the petitioner to relief. A petitioner who 
fails to satisfy the requirements at 10 CFR 2.309(f) with respect to at 
least one contention will not be permitted to participate as a party.
    Those permitted to intervene become parties to the proceeding, 
subject to any limitations in the order granting leave to intervene. 
Parties have the opportunity to participate fully in the conduct of the 
hearing with respect to resolution of that party's admitted 
contentions, including the opportunity to present evidence, consistent 
with the NRC's regulations, policies, and procedures.
    Petitions must be filed no later than 60 days from the date of 
publication of this notice. Petitions and motions for leave to file new 
or amended contentions that are filed after the deadline will not be 
entertained absent a determination by the presiding officer that the 
filing demonstrates good cause by satisfying the three factors in 10 
CFR 2.309(c)(1)(i) through (iii). The petition must be filed in 
accordance with the filing instructions in the ``Electronic Submissions 
(E-Filing)'' section of this document.
    If a hearing is requested, and the Commission has not made a final 
determination on the issue of no significant hazards consideration, the 
Commission will make a final determination on the issue of no 
significant hazards consideration. The final determination will serve 
to establish when the hearing is held. If the final determination is 
that the amendment request involves no significant hazards 
consideration, the Commission may issue the amendment and make it 
immediately effective, notwithstanding the request for a hearing. Any 
hearing would take place after issuance of the amendment. If the final 
determination is that the amendment request involves a significant 
hazards consideration, then any hearing held would take place before 
the issuance of the amendment unless the Commission finds an imminent 
danger to the health or safety of the public, in which case it will 
issue an appropriate order or rule under 10 CFR part 2.
    A State, local governmental body, Federally-recognized Indian 
Tribe, or agency thereof, may submit a petition to the Commission to 
participate as a party under 10 CFR 2.309(h)(1). The petition should 
state the nature and extent of the petitioner's interest in the 
proceeding. The petition should be submitted to the Commission no later 
than 60 days from the date of publication of this notice. The petition 
must be filed in accordance with the filing instructions in the 
``Electronic Submissions (E-Filing)'' section of this document, and 
should meet the requirements for petitions set forth in this section, 
except that under 10 CFR 2.309(h)(2) a State, local governmental body, 
or Federally-recognized Indian Tribe, or agency thereof does not need 
to address the standing requirements in 10 CFR 2.309(d) if the facility 
is located within its boundaries. Alternatively, a State, local 
governmental body, Federally-recognized Indian Tribe, or agency thereof 
may participate as a non-party under 10 CFR 2.315(c).
    If a hearing is granted, any person who is not a party to the 
proceeding and is not affiliated with or represented by a party may, at 
the discretion of the presiding officer, be permitted to make a limited 
appearance pursuant to the provisions of 10 CFR 2.315(a). A person 
making a limited appearance may make an oral or written statement of 
his or her position on the issues but may not otherwise participate in 
the proceeding. A limited appearance may be made at any session of the 
hearing or at any prehearing conference, subject to the limits and 
conditions as may be imposed by the presiding officer. Details 
regarding the opportunity to make a limited appearance will be provided 
by the presiding officer if such sessions are scheduled.

