[Federal Register Volume 84, Number 191 (Wednesday, October 2, 2019)]
[Notices]
[Pages 52489-52493]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2019-21437]


-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

[Case Number CAC-050]


Energy Conservation Program: Decision and Order Granting a Waiver 
to Johnson Controls, Inc. From the Department of Energy Central Air 
Conditioners and Heat Pumps Test Procedure

AGENCY: Office of Energy Efficiency and Renewable Energy, Department of 
Energy.

ACTION: Notice of decision and order.

-----------------------------------------------------------------------

SUMMARY: The U.S. Department of Energy (``DOE'') gives notice of a 
Decision and Order granting Johnson Controls, Inc. (``JCI'') a waiver 
from specified portions of the DOE test procedure for determining the 
efficiency of specified central air conditioners (``CAC'') and heat 
pump (``HP'') basic models. JCI is required to test and rate specified 
basic models of its central air

[[Page 52490]]

conditioners and heat pumps in accordance with the alternate test 
procedure specified in the Decision and Order.

DATES: The Decision and Order is effective on October 2, 2019. The 
Decision and Order will terminate upon the compliance date of any 
future amendment to the test procedure for central air conditioners and 
heat pumps located at 10 CFR part 430, subpart B, appendix M that 
addresses the issues presented in this waiver. At such time, JCI must 
use the relevant test procedure for this product for any testing to 
demonstrate compliance with the applicable standards, and any other 
representations of energy use.

FOR FURTHER INFORMATION CONTACT: Mr. Pete Cochran, U.S. Department of 
Energy, Office of the General Counsel, Mail Stop GC-33, Forrestal 
Building, 1000 Independence Avenue SW, Washington, DC 20585-0103. 
Telephone: (202) 586-9496. Email: [email protected].

SUPPLEMENTARY INFORMATION: In accordance with Title 10 of the Code of 
Federal Regulations (10 CFR 430.27(f)(2)), DOE gives notice of the 
issuance of its Decision and Order as set forth below. The Decision and 
Order grants JCI a waiver from the applicable test procedure at 10 CFR 
part 430, subpart B, appendix M for specified basic models of central 
air conditioners and heat pumps, provided that JCI tests and rates such 
products using the alternate test procedure specified in the Decision 
and Order. JCI's representations concerning the energy efficiency of 
the specified basic models must be based on testing according to the 
provisions and restrictions in the alternate test procedure set forth 
in the Decision and Order, and the representations must fairly disclose 
the test results. Distributors, retailers, and private labelers are 
held to the same requirements when making representations regarding the 
energy efficiency of these products. (42 U.S.C. 6293(c)).
    Consistent with 10 CFR 430.27(j), not later than December 2, 2019, 
any manufacturer currently distributing in commerce in the United 
States products employing a technology or characteristic that results 
in the same need for a waiver from the applicable test procedure must 
submit a petition for waiver. Manufacturers not currently distributing 
such products in commerce in the United States must petition for and be 
granted a waiver prior to the distribution in commerce of those 
products in the United States. Manufacturers may also submit a request 
for interim waiver pursuant to the requirements of 10 CFR 430.27.

    Signed in Washington, DC, on September 27, 2019.
Alexander Fitzsimmons,
Acting Deputy Assistant Secretary for Energy Efficiency.

Case Number CAC-050 Decision and Order

I. Background and Authority

    The Energy Policy and Conservation Act of 1975, as amended 
(``EPCA''),\1\ among other things, authorizes the U.S. Department of 
Energy (``DOE'') to regulate the energy efficiency of a number of 
consumer products and industrial equipment. (42 U.S.C. 6291-6317) Title 
III, Part B \2\ of EPCA established the Energy Conservation Program for 
Consumer Products Other Than Automobiles, which sets forth a variety of 
provisions designed to improve energy efficiency for certain types of 
consumer products. These products include central air conditioners 
(CACs) and heat pumps (HPs), the focus of this document. (42 U.S.C. 
6292(a)(3))
---------------------------------------------------------------------------

    \1\ All references to EPCA in this document refer to the statute 
as amended through America's Water Infrastructure Act of 2018, 
Public Law 115-270 (October 23, 2018).
    \2\ For editorial reasons, upon codification in the U.S. Code, 
Part B was redesignated as Part A.
---------------------------------------------------------------------------

