[Federal Register Volume 75, Number 36 (Wednesday, February 24, 2010)]
[Proposed Rules]
[Pages 8432-8459]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2010-3094]



[[Page 8431]]

-----------------------------------------------------------------------

Part II





Department of Homeland Security





-----------------------------------------------------------------------



Coast Guard



-----------------------------------------------------------------------



46 Parts 25, 27, 28, et al.



Carbon Dioxide Fire Suppression Systems on Commercial Vessels; Proposed 
Rule

  Federal Register / Vol. 75 , No. 36 / Wednesday, February 24, 2010 / 
Proposed Rules  

[[Page 8432]]


-----------------------------------------------------------------------

DEPARTMENT OF HOMELAND SECURITY

Coast Guard

46 CFR Parts 25, 27, 28, 31, 34, 35, 62, 71, 76, 78, 91, 95, 97, 
107, 108, 112, 115, 118, 119, 122, 131, 132, 147, 162, 167, 169, 
176, 181, 182, 185, 189, 190, 193, 194, and 196

[USCG-2006-24797]
RIN 1625-AB44


Carbon Dioxide Fire Suppression Systems on Commercial Vessels

AGENCY: Coast Guard, DHS.

ACTION: Notice of proposed rulemaking.

-----------------------------------------------------------------------

SUMMARY: The Coast Guard proposes to amend the current regulations for 
fire suppression systems on several classes of commercial vessels. The 
amendments would clarify that approved alternatives to carbon dioxide 
systems may be used to protect some spaces on these vessels and would 
set general requirements for alternative systems.
    Additionally, new and existing carbon dioxide systems, when used in 
spaces that can be accessed by persons onboard the specified commercial 
vessels, would need to be equipped with lockout valves and olfactory 
additives to protect persons in the event of a carbon dioxide 
discharge. By requiring these features on carbon dioxide systems and by 
making a wider range of fire suppression systems available, the 
proposed regulations advance the Coast Guard's mission of promoting 
maritime safety and mobility.

DATES: Comments and related material must either be submitted to our 
online docket via http://www.regulations.gov on or before May 25, 2010 
or reach the Docket Management Facility by that date.

ADDRESSES: You may submit comments identified by docket number USCG-
2006-24797 using any one of the following methods:
    (1) Federal eRulemaking Portal: http://www.regulations.gov.
    (2) Fax: 202-493-2251.
    (3) Mail: Docket Management Facility (M-30), U.S. Department of 
Transportation, West Building Ground Floor, Room W12-140, 1200 New 
Jersey Avenue, SE., Washington, DC 20590-0001.
    (4) Hand delivery: Same as mail address above, between 9 a.m. and 5 
p.m., Monday through Friday, except Federal holidays. The telephone 
number is 202-366-9329.
    To avoid duplication, please use only one of these four methods. 
See the ``Public Participation and Request for Comments'' portion of 
the SUPPLEMENTARY INFORMATION section below for instructions on 
submitting comments.
    Viewing incorporation by reference material: You may inspect the 
material proposed for incorporation by reference at room 1308, U.S. 
Coast Guard Headquarters, 2100 2nd Street, SW., Stop 7126, Washington, 
DC 20593-7126 between 9 a.m. and 3 p.m., Monday through Friday, except 
Federal holidays. The telephone number is 202-372-1356. Copies of the 
material are available as indicated in the ``Incorporation by 
Reference'' section of this preamble.

FOR FURTHER INFORMATION CONTACT: If you have questions on this proposed 
rule, call or e-mail Lieutenant Commander Suzanne Hemann, U.S. Coast 
Guard; telephone 202-372-1356, e-mail [email protected]. If you 
have questions on viewing or submitting material to the docket, call 
Renee V. Wright, Program Manager, Docket Operations, telephone 202-366-
9826.

SUPPLEMENTARY INFORMATION: 

Table of Contents for Preamble

I. Public Participation and Request for Comments
    A. Submitting Comments
    B. Viewing Comments and Documents
    C. Privacy Act
    D. Public Meeting
II. Abbreviations
III. Background
IV. Discussion of Proposed Rule
V. Incorporation by Reference
VI. Regulatory Analysis
    A. Regulatory Planning and Review
    B. Small Entities
    C. Assistance for Small Entities
    D. Collection of Information
    E. Federalism
    F. Unfunded Mandates Reform Act
    G. Taking of Private Property
    H. Civil Justice Reform
    I. Protection of Children
    J. Indian Tribal Governments
    K. Energy Effects
    L. Technical Standards
    M. Environment

I. Public Participation and Request for Comments

    We encourage you to participate in this rulemaking by submitting 
comments and related materials. All comments received will be posted 
without change to http://www.regulations.gov and will include any 
personal information you have provided.

A. Submitting Comments

    If you submit a comment, please include the docket number for this 
rulemaking (USCG-2006-24797), indicate the specific section of this 
document to which each comment applies, and provide a reason for each 
suggestion or recommendation. You may submit your comments and material 
online or by fax, mail, or hand delivery, but please use only one of 
these means. We recommend that you include your name and a mailing 
address, an e-mail address, or a phone number in the body of your 
document so that we can contact you if we have questions regarding your 
submission.
    To submit your comment online, go to http://www.regulations.gov, 
select the Advanced Docket Search option on the right side of the 
screen, insert ``USCG-2006-24797'' in the Docket ID box, press Enter, 
and then click on the balloon shape in the Actions column. If you 
submit your comments by mail or hand delivery, submit them in an 
unbound format, no larger than 8\1/2\ by 11 inches, suitable for 
copying and electronic filing. If you submit comments by mail and would 
like to know that they reached the Facility, please enclose a stamped, 
self-addressed postcard or envelope. We will consider all comments and 
material received during the comment period and may change this 
proposed rule based on your comments.

B. Viewing Comments and Documents

    To view comments, as well as documents mentioned in this preamble 
as being available in the docket, go to http://www.regulations.gov, 
select the Advanced Docket Search option on the right side of the 
screen, insert ``USCG-2006-24797'' in the Docket ID box, press Enter, 
and then click on the item in the Docket ID column. If you do not have 
access to the Internet, you may view the docket online by visiting the 
Docket Management Facility in Room W12-140 on the ground floor of the 
Department of Transportation West Building, 1200 New Jersey Avenue, 
SE., Washington, DC 20590, between 9 a.m. and 5 p.m., Monday through 
Friday, except Federal holidays. We have an agreement with the 
Department of Transportation to use the Docket Management Facility.

C. Privacy Act

    Anyone can search the electronic form of comments received into any 
of our dockets by the name of the individual submitting the comment (or 
signing the comment, if submitted on behalf of an association, 
business, labor union, etc.). You may review a Privacy Act notice 
regarding our public dockets in the January 17, 2008 issue of the 
Federal Register (73 FR 3316).

[[Page 8433]]

D. Public Meeting

    We do not now plan to hold a public meeting. But you may submit a 
request for one to the docket using one of the methods specified under 
ADDRESSES. In your request, explain why you believe a public meeting 
would be beneficial. If we determine that one would aid this 
rulemaking, we will hold one at a time and place announced by a later 
notice in the Federal Register.

II. Abbreviations

CO2                                  Carbon dioxide
DHS                                  Department of Homeland Security
FK[dash]5[dash]1[dash]12             Dodecafluoro-2-methylpentan-3-one
FR                                   Federal Register
HFC[dash]227ea                       Heptafluoropropane
IG[dash]541                          Nitrogen 52%, argon 40%, and carbon
                                      dioxide 8%
MODUs                                Mobile offshore drilling units
U.S.C.                               United States Code
 

III. Background

    Until recently, carbon dioxide (CO2) systems were the 
only systems suitable for suppressing or extinguishing fires in certain 
vessel spaces, such as those used for cargo and various types of 
machinery. Our current regulations require the use of CO2 
systems in such spaces on towing vessels, tank vessels, cargo and 
miscellaneous vessels, mobile offshore drilling units (MODUs), offshore 
supply vessels, public nautical school ships, and large passenger 
vessels (``Subchapter H'' vessels). We also allow carbon dioxide 
systems on small passenger vessels carrying more than 150 passengers or 
with overnight accommodations for more than 49 passengers (``Subchapter 
K'' vessels) and other small passenger vessels (``Subchapter T'' 
vessels).
    Carbon dioxide systems work by flooding a protected space with 
CO2, thereby depriving a fire of the oxygen it needs to 
burn. Unfortunately, when a carbon dioxide discharge occurs, oxygen 
deprivation poses a risk to persons who may be in this protected space. 
Crew members have died when odorless CO2 gas was discharged 
in their spaces accidentally or without adequate warning to evacuate.
    In recent years, alternative systems have been developed that are 
comparable to carbon dioxide systems in their ability to suppress 
fires, but that do not pose the same risks to persons onboard. Our 
regulations currently allow for the use of Coast Guard-approved 
alternative systems. At present, most approved systems use halocarbon 
clean agents HFC[dash]227ea (heptafluoropropane), 
FK[dash]5[dash]1[dash]12 (dodecafluoro-2-methylpentan-3-one), or 
IG[dash]541 (nitrogen 52%, argon 40%, and carbon dioxide 8%). We have 
also approved water mist systems for some applications. These systems 
have been tested by independent testing laboratories and have 
laboratory listings. Systems using other agents may be developed and 
approved in the future.
    Along with the manufacturers of alternative systems, shipyards, and 
independent testing laboratories, we believe it would promote safety 
and be advantageous to industry to issue new regulations for 
installing, maintaining, and using approved carbon dioxide-alternative 
fire suppression systems.

IV. Discussion of Proposed Rule

    We are proposing two overall changes to our regulations.
    1. Lockout valves and olfactory additives.
    We propose requiring lockout valves and olfactory additives in any 
CO2 system used in a space that may be occupied by persons 
onboard, even if only occasionally.
    Lockout valves, which are already required for shore-based 
facilities by National Fire Protection Association standards (NFPA 12, 
2008 edition), are intended to be used during system maintenance to 
prevent inadvertent flooding of a protected space. We would require 
lockout valves on vessels that use CO2 systems in spaces 
containing more than 6,000 cubic feet and in smaller spaces that do not 
have horizontal escapes, which provide a quick way to evacuate. 
Odorizer units would be required for CO2 systems of any size 
to provide a scent to normally odorless CO2 during 
discharge. A distinctive-smelling substance, like wintergreen, is added 
to the CO2 so that in the event of a CO2 
discharge in a vessel's space, any persons in that space can quickly 
smell the discharge and evacuate.
    Additionally, the odor would warn persons in adjacent spaces that 
the CO2 may have migrated. The new lockout valve and 
olfactory additive requirements would apply immediately to new systems. 
They would be phased-in for existing systems, allowing the necessary 
simple retrofits to be made during drydocking or routine maintenance, 
thereby reducing the financial impact on vessel owners. Retrofitting 
would involve dismantling and reassembling a small section of system 
piping to include a lockout valve.
    2. Alternative systems.
    The second overall change we propose is to amend our existing 
regulations to make it clear that alternative systems using clean agent 
and inert gases may be used. Furthermore, we are proposing 
clarifications to the general requirements for maintaining, installing, 
and using an alternative system. System layout and control requirements 
would be based on the current regulations for engineered CO2 
systems on inspected vessels. Independent laboratories would oversee 
prototype testing and follow-up quality control supervision.
    The following table lists the parts within 46 CFR that are affected 
by our proposal and the specific sections we propose to amend. The 
foregoing discussion provides a general explanation for each of these 
changes. When additional information is required, it appears in the 
table in parentheses. The table omits any discussion of numerous minor 
and nonsubstantive style, format, or wording changes that we are 
proposing solely to improve the clarity of our regulations.

                   Table 1--Proposed Changes to 46 CFR
------------------------------------------------------------------------
    46 CFR part and topic        46 CFR sections affected (& comments)
------------------------------------------------------------------------
25--Uninspected vessels......  25.30-15 (remove paragraph designations
                                and remove redundant second paragraph).
27--Towing vessels...........  27.101.
28--Commercial fishing         28.825.
 industry vessels.
31, 34, 35--Tank vessels.....  31.10-18 (remove flow test requirement in
                                para. (f)), 34.01-15 (incorporation by
                                reference), 34.05-5, 34.15-50 (new),
                                34.15-60 (new), 35.40-7, 35.40-8 (new),
                                35.40-10.
62--Marine engineering, vital  62.25-20.
 systems automation.
71, 76, 78--Subchapter H       71.20-20, 71.25-20, 71.65-5, 76.05-1,
 passenger vessels ([gteqt]     76.10-5, 76.15-50 (new), 76.16-60 (new),
 100 gross tons).               78.47-9, 78-47.11 (new), 78.47-17.

[[Page 8434]]

 
91, 95, 97--Cargo &            91.20-20, 91.25-20, 91.55-5, 95.01-2
 miscellaneous vessels.         (incorporation by reference), 95.05-10,
                                95.10-5, 95.15-5 (lengthen discharge
                                time from 2 to 10 min. for spaces
                                specially suitable for vehicles to
                                provide greater safety margin and meet
                                the International Maritime
                                Organization's Safety of Life at Sea
                                (SOLAS) requirements), 95.15-30 (provide
                                for nitrogen pilot cylinders), 95.15-50
                                (new), 95.15-60 (new), 95.16-1--95.16-90
                                (new; based on current subpart 95.15,
                                modified and reorganized), 97.37-9,
                                97.37-11 (new), 97.37-13.
107, 108--Mobile offshore      107.231, 107.235, 108.444 (new), 108.446
 drilling units.                (new), 108.626 (new), 108.627, 108.631.
112--Electrical engineering,   112.15-5.
 emergency lighting & power
 systems.
115, 118, 119, 122--           115.810, 118.410, 119.710, 122.612.
 Subchapter K passenger
 vessels (< 100 gross tons &
 > 150 passengers or > 49
 overnight passengers).
131, 132--Offshore supply      131.815, 131.817 (new), 131.825, 132.350.
 vessels.
147--Hazardous ships' stores.  147.7 (incorporation by reference),
                                147.45 (nonsubstantive change), 147.60
                                (nonsubstantive change), 147.66 (new),
                                147.67 (new).
162--Engineering equipment...  162.161-1--162.161-9 (new).
167--Public nautical school    167.45-1, 167.45-45, 167.55-5.
 ships.
169--Sailing school vessels..  169.247, 169.564, 169.570 (new), 169.571
                                (new), 169.732, 169.734.
176, 181, 182, 185--           176.810, 181.410, 182.710, 185.612.
 Subchapter T passenger
 vessels (< 100 gross tons &
 <= 150 passengers or <= 49
 passengers overnight).
189, 190, 193, 194, 196--      189.25-20, 189.55-5, 190.15-5, 193.05-10,
 Oceanographic research         193.10-5, 193.15-16 (new), 193.15-17
 vessels.                       (new), 193.15-50 (new), 194.20-7, 196.37-
                                8 (new), 196.37-9, 196.37-13.
------------------------------------------------------------------------

V. Incorporation by Reference

    Material proposed for incorporation by reference appears in 46 CFR 
34.01-15, 46 CFR 147.7, and 46 CFR 162.161-2. You may inspect this 
material at U.S. Coast Guard Headquarters where indicated under 
ADDRESSES. Copies of the material are available from the sources listed 
in 46 CFR 34.01-15, 46 CFR 147.7, and 46 CFR 162.161-2.
    Before publishing a binding rule, we will submit this material to 
the Director of the Federal Register for approval of the incorporation 
by reference.

VI. Regulatory Analysis

    We developed this proposed rule after considering numerous statutes 
and executive orders related to rulemaking. Below we summarize our 
analyses based on 13 of these statutes or executive orders.