B. Electronic Submissions (E-Filing)

    All documents filed in NRC adjudicatory proceedings, including a 
request for hearing and petition for leave to intervene (petition), any 
motion or other document filed in the proceeding prior to the 
submission of a request for hearing or petition to intervene, and 
documents filed by interested governmental entities that request to 
participate under 10 CFR 2.315(c), must be filed in accordance with the 
NRC's E-Filing rule (72 FR 49139; August 28, 2007, as amended at 77 FR 
46562; August 3, 2012). The E-Filing process requires participants to 
submit and serve all adjudicatory documents over the internet, or in 
some cases to mail copies on electronic storage media. Detailed 
guidance on making electronic submissions may be found in the Guidance 
for Electronic Submissions to the NRC and on the NRC website at https://www.nrc.gov/site-help/e-submittals.html. Participants may not submit 
paper copies of their filings unless they seek an exemption in 
accordance with the procedures described below.
    To comply with the procedural requirements of E-Filing, at least 10 
days prior to the filing deadline, the participant should contact the 
Office of the Secretary by email at [email protected], or by 
telephone at 301-415-1677, to (1) request a digital identification (ID) 
certificate, which allows the participant (or its counsel or 
representative) to digitally sign submissions and access the E-Filing 
system for any proceeding in which it is participating; and (2) advise 
the Secretary that the participant will be submitting a petition or 
other adjudicatory document (even in instances in which the 
participant, or its counsel or representative, already holds an NRC-
issued digital ID certificate). Based upon this information, the 
Secretary will establish an electronic docket for the hearing in this 
proceeding if the Secretary has not already established an electronic 
docket.
    Information about applying for a digital ID certificate is 
available on the NRC's public website at https://www.nrc.gov/site-help/e-submittals/getting-started.html. Once a participant has obtained a 
digital ID certificate and a docket has been created, the participant 
can then submit adjudicatory documents. Submissions must be in Portable 
Document Format (PDF). Additional guidance on PDF submissions is 
available on the NRC's public website at https://www.nrc.gov/site-help/electronic-sub-ref-mat.html. A filing is considered complete at the 
time the document is submitted through the NRC's E-Filing system. To be 
timely, an electronic filing must be submitted to the E-Filing system 
no later than 11:59 p.m. Eastern Time on the due date. Upon receipt of 
a transmission, the E-Filing system time-stamps the document and sends 
the submitter an email notice confirming receipt of the document. The 
E-Filing system also distributes an email notice that provides access 
to the document to the NRC's Office of the General Counsel and any 
others who have advised the Office of the Secretary that they wish to 
participate in the proceeding, so that the filer need not serve the 
document on those participants separately. Therefore, applicants and 
other participants (or their counsel or representative) must apply for 
and receive a digital ID certificate before adjudicatory documents are 
filed so that they can obtain access to the documents via the E-Filing 
system.
    A person filing electronically using the NRC's adjudicatory E-
Filing system

[[Page 59562]]

may seek assistance by contacting the NRC's Electronic Filing Help Desk 
through the ``Contact Us'' link located on the NRC's public website at 
https://www.nrc.gov/site-help/e-submittals.html, by email to 
[email protected], or by a toll-free call at 1-866-672-7640. The 
NRC Electronic Filing Help Desk is available between 9 a.m. and 6 p.m., 
Eastern Time, Monday through Friday, excluding government holidays.
    Participants who believe that they have a good cause for not 
submitting documents electronically must file an exemption request, in 
accordance with 10 CFR 2.302(g), with their initial paper filing 
stating why there is good cause for not filing electronically and 
requesting authorization to continue to submit documents in paper 
format. Such filings must be submitted by: (1) First class mail 
addressed to the Office of the Secretary of the Commission, U.S. 
Nuclear Regulatory Commission, Washington, DC 20555-0001, Attention: 
Rulemaking and Adjudications Staff; or (2) courier, express mail, or 
expedited delivery service to the Office of the Secretary, 11555 
Rockville Pike, Rockville, Maryland 20852, Attention: Rulemaking and 
Adjudications Staff. Participants filing adjudicatory documents in this 
manner are responsible for serving the document on all other 
participants. Filing is considered complete by first-class mail as of 
the time of deposit in the mail, or by courier, express mail, or 
expedited delivery service upon depositing the document with the 
provider of the service. A presiding officer, having granted an 
exemption request from using E-Filing, may require a participant or 
party to use E-Filing if the presiding officer subsequently determines 
that the reason for granting the exemption from use of E-Filing no 
longer exists.
    Documents submitted in adjudicatory proceedings will appear in the 
NRC's electronic hearing docket which is available to the public at 
https://adams.nrc.gov/ehd, unless excluded pursuant to an order of the 
Commission or the presiding officer. If you do not have an NRC-issued 
digital ID certificate as described above, click ``cancel'' when the 
link requests certificates and you will be automatically directed to 
the NRC's electronic hearing dockets where you will be able to access 
any publicly available documents in a particular hearing docket. 
Participants are requested not to include personal privacy information, 
such as social security numbers, home addresses, or personal phone 
numbers in their filings, unless an NRC regulation or other law 
requires submission of such information. For example, in some 
instances, individuals provide home addresses in order to demonstrate 
proximity to a facility or site. With respect to copyrighted works, 
except for limited excerpts that serve the purpose of the adjudicatory 
filings and would constitute a Fair Use application, participants are 
requested not to include copyrighted materials in their submission.
    The table below provides the plant name, docket number, date of 
application, ADAMS accession number, and location in the application of 
the licensee's proposed NSHC determination. For further details with 
respect to these license amendment applications, see the application 
for amendment which is available for public inspection in ADAMS. For 
additional direction on accessing information related to this document, 
see the ``Obtaining Information and Submitting Comments'' section of 
this document.