    Under EPCA, DOE's energy conservation program consists essentially 
of four parts: (1) Testing, (2) labeling, (3) Federal energy 
conservation standards, and (4) certification and enforcement 
procedures. Relevant provisions of EPCA include definitions (42 U.S.C. 
6291), energy conservation standards (42 U.S.C. 6295), test procedures 
(42 U.S.C. 6293), labeling provisions (42 U.S.C. 6294), and the 
authority to require information and reports from manufacturers (42 
U.S.C. 6296).
    The Federal testing requirements consist of test procedures that 
manufacturers of covered products must use as the basis for: (1) 
Certifying to DOE that their products comply with the applicable energy 
conservation standards adopted pursuant to EPCA (42 U.S.C. 6295(s)), 
and (2) making representations about the efficiency of that product (42 
U.S.C. 6293(c)). Similarly, DOE must use these test procedures to 
determine whether the product complies with relevant standards 
promulgated under EPCA. (42 U.S.C. 6295(s))
    Under 42 U.S.C. 6293, EPCA sets forth the criteria and procedures 
DOE is required to follow when prescribing or amending test procedures 
for covered products. EPCA requires that any test procedures prescribed 
or amended under this section must be reasonably designed to produce 
test results which reflect energy efficiency, energy use or estimated 
annual operating cost of a covered product during a representative 
average use cycle or period of use and requires that test procedures 
not be unduly burdensome to conduct. (42 U.S.C. 6293(b)(3)) The test 
procedure for central air conditioners and heat pumps is contained in 
the Code of Federal Regulations (``CFR'') at 10 CFR part 430, subpart 
B, appendix M, Uniform Test Method for Measuring the Energy Consumption 
of Central Air Conditioners and Heat Pumps (``Appendix M'').
    Under 10 CFR 430.27, any interested person may submit a petition 
for waiver from DOE's test procedure requirements. DOE will grant a 
waiver from the test procedure requirements if DOE determines either 
that the basic model for which the waiver was requested contains a 
design characteristic that prevents testing of the basic model 
according to the prescribed test procedures, or that the prescribed 
test procedures evaluate the basic model in a manner so 
unrepresentative of its true energy consumption characteristics as to 
provide materially inaccurate comparative data. 10 CFR 430.27(f)(2). 
DOE may grant the waiver subject to conditions, including adherence to 
alternate test procedures. Id.

II. Petition for Waiver

A. JCI's Assertions

    On April 6, 2017, JCI filed a petition for waiver and an 
application for interim waiver from certain testing requirements of 
Appendix M. Subsequently, JCI filed an amended petition for waiver and 
application for interim waiver on June 5, 2018. The amended petition 
serves as the basis for this Decision and Order. On August 13, 2018, 
DOE published a notice announcing its receipt of the petition for 
waiver, granting JCI an interim waiver, and requesting public comment 
on the waiver (``Notice of Petition for Waiver''). 83 FR 40011.
    According to JCI, the basic models listed in its petition, which 
use R-407C as the refrigerant, are offered as new, matched systems and 
testing them as outdoor units with no match (as required by the DOE 
test procedure) will overstate their energy usage, resulting in 
materially inaccurate comparative data. JCI states that it has 
certified more than 1,100 unique CAC combinations that use R-407C as a 
refrigerant. The certified ratings range from 14 to 16

[[Page 52491]]

SEER (Seasonal Energy Efficiency Ratio) when tested as new, matched 
systems, but would fall below the minimum standard of 13 SEER in 10 CFR 
430.32(c) if tested as outdoor units with no match. Further, JCI 
contends that many CAC components, including outdoor units, regardless 
of refrigerant type, are also used to replace failed components of 
previously-installed systems. For example, an outdoor unit that uses R-
410A as a refrigerant can be used to replace a failed outdoor unit in a 
previously-installed system. But, as opposed to one of the R-407C 
outdoor units listed in JCI's petition, the R-410A outdoor unit is 
rated based on testing as a new, matched system; it is not rated based 
on an approximation of its efficiency performance when matched with 
older, less-efficient indoor units. As a result, in addition to 
providing materially inaccurate data regarding energy usage when 
installed as new, matched systems, JCI also contends that the outdoor 
unit with no match test procedure provisions provide materially 
inaccurate data in outdoor unit only replacement scenarios when 
comparing the performance of R-407C outdoor units and outdoor units 
that use other refrigerants, such as R-410A. (JCI, No. 7, pp. 4-5) \3\
---------------------------------------------------------------------------

    \3\ [thinsp]DOE will cite to information in the waiver petition 
docket as follows: (Commenter name, comment docket ID number, page 
of that document). The docket is available at https://www.regulations.gov/docket?D=EERE-2017-BT-WAV-0039.
---------------------------------------------------------------------------

B. Comments Received in Response to the Notice of Petition for Waiver

    In response to the Notice of Petition for Waiver, DOE received 
substantive comments \4\ from the nine stakeholders listed in the table 
below:
---------------------------------------------------------------------------

    \4\ DOE received one comment that simply stated ``I object to 
the waiver,'' and three other comments that did not discuss the 
waiver at all.