A. Regulatory Planning and Review

    This proposed rule is not a significant regulatory action under 
section 3(f) of Executive Order 12866, Regulatory Planning and Review, 
and does not require an assessment of potential costs and benefits 
under section 6(a)(3) of that Order. The Office of Management and 
Budget (OMB) has not reviewed it under that Order.
    A draft Regulatory Analysis is available in the docket where 
indicated under the ``Public Participation and Request for Comments'' 
section of this preamble. A summary of the preliminary Regulatory 
Analysis follows.
    We propose to amend the current regulations for carbon dioxide fire 
suppression systems on commercial vessels. The amendments would require 
certain safety requirements for current and future users of 
CO2 systems. The proposed rule would require lockout valves 
for certain protected spaces as well as for an olfactory additive as a 
warning measure for all CO2 systems. The proposed rule would 
also clarify what approved alternatives to CO2 systems may 
be used to protect some spaces on these vessels and would set general 
requirements for alternative systems. We do not expect industry would 
incur additional costs as a result of the provisions for alternative 
systems. See below for additional discussion of alternative systems.
    Carbon dioxide fire suppression systems pose a risk of asphyxiation 
to personnel. Lockout valves and olfactory additives help protect 
persons in the event of an inadvertent release during maintenance. 
Olfactory additives offer additional protection from leaks from a 
protected space to adjacent spaces and help alert personnel when 
CO2 has been released. By requiring these features on carbon 
dioxide systems and making a wider range of fire suppression systems 
available, the proposed amendments would advance the Coast Guard's 
missions of promoting maritime safety and mobility.
    U.S. flag vessel owners are expected to incur costs associated with 
this proposed rule. Vessel owners with existing CO2 fire 
suppression systems would be required to add the lockout valves and 
olfactory units within five years of the publication of the final rule. 
This would allow enough time for vessel owners to add these features 
during scheduled vessel maintenance periods and would reduce the cost 
of compliance for vessel owners. For purposes of this regulatory 
assessment, we assume an equal proportion of systems will be 
retrofitted each year for five years. New vessel owners will incur the 
costs as systems are incorporated into new ships at construction.
Affected Population
    Vessels with CO2 fire suppression systems that are not 
in compliance with the proposed regulation would be required to install 
lockout valves at entrances to all spaces greater than 6,000 cubic feet 
in volume where personnel may enter, as well as, in spaces with 6,000 
cubic feet in volume or less that do not have a horizontal escape for 
quick escape. Vessels equipped with existing CO2 fire 
suppression systems would incur a cost for retrofitting valves to the 
systems. Newly constructed vessels installing new fire CO2 
suppression systems in similar spaces would also incur a cost for 
installation of lockout valves, although at a lower cost than 
retrofitting systems on existing vessels because installations during 
vessel construction are typically less costly.
    Based on Coast Guard Marine Investigation Security and Law 
Enforcement (MISLE) data, we estimate

[[Page 8435]]

there are potentially 1,702 existing vessels with a total of 3,204 
CO2 fire suppression systems that would require lockout 
valves. The 3,204 existing systems consist of 1,054 larger systems that 
would require more expensive lockout valves and 2,150 smaller systems 
that would require less expensive lockout valves. Using MILSE data, we 
estimate there are potentially 22 small systems and 12 large systems 
installed each year on new vessels, which would be required to have 
lockout valves.
    The population of affected vessels that would need to install 
olfactory additives (odorizers) includes all existing and new vessels 
with CO2 systems. All existing vessels with CO2 
systems would require a retrofit for each protected space. Based on 
MISLE data, we estimate there are potentially 7,815 systems on 3,567 
vessels that would be required to install odorizers.\1\ Each new vessel 
with CO2 systems would also require an odorizer for 
compartments of all sizes. Of the new vessels constructed annually, we 
estimate the 46 new systems/year installed would require odorizers.
---------------------------------------------------------------------------

    \1\ The difference in the vessel populations and system counts 
(lockout valve vs. odorizers) is reflective of the large number of 
extremely small sized systems that need odorizers, but do not need 
lockout valves (the balance of 7,815-3,204 or 4,611).
---------------------------------------------------------------------------

Costs
    Based on industry data, we estimate that average 2008 industry 
prices for installed retrofit large and small lockout valves are $3,513 
and $1,475, respectively. Systems that handle more than 2,450 pounds of 
CO2 require a valve larger than 2 inches. Of the 3,204 
existing systems affected by this proposed rule, 1,054 would require 
the larger, more expensive lockout valves, while 2,150 systems require 
the smaller valves for a total undiscounted cost of about $6,873,425. 
The annual undiscounted cost for owners of vessels with existing 
systems to meet the lockout valve requirement of this proposed rule 
would be approximately $1,374,685 for each year of the five-year phase-
in period.
    Vessel owners wishing to install a new CO2 fire 
suppression system would be required to have the lockout valves 
included in the installation. We estimate that the annual undiscounted 
industry cost for adding lockout valves to new CO2 fire 
suppression systems to be $65,932 per year (based on installed costs on 
new systems of $1,258 for small valves and $3,188 for large valves). 
Industry would incur this cost for each year over the ten-year period 
of analysis.
    As for odorizers, we estimate that the retrofit installed costs, 
including three warning signs, are $551/unit based on industry 
information. This is about $35 more than the estimated cost for new 
odorizers installed. With a five-year phase-in for all 7,815 systems, 
1,563 systems will be retrofitted on average each year. We estimate the 
total annual undiscounted cost of the retrofit will be $861,213. For 
new systems using the lockout valve, we estimate the total annual 
undiscounted cost to be about $17,558 for all 34 protected areas. For 
the remaining systems not required to have a lockout valve, the cost 
for installing odorizers in 12 areas will be about $6,197. The total 
cost per vessel would be dependent on the number of areas protected by 
CO2.
    We estimated the total cost of this rulemaking over a ten-year 
period to be $12.1 million (see Table 2). For the first five years, we 
estimated the undiscounted costs to be $2,325,584/year for both 
retrofits and new installations.

                    Table 2--Total Cost of Adding Lockout Valves and Odorizers to CO2 Systems
----------------------------------------------------------------------------------------------------------------
                                                                                     Total 7%        Total 3%
              Year                Lockout valves     Odorizers         Total         discount        discount
----------------------------------------------------------------------------------------------------------------
2011............................      $1,440,617        $884,967      $2,325,584      $2,173,443      $2,257,849
2012............................       1,440,617         884,967       2,325,584       2,031,255       2,192,086
2013............................       1,440,617         884,967       2,325,584       1,898,370       2,128,239
2014............................       1,440,617         884,967       2,325,584       1,774,177       2,066,252
2015............................       1,440,617         884,967       2,325,584       1,658,110       2,006,070
2016............................          65,932          23,754          89,686          59,762          75,111
2017............................          65,932          23,754          89,686          55,582          72,923
2018............................          65,932          23,754          89,686          52,198          70,799
2019............................          65,932          23,754          89,686          48,783          68,737
2020............................          65,932          23,754          89,686          45,592          66,735
                                 -------------------------------------------------------------------------------
    Total.......................       7,532,745       4,543,609      12,076,354       9,797,543      11,004,801
Annualized Costs................  ..............  ..............  ..............       1,394,950       1,290,198
----------------------------------------------------------------------------------------------------------------
Source: USCG Calculations.
Note: Totals may not add due to rounding.

    For the remaining years, the undiscounted costs are $89,686/year 
due to the new installations only. We discounted the annual costs at 3 
percent and 7 percent and also annualized the total costs at the same 
rates. The total 10-year cost of the proposed rule is $9.8 million at a 
7 percent discount rate and $11 million at 3 percent.
    This proposed regulation would clarify Coast Guard acceptance of 
alternatives to using CO2 systems. We do not believe that 
these provisions would have a cost impact because the Coast Guard has 
been approving alternative systems on an ad hoc basis. We believe these 
approved installed alternative systems would be compliant with the 
requirements for alternative systems proposed in this rulemaking.
    With regard to alternative fire suppression systems, the use of 
halocarbon (only one of a number of alternatives) fire suppression 
systems has been increasing in recent years (2006-2008). Our records 
indicate that industry installed an average of 21 halocarbon fire 
suppression systems compared to an average of 34 CO2 fire 
suppression systems with capacity over 6,000 cubic feet during this 
period.
Benefits
    The primary benefit associated with this proposed rule is the 
reduction in risk of injuries and fatalities related to CO2 
exposure. CO2 exposure has long been recognized as a 
potential hazard to human health. The National Institute of 
Occupational Safety and Health (NIOSH), in its publication NIOSH 76-
194, ``Criteria for a Recommended

[[Page 8436]]

Standard--Occupational Exposure to Carbon Dioxide,'' available at 
http://www.cdc.gov/niosh/76-194.html, has set criteria for a standard 
for limits of exposure to CO2 in workplace settings.
    Other Federal and industry agencies and associations have also 
recently concluded that CO2 fire suppression systems could 
pose a risk. For example, the National Fire Prevention Association 
(NFPA) guidance in its 2005 Edition for CO2 fire suppression 
systems located on land states that ``total flooding CO2 
suppression systems shall not be used in normally occupied 
enclosures''. In addition, the EPA, in its 2000 report, ``Carbon 
Dioxide as a Fire Suppressant: Examining the Risk,'' has suggested that 
clarifying maritime regulation would be beneficial to reducing 
accidental exposure.
    The Regulatory Analysis available in the docket has additional 
detail on the assessment of the benefits and costs of this rulemaking. 
The assessment also contains details and analysis of the alternatives 
considered for this rulemaking.

B. Small Entities

    Under the Regulatory Flexibility Act (5 U.S.C. 601-612), we have 
considered whether this proposed rule would have a significant economic 
impact on a substantial number of small entities. The term ``small 
entities'' comprises small businesses, not-for-profit organizations 
that are independently owned and operated as well as not being dominant 
in their fields, and governmental jurisdictions with populations of 
less than 50,000.
    A combined Regulatory Assessment and Initial Regulatory Flexibility 
Analysis discussing the impact of this proposed rule on small entities 
is available in the docket where indicated under the ``Public 
Participation and Request for Comments'' section of this preamble.
    Our data shows that there are 489 known entities that owned vessels 
with CO2 fire suppression systems onboard in 2008. Of the 
489, 26 are government entities with populations of more than 50,000 
that we excluded from the small business analysis. Of the remaining 463 
entities, we were able to find revenue and employment information for 
100 entities. Of the 100, we confirmed that 37 were small as defined by 
Small Business Administration (SBA) size standards.
    We assumed the remaining 363 entities to be small because we were 
unable to find revenue or employment information. Given that assumption 
of size, we concluded that small entities likely comprise 400 (363 + 
37) or 81.8% of the total affected population.
    Of the small entities with revenue and employee size data, we 
determined that 83.8% would have an annual revenue impact of less than 
1 percent. Further, we estimated that the impact on 97.3% of these 
small entities would be less than 3% of annual revenue.
    Therefore, the Coast Guard certifies under 5 U.S.C. Sec.  605(b) 
that this rulemaking would not have a significant economic impact on a 
substantial number of small entities. We are interested in the 
potential impacts from this proposed rule on small businesses and we 
request public comment on these potential impacts. If you think that 
your business, organization, or governmental jurisdiction qualifies as 
a small entity and that this rulemaking would have a significant 
economic impact on it, please submit a comment to the Docket Management 
Facility at the address under the ``Public Participation and Request 
for Comments'' section of this preamble. In your comment, explain why, 
how, and to what degree you think this rule would have an economic 
impact on you.

C. Assistance for Small Entities

    Under section 213(a) of the Small Business Regulatory Enforcement 
Fairness Act of 1996 (Pub. L. 104-121), we want to assist small 
entities in understanding the proposed rule so that they can better 
evaluate its effects on them and participate in the rulemaking. If the 
rule affects your small business, organization, or governmental 
jurisdiction and you have questions concerning its provisions or 
options for compliance, please call Lieutenant Commander Suzanne 
Hemann, CG-5214, U.S. Coast Guard, telephone 202-372-1356 or send her 
an e-mail at [email protected]. The Coast Guard will not 
retaliate against small entities that question or complain about this 
rule or any policy or action of the Coast Guard.
    Small businesses may send comments on the actions of Federal 
employees who enforce, or otherwise determine compliance with, Federal 
regulations to the Small Business and Agriculture Regulatory 
Enforcement Ombudsman and the Regional Small Business Regulatory 
Fairness Boards. The Ombudsman evaluates these actions annually and 
rates each agency's responsiveness to small business. If you wish to 
comment on actions by employees of the Coast Guard, call 1-888-REG-FAIR 
(1-888-734-3247).

D. Collection of Information

    This proposed rule would require no new collection of information 
(COI) under the Paperwork Reduction Act (44 U.S.C. 3501-3520). The U.S. 
Coast Guard has been approving alternatives to CO2 systems 
for a number of years and accounting for it in COI document ``OMB 
Control Number 1625-0035''. This rulemaking would not require any new 
recordkeeping or reporting requirements. Satisfactory lockout valve and 
olfactory installation will be confirmed by normal future Coast Guard 
inspections.

E. Federalism

    A rule has implications for federalism under Executive Order 13132, 
Federalism, if it has a substantial direct effect on State or local 
governments and would either preempt State law or impose a substantial 
direct cost of compliance on them. We have analyzed this proposed rule 
under that Order and have determined that it does not have implications 
for federalism.

F. Unfunded Mandates Reform Act

    The Unfunded Mandates Reform Act of 1995 (2 U.S.C. 1531-1538) 
requires Federal agencies to assess the effects of their discretionary 
regulatory actions. In particular, the Act addresses actions that may 
result in the expenditure by a State, local, or tribal government, in 
the aggregate, or by the private sector of $100,000,000 or more in any 
one year. Though this proposed rule would not result in such an 
expenditure, we do discuss the effects of this rule elsewhere in this 
preamble.

G. Taking of Private Property

    This proposed rule would not affect a taking of private property or 
otherwise have taking implications under Executive Order 12630, 
Governmental Actions and Interference with Constitutionally Protected 
Property Rights.

H. Civil Justice Reform

    This proposed rule meets applicable standards in sections 3(a) and 
3(b)(2) of Executive Order 12988, Civil Justice Reform, to minimize 
litigation, eliminate ambiguity, and reduce burden.

I. Protection of Children

    We have analyzed this proposed rule under Executive Order 13045, 
Protection of Children from Environmental Health Risks and Safety 
Risks. This rule is not an economically significant rule and would not 
create an environmental risk to health or risk to

[[Page 8437]]

safety that might disproportionately affect children.

J. Indian Tribal Governments

    This proposed rule does not have tribal implications under 
Executive Order 13175, Consultation and Coordination with Indian Tribal 
Governments, because it would not have a substantial direct effect on 
one or more Indian tribes, on the relationship between the Federal 
Government and Indian tribes, or on the distribution of power and 
responsibilities between the Federal Government and Indian tribes.

K. Energy Effects

    We have analyzed this proposed rule under Executive Order 13211, 
Actions Concerning Regulations That Significantly Affect Energy Supply, 
Distribution, or Use. We have determined that it is not a ``significant 
energy action'' under that order because it is not a ``significant 
regulatory action'' under Executive Order 12866 and is not likely to 
have a significant adverse effect on the supply, distribution, or use 
of energy. The Administrator of the Office of Information and 
Regulatory Affairs has not designated it as a significant energy 
action. Therefore, it does not require a Statement of Energy Effects 
under Executive Order 13211.