                   Table 1--License Amendment Requests
------------------------------------------------------------------------
 
------------------------------------------------------------------------
  Energy Harbor Nuclear Corp. and Energy Harbor Nuclear Generation LLC;
  Beaver Valley Power Station, Units 1 and 2; Beaver County, PA, Energy
  Harbor Nuclear Corp. and Energy Harbor Nuclear Generation LLC; Davis-
       Besse Nuclear Power Station, Unit No. 1; Ottawa County, OH
------------------------------------------------------------------------
Docket No(s).................  50-334, 50-346, 50-412.
Application Date.............  July 27, 2020.
ADAMS Accession No...........  ML20209A540.
Location in Application of     Pages 6-8 of the Enclosure.
 NSHC.
Brief Description of           The proposed amendments would change the
 Amendment(s).                  Beaver Valley Power Station, Unit Nos. 1
                                and 2, and the Davis-Besse Nuclear Power
                                Station, Unit No. 1, Technical
                                Specification 5.2, ``Unit Staff,''
                                subpart 2.e, to align with the standard
                                technical specifications (STS) for each
                                type of facility. Additionally, a title
                                listed in the STS would be revised to
                                reflect a more generic title. These
                                changes would not alter any technical
                                requirements and are administrative in
                                nature.
Proposed Determination.......  NSHC.
Name of Attorney for           Rick Giannantonio, General Counsel,
 Licensee, Mailing Address.     Energy Harbor Corp., 168 E Market
                                Street, Akron, OH 44308-2014.
NRC Project Manager,           Bhalchandra Vaidya, 301-415-3308.
 Telephone Number.
------------------------------------------------------------------------
 Entergy Operations, Inc.; Waterford Steam Electric Station, Unit 3; St.
                           Charles Parish, LA
------------------------------------------------------------------------
Docket No(s).................  50-382.
Application Date.............  June 1, 2020.
ADAMS Accession No...........  ML20153A457.
Location in Application of     Pages 6-7 of the Enclosure.
 NSHC.
Brief Description of           The amendment would revise the emergency
 Amendment(s).                  plan for the Waterford Steam Electric
                                Station, Unit 3, to adopt (with
                                deviations and differences) the Nuclear
                                Energy Institute's (NEI's) revised
                                emergency action level scheme described
                                in NEI 99-01, Revision 6, ``Development
                                of Emergency Action Levels for Non-
                                Passive Reactors'' (ADAMS Accession No.
                                ML12326A805).
Proposed Determination.......  NSHC.
Name of Attorney for           Anna Vinson Jones, Senior Counsel,
 Licensee, Mailing Address.     Entergy Services, Inc., 101 Constitution
                                Avenue NW, Suite 200 East, Washington,
                                DC 20001.
NRC Project Manager,           Audrey Klett, 301-415-0489.
 Telephone Number.
------------------------------------------------------------------------
 NextEra Energy Point Beach, LLC; Point Beach Nuclear Plant, Units 1 and
                         2; Manitowoc County, WI
------------------------------------------------------------------------
Docket No(s).................  50-266, 50-301.
Application Date.............  July 30, 2020.
ADAMS Accession No...........  ML20216A243.
Location in Application of     Pages 10-11 of the Enclosure.
 NSHC.
Brief Description of           The proposed amendments would modify the
 Amendment(s).                  technical specifications for Point Beach
                                Nuclear Plant, Units 1 and 2, to resolve
                                nonconservative surveillance
                                requirements by implementing selected
                                improvements in the surveillance
                                formulations and required actions for
                                nuclear transient heat flux hot channel
                                factor, FQ \w\(Z), proposed in Topical
                                Report, WCAP-17661-P-A, Revision 1,
                                ``Improved RAOC and CAOC FQ Surveillance
                                Technical Specifications'' (ADAMS
                                Accession No. ML18298A314 (non-publicly
                                available)).
Proposed Determination.......  NSHC.