                           Table of Commenters
------------------------------------------------------------------------
         Commenter(s)              Affiliation           Identifier
------------------------------------------------------------------------
Appliance Standards Awareness   Advocacy Group...  ASAP.
 Project.
California Energy Commission..  State............  CEC.
California Investor-Owned       Utilities........  CA-IOUs.
 Utilities.
Carrier Corporation...........  Manufacturer.....  Carrier.
Goodman Global, Inc...........  Manufacturer.....  Goodman.
Lennox International Inc......  Manufacturer.....  Lennox.
Natural Resources Defense       Advocacy Group...  NRDC.
 Council.
Nortek Global HVAC............  Manufacturer.....  Nortek.
Rheem Manufacturing Company...  Manufacturer.....  Rheem.
------------------------------------------------------------------------

    All of the commenters, with the exception of Rheem,\5\ oppose JCI's 
petition for waiver. In general, commenters state that the basic models 
listed in JCI's petition are primarily installed as replacement outdoor 
units, and not as new, matched systems. For example, Goodman states 
that ``JCI's R407C equipment is predominantly distributed, sold and 
installed as an outdoor[hyphen]only unit replacement for an existing 
R22 system, and in such circumstances it is matched with an existing 
smaller R22 indoor coil. JCI's R407C outdoor units are not typically 
distributed, sold and installed as part of a matched R407C system (that 
is, matched with a new R407C indoor coil) because contractors are 
highly unlikely to install the much larger R407C indoor coils.'' 
(Goodman, No. 30, p. 2) (emphasis in original) Similarly, ASAP states 
that ``JCI's R-407C products are marketed and sold to replace outdoor 
units on legacy systems that use R-22 refrigerant,'' and are ``rarely, 
if ever, installed'' as new, matched systems. (ASAP, No. 27, pp. 1-2)
---------------------------------------------------------------------------

    \5\ Rheem submitted a comment to clarify that it has not 
certified any product that uses R-407C as a refrigerant since the 
latest revision to the test procedure in 2017.
---------------------------------------------------------------------------

    As a result, these commenters believe that the current test 
procedure, which requires the basic models listed in the petition to be 
tested as outdoor units with no match, measures the energy efficiency 
of these models during a representative average use cycle. Thus, if the 
petition is granted, consumers and other entities, such as utilities, 
will not be able to rely on JCI's certified efficiency ratings when 
making decisions based on the energy consumption of the basic models. 
For instance, Lennox states that ``JCI provided no evidence that 407C 
condensers are predominantly installed in consumers' homes matched with 
407C coils. Therefore, DOE's applying the No Match Requirements to 
JCI's 407C condensers will yield representative test results of average 
consumer use, as required by statute.'' (Lennox, No. 26, p. 9) The CA-
IOUs state that ``[s]hould this waiver be granted, it will not be 
possible to know the energy usage of JCI's affected units when paired 
with existing installed indoor coils.'' (CA-IOUs, No. 25, p. 2)
    Some commenters also state that granting the waiver would have the 
effect of lowering the energy conservation standard for the basic 
models listed in JCI's petition. For example, ASAP states that 
``[g]ranting this waiver would be tantamount to a lowering of the 
standard for products that use a particular refrigerant'' and would 
``circumvent the anti-backsliding clause'' of EPCA. (ASAP, No. 27, p. 
2)

C. DOE's Determination

    As discussed above, JCI asserts that the basic models listed in the 
petition, which use R-407C as the refrigerant, are installed as both 
replacement outdoor units in existing installations and as new, matched 
systems. As such, testing JCI's R-407C units under the outdoor unit 
with no match provisions results in materially inaccurate comparative 
data for both outdoor unit only replacement installations and new, 
matched system installations. In order to evaluate JCI's claim that 
these basic models are installed as both replacement outdoor units and 
as new, matched systems, DOE reviewed JCI's public-facing materials, 
including marketing materials and technical guides for the basic models 
listed in the petition, comments received in response to the Notice of 
Petition for Waiver, and other information submitted by JCI.\6\ These 
materials support JCI's assertion that these models are offered as both 
replacement outdoor units in existing installations and as new, matched 
systems. Further, while JCI states that it principally sells these 
basic models through independent distributors and