L. Technical Standards

    The National Technology Transfer and Advancement Act (NTTAA) (15 
U.S.C. 272 note) directs agencies to use voluntary consensus standards 
in their regulatory activities unless the agency provides Congress, 
through the Office of Management and Budget, with an explanation of why 
using these standards would be inconsistent with applicable law or 
otherwise impractical. Voluntary consensus standards are technical 
standards (e.g. specifications of materials, performance, design, or 
operation; test methods; sampling procedures; and related management 
systems practices) that are developed or adopted by voluntary consensus 
standard bodies.
    This proposed rule uses the following consensus standards: 
Underwriters Laboratories (UL) standards UL 2127 entitled ``Standard 
for Inert Gas Clean Agent Extinguishing System Units,'' UL 2166 
entitled ``Standard for Halocarbon Clean Agent Extinguishing System 
Units,'' and National Fire Protection Association (NFPA) 2001 entitled 
``Standard on Clean Agent Fire Extinguishing Systems.'' The proposed 
sections that reference these standards and the locations where these 
standards are available are listed in the proposed regulatory text for 
46 CFR 34.01-15, 147.7, and 162.161-2.
    This proposed rule also uses technical standards other than 
voluntary consensus standards. The test described in the regulatory 
text proposed for 46 CFR 162.161-6 is in accordance with requirements 
of the International Maritime Organization, IMO MSC/Circ.848 entitled 
``Revised Guidelines for the Approval of Equivalent Fixed Gas Fire-
Extinguishing Systems, as referred to in chapter II-2 of SOLAS 74, for 
machinery spaces and cargo pump-rooms'' and IMO MSC.1/Circ. 1267 
entitled ``Amendments to the Revised Guidelines for the Approval of 
Equivalent Fixed Gas Fire-Extinguishing Systems, as referred to in 
chapter II-2 of SOLAS 74, for machinery spaces and cargo pump-rooms 
(MSC/Circ. 848)''. The remaining requirements and tests were developed 
by the Coast Guard and used to evaluate currently-approved carbon 
dioxide-alternative fire suppression systems. These requirements are 
described throughout the proposed regulations. They are used because we 
did not find voluntary consensus standards that are applicable to this 
rule. If you disagree with our analysis of the voluntary consensus 
standards listed above or are aware of voluntary consensus standards 
that might apply, but are not listed, please send a comment to the 
docket using one of the methods under ADDRESSES. In your comment, 
please explain why you disagree with our analysis and/or identify 
voluntary consensus standards we have not listed that might apply.

M. Environment

    We have analyzed this proposed rule under Department of Homeland 
Security Management Directive 023-01 and Commandant Instruction 
M16475.lD, which guide the Coast Guard in complying with the National 
Environmental Policy Act of 1969 (NEPA) (42 U.S.C. 4321-4370f), and 
have made a preliminary determination that this action is one of a 
category of actions which do not individually or cumulatively have a 
significant effect on the human environment. A preliminary 
environmental analysis checklist supporting this determination is 
available in the docket where indicated under the ``Public 
Participation and Request for Comments'' section of this preamble. This 
rule involves amending the current regulations for carbon dioxide fire 
suppression systems on several classes of commercial vessels. Exclusion 
under paragraphs (34)(d) of Figure 2.1 of the Instruction and section 
6(a) of the Federal Register, Vol. 67, No. 141, Tuesday July 23, 2002, 
page 48243 apply because this rule pertains to regulations concerning 
the equipping of vessels, as well as equipment approval. We seek any 
comments or information that may lead to the discovery of a significant 
environmental impact from this proposed rule.

List of Subjects

46 CFR Part 25

    Fire prevention, Marine safety, Reporting and recordkeeping 
requirements.

46 CFR Part 27

    Fire prevention, Incorporation by reference, Marine safety, 
Reporting and recordkeeping requirements, Vessels.

46 CFR Part 28

    Alaska, Fire prevention, Fishing vessels, Marine safety, 
Occupational safety and health, Reporting and recordkeeping 
requirements, Seamen.

46 CFR Part 31

    Cargo vessels, Marine safety, Reporting and recordkeeping 
requirements.

46 CFR Part 34

    Cargo vessels, Fire prevention, Marine safety.

46 CFR Part 35

    Cargo vessels, Marine safety, Navigation (water), Occupational 
safety and health, Reporting and recordkeeping requirements, Seamen.

46 CFR Part 62

    Reporting and recordkeeping requirements, Vessels.

46 CFR Part 71

    Marine safety, Passenger vessels, Reporting and recordkeeping 
requirements.

46 CFR Part 76

    Fire prevention, Marine safety, Passenger vessels.

46 CFR Part 78

    Marine safety, Navigation (water), Passenger vessels, Penalties, 
Reporting and recordkeeping requirements.

46 CFR Part 91

    Cargo vessels, Marine safety, Reporting and recordkeeping 
requirements.

46 CFR Part 95

    Cargo vessels, Fire prevention, Incorporation by reference, Marine 
safety.

[[Page 8438]]

46 CFR Part 97

    Cargo vessels, Marine safety, Navigation (water), Reporting and 
recordkeeping requirements.

46 CFR Part 107

    Marine safety, Oil and gas exploration, Reporting and recordkeeping 
requirements, Vessels.

46 CFR Part 108

    Fire prevention, Marine safety, Occupational safety and health, Oil 
and gas exploration, Vessels.

46 CFR Part 112

    Vessels.

46 CFR Part 115

    Fire prevention, Marine safety, Passenger vessels, Reporting and 
recordkeeping requirements.

46 CFR Part 118

    Fire prevention, Marine safety, Passenger vessels.

46 CFR Part 119

    Marine safety, Passenger vessels.

46 CFR Part 122

    Marine safety, Passenger vessels, Penalties, Reporting and 
recordkeeping requirements.

46 CFR Part 131

    Cargo vessels, Fire prevention, Marine safety, Navigation (water), 
Occupational safety and health, Reporting and recordkeeping 
requirements.

46 CFR Part 132

    Cargo vessels, Fire prevention, Marine safety, Reporting and 
recordkeeping requirements.

46 CFR Part 147

    Hazardous materials transportation, Incorporation by reference, 
Labeling, Marine safety, Packaging and containers, Reporting and 
recordkeeping requirements.

46 CFR Part 162

    Fire prevention, Incorporation by reference, Marine safety, Oil 
pollution, Reporting and recordkeeping requirements.

46 CFR Part 167

    Fire prevention, Marine safety, Reporting and recordkeeping 
requirements, Schools, Seamen, Vessels.

46 CFR Part 169

    Fire prevention, Marine safety, Reporting and recordkeeping 
requirements, Schools, Vessels.

46 CFR Part 176

    Fire prevention, Marine safety, Passenger vessels, Reporting and 
recordkeeping requirements.

46 CFR Part 181

    Fire prevention, Marine safety, Passenger vessels.

46 CFR Part 182

    Marine safety, Passenger vessels.

46 CFR Part 185

    Marine safety, Passenger vessels, Reporting and recordkeeping 
requirements.

46 CFR Part 189

    Marine safety, Oceanographic research vessels, Reporting and 
recordkeeping requirements.

46 CFR Part 190

    Fire prevention, Marine safety, Occupational safety and health, 
Oceanographic research vessels.

46 CFR Part 193

    Fire prevention, Marine safety, Oceanographic research vessels.

46 CFR Part 194

    Explosives, Hazardous materials transportation, Marine safety, 
Oceanographic research vessels.

46 CFR Part 196

    Marine safety, Oceanographic research vessels, Reporting and 
recordkeeping requirements.

    For the reasons listed in the preamble, the Coast Guard proposes to 
amend 46 CFR parts 25, 27, 28, 31, 34, 35, 62, 71, 76, 78, 91, 95, 97, 
107, 108, 112, 115, 118, 119, 122, 131, 132, 147, 162, 167, 169, 176, 
181, 182, 185, 189, 190, 193, 194, and 196 as follows:

PART 25--REQUIREMENTS

    1. The authority citation for Part 25 continues to read as follows:

    Authority: 33 U.S.C. 1903(b); 46 U.S.C. 3306, 4102, 4302; 
Department of Homeland Security Delegation No. 0170.1.

    2. Revise Sec.  25.30-15 to read as follows:


Sec.  25.30-15  Fixed fire-extinguishing systems.

    When a fixed fire-extinguishing system is installed, it must be a 
type approved or accepted by the Commandant (CG-5214) or the Commanding 
Officer, U.S. Coast Guard Marine Safety Center.

PART 27--TOWING VESSELS

    3. The authority citation for Part 27 continues to read as follows:

    Authority: 46 U.S.C. 3306, 4102 (as amended by Pub. L. 104-324, 
110 Stat. 3901); Department of Homeland Security Delegation No. 
0170.1.

    4. In Sec.  27.101, in the definition of ``Fixed fire-extinguishing 
system'', revise paragraphs (1) and (3), and add a new paragraph (4), 
to read as follows:


Sec.  27.101  Definitions.

* * * * *
    Fixed fire-extinguishing system means:
    (1) A carbon dioxide system that satisfies 46 CFR 76.15 and the 
system labeling requirements in 46 CFR 78.47-7 and 78.47-11 and that is 
approved by the Commandant;
* * * * *
    (3) A manually-operated water-mist system that satisfies NFPA 750 
(incorporated by reference; see 46 CFR 27.102) and that is approved by 
the Commandant; or
    (4) A clean agent system that satisfies 46 CFR 95.16 and the 
labeling requirements of 46 CFR 97.37-9 and 97.37-11 and that is 
approved by the Commandant.
* * * * *

PART 28--REQUIREMENTS FOR COMMERCIAL FISHING INDUSTRY VESSELS

    5. The authority citation for Part 28 continues to read as follows:

    Authority: 46 U.S.C. 3316, 4502, 4505, 4506, 6104, 10603; 
Department of Homeland Security Delegation No. 0170.1.

    6. Revise Sec.  28.825(b)(2)(iv) to read as follows:


Sec.  28.825  Excess fire detection and protection equipment.

* * * * *
    (b) * * *
    (2) * * *
    (iv) The control cabinets or spaces containing valves or manifolds 
for the various fire extinguishing systems must be distinctly marked in 
conspicuous red letters at least 2 inches high: ``[CARBON DIOXIDE/FOAM/
CLEAN AGENT--as appropriate] FIRE SYSTEM.''
* * * * *

PART 31--INSPECTION AND CERTIFICATION

    7. The authority citation for Part 31 continues to read as follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2103, 3205, 3306, 3307, 
3703; 46 U.S.C. Chapter 701; 49 U.S.C. 5103, 5106; E.O. 12234, 45 FR 
58801, 3 CFR, 1980 Comp., p. 277; E.O. 12777, 56 FR 54757, 3 CFR, 
1991 Comp., p. 351; Department of Homeland Security Delegation No. 
0170.1. Section

[[Page 8439]]

31.10-21 also issued under the authority of Sect. 4109, Pub. L. 101-
380, 104 Stat. 515.

    8. In Sec.  31.10-18, revise Table 31.10-18(c) and paragraph (f) to 
read as follows:


Sec.  31.10-18  Firefighting equipment: General--TB/ALL.

* * * * *
    (c) * * *

                            Table 31.10-18(c)
------------------------------------------------------------------------
         Type system                              Test
------------------------------------------------------------------------
Foam.........................  Systems utilizing a soda solution must
                                have that solution replaced. In all
                                cases, ascertain that powder is not
                                caked.
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.
Halon 1301 and halocarbon....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge, or, if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                               NOTE: Halon 1301 system approvals have
                                expired, but existing systems may be
                                retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Inert gas....................  Recharge or replace cylinder if cylinder
                                pressure loss exceeds 5% of specified
                                gauge pressure, adjusted for
                                temperature. Test time delays, alarms,
                                and ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed inert
                                extinguishers must be tested or renewed,
                                as required by 46 CFR 147.60 and 147.66.
Water mist...................  Maintain system in accordance with the
                                maintenance instructions in the system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------

* * * * *
    (f) The marine inspector must check all fire extinguishing system 
piping, controls, valves, and alarms to ascertain that the system is in 
good operating condition. For carbon dioxide or clean agent systems as 
described in 46 CFR subpart 95.16, the marine inspector must:
    (1) Verify that flow is continuous and that the piping and nozzles 
are unobstructed; and
    (2) Verify that any discharge delays and pre-discharge alarms 
function properly during the flow test.
* * * * *

PART 34--FIREFIGHTING EQUIPMENT

    9. The authority citation for Part 34 continues to read as follows:

    Authority: 46 U.S.C. 3306, 3703; E.O. 12234, 45 FR 58801, 3 CFR, 
1980 Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    10. Revise Sec.  34.01-15 to read as follows:


Sec.  34.01-15  Incorporation by reference.

    (a) Certain material is incorporated by reference into this part 
with the approval of the Director of the Federal Register in accordance 
with 5 U.S.C. 552(a). To enforce any edition other than that specified 
in paragraph (b) of this section, the Coast Guard must publish notice 
of change in the Federal Register and make the material available to 
the public. All approved material is on file at the U.S. Coast Guard, 
Office of Design and Engineering Standards (CG-521), 2100 2nd Street, 
SW., Stop 7126, Washington, DC 20593-7126 or at the National Archives 
and Records Administration (NARA). For information on the availability 
of this material at NARA, call 202-741-6030, or go to: http://www.archives.gov/federal_register/code_of_federal_regulations/ibr_locations.html. All material is available from the sources indicated in 
paragraph (b) of this section.
    (b) The material approved for incorporation by reference in this 
part and the sections affected are:
    (1) American Society for Testing and Materials (ASTM)
    100 Barr Harbor Drive, West Conshohocken, PA 19428-2959.
    (2) ASTM F 1121-87 (Reapproved 1993), Standard Specification for 
International Shore Connections for Marine Fire Applications, 1987.
    (c) National Fire Protection Association (NFPA) 1 Batterymarch 
Park, Quincy, MA 02269-9101.
    (1) NFPA 13-1996, Standard for the Installation of Sprinkler 
Systems--34.30-1.
    (2) NFPA 2001-2008, Standard on Clean Agent Fire Extinguishing 
Systems--34.05-5(a)(4).
    11. In Sec.  34.05-5, revise the section heading and paragraphs 
(a)(3) through (7) to read as follows:


Sec.  34.05-5  Fire extinguishing systems-- T/ALL.

    (a) * * *
    (3) Lamp and paint lockers and similar spaces. A carbon dioxide or 
clean agent system as described in 46 CFR subpart 95.16 or a water 
spray system must be installed in all lamp and paint lockers, oil 
rooms, and similar spaces.
    (4) Pump rooms. A carbon dioxide or clean agent system as described 
in 46 CFR subpart 95.16, a foam spray system, or water spray system 
must be installed for the protection of all pump rooms. If a clean 
agent system is installed for the pump room of a tank ship carrying 
chemical cargos, the amount of extinguishing agent must be determined 
by using the agent design concentration determined by the cup burner 
method, described in NFPA 2001 (incorporated by reference; see 46 CFR 
34.01-15) for the cargo requiring the greatest amount of agent.
    (5) Boiler rooms. On tankships contracted for on or after November 
19, 1952, a carbon dioxide or clean agent system as described in 46 CFR 
subpart 95.16 or a foam system must be installed to protect any space 
containing a main or auxiliary oil fired boiler, the boiler fuel oil 
service pump, or any fuel oil units such as heaters, strainers, valves, 
manifolds, etc., that are subject to the discharge pressure of the fuel 
oil service pumps.

[[Page 8440]]

    (6) Machinery spaces. A carbon dioxide or clean agent system as 
described in 46 CFR subpart 95.16 must be installed to protect any 
machinery space containing an internal combustion-propelling engine 
that uses fuel having a flashpoint of less than 110 degrees Fahrenheit.
    (7) Internal combustion installations. A fire extinguishing system 
must be provided for an internal combustion installation and:
    (i) The system must be a carbon dioxide or clean agent system as 
described in 46 CFR subpart 95.16;
    (ii) On vessels of 1,000 gross tons and over on an international 
voyage, the construction or conversion of which is contracted for on or 
after May 26, 1965, a carbon dioxide or clean agent system as described 
in 46 CFR subpart 95.16 must be installed in any space containing 
internal combustion or gas turbine main propulsion machinery, 
auxiliaries with an aggregate power of 1,000 b.h.p. or greater, or 
their fuel oil units, including purifiers, valves, and manifolds; and
    (iii) On vessels of 1,000 gross tons and over, the construction, 
conversion or automation of which is contracted for on or after January 
1, 1968, a carbon dioxide or clean agent system as described in 46 CFR 
subpart 95.16 must be installed in any space containing internal 
combustion or gas turbine main propulsion machinery, auxiliaries with 
an aggregate power of 1,000 b.h.p. or greater, or their fuel oil units, 
including purifiers, valves and manifolds.
* * * * *
    12. Add a new Sec.  34.15-50 to read as follows:


Sec.  34.15-50  Lockout valves--T/ALL.

