[Federal Register Volume 85, Number 13 (Tuesday, January 21, 2020)]
[Rules and Regulations]
[Page 3232]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: C1-2019-26354]


-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

10 CFR Part 430

[Docket Number EERE-2016-BT-STD-0022]
RIN 1904-AD69


Energy Conservation Program: Energy Conservation Standards for 
Uninterruptible Power Supplies

Correction

    In rule document 2019-2635 beginning on page 1447 in the issue of 
Friday, January 10, 2020, make the following correction:


Sec.  430.32   [Corrected]

    On page 1503, in Sec.  430.32(z)(3) the table should appear as 
follows:

----------------------------------------------------------------------------------------------------------------
      Battery charger product class              Rated output power                  Minimum efficiency
----------------------------------------------------------------------------------------------------------------
10a (VFD UPSs)..........................  0 W < P <= 300 W................  -1.20E-06 * P 2 + 7.17E-04 * P +
                                                                             0.862.
                                          300 W < P <= 700 W..............  -7.85E-08 * P 2 + 1.01E-04 * P +
                                                                             0.946.
                                          P > 700 W.......................  -7.23E-09 * P 2 + 7.52E-06 * P +
                                                                             0.977.
10b (VI UPSs)...........................  0 W < P <= 300 W................  -1.20E-06 * P 2 + 7.19E-04 * P +
                                                                             0.863.
                                          300 W < P <= 700 W..............  -7.67E-08 * P 2 + 1.05E-04 * P +
                                                                             0.947.
                                          P > 700 W.......................  -4.62E-09 * P 2 + 8.54E-06 * P +
                                                                             0.979.
10c (VFI UPSs)..........................  0 W < P <= 300 W................  -3.13E-06 * P 2 + 1.96E-03 * P +
                                                                             0.543.
                                          300 W < P <= 700 W..............  -2.60E-07 * P 2 + 3.65E-04 * P +
                                                                             0.764.
                                          P > 700 W.......................  -1.70E-08 * P 2 + 3.85E-05 * P +
                                                                             0.876.
----------------------------------------------------------------------------------------------------------------

[FR Doc. C1-2019-26354 Filed 1-17-20; 8:45 am]
BILLING CODE 1301-00-D