[[Page 52492]]

has limited information about how these models are installed in the 
field, warranty registrations for these models indicate some consumers 
are installing these products as matched systems. (JCI, No. 33, p. 6) 
Additionally, while commenters claim that these models are ``highly 
unlikely'' to be or ``rarely, if ever,'' installed as new, matched 
systems, they do not claim, or provide evidence, that these systems are 
never installed as new, matched systems. As a result, DOE has 
determined that the basic models listed in JCI's petition are installed 
as replacement outdoor units with existing indoor units and as new, 
matched systems.
---------------------------------------------------------------------------

    \6\ These materials are all available in the docket at https://www.regulations.gov/docket?D=EERE-2017-BT-WAV-0039.
---------------------------------------------------------------------------

    Under 10 CFR 430.27(f)(2), DOE will grant a waiver for one of two 
reasons: (1) The basic model for which the waiver was requested 
contains a design characteristic that prevents testing of the basic 
model according to the prescribed test procedures; or (2) the 
prescribed test procedures evaluate the basic model in a manner so 
unrepresentative of its true energy consumption characteristics as to 
provide materially inaccurate comparative data. JCI asserts that 
application of the outdoor unit with no match testing provisions in 
Appendix M to the basic models listed in its petition would evaluate 
these models in a manner so unrepresentative of their true energy 
consumption characteristics as to provide material inaccurate 
comparative data. To illustrate its claim of materially inaccurate 
comparative data, JCI refers to the difference in how energy 
consumption is determined under DOE's current test procedure between 
the basic models listed in the petition, which use R-407C as a 
refrigerant, and other CAC and HP systems that use R-410A as the 
refrigerant. Under DOE's current test procedure, the energy efficiency 
rating of an R-407C unit is calculated as an outdoor unit with no 
match, regardless of whether it may actually be installed as a new, 
matched system, while the energy efficiency rating of an R-410A unit is 
calculated as a new, matched system, regardless of whether it may 
actually be installed as an outdoor unit only replacement. There is a 
significant difference in calculated energy efficiency between these 
two approaches. JCI states that the certified ratings for its R-407C 
units range from 14 to 16 SEER when tested as new, matched systems, but 
would fall below the minimum standard of 13 SEER if tested as outdoor 
units with no match.
    DOE acknowledged this disparate treatment in response to a comment 
submitted by JCI during the last test procedure rulemaking. ``[I]t has 
always been the case that some outdoor units are installed as 
replacements for failed outdoor units. However, in most cases an 
outdoor unit model would also be sold in substantial numbers as a 
combination with indoor units. This is in contrast to R-407C units, 
which are predominantly sold in scenarios in which the outdoor unit is 
replaced, and the indoor unit is not replaced. Hence the test procedure 
is representative of an average use cycle for R-410A units without 
requiring that it be tested as a unit with no match.'' 82 FR 1426, 1434 
(Jan. 5, 2017).
    Having reexamined this issue in light of JCI's petition for waiver, 
DOE has determined that such disparate treatment between systems that 
use R-407C as a refrigerant and systems that use other refrigerants, 
such as R-410A, is unwarranted and results in materially inaccurate 
comparative data. Testing R-407C units differently from other units 
prevents consumers from making apples-to-apples comparisons about 
energy consumption and operating costs. Consumers cannot make informed 
decisions when, unbeknownst to them, they may be comparing the cost and 
performance of CAC and HP systems based on different installation 
scenarios. Furthermore, even if it is assumed that a representative 
average use cycle for CACs and HPs should account for outdoor unit only 
replacement scenarios, there is no reason to exclude certain outdoor 
units from such treatment simply because these units are also sold in 
``substantial'' numbers as new, matched systems. Being sold in 
``substantial'' numbers as new, matched systems does not preclude these 
units from also being sold in significant numbers as replacements for 
failed outdoor units. In fact, according to information provided by the 
Air-conditioning, Heating and Refrigeration Institute (AHRI) during the 
last energy conservation standards rulemaking for CACs and HPs, 
approximately 25 percent of all replacement installations, regardless 
of refrigerant used, are outdoor unit only replacements. 82 FR 1786, 
1815 (Jan. 6, 2017). This percentage was significant enough for DOE to 
adjust its energy use analysis in the energy conservation standards 
rulemaking to account for the increased energy consumption of outdoor 
unit only replacement installations. Id. Thus, DOE has determined that 
accounting for outdoor unit only replacement installations in the 
average use cycle for CAC and HP systems that use R-407C, but not in 
systems that are sold in ``substantial'' numbers as new, matched 
systems is inconsistent and results in materially inaccurate 
comparative data.
    Finally, with respect to ASAP's comment that granting JCI's waiver 
request would circumvent the anti-backsliding provision in EPCA, DOE 
notes that the anti-backsliding provision prohibits DOE from issuing 
any amended standards that would increase the maximum allowable energy 
use or decrease the minimum required energy efficiency of a covered 
product. (42 U.S.C. 6295(o)(1)) Even if it is assumed that this 
provision applies to test procedure waivers, ASAP's argument that 
granting JCI's waiver request would result in backsliding is 
disingenuous. Under 42 U.S.C. 6293(e), if an amended test procedure 
alters the measured energy efficiency of a covered product, DOE is 
required to make a corresponding adjustment to the energy conservation 
standard to ensure that a previously compliant covered product would 
remain compliant and a previously non-compliant covered product would 
remain non-compliant. When DOE issued the current test procedure for 
CACs and HPs on January 5, 2017, DOE made a determination that the 
amended test procedure provisions from which JCI is seeking a waiver 
would not alter the measured energy efficiency of these covered 
products, and, as a result, did not adjust the energy conservation 
standard for CACs and HPs. 82 FR 1426, 1428. If this determination was 
correct, granting JCI's petition for waiver would have no effect on the 
measured energy efficiency of the basic models listed in the petition 
and, therefore, backsliding of the standard would not be possible. As a 
result, ASAP's argument is that DOE's determination in the test 
procedure rulemaking was incorrect and these test procedure provisions 
do alter the measured energy efficiency of the basic models listed in 
JCI's petition. This argument, concerning the difference in measured 
energy efficiency between DOE's prior and current test procedures, has 
no bearing on whether the current test procedure evaluates the basic 
models listed in the petition in a manner so unrepresentative of their 
true energy consumption characteristics as to provide materially 
inaccurate comparative data.
    For the reasons explained here and in the Notice of Petition for 
Waiver, DOE understands that absent a waiver, the basic models 
identified by JCI in its petition will be evaluated in a manner so 
unrepresentative of their true energy consumption characteristics when 
installed as new, matched systems as to provide materially inaccurate 
comparative data. DOE has reviewed the alternate test procedure 
suggested by JCI and concludes that it is representative of the energy 
consumption of these basic