    (a) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (b) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (c) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (d) A valve is considered a lockout valve if it has a hasp or other 
means of attachment to which, or through which, a lock can be affixed, 
or it has a locking mechanism built into it.
    (e) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (f) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (g) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    13. Add new Sec.  34.15-60 to read as follows:


Sec.  34.15-60  Olfactory additives--T/ALL.

    (a) Each carbon dioxide extinguishing system must have an approved 
odorizing unit to produce the scent of wintergreen, the detection of 
which will serve as an indication that carbon dioxide gas is present in 
a protected area and any other area into which the carbon dioxide may 
migrate.
    (b) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].

PART 35--OPERATIONS

    14. The authority citation for Part 35 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 3306, 3703, 6101; 49 
U.S.C. 5103, 5106; E.O. 12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 
277; E.O. 12777, 56 FR 54757, 3 CFR, 1991 Comp., p. 351; Department 
of Homeland Security Delegation No. 0170.1.

    15. Revise Sec.  35.40-7 to read as follows:


Sec.  35.40-7  Carbon dioxide and clean agent alarms--T/ALL.

    Each carbon dioxide or clean agent fire extinguishing alarm 
installed after November 19, 1952, must be conspicuously marked: ``WHEN 
ALARM SOUNDS VACATE AT ONCE. CARBON DIOXIDE OR CLEAN AGENT BEING 
RELEASED.''
    16. Add a new Sec.  35.40-8 to read as follows:


Sec.  35.40-8  Carbon dioxide olfactory warning signs--T/ALL.

    Each entrance to a space storing carbon dioxide cylinders, a space 
protected by carbon dioxide systems, or any space into which carbon 
dioxide might migrate must be conspicuously marked as follows:
    (a) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (b) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK[dash]OUT SYSTEM WHEN 
SERVICING.''
    (c) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
    17. Revise Sec.  35.40-10 to read as follows:


Sec.  35.40-10  Steam, foam, carbon dioxide, or clean agent fire 
smothering apparatus--TB/ALL.

    Each steam, foam, carbon dioxide, or clean agent fire fighting 
apparatus must be marked ``[CARBON DIOXIDE/STEAM/FOAM/CLEAN AGENT--as 
appropriate] FIRE APPARATUS,'' in red letters at least 2 inches high. 
Branch pipe valves leading to the several compartments must be 
distinctly marked to indicate the compartments or parts of the vessel 
to which they lead.

PART 62--VITAL SYSTEM AUTOMATION

    18. The authority citation for Part 62 continues to read as 
follows:

    Authority: 46 U.S.C. 3306, 3703, 8105; E.O. 12234, 45 FR 58801, 
3 CFR, 1980 Comp., p. 277; Department of Homeland Security 
Delegation No. 0170.1.

    19. Revise Sec.  62.25-20(d)(1)(ii) to read as follows:


Sec.  62.25-20  Instrumentation, alarms, and centralized stations.

* * * * *
    (d) * * *
    (1) * * *
    (ii) Fire, general alarm, carbon dioxide/Halon 1301/clean agent, 
vital machinery, flooding, engineers' assistance-needed, and non-vital 
alarms.
* * * * *

PART 71--INSPECTION AND CERTIFICATION

    20. The authority citation for Part 71 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2113, 3205, 3306, 3307; 
E.O. 12234, 45 FR

[[Page 8441]]

58801, 3 CFR, 1980 Comp., p. 277; E.O. 12777, 56 FR 54757, 3 CFR, 
1991 Comp., p. 351; Department of Homeland Security Delegation No. 
0170.1.

    21. Revise Sec.  71.20-20(b) to read as follows:


Sec.  71.20-20  Specific tests and inspections.

* * * * *
    (b) Installation of carbon dioxide or clean agent extinguishing 
piping in accordance with 46 CFR 76.15-15 and 46 CFR subpart 95.16.
* * * * *
    22. In Sec.  71.25-20, revise the section heading and Table 71.25-
20(a)(2) to read as follows:


Sec.  71.25-20  Fire detecting and extinguishing equipment.

    (a) * * *
    (2) * * *

                          Table 71.25-20(a)(2)
------------------------------------------------------------------------
         Type system                              Test
------------------------------------------------------------------------
Foam.........................  Systems utilizing a soda solution must
                                have that solution replaced. In all
                                cases, ascertain that powder is not
                                caked.
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.
Halon 1301 and halocarbon....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge or if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                               NOTE: Halon 1301 system approvals have
                                expired, but existing systems may be
                                retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Inert gas....................  Recharge or replace cylinder if cylinder
                                pressure loss exceeds 5%of specified
                                gauge pressure, adjusted for
                                temperature. Test time delays, alarms,
                                and ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed inert
                                extinguishers must be tested or renewed,
                                as required by 46 CFR 147.60 and 147.66.
Water mist...................  Maintain system in accordance with the
                                maintenance instructions in the system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------

* * * * *
    23. Revise Sec.  71.65-5(d)(6) to read as follows:


Sec.  71.65-5  Plans and specifications required for new construction.

* * * * *
    (d) * * *
    (6) Extinguishing systems, including fire main, carbon dioxide, 
clean agent, foam, and sprinkling systems.
* * * * *

PART 76--FIRE PROTECTION EQUIPMENT

    24. The authority citation for Part 76 continues to read as 
follows:

    Authority: 46 U.S.C. 3306; E.O. 12234, 45 FR 58801, 3 CFR, 1980 
Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    25. Revise Sec.  76.05-1 to read as follows:


Sec.  76.05-1  Fire detecting systems.

    (a) On the following vessels, approved fire detecting systems must 
be installed in the locations indicated by Table 76.05-1(a):
    (1) Any vessel on an international voyage;
    (2) Any vessel of more than 150 feet in length having sleeping 
accommodations for passengers; and
    (3) Any vessel of 150 feet or less in length that has sleeping 
accommodations for 50 or more passengers. Vessels that are not on an 
international voyage are not required to have a detecting system in the 
cargo spaces.

                            Table 76.05-1(a)
------------------------------------------------------------------------
                                                             Fixed
              Space                Detecting systems     extinguishing
                                                            systems
------------------------------------------------------------------------
                              Safety areas
------------------------------------------------------------------------
Wheelhouse or fire-control room.  None required \1\.  None required.\1\
Stairway and elevator enclosures  None required \1\.  None required.\1\
Communication corridors.........  None required \1\.  None required.\1\
Lifeboat embarkation and          None required \1\.  None required.\1\
 lowering stations.
Radio room......................  None required \1\.  None required.\1\
------------------------------------------------------------------------
                             Accommodations
------------------------------------------------------------------------
Staterooms, toilet spaces,        None required \1\.  None required.\1\
 isolated pantries, etc.
Offices, lockers, and isolated    Electric,           None required.\1\
 storerooms.                       pneumatic, or
                                   automatic
                                   sprinkling \1\.
Public spaces...................  None required with  None required.\1\
                                   20-minute patrol.
                                   Electric,
                                   pneumatic, or
                                   automatic
                                   sprinkling with 1
                                   hour patrol.\1\

[[Page 8442]]

 
Open decks or enclosed            None required.....  None required.
 promenades.
------------------------------------------------------------------------
                             Service spaces
------------------------------------------------------------------------
Galleys.........................  None required \1\.  None required.\1\
Main pantries...................  None required \1\.  None required.\1\
Motion picture booths and film    Electric,           None required.\1\
 lockers.                          pneumatic, or
                                   automatic
                                   sprinkling 1 2.
Paint and lamp rooms............  Smoke detecting     Carbon dioxide \3\
                                   \2\.                system or carbon
                                                       dioxide-
                                                       alternative
                                                       system as
                                                       described in 46
                                                       CFR subpart
                                                       95.16.
Inaccessible baggage, mail, and   Smoke detecting     Carbon dioxide.\3\
 specie rooms and storerooms.      \2\.
Accessible baggage, mail, and     Electric,           None required.\1\
 specie rooms and storerooms.      pneumatic, or
                                   automatic
                                   sprinkling.
Refrigerated storerooms.........  None required.....  None required.
Carpenter, valet, photographic,   Electric,           None required.\1\
 and printing shops, sales         pneumatic, or
 rooms, etc.                       automatic
                                   sprinkling.
------------------------------------------------------------------------
                            Machinery spaces
------------------------------------------------------------------------
Coal fired boilers: Bunker and    None required.....  None required.\1\
 boiler space.
------------------------------------------------------------------------
Oil fired boilers: Spaces         None required.....  Carbon dioxide
 containing oil fired boilers                          system or carbon
 either main or auxiliary, their                       dioxide-
 fuel oil service pumps, and/or                        alternative
 such other fuel oil units as                          system as
 the heaters, strainers, valves,                       described in 46
 manifolds, etc., that are                             CFR subpart 95.16
 subject to the discharge                              or foam.\4\
 pressure of the fuel oil
 service pumps, together with
 adjacent spaces to which oil
 can drain.
Internal combustion or gas        None required.....  Carbon dioxide
 turbine propelling machinery                          system or carbon
 spaces.                                               dioxide-
                                                       alternative
                                                       system as
                                                       described in 46
                                                       CFR subpart
                                                       95.16.\5\
Electric propulsive motors or     None required.....  None required.
 generators of open type.
Enclosed ventilating systems for  None required.....  Carbon dioxide
 motors and generators of                              system or carbon
 electric propelling machinery.                        dioxide-
                                                       alternative
                                                       system as
                                                       described in 46
                                                       CFR subpart 95.16
                                                       (in ventilating
                                                       system).\7\
Auxiliary spaces, internal        None required.....  Carbon dioxide
 combustion, or gas turbine.                           system or carbon
                                                       dioxide-
                                                       alternative
                                                       system as
                                                       described in 46
                                                       CFR subpart
                                                       95.16.\7\
Auxiliary spaces, electric        None required.....  None required.
 motors, or generators.
Auxiliary spaces, steam.........  None required.....  None required.
Trunks to machinery spaces......  None required.....  None required.
Fuel tanks......................  None required.....  None required.\8\
------------------------------------------------------------------------
                              Cargo spaces
------------------------------------------------------------------------
Inaccessible during voyage        Smoke detecting...  Carbon dioxide.\3\
 (combustible cargo), including
 trunks (excluding tanks).
Accessible during voyage          Smoke detecting,    Automatic or
 (combustible cargo).              electric,           manual
                                   pneumatic or        sprinkling.
                                   automatic
                                   sprinkling.
Vehicular deck (except where no   None required.....  Manual sprinkling.
 overhead deck is 30 feet in
 length or less).
Cargo oil tanks.................  None required.....  Carbon dioxide or
                                                       foam.\3\
Specially suitable for vehicles.  Smoke detecting,    Carbon dioxide,
                                   electric,           automatic or
                                   pneumatic or        manual
                                   automatic           sprinkling.
                                   sprinkling.
------------------------------------------------------------------------
Notes to Table 76.05-1(a)
\1\ Vessels of 100 gross tons and over contracted for, on, or before May
  27, 1936, and having combustible joiner work must be fitted with an
  automatic sprinkling system, except in relatively incombustible
  spaces.
\2\ On vessels contracted for prior to November 19, 1952, electric or
  pneumatic detecting may be substituted.
\3\ On vessels contracted for prior to January 1, 1962, a steam
  smothering system may be accepted. However, although existing steam
  smothering systems may be repaired, replaced, or extended, no new
  system contracted for on or after January 1, 1962, will be permitted.
\4\ Protection of auxiliary boilers, fuel oil units, valves, and
  manifolds are not required on vessels contracted for prior to November
  19, 1952.
\5\ Not required on vessels less than 300 gross tons (except on an
  international voyage) using fuel with a flashpoint higher than
  110[deg] F., where the space is normally manned.
\6\ Not required on vessels contracted for prior to November 19, 1952.
\7\ Not required on vessels less than 300 gross tons nor on vessels
  contracted for prior to November 19, 1952, except when fuel, including
  starting fuel, has a flashpoint of 110 [deg]F. or less.
\8\ When fuel with a flashpoint of 110 [deg]F. or lower is used, the
  space containing the fuel tanks must be protected by a carbon dioxide
  system or carbon dioxide-alternative system as described in 46 CFR
  subpart 95.16.


[[Page 8443]]

     (b) The arrangements and details of the fire detecting systems 
must meet the requirements in subparts 76.25 through 76.33 of this 
part.
    26. Revise Sec.  76.10-5(h) to read as follows:


Sec.  76.10-5  Fire pumps.

* * * * *
    (h) If a vessel uses main or auxiliary oil fired boilers or 
internal combustion propulsion machinery, when two fire pumps are 
required, this equipment must be located in separate spaces and the 
arrangement of pumps, sea connections, and sources of power must be 
arranged to ensure that a fire in any one space will not put all of the 
fire pumps out of operation. However, in vessels of less than 300 feet 
in length, when it is shown to the satisfaction of the Commandant that 
it is unreasonable or impracticable to meet this requirement due to the 
size or arrangement of the vessel, or for other reasons, the 
installation of a total flooding carbon dioxide or clean agent 
extinguishing system may be accepted as an alternate method of 
extinguishing any fire that affects the powering and operation of at 
least one of the required fire pumps.
    27. Add a new Sec.  76.15-50 to read as follows:


Sec.  76.15-50  Lockout valves.

    (a) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (b) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (c) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (d) A valve is considered a lockout valve if it has a hasp or other 
means of attachment to which, or through which, a lock can be affixed, 
or it has a locking mechanism built into it.
    (e) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (f) Lockout valves added to existing systems must be included in 
the system Type Approval or acceptable to the Marine Safety Center
    (g) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    28. Add a new Sec.  76.15-60 to read as follows:


Sec.  76.15-60  Olfactory additives.

    (a) Each carbon dioxide extinguishing system must have an approved 
odorizing unit to produce the scent of wintergreen, the detection of 
which will serve as an indication that carbon dioxide gas is present in 
a protected area and any other area into which the carbon dioxide may 
migrate.
    (b) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].

PART 78---OPERATIONS

    29. The authority citation for Part 78 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2103, 3306, 6101; 49 
U.S.C. 5103, 5106; E.O. 12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 
277; E.O. 12777, 56 FR 54757, 3 CFR, 1991 Comp., p. 351; Department 
of Homeland Security Delegation No. 0170.1.

    30. Revise Sec.  78.47-9 to read as follows:


Sec.  78.47-9  Carbon dioxide and clean agent alarms.

    Each carbon dioxide or clean agent fire extinguishing alarm must be 
conspicuously marked: ``WHEN ALARM SOUNDS VACATE AT ONCE. CARBON 
DIOXIDE OR CLEAN AGENT BEING RELEASED.''
    31. Add a new Sec.  78.47-11 to read as follows:


Sec.  78.47-11  Carbon dioxide olfactory warning signs.

    Each entrance to a space storing carbon dioxide cylinders, a space 
protected by carbon dioxide systems, or any space into which carbon 
dioxide might migrate must be conspicuously marked as follows:
    (a) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (b) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK-OUT SYSTEM WHEN 
SERVICING.''
    (c) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
    32. Revise Sec.  78.47-17 to read as follows:


Sec.  78.47-17  Fire extinguishing system controls.

    Each control cabinet or space containing valves or manifolds for a 
fire extinguishing system must be distinctly marked in conspicuous red 
letters at least 2 inches high: ``[CARBON DIOXIDE/STEAM/FOAM/WATER 
SPRAY/MANUAL SPRINKLING/AUTOMATIC SPRINKLING/CLEAN AGENT--as 
appropriate] FIRE SYSTEM.''

PART 91--INSPECTION AND CERTIFICATION

    33. The authority citation for Part 91 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 3205, 3306, 3307; 46 
U.S.C. Chapter 701; Executive Order 12234; 45 FR 58801; 3 CFR, 1980 
Comp., p. 277; Executive Order 12777, 56 FR 54757, 3 CFR, 1991 
Comp., p. 351; Department of Homeland Security Delegation No. 
0170.1.