[[Page 59563]]

 
Name of Attorney for           Debbie Hendell, Managing Attorney--
 Licensee, Mailing Address.     Nuclear, Florida Power & Light Company,
                                700 Universe Blvd., MS LAW/JB, Juno
                                Beach, FL 33408-0420.
NRC Project Manager,           Booma Venkataraman, 301-415-2934.
 Telephone Number.
------------------------------------------------------------------------
    PSEG Nuclear LLC; Hope Creek Generating Station; Salem County, NJ
------------------------------------------------------------------------
Docket No(s).................  50-354.
Application Date.............  August 19, 2020.
ADAMS Accession No...........  ML20232D120.
Location in Application of     Page 3 of Attachment 1.
 NSHC.
Brief Description of           The proposed amendment would modify the
 Amendment(s).                  Hope Creek Technical Specification (TS)
                                requirements for unavailable barriers by
                                adding Limiting Condition for Operation
                                3.0.9. This change is consistent with
                                NRC-approved Industry Technical
                                Specifications Task Force Change
                                Traveler, TSTF-427, Revision 2,
                                ``Allowance for Non-Technical
                                Specification Barrier Degradation on
                                Supported System OPERABILITY.'' The
                                availability of this TS improvement was
                                published in the Federal Register on
                                November 21, 2007, as part of the
                                Consolidated Line Item Improvement
                                Process (CLllP) (72 FR 65610).
Proposed Determination.......  NSHC.
Name of Attorney for           Jodi Varon, PSEG Services Corporation, 80
 Licensee, Mailing Address.     Park Plaza, T-5, Newark, NJ 07101.
NRC Project Manager,           James Kim, 301-415-4125.
 Telephone Number.
------------------------------------------------------------------------
   Southern Nuclear Operating Company, Inc.; Joseph M. Farley Nuclear
   Plant, Units 1 and 2; Edwin I. Hatch Nuclear Plant, Units 1 and 2;
  Vogtle Electric Generating Plant, Units 1 and 2; and Vogtle Electric
            Generating Plant, Units 3 and 4; Burke County, GA
------------------------------------------------------------------------
Docket No(s).................  50-321, 50-348, 50-424, 52-025, 50-366,
                                50-364, 50-425, 52-026.
Application Date.............  June 30, 2020, as supplemented August 11,
                                2020.
ADAMS Accession No...........  ML20192A140, ML20224A464.
Location in Application of     Pages E1-9 to E1-11 of the Enclosure.
 NSHC.
Brief Description of           The proposed amendments would revise the
 Amendment(s).                  Southern Nuclear Operating Company
                                Standard Emergency Plan, including the
                                Site Annexes, to change the emergency
                                response organization staffing
                                composition and extend staff
                                augmentation times from 75 to 90
                                minutes.
Proposed Determination.......  NSHC.
Name of Attorney for           Millicent Ronnlund, Vice President and
 Licensee, Mailing Address.     General Counsel, Southern Nuclear
                                Operating Co., Inc., P.O. Box 1295,
                                Birmingham, AL 35201-1295.
NRC Project Manager,           John Lamb, 301-415-3100.
 Telephone Number.
------------------------------------------------------------------------
   Susquehanna Nuclear, LLC and Allegheny Electric Cooperative, Inc.;
 Susquehanna Steam Electric Station, Units 1 and 2; Susquehanna County,
                                   PA
------------------------------------------------------------------------
Docket No(s).................  50-387, 50-388.
Application Date.............  June 25, 2020.
ADAMS Accession No...........  ML20177A534.
Location in Application of     Pages 2-3 of Enclosure 1.
 NSHC.
Brief Description of           The proposed amendments would adopt
 Amendment(s).                  Technical Specifications Task Force
                                Traveler, TSTF[dash]529, ``Clarify Use
                                and Application Rules.'' The proposed
                                changes would revise Section 1.3,
                                ``Completion Times,'' and Section 3.0,
                                ``Limiting Condition for Operation (LCO)
                                Applicability,'' of the Technical
                                Specifications (TS) to clarify the use
                                and application of the TS usage rules.
Proposed Determination.......  NSHC.
Name of Attorney for           Damon D. Obie, Esq, 835 Hamilton St.,
 Licensee, Mailing Address.     Suite 150, Allentown, PA 18101.
NRC Project Manager,           Sujata Goetz, 301-415-8004.
 Telephone Number.
------------------------------------------------------------------------
 Vistra Operations Company LLC; Comanche Peak Nuclear Power Plant, Unit
                   Nos. 1 and 2; Somervell County, TX
------------------------------------------------------------------------
Docket No(s).................  50-445, 50-446.
Application Date.............  July 2, 2020, as supplemented August 17,
                                2020.
ADAMS Accession No...........  ML20184A064, ML20230A345.
Location in Application of     Pages 1-3 of the Enclosure.
 NSHC.
Brief Description of           The proposed amendments would adopt TSTF-
 Amendment(s).                  569, ``Revise Response Time Testing
                                Definition.'' The amendments would
                                revise the technical specification
                                definitions for engineered safety
                                feature response time and reactor trip
                                system response time.
Proposed Determination.......  NSHC.
Name of Attorney for           Timothy P. Matthews, Esq., Morgan, Lewis
 Licensee, Mailing Address.     and Bockius, 1111 Pennsylvania Avenue
                                NW, Washington, DC 20004.
NRC Project Manager,           Dennis Galvin, 301-415-6256.
 Telephone Number.
------------------------------------------------------------------------