[[Page 52493]]

models when installed as new, matched systems, and will allow for 
accurate comparisons of energy use between CAC and HP systems that use 
different refrigerants. Thus, DOE grants JCI's petition for waiver and 
requires that JCI test and rate the CAC and HP basic models listed in 
its petition according to the alternate test procedure specified in the 
Decision and Order, which is identical to the alternate test procedure 
provided in the interim waiver.
    This Decision and Order is applicable only to the basic models 
listed and does not extend to any other basic models. DOE evaluates and 
grants waivers for only those basic models specifically set out in the 
petition, not future models that may be manufactured by the petitioner.
    JCI may request that the scope of this waiver be extended to 
include additional basic models that employ the same technology as 
those listed in this waiver. 10 CFR 430.27(g). JCI may also submit 
another petition for waiver from the test procedure for additional 
basic models that employ a different technology and meet the criteria 
for test procedure waivers. 10 CFR 430.27(a)(1).
    DOE notes that it may modify or rescind the waiver at any time upon 
DOE's determination that the factual basis underlying the petition for 
waiver is incorrect, or upon a determination that the results from the 
alternate test procedure are unrepresentative of the basic models' true 
energy consumption characteristics. 10 CFR 430.27(k)(1). Likewise, JCI 
may request that DOE rescind or modify the waiver if the company 
discovers an error in the information provided to DOE as part of its 
petition, determines that the waiver is no longer needed, or for other 
appropriate reasons. 10 CFR 430.27(k)(2).
    DOE recognizes that commenters have raised valid concerns about the 
need to provide information regarding the energy consumption of CACs 
and HPs when a new outdoor unit is paired with an existing, older 
indoor unit. DOE is mindful that consumers need accurate comparative 
data in order to make informed purchasing decisions. Under DOE's waiver 
regulations, DOE is required to revise the CAC and HP test procedure so 
as to eliminate the need for this waiver. 10 CFR 430.27(l). During this 
process, DOE will explore all options within its statutory authority to 
provide energy consumption information to consumers that accounts for 
these replacement scenarios for all CAC and HP systems in the market, 
regardless of refrigerant.