    34. Revise Sec.  91.20-20(b) to read as follows:


Sec.  91.20-20  Specific tests and inspections.

* * * * *
    (b) For installation of carbon dioxide fire extinguishing system 
piping, see 46 CFR 95.15-15. For clean agent fire extinguishing piping, 
see 46 CFR 95.16-15.
* * * * *
    35. In Sec.  91.25-20, revise the section heading and Table 91.25-
20(a)(2) to read as follows:


Sec.  91.25-20  Fire extinguishing equipment.

    (a) * * *
    (2) * * *

[[Page 8444]]



                          Table 91.25-20(a)(2)
------------------------------------------------------------------------
         Type system                              Test
------------------------------------------------------------------------
Foam.........................  Systems utilizing a soda solution must
                                have that solution replaced. In all
                                cases, ascertain that powder is not
                                caked.
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.
Halon 1301 and halocarbon....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge or if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                               NOTE: Halon 1301 system approvals have
                                expired, but existing systems may be
                                retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Inert gas....................  Recharge or replace cylinder if cylinder
                                pressure loss exceeds 5% of specified
                                gauge pressure, adjusted for
                                temperature. Test time delays, alarms,
                                and ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed inert
                                extinguishers must be tested or renewed,
                                as required by 46 CFR 147.60 and 147.66.
Water mist...................  Maintain system in accordance with the
                                maintenance instructions in the system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------

* * * * *
    36. Revise Sec.  91.55-5(d)(4) to read as follows:


Sec.  91.55-5  Plans and specifications required for new construction.

* * * * *
    (d) * * *
    (4) Details of extinguishing systems, including fire mains, carbon 
dioxide, clean agent, foam, and sprinkling systems.
* * * * *

PART 95--FIRE PROTECTION EQUIPMENT

    37. The authority citation for Part 95 continues to read as 
follows:

    Authority: 46 U.S.C. 3306; E.O. 12234, 45 FR 58801, 3 CFR, 1980 
Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    38. Revise Sec.  95.05-10(e)(3)(ii) to read as follows:


Sec.  95.05-10  Fixed fire extinguishing systems.

* * * * *
    (e) * * *
    (3) * * *
    (ii) On vessels of 1,000 gross tons and greater, a fixed carbon 
dioxide or clean agent system as described in subpart 95.16 of this 
part must be installed in any space that contains internal combustion 
or gas turbine main propulsion machinery, or auxiliary machinery with 
an aggregate power of 1,000 b.h.p. or greater, or the fuel oil units of 
such machinery, including purifiers, valves, and manifolds.
* * * * *
    39. In Sec.  95.10-5(h), revise the second sentence to read as 
follows:


Sec.  95.10-5  Fire pumps.

* * * * *
    (h) * * * However, when it is shown to the satisfaction of the 
Commandant that it is unreasonable or impracticable to meet this 
requirement due to the size or arrangement of the vessel, or for other 
reasons, the installation of a total flooding carbon dioxide or clean 
agent system may be accepted as an alternate method of extinguishing 
any fire that could affect the powering and operation of at least one 
of the required fire pumps.
    40. Revise Sec.  95.15-5(e)(2) to read as follows:


Sec.  95.15-5  Quantity, pipe sizes, and discharge rates.

* * * * *
    (e) * * *
    (2) The valves must be arranged so that the required quantity of 
carbon dioxide is discharged into any ``tight'' space. The discharge of 
two thirds of the required quantity of carbon dioxide must be completed 
within 10 minutes. Any faster discharge rate is also acceptable.
* * * * *
    41. Revise Sec.  95.15-30 to read as follows:


Sec.  95.15-30  Alarms.

    (a) A protected space must be fitted with an approved audible alarm 
if:
    (1) The space is normally accessible to persons onboard while the 
vessel is being navigated; and
    (2) Is not a paint locker or similar small space.
    (b) The alarm must:
    (1) Sound automatically and audibly for at least 20 seconds before 
carbon dioxide is discharged into the space;
    (2) Be conspicuously and centrally located and be marked as 
required by 46 CFR 97.37-9; and
    (3) Use stored gas power provided by the extinguishing agent, gas 
from pilot cylinders, or gas from cylinders specifically provided to 
power the alarms.
    (c) For systems installed on or after July 1, 1957, alarms are 
mandatory only for systems required to be fitted with a delayed 
discharge.
    42. Add a new Sec.  95.15-50 to read as follows:


Sec.  95.15-50  Lockout valves.

    (a) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (b) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (c) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.

[[Page 8445]]

    (d) A valve is considered a lockout valve if it has a hasp or other 
means of attachment to which, or through which, a lock can be affixed, 
or it has a locking mechanism built into it.
    (e) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (f) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (g) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    43. Add a new Sec.  95.15-60 to read as follows:


Sec.  95.15-60  Olfactory warnings.

    (a) Each carbon dioxide extinguishing system must have an approved 
odorizing unit to produce the scent of wintergreen, the detection of 
which will serve as an indication that carbon dioxide gas is present in 
a protected area and any other area into which the carbon dioxide may 
migrate.
    (b) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].
    44. Add a new subpart 95.16 to read as follows:
Subpart 95.16--Fixed Clean Agent Gas Extinguishing Systems, Details
Sec.
95.16-1 Application.
95.16-5 Controls.
95.16-10 Piping, fittings, valves, nozzles.
95.16-15 Extinguishing agent: quantity.
95.16-20 Extinguishing agent: cylinder storage.
95.16-25 Manifold and cylinder arrangements.
95.16-30 Enclosure openings.
95.16-35 Pressure relief.
95.16-40 Locked spaces.
95.16-45 Discharge delays and alarms.
95.16-50 Instructions.
95.16-60 System piping installation testing.
95.16-90 Installations contracted for prior to [EFFECTIVE DATE OF 
THIS RULE].

Subpart 95.16--Fixed Clean Agent Gas Extinguishing Systems, Details


Sec.  95.16-1  Application.

    (a) ``Clean agent'' means a halocarbon or inert gas used as a fire 
extinguishing agent.
    (b) A clean agent extinguishing system must comply with this part. 
Systems contracted for prior to [THE EFFECTIVE DATE OF THIS RULE] may, 
as an alternative, comply with 46 CFR 95.16-90.
    (c) Each clean agent system must:
    (1) Be of a total flooding type to protect against Class B and 
Class C hazards as defined in 46 CFR 95.50-5;
    (2) Address and minimize any hazard to personnel created by the 
effects of extinguishing agent decomposition products and combustion 
products, especially the effects of decomposition product hydrogen 
fluoride (HF), if applicable;
    (3) Be accompanied by an approved manufacturer's design, 
installation, operation, and maintenance manual that provides safety 
and remedial instructions;
    (4) Be used only to protect enclosed spaces;
    (5) Not employ electric power for system actuation, controls, or 
alarms; and
    (6) Not use any source of power for alarms in protected spaces, 
other than the extinguishing agent, gas from pilot cylinders, or gas 
from cylinders specifically provided to power the alarms.


Sec.  95.16-5  Controls.

    (a) At least one releasing station must be installed near the main 
entrance/exit to the protected space.
    (b) System controls must be of an approved type and be suitably 
protected from damage and located outside the protected space.
    (c) Systems must have releasing stations consisting of one control 
to operate the stop valve to the protected space and a second control 
to release at least the required amount of agent. These two controls 
must be located in a box or other enclosure clearly identified for the 
particular space.
    (d) Systems protecting a single space not exceeding 6,000 cubic 
feet in gross volume may be installed without a stop valve if a 
suitable horizontal means of escape from the space exists.
    (e) Controls may not be located in any space that could be cut off 
from the operator in the event of fire in the protected space.
    (f) Where the extinguishing agent can be released by remote 
control, the system must have a manual local control at the cylinders.
    (g) A pneumatic releasing control must have a local mechanical 
manual override feature.
    (h) Automatic discharge arrangements may be used for spaces having 
a volume less than 6,000 cubic feet. However, automatic discharge is 
required for spaces having a volume less than 6,000 cubic feet where 
the agent is stored in the protected space, as allowed by 46 CFR 95.16-
20.
    (i) A system designed to use gas pressure from one or more agent 
storage cylinders and provide pilot pressure to actuate the release of 
extinguishing agent from other storage cylinders that contains three or 
more total storage cylinders must be equipped with at least two 
designated pilot cylinders, each of which is capable of manual control 
at the pilot cylinder.


Sec.  95.16-10  Piping, fittings, valves, nozzles.

    (a) Piping, fittings, and valves must be:
    (1) In accordance with the manufacturer's approved design, 
installation, operation, and maintenance manual;
    (2) Securely supported and when necessary protected against damage;
    (3) Protected inside and out against corrosion; and
    (4) Equipped with:
    (i) Dead end lines (dirt traps) that extend at least 2 inches 
beyond the last nozzle of each distribution line and that are closed 
with a cap or plug; and
    (ii) Drains and dirt traps, fitted where necessary to prevent dirt 
or moisture accumulation and located in accessible locations where 
possible.
    (b) Piping requirements. Piping must be:
    (1) Used exclusively for extinguishing system purposes;
    (2) Protected by a pressure relief valve or equivalent in sections 
where gas pressure can be trapped between closed valves; and
    (3) Welded if it passes through living quarters.
    (c) Piping prohibitions. Piping must not:
    (1) Use rolled groove or cut groove ends; or
    (2) Be fitted with drains or other openings if it passes through 
living quarters.
    (d) Valve requirements. Valves for system operation must be:
    (1) Outside the protected space, and
    (2) Marked, if serving a branch line, to indicate the space the 
branch line serves.
    (e) Valve prohibitions. Valves may not be located in any space that 
could be cut off from the operator in the event of fire in the 
protected space.


Sec.  95.16-15  Extinguishing agent: quantity.

    A separate supply need not be provided for each space protected, 
but the total available supply must be at least sufficient for the 
space requiring the greatest amount.

[[Page 8446]]

Sec.  95.16-20  Extinguishing agent: cylinder storage.

    (a) Unless installed as required in paragraph (b) of this section, 
the agent must be stored outside of the protected space. Common 
bulkheads and decks located between the cylinder storage room and the 
protected spaces must meet the insulation criteria for Class A-60, as 
defined in 46 CFR 72.05-10.
    (b) The cylinders may be stored inside the protected space, if:
    (1) The space does not exceed 6,000 cubic feet gross volume; and
    (2) The system can be automatically operated by a pneumatic heat 
actuator as well as a remote manual control.
    (c) The cylinder storage space must be properly ventilated and 
designed to preclude an anticipated ambient temperature in excess of 
130[deg] Fahrenheit.
    (d) The cylinders must be securely fastened and supported as 
directed in the manufacturer's approved design, installation, 
operation, and maintenance manual, and where necessary protected 
against damage.
    (e) The cylinders must be mounted so they are readily accessible 
and capable of easy removal for recharging and inspection and for 
weighing in the case of halocarbon system cylinders.
    (f) The cylinders must be installed to provide a space of at least 
2 inches between the deck and the bottom of the cylinders.
    (g) The cylinders must be mounted upright, unless otherwise 
specified in the instruction manual.
    (h) All cylinder storage room doors must open outward.


Sec.  95.16-25  Manifold and cylinder arrangements.

    (a) A check valve must be provided between each cylinder and 
manifold or distribution piping. The valve must be permanently marked 
to indicate the direction of flow.
    (b) If the same cylinder is used to protect more than one space, 
normally, closed stop valves must be provided to direct the agent into 
each protected space.
    (c) Each cylinder must be fabricated, tested, and marked in 
accordance with 46 CFR 147.60(b) and 49 CFR Part 180.
    (d) The cylinders in a common manifold must be:
    (1) Of the same size;
    (2) Filled with the same amount of agent; and
    (3) Pressurized to the same working pressure.


Sec.  95.16-30  Enclosure openings.

    (a) If mechanical ventilation is provided for in a protected space, 
the ventilation system must automatically shut down prior to discharge 
of the system to that space.
    (b) If natural ventilation is provided for in a space protected by 
a clean agent extinguishing system, the ventilation must be capable of 
being easily and effectively closed off.
    (c) All other openings to a protected space must be capable of 
being closed. Doors, shutters, or dampers must be installed for 
openings in the lower portion of the space. Openings in the upper 
portion of the space must be capable of being closed off either by 
permanently installed means or by the use of canvas or other material 
normally carried on the vessel.


Sec.  95.16-35  Pressure relief.

    Tight compartments like refrigeration spaces and paint lockers must 
have a way to relieve the accumulation of excessive pressure within the 
compartment when the extinguishing agent is injected.


Sec.  95.16-40  Locked spaces.

    If a space or enclosure containing extinguishing agent supply or 
controls is lockable, a key to the space or enclosure must be in a 
break glass type box conspicuously located adjacent to the opening.


Sec.  95.16-45  Discharge delays and alarms.

    (a) Each system protecting a space with greater than 6,000 cubic 
feet gross volume or a space less than 6,000 cubic feet gross volume 
without a suitable horizontal escape route must have a pneumatic pre-
discharge alarm and time delay.
    (1) The time delay period must:
    (i) Last at least 20 seconds;
    (ii) Be approved by the Officer in Charge, Marine Inspection during 
system installation; and
    (iii) Provide enough time for one person to walk from the farthest 
area of the protected space to the primary exit.
    (2) The time delay device must be pneumatically operated and have 
an accuracy of -0/+20% of the rated time delay period throughout the 
operating temperature range and range of delay settings.
    (b) The pre-discharge alarm must:
    (1) Sound for the duration of the time delay;
    (2) Be conspicuously and centrally located and marked as required 
by 46 CFR 97.37-9;
    (3) Depend on the extinguishing agent, gas from a pilot cylinder, 
or a nitrogen cylinder specifically provided to power the alarm for its 
source of power; and
    (4) Be audible over running machinery.


Sec.  95.16-50  Instructions.

    (a) Simple, complete operating instructions must be conspicuously 
located at or near any release station and in the extinguishing agent 
cylinder storage room.
    (b) On a system in which extinguishing agent cylinders are stored 
outside the protected space, operating instructions must also:
    (1) Include a schematic diagram of the system; and
    (2) Describe alternate methods of discharging the extinguishing 
agent into protected spaces should the manual releases or stop valve 
controls fail to operate.


Sec.  95.16-60  System piping installation testing.

    (a) Halocarbon systems. A pressure test using the extinguishing 
agent, air or inert gas, must be conducted on halocarbon system 
discharge piping on completion of piping installation and before 
extinguishing agent cylinders are connected.
    (1) Except as otherwise specified in this section:
    (i) Piping from the cylinders to the stop valves or selector valves 
must be subjected to a pressure of 1\1/2\ times the cylinder charging 
pressure at 70[deg] Fahrenheit; and
    (ii) The leakage during a 2-minute period must not exceed a 
pressure drop of 10 percent.
    (2) Individual branch lines to a protected space must be tested as 
described in paragraph (a)(1) of this section, except that:
    (i) The pressure must be 150 pounds per square inch; and
    (ii) Distribution piping must be capped within the protected space 
at the first joint upstream of the nozzles.
    (3) Pneumatic actuation piping must be tested as described in 
paragraph (a)(1) of this section.
    (b) Inert gas systems. A pressure test using air or inert gas must 
be conducted on each inert gas system's piping on completion of piping 
installation and before extinguishing agent cylinders are connected.
    (1) Except as otherwise specified in this section:
    (i) Piping from the cylinders to the stop valves or selector valves 
must be subjected to a pressure of 1,000 pounds per square inch at 
70[deg] Fahrenheit; and
    (ii) The leakage during a 2-minute period must not exceed a 
pressure drop of 10 percent.
    (2) Individual branch lines to a protected space must be tested as 
described in paragraph (b)(1) of this section, except that:
    (i) The pressure must be 600 pounds per square inch; and

[[Page 8447]]

    (ii) Distribution piping must be capped within the protected space 
at the first joint upstream of the nozzles.
    (3) Pneumatic actuation piping must be tested as described in 
paragraph (b)(1) of this section.
    (c) Small independent systems. In lieu of test requirements in 
paragraphs (a) or (b) of this section, a small independent halocarbon 
or inert gas system, like those found in emergency generator rooms and 
paint lockers, may be tested by blowing out the piping with air 
pressure of at least 100 pounds per square inch, if:
    (1) There are no valves in the system discharge piping; and
    (2) There is not more than one change in direction between the 
agent container and the discharge nozzle.