III. Notice of Issuance of Amendments to Facility Operating Licenses 
and Combined Licenses

    During the period since publication of the last biweekly notice, 
the Commission has issued the following amendments. The Commission has 
determined for each of these amendments that the application complies 
with the standards and requirements of the Atomic Energy Act of 1954, 
as amended (the Act), and the Commission's rules and regulations. The 
Commission has made appropriate findings as required by the Act and the 
Commission's rules and regulations in 10 CFR chapter I, which are set 
forth in the license amendment.
    A notice of consideration of issuance of amendment to facility 
operating license or combined license, as applicable, proposed NSHC 
determination, and opportunity for a hearing in connection with these 
actions, was published in the Federal Register as indicated.
    Unless otherwise indicated, the Commission has determined that 
these amendments satisfy the criteria for categorical exclusion in 
accordance with 10 CFR 51.22. Therefore, pursuant to 10 CFR 51.22(b), 
no environmental impact statement or environmental assessment need be 
prepared for these amendments. If the Commission has prepared an 
environmental assessment under the special circumstances provision in 
10 CFR 51.22(b) and has made a determination based on that assessment, 
it is so indicated.
    For further details with respect to the action, see (1) the 
application for amendment; (2) the amendment; and (3) the Commission's 
related letter, Safety

[[Page 59564]]

Evaluation, and/or Environmental Assessment as indicated. All of these 
items can be accessed as described in the ``Obtaining Information and 
Submitting Comments'' section of this document.

                  Table 2--License Amendment Issuances
------------------------------------------------------------------------
 
