[Federal Register Volume 77, Number 205 (Tuesday, October 23, 2012)]
[Notices]
[Pages 64834-64835]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2012-26051]


-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION

[Docket No. 50-219; NRC-2009-0320]


Exelon Generation Company, LLC; Oyster Creek Nuclear Generating 
Station; Exemption

AGENCY: Nuclear Regulatory Commission.

ACTION: Notice of issuance; correction.

-----------------------------------------------------------------------

SUMMARY: This document corrects a notice appearing in the Federal 
Register on April 8, 2011 (76 FR 19795), that incorrectly described 
Sections 3.9.2 and 3.18.2, ``Detection, Control, and Extinguishment.'' 
This action is necessary to correct erroneous information.

[[Page 64835]]


FOR FURTHER INFORMATION CONTACT: John G. Lamb, Office of Nuclear 
Reactor Regulation, U.S. Nuclear Regulatory Commission, Washington, DC 
20555-0001; telephone: 301-415-3100, email: [email protected].

SUPPLEMENTARY INFORMATION: On page 19805, in the first column, in the 
third complete paragraph, it is corrected to read from, ``The licensee 
stated that RB-FZ-1E has an area-wide smoke detection system and an 
automatic fixed deluge water spray system installed over cable trays 
and open hatches. The deluge suppression system protecting safety-
related cable trays is automatically activated by a cross-zoned 
detection system consisting of linear heat detection wire located on 
top of the cables in each original safety-related cable trays and smoke 
detectors are located in each beam pocket at the ceiling,'' to ``The 
licensee stated that RB-FZ-1E has a smoke detection system and an 
automatic fixed deluge water spray system installed over cable trays 
and open hatches. The deluge suppression system protecting safety-
related cable trays is automatically activated by a cross-zoned 
detection system.''
    On page 19812, in the first column, in the second complete 
paragraph, it is corrected to read from, ``The licensee stated that a 
closed head automatic sprinkler and spray systems protect the south end 
basement area and the hydrogen seal oil unit,'' to ``The closed head 
automatic sprinkler system in the condenser bay area was designed, 
installed and tested in accordance with NFPA 13, 1976 Edition, which 
was the latest edition of this code at the time of design.''

    Dated in Rockville, Maryland, this 15th day of October 2012.

    For the Nuclear Regulatory Commission.
Michele G. Evans,
Director, Division of Operating Reactor Licensing, Office of Nuclear 
Reactor Regulation.
[FR Doc. 2012-26051 Filed 10-22-12; 8:45 am]
BILLING CODE 7590-01-P