Sec.  95.16-90  Installations contracted for prior to [EFFECTIVE DATE 
OF THIS RULE].

    Installations contracted for prior to [EFFECTIVE DATE OF THIS RULE] 
must meet the requirements of this subpart unless previously approved 
existing arrangements, materials, and facilities are:
    (a) Maintained in good condition to the satisfaction of the Officer 
in Charge, Marine Inspection; and
    (b) Subjected to no more than minor repairs or alterations 
implemented to the same standards as the original installation.

PART 97--OPERATIONS

    45. The authority citation for Part 97 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2103, 3306, 6101; 49 
U.S.C. 5103, 5106; E.O. 12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 
277; E.O. 12777, 56 FR 54757; 3 CFR, 1991 Comp., p. 351; Department 
of Homeland Security Delegation No. 0170.1.

    46. Revise Sec.  97.37-9 to read as follows:


Sec.  97.37-9  Carbon dioxide and clean agent alarms.

    Each carbon dioxide or clean agent fire extinguishing alarm must be 
conspicuously marked: ``WHEN ALARM SOUNDS VACATE AT ONCE. CARBON 
DIOXIDE OR CLEAN AGENT BEING RELEASED.''
    47. Add a new Sec.  97.37-11 to read as follows:


Sec.  97.37-11  Carbon dioxide warnings.

    Each entrance to a space storing carbon dioxide cylinders, a space 
protected by carbon dioxide systems, or any space into which carbon 
dioxide might migrate must be conspicuously marked as follows:
    (a) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (b) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK[dash]OUT SYSTEM WHEN 
SERVICING.''
    (c) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
    48. Revise Sec.  97.37-13 to read as follows:


Sec.  97.37-13  Fire extinguishing system controls.

    The control cabinets or spaces containing valves or manifolds for 
the various fire extinguishing systems must be distinctly marked in 
conspicuous red letters at least 2 inches high: ``[STEAM/CARBON 
DIOXIDE/CLEAN AGENT/FOAM/WATER SPRAY--as appropriate] FIRE APPARATUS.''

PART 107---INSPECTION AND CERTIFICATION

    49. The authority citation for Part 107 continues to read as 
follows:

    Authority: 43 U.S.C. 1333; 46 U.S.C. 3306, 3307; 46 U.S.C. 3316; 
Department of Homeland Security Delegation No. 0170.1; Sec.  107.05 
also issued under the authority of 44 U.S.C. 3507.

    50. Add Sec.  107.231(w) to read as follows:


Sec.  107.231  Inspection for certification.

* * * * *
    (w) Piping for each halocarbon and inert gas extinguishing system 
must be tested in accordance with 46 CFR 95.16-60.
* * * * *
    51. In Sec.  107.235, revise paragraph (b) and add paragraph (c) to 
read as set out below, and remove the note at the end of the section.


Sec.  107.235  Servicing of hand portable fire extinguishers, semi-
portable fire extinguishers and fixed fire-extinguishing systems.

* * * * *
    (b) Each fixed fire extinguishing system must be examined for 
excessive corrosion and general condition and checked and serviced as 
indicated, depending on the extinguishing agent used by the system.
    (1) Carbon dioxide: Weigh cylinders. Recharge cylinder if weight 
loss exceeds 10% of weight of charge. Test time delays, alarms, and 
ventilation shutdowns with carbon dioxide, nitrogen, or other 
nonflammable gas as stated in the system manufacturer's instruction 
manual. Inspect hoses for damage or decay. Ensure that nozzles are 
unobstructed. Cylinders must be tested and marked, and all flexible 
connections on fixed carbon dioxide systems must be tested or renewed, 
as required by 46 CFR 147.60 and 147.65.
    (2) Halon 1301 or Halocarbon: Recharge or replace if weight loss 
exceeds 5% of weight of charge or, if cylinder has a pressure gauge, 
recharge cylinder if pressure loss exceeds 10%, adjusted for 
temperature. Test time delays, alarms, and ventilation shutdowns with 
carbon dioxide, nitrogen, or other nonflammable gas as stated in the 
system manufacturer's instruction manual. Inspect hoses for damage or 
decay. Ensure that nozzles are unobstructed. Cylinders must be tested 
and marked, and all flexible Halon 1301 and halocarbon cylinders must 
be tested or renewed as required by 46 CFR 147.60 and 147.65 or 147.67. 
Note that Halon 1301 system approvals have expired, but that existing 
systems may be retained if they are in good and serviceable condition 
to the satisfaction of the Coast Guard inspector.
    (3) Inert gas: Recharge or replace cylinder if cylinder pressure 
loss exceeds 5% of specified gauge pressure, adjusted for temperature. 
Test time delays, alarms, and ventilation shutdowns with carbon 
dioxide, nitrogen, or other nonflammable gas as stated in the system 
manufacturer's instruction manual. Inspect hoses for damage or decay. 
Ensure that nozzles are unobstructed. Cylinders must be tested and 
marked, and all flexible connections on fixed inert extinguishers must 
be tested or renewed as required by 46 CFR 147.60 and 147.66.
    (4) Foam, except premix systems: Discharge foam for approximately 
15 seconds from a nozzle designated by the marine inspector, by:
    (i) Discharging water from all other lines and nozzles; and
    (ii) Submitting a sample of the foam liquid to the manufacturer or 
its authorized representative for determination of specific gravity, 
pH, percentage of water dilution, and solid content and for 
certification as a suitable firefighting foam.
    (5) Premix aqueous film forming foam: Remove the pressure cartridge 
and replace the cartridge if the seal is

[[Page 8448]]

punctured, sampling the premix solution in accordance with the 
manufacturer's instructions, and replacing any cylinders that are 
discharged.
    (c) Fire extinguishing equipment must be tested and marked as 
indicated, depending on the extinguishing agent used by the system --
    (1) Carbon dioxide and Halon 1301, semi-portable systems: Cylinders 
and discharge hoses in accordance with 46 CFR 147.60 and 147.65; or
    (2) Halocarbon and inert gas: Cylinders and flexible connectors in 
accordance with 46 CFR 147.66 and 147.67.

PART 108--DESIGN AND EQUIPMENT

    52. The authority citation for Part 108 continues to read as 
follows:

    Authority: 43 U.S.C. 1333; 46 U.S.C. 3102, 3306; Department of 
Homeland Security Delegation No. 0170.1.

    53. Add new Sec.  108.444 to read as follows:


Sec.  108.444  Lockout valves.

    (a) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (b) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (c) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (d) A valve is considered a lockout valve if it has a hasp or other 
means of attachment to which, or through which, a lock can be affixed, 
or it has a locking mechanism built into it.
    (e) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (f) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (g) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    54. Add a new Sec.  108.446 to read as follows:


Sec.  108.446  Olfactory additives.

    (a) Each carbon dioxide extinguishing system must have an approved 
odorizing unit to produce the scent of wintergreen, the detection of 
which will serve as an indication that carbon dioxide gas is present in 
a protected area and any other area into which the carbon dioxide may 
migrate.
    (b) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].
    55. Add a new Sec.  108.626 to read as follows:


Sec.  108.626  Carbon dioxide olfactory warning signs.

    Each entrance to a space storing carbon dioxide cylinders, a space 
protected by carbon dioxide systems, or any space into which carbon 
dioxide might migrate must be conspicuously marked as follows:
    (a) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (b) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK[dash]OUT SYSTEM WHEN 
SERVICING.''
    (c) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
    56. Revise the section heading to Sec.  108.627 to read as follows:


Sec.  108.627  Carbon dioxide and clean agent alarms.

* * * * *
    57. Revise Sec.  108.631(a) to read as follows:


Sec.  108.631  Fixed fire extinguishing system controls.

    (a) Each cabinet or space that contains a valve, control, or 
manifold of a fixed fire extinguishing system must be marked in 
conspicuous red letters at least 2 inches high: ``[CARBON DIOXIDE/CLEAN 
AGENT/FOAM/WATER SPRAY--as appropriate] FIRE APPARATUS.''
* * * * *

PART 112--EMERGENCY LIGHTING AND POWER SYSTEMS

    58. The authority citation for Part 112 continues to read as 
follows:

    Authority: 46 U.S.C. 3306, 3703; Department of Homeland Security 
Delegation No. 0170.1.

    59. Revise Sec.  112.15-5(v) to read as follows:


Sec.  112.15-5  Final emergency loads.

* * * * *
    (v) Each smoke extraction fan, not including smoke detector 
sampling, and carbon dioxide or clean agent exhaust fans for spaces.

PART 115--INSPECTION AND CERTIFICATION

    60. The authority citation for Part 115 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2103, 3205, 3306, 3307; 
49 U.S.C. App. 1804; E.O. 11735, 38 FR 21243, 3 CFR, 1971-1975 
Comp., p. 743; E.O. 12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 277; 
Department of Homeland Security Delegation No. 0170.1

    61. In Sec.  115.810, revise Table 115.810(b) to read as follows:


Sec.  115.810  Fire protection.

* * * * *
    (b) * * *

   Table 115.810(b)--Semiportable and Fixed Fire Extinguishing Systems
------------------------------------------------------------------------
         Type system                              Test
------------------------------------------------------------------------
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.

[[Page 8449]]

 
Halon 1301 and halocarbon....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge or if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                                Note that Halon 1301 system approvals
                                have expired, but that existing systems
                                may be retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Dry chemical (cartridge        Examine pressure cartridge and replace if
 operated).                     end is punctured, has leaked, or is
                                otherwise unsuitable. Inspect hose and
                                nozzle to see if they are clear. Insert
                                charged cartridge. Ensure dry chemical
                                is free flowing, not caked, and
                                extinguisher contains full charge.
Dry chemical (stored           See that pressure gauge is in operating
 pressure).                     range. If not, or if the seal is broken,
                                weigh or otherwise determine that
                                extinguisher is fully charged with dry
                                chemical. Recharge cylinder if pressure
                                is low or if dry chemical is needed.
Foam (stored pressure).......  See that any pressure gauge is in the
                                operating range. If not, or if the seal
                                is broken, weigh or otherwise determine
                                that extinguisher is fully charged with
                                foam. Recharge cylinder if pressure is
                                low or if foam is needed. Replace
                                premixed agent every 3 years.
Inert gas....................  Recharge or replace cylinder if cylinder
                                pressure loss exceeds 5% of specified
                                gauge pressure, adjusted for
                                temperature. Test time delays, alarms,
                                and ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed inert
                                extinguishers must be tested or renewed
                                as required by 46 CFR 147.60 and 147.66.
Water mist...................  Maintain system in accordance with
                                maintenance instructions in system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------

* * * * *

PART 118--FIRE PROTECTION EQUIPMENT

    62. The authority citation for Part 118 continues to read as 
follows:

    Authority: 46 U.S.C. 2103, 3306; E.O. 12234, 45 FR 58801, 3 CFR, 
1980 Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    63. In Sec.  118.410, add new paragraphs (f)(7) through (f)(13) and 
add new paragraph (h) to read as follows:


Sec.  118.410  Fixed gas fire extinguishing systems.

* * * * *
    (f) * * *
    (7) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (8) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (9) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (10) A valve is considered a lockout valve if it has a hasp or 
other means of attachment to which, or through which, a lock can be 
affixed, or it has a locking mechanism built into it.
    (11) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (12) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (13) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
* * * * *
    (h) Olfactory additives. (1) Each carbon dioxide extinguishing 
system must have an approved odorizing unit to produce the scent of 
wintergreen, the detection of which will serve as an indication that 
carbon dioxide gas is present in a protected area and any other area 
into which the carbon dioxide may migrate.
    (2) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].

PART 119--MACHINERY INSTALLATION

    64. The authority citation for Part 119 continues to read as 
follows:

    Authority: 46 U.S.C. 2103, 3306; E.O. 12234, 45 FR 58801, 3 CFR, 
1980 Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    65. Revise Sec.  119.710(a)(3) to read as follows:


Sec.  119.710  Piping for vital systems.

    (a) * * *
    (3) Carbon dioxide, Halon 1301, and clean agent systems;
* * * * *

PART 122--OPERATIONS

    66. The authority citation for Part 122 continues to read as 
follows:

    Authority: 46 U.S.C. 2103, 3306, 6101; E.O. 12234, 45 FR 58801, 
3 CFR, 1980 Comp., p. 277; Department of Homeland Security 
Delegation No. 0170.1.

    67. In Sec.  122.612, add new paragraph (i) to read as follows:


Sec.  122.612  Fire protection equipment.

* * * * *
    (i) Carbon dioxide olfactory warning signs. Each entrance to a 
space storing carbon dioxide cylinders, a space protected by carbon 
dioxide systems, or any space into which carbon dioxide might migrate 
must be conspicuously marked as follows:
    (1) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''

[[Page 8450]]

    (2) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK[dash]OUT SYSTEM WHEN 
SERVICING.''
    (3) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''

PART 131--OPERATIONS

    68. The authority citation for Part 131 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 3306, 6101, 10104; E.O. 
12234, 3 CFR, 1980 Comp., p. 277; E.O. 12777, 3 CFR, 1991 Comp., p. 
351; Department of Homeland Security Delegation No. 0170.1.

    69. Revise Sec.  131.815 to read as follows:


Sec.  131.815  Carbon dioxide and clean agent alarms.

    Each carbon dioxide or clean agent fire extinguishing alarm must be 
conspicuously marked: ``WHEN ALARM SOUNDS VACATE AT ONCE. CARBON 
DIOXIDE OR CLEAN AGENT BEING RELEASED.''
    70. Add a new Sec.  131.817 to read as follows:


Sec.  131.817  Carbon dioxide olfactory warning signs.

    Each entrance to a space storing carbon dioxide cylinders, a space 
protected by carbon dioxide systems, or any space into which carbon 
dioxide might migrate must be conspicuously marked as follows:
    (a) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (b) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK-OUT SYSTEM WHEN 
SERVICING.''
    (c) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
    71. Revise Sec.  131.825 to read as follows:


Sec.  131.825  Fixed fire extinguishing system controls.

    Each control cabinet or space containing a valve or manifold for a 
fire extinguishing system must be distinctly marked in conspicuous red 
letters at least 2 inches high: ``[CARBON DIOXIDE/HALON/CLEAN AGENT] 
FIRE APPARATUS'', as appropriate.

PART 132--FIRE-PROTECTION EQUIPMENT

    72. The authority citation for Part 132 continues to read as 
follows:

    Authority: 46 U.S.C. 3306, 3307; Department of Homeland Security 
Delegation No. 0170.1.

    73. In Sec.  132.350, revise Table 132.350 to read as follows:


Sec.  132.350  Tests and inspections of fire-extinguishing equipment.