------------------------------------------------------------------------
 Entergy Operations, Inc.; Waterford Steam Electric Station, Unit 3; St.
                           Charles Parish, LA
------------------------------------------------------------------------
Docket No(s).................  50-382.
Amendment Date...............  August 25, 2020.
ADAMS Accession No...........  ML20205L574.
Amendment No(s)..............  257.
Brief Description of           The amendment revised the Waterford Steam
 Amendment(s).                  Electric Station, Unit 3, control room
                                emergency air filtration system
                                Technical Specification Surveillance
                                Requirements 4.7.6.1.d.2 and 4.7.6.1.d.4
                                by adding an exception for dampers and
                                valves that are locked or sealed.
------------------------------------------------------------------------
  Indiana Michigan Power Company; Donald C. Cook Nuclear Plant, Unit 1;
                           Berrien County, MI
------------------------------------------------------------------------
Docket No(s).................  50-315.
Amendment Date...............  September 3, 2020.
ADAMS Accession No...........  ML20213C704.
Amendment No(s)..............  353.
Brief Description of           The amendment revised Technical
 Amendment(s).                  Specification 5.5.14, ``Containment
                                Leakage Rate Testing Program,'' to
                                extend the frequency of the primary
                                containment integrated leak rate test,
                                or Type A test, at Cook Nuclear Plant,
                                Unit 1. Specifically, the amendment
                                allows for a one-time extension of the
                                integrated leak-rate test frequency from
                                15 years to no later than the plant
                                restart after the Cook Nuclear Plant,
                                Unit 1, Spring 2022 refueling outage
                                (i.e., approximately 15 years and 5
                                months).
------------------------------------------------------------------------
 Vistra Operations Company LLC; Comanche Peak Nuclear Power Plant, Unit
                   Nos. 1 and 2; Somervell County, TX
------------------------------------------------------------------------
Docket No(s).................  50-445, 50-446.
Amendment Date...............  August 31, 2020.
ADAMS Accession No...........  ML20223A349.
Amendment No(s)..............  175, 175.
Brief Description of           The amendments revised Comanche Peak,
 Amendment(s).                  Unit Nos. 1 and 2, Technical
                                Specification (TS) 3.7.19, ``Safety
                                Chilled Water,'' to extend the
                                completion time for one safety chilled
                                water train inoperable from 72 hours to
                                7 days on a one-time basis to allow the
                                replacement of Unit No. 2 Safety Chiller
                                2-06 (Train B) compressor during Unit
                                No. 2 Cycle 19. Revised TS 3.7.19
                                includes a regulatory commitment that
                                identifies compensatory measures to be
                                implemented during the extended
                                completion time.
------------------------------------------------------------------------
Wolf Creek Nuclear Operating Corporation; Wolf Creek Generating Station,
                        Unit 1; Coffey County, KS
------------------------------------------------------------------------
Docket No(s).................  50-482.
Amendment Date...............  August 25, 2020.
ADAMS Accession No...........  ML20205L304.
Amendment No(s)..............  225.
Brief Description of           The amendment added additional conditions
 Amendment(s).                  to the limiting conditions for operation
                                for Technical Specification 3.7.5,
                                ``Auxiliary Feedwater (AFW) System,''
                                such that one supply of essential
                                service water to the turbine-driven AFW
                                pump can be inoperable up to 72 hours
                                while still considering the turbine-
                                driven AFW pump train operable.
------------------------------------------------------------------------

IV. Previously Published Notice of Consideration of Issuance of 
Amendments to Facility Operating Licenses and Combined Licenses, 
Proposed No Significant Hazards Consideration Determination, and 
Opportunity for a Hearing

    The following notices were previously published as separate 
individual notices. They were published as individual notices either 
because time did not allow the Commission to wait for this biweekly 
notice or because the action involved exigent circumstances. They are 
repeated here because the biweekly notice lists all amendments issued 
or proposed to be issued involving no significant hazards 
consideration.
    For details, including the applicable notice period, see the 
individual notice in the Federal Register on the day and page cited.

   Table 3--License Amendment Issuance--Repeat of Individual  Federal
                             Register Notice
------------------------------------------------------------------------
 
------------------------------------------------------------------------
  Pacific Gas and Electric Company; Diablo Canyon Nuclear Power Plant,
            Units 1 and 2; San Luis Obispo County, California
------------------------------------------------------------------------
Docket No(s).................  50-275, 50-323.
Amendment Date...............  August 31, 2020.
ADAMS Accession No...........  ML20235R635.
Brief Description of           The amendments provide a new Technical
 Amendment(s).                  Specification (TS) 3.7.5, ``Auxiliary
                                Feedwater (AFW) System,'' action and
                                continued operation of Unit 1 during
                                Cycle 22 with the AFW system aligned in
                                a manner for which current TS 3.7.5
                                would require a shutdown.
Date & Cite of Federal         September 9, 2020; 85 FR 55700-55703.
 Register Individual Notice.
Expiration Date for Hearing    November 9, 2020.
 Requests.
------------------------------------------------------------------------



[[Page 59565]]

    Dated: September 15, 2020.

    For the Nuclear Regulatory Commission.
Caroline L. Carusone,
Deputy Director, Division of Operating Reactor Licensing, Office of 
Nuclear Reactor Regulation.
[FR Doc. 2020-20720 Filed 9-21-20; 8:45 am]
BILLING CODE 7590-01-P