III. Consultations With Other Agencies

    In accordance with 10 CFR 430.27(f)(2), DOE consulted with the 
Federal Trade Commission (``FTC'') staff concerning JCI's petition for 
waiver.

IV. Order

    After careful consideration of all the material that was submitted 
by JCI for the models identified in the petition and the comments 
received, in this matter, it is ordered that:
    (1) JCI must, as of the date of publication of this Order in the 
Federal Register, test and rate the CAC and HP basic models listed in 
paragraph (A) with the alternate test procedure set forth in paragraph 
(2):
    (A) GAW14L18C2*S, GAW14L24C2*S, GAW14L30C2*S, GAW14L36C2*S, 
GAW14L42C2*S, GAW14L48C2*S, GAW14L60C2*S
    (2) The applicable method of test for the JCI basic models listed 
in paragraph (1)(A) is the test procedure for CACs and HPs prescribed 
by DOE at 10 CFR part 430, subpart B, appendix M, except that 10 CFR 
429.16(a)(3)(i) shall be as detailed below. All other requirements of 
10 CFR 429.16 remain applicable.
    In Sec.  429.16(a), Determination of Represented Value:
    (3) Refrigerants. (i) If a model of outdoor unit (used in a single-
split, multi-split, multi-circuit, multi-head mini-split, and/or 
outdoor unit with no match system) is distributed in commerce and 
approved for use with multiple refrigerants, a manufacturer must 
determine all represented values for that model using each refrigerant 
that can be used in an individual combination of the basic model 
(including outdoor units with no match or ``tested combinations''). 
This requirement may apply across the listed categories in the table in 
paragraph (a)(1) of this section. A refrigerant is considered approved 
for use if it is listed on the nameplate of the outdoor unit. If any of 
the refrigerants approved for use is HCFC-22 or if there are no 
refrigerants designated as approved for use, a manufacturer must 
determine represented values (including SEER, EER, HSPF, SEER2, EER2, 
HSPF2, PW,OFF, cooling capacity, and heating capacity, as 
applicable) for, at a minimum, an outdoor unit with no match. If a 
model of outdoor unit is not charged with a specified refrigerant from 
the point of manufacture (unless either (a) the factory charge is equal 
to or greater than 70% of the outdoor unit internal volume times the 
liquid density of refrigerant at 95 [deg]F or (b) an A2L refrigerant is 
approved for use and listed in the certification report), a 
manufacturer must determine represented values (including SEER, EER, 
HSPF, SEER2, EER2, HSPF2, PW,OFF, cooling capacity, and 
heating capacity, as applicable) for, at a minimum, an outdoor unit 
with no match.
    (3) Representations. JCI may not make representations about the 
efficiency of the basic models identified in paragraph (1) of this 
Order for compliance, marketing, or other purposes unless the basic 
model has been tested in accordance with the provisions set forth above 
and such representations fairly disclose the results of such testing.
    (4) This waiver shall remain in effect consistent with the 
provisions of 10 CFR 430.27.
    (5) This waiver is issued on the condition that the statements, 
representations, and documentation provided by JCI are valid. DOE may 
rescind or modify this waiver at any time if it determines the factual 
basis underlying the petition for waiver is incorrect, or the results 
from the alternate test procedure are unrepresentative of the basic 
models' true energy consumption characteristics. 10 CFR 430.27(k)(1). 
Likewise, JCI may request that DOE rescind or modify the waiver if JCI 
discovers an error in the information provided to DOE as part of its 
petition, determines that the waiver is no longer needed, or for other 
appropriate reasons. 10 CFR 430.27(k)(2).
    (6) Granting of this waiver does not release JCI from the 
certification requirements set forth at 10 CFR part 429.

    Signed in Washington, DC, on September 27, 2019.
Alexander Fitzsimmons
Acting Deputy Assistant Secretary For Energy Efficiency.
[FR Doc. 2019-21437 Filed 10-1-19; 8:45 am]
 BILLING CODE 6450-01-P