* * * * *

    Table 132.350--Tests of Semiportable and Fixed Fire-Extinguishing
                                 Systems
------------------------------------------------------------------------
        Type of system                            Test
------------------------------------------------------------------------
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.
Halon 1301 and halocarbon....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge or if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                                Note that Halon 1301 system approvals
                                have expired, but that existing systems
                                may be retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Dry chemical (cartridge-       Examine pressure cartridge and replace if
 operated).                     end is punctured or if cartridge has
                                leaked or is otherwise unsuitable.
                                Inspect hose and nozzle to see that they
                                are clear. Insert charged cartridge.
                                Ensure that dry chemical is free-flowing
                                (not caked) and that extinguisher
                                contains full charge.
Dry chemical (stored           See that pressure gauge is in operating
 pressure).                     range. If not, or if seal is broken,
                                weigh or otherwise determine that
                                extinguisher is fully charged with dry
                                chemical. Recharge if pressure is low or
                                if dry chemical is needed.
Foam (stored pressure).......  See that any pressure gauge is in
                                operating range. If it is not, or if
                                seal is broken, weigh or otherwise
                                determine that extinguisher is fully
                                charged with foam. Recharge if pressure
                                is low or if foam is needed. Replace
                                premixed agent every 3 years.
Inert gas....................  Recharge or replace cylinder if cylinder
                                pressure loss exceeds 5% of specified
                                gauge pressure, adjusted for
                                temperature. Test time delays, alarms,
                                and ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed inert
                                extinguishers must be tested or renewed
                                as required by 46 CFR 147.60 and 147.66.
Water mist...................  Maintain system in accordance with the
                                maintenance instructions in the system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------


[[Page 8451]]

* * * * *

PART 147--HAZARDOUS SHIPS' STORES

    74. The authority citation for Part 147 continues to read as 
follows:


    Authority: 46 U.S.C. 3306; E.O. 12234, 45 FR 58801, 3 CFR, 1980 
Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    75. Revise Sec.  147.7 to read as follows:


Sec.  147.7  Incorporation by reference.

    (a) Certain material is incorporated by reference into this part 
with the approval of the Director of the Federal Register in accordance 
with 5 U.S.C. 552(a). To enforce any edition other than that specified 
below, the Coast Guard must publish notice of change in the Federal 
Register and make the material available to the public. All approved 
material is on file at the U.S. Coast Guard, Office of Design and 
Engineering Standards (CG-521), 2100 2nd Street, SW., Stop 7126, 
Washington, DC 20593-7126 or at the National Archives and Records 
Administration (NARA). For information on the availability of this 
material at NARA, call 202-741-6030, or go to: http://www.archives.gov/federal_register/code_of_federal_regulations/ibr_locations.html. 
All material is available from the sources indicated below.
    (b) American Boat and Yacht Council, Inc. (ABYC), 3069 Solomons 
Island Road, Edgewater, MD 21037.
    (1) ABYC H-25-81--Portable Fuel Systems and Portable Containers for 
Flammable Liquids, May 12, 1981: 147.45.
    (2) [Reserved].
    (c) American Society of Heating, Refrigerating, and Air-
Conditioning Engineers, Inc. (ASHRAE), Publication Sales Department, 
1791 Tullie Circle, NE, Atlanta, GA 30329.
    (1) ANSI/ASHRAE 34-78--Number Designation of Refrigerants, approved 
1978: 147.90.
    (2) [Reserved].
    (d) National Fire Protection Association (NFPA), 1 Batterymarch 
Park, Quincy, MA 02269-9101.
    (1) NFPA 2001, ``Standard on Clean Agent Fire Extinguishing 
Systems'' 2008 Edition: 147.66, 147.67.
    (2) [Reserved].
    (e) Public Health Service, Department of Health and Human Services 
(DHHS), Superintendent of Documents, U.S. Government Printing Office, 
Washington, DC 20402.
    (1) DHHS Publication No. (PHS) 84-2024--The Ship's Medicine Chest 
and Medical Aid at Sea, revised 1984: 147.105.
    (2) [Reserved].
    (f) Underwriters Laboratories, Inc. (UL), 333 Pfingsten Road, 
Northbrook, IL 60062.
    (1) UL 30--Standard for Metal Safety Cans, 7th Ed., March 11, 1985, 
revised March 12, 1985 and March 3, 1987: 147.45.
    (2) UL 1185--Standard for Portable Marine Fuel Tanks, Second 
Edition, March 13, 1978, revised July 6, 1984: 147.45.
    (3) UL 1313--Standard for Nonmetallic Safety Cans for Petroleum 
Products, 1st Ed., March 15, 1982, revised January 3, 1984 and March 
22, 1985: 147.45.
    (4) UL 1314--Standard for Special-Propose Containers, 1st Ed., July 
7, 1983, revised February 7, 1984 and September 23, 1986: 147.45.
    76. Revise Sec.  147.45(f)(4), (5), and (6) to read as follows:


Sec.  147.45  Flammable and combustible liquids.

* * * * *
    (f) * * *
    (4) A portable outboard fuel tank meeting the specifications of 
ABYC H-25-81 (incorporated by reference, see 46 CFR 147.7) or one 
identified by Underwriters Laboratories as meeting the specifications 
of UL 1185 (incorporated by reference, see 46 CFR 147.7);
    (5) A portable safety container identified by Underwriters 
Laboratories as meeting the specifications of UL 30 or UL 1313 (both 
incorporated by reference, see 46 CFR 147.7); or
    (6) A portable safety container identified by Underwriters 
Laboratories as meeting the requirements of UL 1314 (incorporated by 
reference, see 46 CFR 147.7).
* * * * *
    77. Revise Sec.  147.60(a)(4) to read as follows:


Sec.  147.60  Compressed gases.

    (a) * * *
    (4) Except as provided in 46 CFR 147.65, 147.66, and 147.67, 
maintained and retested in accordance with 49 CFR 180.
* * * * *
    78. Add a new Sec.  147.66 to read as follows:


Sec.  147.66  Inert gas fire extinguishing systems.

    (a) Inert gas cylinders forming part of a clean agent fixed fire 
extinguishing system must be retested every five years, except that 
cylinders with a water capacity of 125 pounds or less may be retested 
every 10 years in accordance with 49 CFR 180.209(b).
    (b) An inert gas cylinder must be removed from service if it:
    (1) Leaks;
    (2) Is dented, bulging, severely corroded, or otherwise weakened;
    (3) Has lost more than five percent of its tare weight; or
    (4) Has been involved in a fire.
    (c) Flexible connections between cylinders and discharge piping for 
fixed inert gas fire extinguishing systems must be renewed or retested 
in accordance with Sec.  7.3 of NFPA 2001 (incorporated by reference, 
see 46 CFR 147.7).
    79. Add new Sec.  147.67 to read as follows:


Sec.  147.67  Halocarbon fire extinguishing systems.

    (a) Each halocarbon cylinder forming part of a clean agent fixed 
fire extinguishing system must be:
    (1) Retested at least once every 12 years and before recharging if 
it has been discharged and more than five years have elapsed since the 
last test; or
    (2) As an alternative, a cylinder conforming to the requirements of 
49 CFR 180.209(g) may be given the complete external visual inspection 
in lieu of hydrostatic testing provided for by that section.
    (b) A halocarbon cylinder must be removed from service if it:
    (1) Leaks;
    (2) Is dented, bulging, severely corroded, or otherwise weakened;
    (3) Has lost more than five percent of its tare weight; or
    (4) Has been involved in a fire.
    (c) Flexible connections between cylinders and discharge piping for 
halocarbon fire extinguishing systems must be renewed or retested in 
accordance with section 7.3 of NFPA 2001 (incorporated by reference, 
see 46 CFR 147.7).

PART 162--ENGINEERING EQUIPMENT

    80. The authority citation for Part 162 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j), 1903; 46 U.S.C. 3306, 3703, 4104, 
4302; E.O. 12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 277; E.O. 
11735, 38 FR 21243, 3 CFR, 1971-1975 Comp., p. 793; Department of 
Homeland Security Delegation No. 0170.1.

    81. Add a new subpart 162.161 to read as follows:
Subpart 162.161--Fixed Clean Agent Fire Extinguishing Systems
Sec.
162.161-1 Scope.
162.161-2 Incorporation by reference.

[[Page 8452]]

162.161-3 Materials.
162.161-4 Construction.
162.161-5 Instruction manual for design, installation, operation, 
and maintenance.
162.161-6 Tests for approval.
162.161-7 Inspections at production.
162.161-8 Marking.
162.161-9 Procedure for approval.

Subpart 162.161--Fixed Clean Agent Fire Extinguishing Systems


Sec.  162.161-1  Scope.

    (a) This subpart applies to each engineered fixed fire 
extinguishing system using a halocarbon or an inert gas as agent. It 
does not apply to pre-engineered systems.
    (b) Each system must be designed for protection against fires in 
both Class B flammable liquids and Class C energized electrical 
equipment, as those hazard classes are defined in NFPA 2001 
(incorporated by reference, see 46 CFR 162.161-2).
    (c) Each system must meet the requirements of this subpart, be 
listed or approved by an independent laboratory approved by the Coast 
Guard and listed at http://cgmix.uscg.mil/, bear the mark of the 
laboratory, and be approved by the Coast Guard under 46 CFR 159.005-13.


Sec.  162.161-2  Incorporation by reference.

    (a) Certain material is incorporated by reference into this part 
with the approval of the Director of the Federal Register in accordance 
with 5 U.S.C. 552(a). To enforce any edition other than that specified 
below, the Coast Guard must publish notice of change in the Federal 
Register and make the material available to the public. All approved 
material is on file at the U.S. Coast Guard, Office of Design and 
Engineering Standards (CG-521), 2100 2nd Street, SW., Stop 7126, 
Washington, DC 20593-7126 or at the National Archives and Records 
Administration (NARA). For information on the availability of this 
material at NARA, call 202-741-6030, or go to: http://www.archives.gov/federal_register/code_of_federal_regulations/ibr_locations.html. 
All material is available from the sources indicated below.
    (b) National Fire Protection Association (NFPA), 1 Batterymarch 
Park, Quincy, MA 02269-9101.
    (1) NFPA 2001, ``Standard on Clean Agent Fire Extinguishing 
Systems'' 2008 Edition: 162.161-1, 162.161-3.
    (2) [Reserved]
    (c) Underwriters Laboratories, Inc. (UL), 333 Pfingsten Road, 
Northbrook, IL 60062.
    (1) UL 2127, ``Standard for Inert Gas Clean Agent Extinguishing 
System Units'' 1999 Edition: 162.161-5, 162.161-6, 162.161-7.
    (2) UL 2166, ``Standard for Halocarbon Clean Agent Extinguishing 
System Units'' 1999 Edition: 162.161-5, 162.161-6, 162.161-7.
    (d) International Maritime Organization (IMO), Publications 
Section, 4 Albert Embankment, London SE1 7SR, United Kingdom:
    (1) MSC/Circ. 848, ``Revised Guidelines for The Approval of 
Equivalent Fixed Gas Fire-Extinguishing Systems, as Referred to in 
Chapter II-2 of SOLAS 74, for Machinery Spaces and Cargo Pump-Rooms'' 
1998 Edition: 162.161-6.
    (2) MSC.1/Circ. 1267, ``Amendments to Revised Guidelines for The 
Approval of Equivalent Fixed Gas Fire-Extinguishing Systems, as 
Referred to in SOLAS 74, for Machinery Spaces and Cargo Pump-Rooms 
(MSC/Circ. 848)'' 2008 Edition: 162.161-6.


Sec.  162.161-3  Materials.

    (a) All system components must meet the requirements of NFPA 2001 
(incorporated by reference, see 46 CFR 162.161-2) and be made of metal, 
except for bushings, o-rings, and gaskets. Aluminum or aluminum alloys 
may not be used.
    (b) Metal components must:
    (1) Have a solidus melting point of at least 1700[deg] Fahrenheit;
    (2) Be corrosion resistant; and
    (3) Be galvanically compatible with each adjoining metal component, 
or if galvanically incompatible, be separated by a bushing, o-ring, 
gasket, or similar device. (c) Each extinguishing agent must be:
    (1) Listed as an acceptable total flooding agent for occupied areas 
on the Environmental Protection Agency's Significant New Alternative 
Products (SNAP) list, 40 CFR part 82, subpart G, Appendix A; and
    (2) Identified as an extinguishing agent in NFPA 2001 (incorporated 
by reference, see 46 CFR 162.161-2).
    (d) The design concentration of extinguishing agent required for 
each system must be determined by the cup burner method, described in 
NFPA 2001, for the specific fuel requiring the highest extinguishing 
concentration.
    (e) The quantity of agent required for each protected space must be 
calculated using a safety factor of 1.3 times the design concentration. 
The quantity must be calculated at the minimum expected ambient 
temperature using the design concentration based on either:
    (1) Gross volume, including the casing, bilge, and free air 
contained in air receivers; or
    (2) Net volume, calculated as shown in NFPA 2001 (incorporated by 
reference, see 46 CFR 162.161-2), including the casing, bilge, and free 
air contained in air receivers, if one of the following is 
satisfactorily performed:
    (i) Full discharge test; or
    (ii) Enclosure integrity procedure in accordance with Annex C of 
NFPA 2001; for discharge or enclosure integrity tests, the minimum 
concentration hold time must be 15 minutes, and the extinguishing agent 
concentration at the end of the hold time must be at least 85% of the 
design concentration.
    (f) If fuel can drain from the compartment being protected to an 
adjacent compartment or if the compartments are not entirely separate, 
the quantity must be sufficient for both compartments.


Sec.  162.161-4  Construction.

    (a) Each pressure vessel must comply with 46 CFR 147.60(a) and (b).
    (b) Each system must be capable of operation without an external 
power source.
    (c) Manual actuation for the system must be by mechanical or 
pneumatic means.
    (d) Automatically actuated systems must be released by pneumatic or 
fusible element detection systems.
    (e) Each system installed with the extinguishing agent cylinders 
stored inside a protected space of 6,000 cubic feet or less must use 
automatic actuation as the primary means of actuation and have a remote 
backup manual mechanical actuator.
    (f) Each container charged with nitrogen must have a pressure 
gauge.


Sec.  162.161-5  Instruction manual for design, installation, 
operation, and maintenance.

    (a) The manufacturer must prepare a system instruction manual for 
design, installation, operation, and maintenance of the system. The 
manual must be reviewed and accepted by an independent laboratory 
listed in 46 CFR 162.161-10 and be approved by the Coast Guard under 46 
CFR 159.005-13.
    (b) The manual must include:
    (1) The design information as required in the Design Manual as 
detailed in UL 2166 (incorporated by reference, see 46 CFR 162.161-2) 
for halocarbon systems and UL 2127 (incorporated by reference, see 46 
CFR 162.161-2) for inert gas systems;
    (2) Installation, operation, and maintenance instructions as 
required in the Installation, Operation, and Maintenance Instruction 
Manual detailed in UL 2166 for halocarbon systems and UL 2127 for inert 
gas systems;
    (3) Identification of the computer program listed or approved by 
the

[[Page 8453]]

independent laboratory for designing the system;
    (4) A sample diagram and calculation for a marine system for a 
large inspected vessel with several spaces to be protected by the same 
system;
    (5) The approval number issued by the Coast Guard for the system 
under 46 CFR 159.005-13;
    (6) A parts list with manufacturer's parts numbers and description 
of each system component;
    (7) An index of chapters; and
    (8) Issue and revision dates for each page.
    (c) The manufacturer of each system must provide at least one copy 
of the system manual with each system.


Sec.  162.161-6  Tests for approval.

    Prior to approval by an independent laboratory each system must:
    (a) Satisfy the test method of MSC/Circ. 848 as amended by MSC.1/
Circ. 1267 (both incorporated by reference, see Sec.  162.161-2), 
except that:
    (1) The Fire Type A (Tell tale) test must be conducted when the 
charged system cylinders have been conditioned for 24 hours at 32[deg] 
Fahrenheit or at the expected service temperature, if lower than 
32[deg] F.
    (2) [Reserved]
    (b) Satisfy the following test requirements as indicated in UL 2166 
(incorporated by reference, see 46 CFR 162.161-2) for halocarbon 
systems or UL 2127 for inert gas systems (incorporated by reference, 
see 46 CFR 162.161-2):
    (1) Nozzle distribution;
    (2) Flow calculation method verification to determine that the 
manufacturer's calculation method accurately predicts the discharge 
time, nozzle pressure, and distribution of the extinguishing agent;
    (3) Salt spray corrosion resistance for marine-type systems;
    (4) Vibration resistance of installed components for marine-type 
systems; and
    (5) Any additional tests contained in UL 2166 for halocarbon 
systems or UL 2127 for inert gas systems, as required for listing by 
the independent laboratory.
    (c) Equivalent length of installed components must be identified 
and included in the test report in accordance with UL 2166 for 
halocarbon systems or UL 2127 for inert gas systems.


Sec.  162.161-7  Inspections at production.

    (a) The system must be inspected in accordance with this section 
and 46 CFR 159.007-1 through 159.007-13, and tested using any 
additional tests that the Commandant (CG-5214) may deem necessary to 
maintain control of quality and to ensure compliance with this subpart.
    (b) The manufacturer must:
    (1) Institute procedures to maintain control over the materials 
used, over the manufacturing of the systems, and over finished systems;
    (2) Admit the independent laboratory inspector and any 
representative of the Coast Guard to any place where work is being done 
on systems and any place where parts or complete systems are stored;
    (3) Allow the independent laboratory inspector and any 
representative of the Coast Guard to take samples of systems for tests 
prescribed by this subpart; and
    (4) Conduct a leakage test on each system cylinder-valve assembly 
in accordance with subsections 57.1 through 57.4.2 of UL 2166 
(incorporated by reference, see 46 CFR 162.161-2) for halocarbon 
systems or subsection 55.4 of UL 2127 (incorporated by reference, see 
46 CFR 162.161-2) for inert gas systems.


Sec.  162.161-8  Marking.

    The following information must be displayed on a permanent metal or 
pressure-sensitive nameplate attached to each agent storage cylinder/
valve assembly:
    (a) Manufacturer's name, address, and telephone number;
    (b) Coast Guard approval number assigned to the system under 46 CFR 
159.005-13;
    (c) Identifying mark of the laboratory;
    (d) Reference to the laboratory's listing standard;
    (e) Type extinguishing agent;
    (f) Operating pressure at 70[deg] Fahrenheit;
    (g) Storage temperature range;
    (h) Factory test pressure of the cylinder;
    (i) Reference to the manufacturer's marine design, installation, 
operation, and maintenance manual;
    (j) Weight of agent charge and gross weight of cylinder/valve 
assembly;
    (k) Minimum maintenance instructions; and
    (l) Any other information required by the laboratory or another 
government agency.


Sec.  162.161-9  Procedure for approval.

    (a) Preapproval review is required as detailed in 46 CFR 159.005-5 
and 159.005-7.
    (b) Applications for approval must be submitted in accordance with 
46 CFR 159.005-9 through 159.005-12 to the Commandant (CG-5214). In 
addition to the listed requirements:
    (1) Evidence must be shown that an acceptable follow-up factory 
inspection program is in place in each factory location. This could be 
demonstrated by providing an original copy of the contract for a 
follow-up program between the manufacturer and the independent 
laboratory. The follow-up program must include provisions that prohibit 
changes to the approved equipment without review and approval by the 
independent laboratory.
    (2) Two design, installation, operation and maintenance manuals 
must be submitted.

PART 167--PUBLIC NAUTICAL SCHOOL SHIPS

    82. The authority citation for Part 167 continues to read as 
follows:

    Authority: 46 U.S.C. 3306, 3307, 6101, 8105; E.O. 12234, 45 FR 
58801, 3 CFR, 1980 Comp., p. 277; Department of Homeland Security 
Delegation No. 0170.1.

    83. Amend Sec.  167.45-1(a)(3), (a)(7), (a)(8), and (a)(9) to read 
as follows:


Sec.  167.45-1  Steam, carbon dioxide, Halon 1301, and clean agent fire 
extinguishing systems.

    (a) * * *
    (3) Cabinets, boxes, or casings enclosing manifolds or valves must 
be marked in conspicuous red letters at least 2 inches high: ``[STEAM/
CARBON DIOXIDE/HALON/CLEAN AGENT--as appropriate] FIRE APPARATUS.''
* * * * *
    (7) At annual inspections, each carbon dioxide cylinder, whether 
fixed or portable, each Halon 1301 cylinder, and each clean agent 
cylinder must be examined externally and replaced if excessive 
corrosion is found; and:
    (i) Each carbon dioxide cylinder must be weighed and recharged if 
its weight loss exceeds 10% of the charge;
    (ii) Each Halon 1301 and halocarbon cylinder must be weighed and 
checked, and recharged or replaced if weight loss exceeds 5% of 
required weight of charge or if cylinder pressure loss exceeds 10% of 
specified gauge pressure adjusted for temperature; and
    (iii) Each inert gas cylinder must be checked and recharged or 
replaced if cylinder pressure loss exceeds 5% of specified gauge 
pressure adjusted for temperature.
    (8) Carbon dioxide, Halon 1301, and clean agent cylinders carried 
on board nautical school ships must be tested and marked in accordance 
with the requirements of 46 CFR 147.60, 147.65, 147.66, and 147.67.
    (9) On all systems test time delays, alarms, and ventilation 
shutdowns with carbon dioxide, nitrogen, or other nonflammable gas as 
stated in the system manufacturer's instruction

[[Page 8454]]

manual. Inspect hoses for damage or decay. Ensure that nozzles are 
unobstructed.
* * * * *
    84. In Sec.  167.45-45, add new paragraphs (d) and (e) to read as 
follows:


Sec.  167.45-45  Carbon dioxide fire extinguishing system requirements.

* * * * *
    (d) Lockout valve. (1) A lockout valve must be provided on any 
carbon dioxide extinguishing system protecting a space over 6,000 cubic 
feet in volume or a space 6,000 cubic feet or less in volume that does 
not have a horizontal escape.
    (2) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (3) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (4) A valve is considered a lockout valve if it has a hasp or other 
means of attachment to which, or through which, a lock can be affixed, 
or it has a locking mechanism built into it.
    (5) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (6) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (7) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    (e)(1) Each carbon dioxide extinguishing system must have an 
approved odorizing unit to produce the scent of wintergreen, the 
detection of which will serve as an indication that carbon dioxide gas 
is present in a protected area and any other area into which the carbon 
dioxide may migrate.
    (2) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].
    85. Revise Sec.  167.55-5(c) to read as follows:


Sec.  167.55-5  Marking of fire and emergency equipment.

* * * * *
    (c)(1) Steam, foam, carbon dioxide, Halon, or clean agent fire 
smothering apparatus. Steam, foam, carbon dioxide, Halon, or clean 
agent fire smothering apparatus must be marked ``[STEAM/FOAM/CARBON 
DIOXIDE/HALON/CLEAN AGENT--as appropriate] FIRE APPARATUS,'' in red 
letters at least 2 inches high, and the valves of all branch piping 
leading to the several compartments must be distinctly marked to 
indicate the compartments or parts of the nautical school ship to which 
they lead.
    (2) Each entrance to a space storing carbon dioxide cylinders, a 
space protected by carbon dioxide systems, or any space into which 
carbon dioxide might migrate must be conspicuously marked as follows:
    (i) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (ii) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK[dash]OUT SYSTEM WHEN 
SERVICING.''
    (iii) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
* * * * *

PART 169--SAILING SCHOOL VESSELS

    86. The authority citation for Part 169 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 3306, 6101; Pub. L. 103-
206, 107 Stat. 2439; E.O. 11735, 38 FR 21243, 3 CFR, 1971-1975 
Comp., p. 793; Department of Homeland Security Delegation No. 
0170.1; Sec.  169.117 also issued under the authority of 44 U.S.C. 
3507.

    87. In Sec.  169.247, revise Table 169.247(a)(2) and add and 
reserve paragraph (b) to read as follows:


Sec.  169.247  Firefighting equipment.

* * * * *

                   Table 169.247(a)(2)--Fixed Systems
------------------------------------------------------------------------
         Type system                              Test
------------------------------------------------------------------------
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.
Halon 1301 or halocarbon.....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge or if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                                Note that Halon 1301 system approvals
                                have expired, but that existing systems
                                may be retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Inert gas....................  Recharge or replace recharge or replace
                                cylinder if cylinder pressure loss
                                exceeds 5% of specified gauge pressure,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                on fixed inert extinguishers must be
                                tested or renewed as required by 46 CFR
                                147.60 and 147.66.
Water mist...................  Maintain system in accordance with the
                                maintenance instructions in the system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------


[[Page 8455]]

    (b) [Reserved].
    88. Revise Sec.  169.564 to read as follows:


Sec.  169.564  Fixed extinguishing system, general.

    (a) A fixed carbon dioxide, Halon 1301, or clean agent 
extinguishing system must be installed to protect the following spaces:
    (1) Any vessel machinery or fuel tank space, except where the space 
is so open to the atmosphere as to make the use of a fixed system 
ineffective;
    (2) Any paint or oil room or similar hazardous space; and
    (3) Any galley stove area on a vessel greater than 90 feet in 
length and certificated for exposed or partially protected water 
service.
    (b) Each fixed extinguishing system must be of an approved carbon 
dioxide, Halon 1301, halogenated, or clean agent type and installed to 
the satisfaction of the Officer in Charge, Marine Inspection.
    89. Add a new Sec.  169.570 to read as follows:


Sec.  169.570  Lockout valves.

    (a) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (b) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (c) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (d) A valve is considered a lockout valve if it has a hasp or other 
means of attachment to which, or through which, a lock can be affixed, 
or it has a locking mechanism built into it.
    (e) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (f) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (g) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    90. Add a new Sec.  169.571 to read as follows:


Sec.  169.571  Olfactory additives.

    (a) Each carbon dioxide extinguishing system must have an approved 
odorizing unit to produce the scent of wintergreen, the detection of 
which will serve as an indication that carbon dioxide gas is present in 
a protected area and any other area into which the carbon dioxide may 
migrate.
    (b) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].
    91. Revise Sec.  169.732 to read as follows:


Sec.  169.732  Carbon dioxide and clean agent alarms.

    (a) Each carbon dioxide or clean agent fire extinguishing alarm 
must be conspicuously marked: ``WHEN ALARM SOUNDS VACATE AT ONCE. 
CARBON DIOXIDE OR CLEAN AGENT BEING RELEASED.''
    (b) Each entrance to a space storing carbon dioxide cylinders, a 
space protected by carbon dioxide systems, or any space into which 
carbon dioxide might migrate must be conspicuously marked as follows:
    (1) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (2) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK[dash]OUT SYSTEM WHEN 
SERVICING.''
    (3) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
    92. Revise Sec.  169.734 to read as follows:


Sec.  169.734  Fire extinguishing system controls.

    Each control cabinet or space containing valves or manifolds for 
the various fire extinguishing systems must be distinctly marked in 
conspicuous red letters at least 2 inches high: ``CARBON DIOXIDE FIRE 
EXTINGUISHING SYSTEM,'' ``HALON EXTINGUISHING SYSTEM,'' or ``CLEAN 
AGENT EXTINGUISHING SYSTEM,'' as appropriate.

PART 176--INSPECTION AND CERTIFICATION

    93. The authority citation for Part 176 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2103, 3205, 3306, 3307; 
49 U.S.C. App. 1804; E.O. 11735, 38 FR 21243, 3 CFR, 1971-1975 
Comp., p. 743; E.O. 12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 277; 
Department of Homeland Security Delegation No. 0170.1

    94. Revise Sec.  176.810(b)(2) to read as follows:


Sec.  176.810  Fire protection.

* * * * *
    (b) * * *
    (2) For semiportable and fixed gas fire extinguishing systems, the 
inspections and tests required by Table 176.810(b)(2), in addition to 
the tests required by 46 CFR 147.60, 147.65, 147.66, and 147.67. The 
owner or managing operator must provide satisfactory evidence of the 
required servicing to the marine inspector. If any equipment or record 
has not been properly maintained, a qualified servicing facility may be 
required to perform the required inspections, maintenance procedures, 
and hydrostatic pressure tests.

 Table 176.810(b)(2)--Semiportable and Fixed Fire Extinguishing Systems
------------------------------------------------------------------------
         Type system                              Test
------------------------------------------------------------------------
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.

[[Page 8456]]

 
Halon 1301 and halocarbon....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge or if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                                Note that Halon 1301 system approvals
                                have expired, but that existing systems
                                may be retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Dry chemical (cartridge        Examine pressure cartridge and replace if
 operated).                     end is punctured or if determined to
                                have leaked or to be in unsuitable
                                condition. Inspect hose and nozzle to
                                see if they are clear. Insert charged
                                cartridge. Ensure dry chemical is free
                                flowing (not caked) and extinguisher
                                contains full charge.
Dry chemical (stored           See that pressure gauge is in operating
 pressure).                     range. If not, or if the seal is broken,
                                weigh or otherwise determine that
                                extinguisher is fully charged with dry
                                chemical. Recharge if pressure is low or
                                if dry chemical is needed.
Foam (stored pressure).......  See that any pressure gauge is in the
                                operating range. If not, or if the seal
                                is broken, weigh or otherwise determine
                                that extinguisher is fully charged with
                                foam. Recharge if pressure is low or if
                                foam is needed. Replace premixed agent
                                every 3 years.
Inert gas....................  Recharge or replace cylinder if cylinder
                                pressure loss exceeds 5% of specified
                                gauge pressure, adjusted for
                                temperature. Test time delays, alarms,
                                and ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed inert
                                extinguishers must be tested or renewed
                                as required by 46 CFR 147.60 and 147.66.
Water mist...................  Maintain system in accordance with the
                                maintenance instructions in the system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------

* * * * *

PART 181--FIRE PROTECTION EQUIPMENT

    95. The authority citation for Part 181 continues to read as 
follows:

    Authority: 46 U.S.C. 2103, 3306; E.O. 12234, 45 FR 58801, 3 CFR, 
1980 Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    96. Amend Sec.  181.410, to revise paragraph (c)(7) and add 
paragraphs (f)(7) to (15) to read as follows:


Sec.  181.410  Fixed gas fire extinguishing systems.

* * * * *
    (c) * * *
    (7) A Halon 1301 storage cylinder must be stowed in an upright 
position unless otherwise listed by the independent laboratory. A 
carbon dioxide cylinder may not be inclined more than 30[deg] from the 
vertical unless fitted with flexible or bent siphon tubes, in which 
case it may be inclined not more than 80[deg] from the vertical. 
Cylinders for clean agent systems must be installed in an upright 
position unless otherwise specified in the system's instruction manual.
* * * * *
    (f) * * *
    (7) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (8) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (9) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (10) A valve is considered a lockout valve if it has a hasp or 
other means of attachment to which, or through which, a lock can be 
affixed, or it has a locking mechanism built into it.
    (11) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (12) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (13) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    (14) Each carbon dioxide extinguishing system must have an approved 
odorizing unit to produce the scent of wintergreen, the detection of 
which will serve as an indication that carbon dioxide gas is present in 
a protected area and any other area into which the carbon dioxide may 
migrate.
    (15) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].
* * * * *

PART 182--MACHINERY INSTALLATION

    97. The authority citation for Part 182 continues to read as 
follows:


    Authority: 46 U.S.C. 3306; E.O. 12234, 45 FR 58801, 3 CFR, 1980 
Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    98. Revise Sec.  182.710(a)(3) to read as follows:


Sec.  182.710  Piping for vital systems.

    (a) * * *
    (3) Carbon dioxide, Halon 1301, and clean agent systems;
* * * * *

PART 185--OPERATIONS

    99. The authority citation for Part 185 continues to read as 
follows:

    Authority: 46 U.S.C. 2103, 3306, 6101; E.O. 12234, 45 FR 58801, 
3 CFR, 1980 Comp., p. 277; Department of Homeland Security 
Delegation No. 0170.1.

    100. Amend Sec.  185.612, to revise paragraph (f) and to add a 
paragraph (g) to read as follows:


Sec.  185.612  Fire protection equipment.

* * * * *
    (f) The control cabinets or spaces containing valves, manifolds or 
controls for the various fire extinguishing

[[Page 8457]]

systems must be marked in conspicuous red letters at least 2 inches 
high: ``[STEAM/CARBON DIOXIDE/CLEAN AGENT/FOAM/WATER SPRAY--as 
appropriate] FIRE APPARATUS.''
    (g) Each entrance to a space storing carbon dioxide cylinders, a 
space protected by carbon dioxide systems, or any space into which 
carbon dioxide might migrate must be conspicuously marked as follows:
    (1) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (2) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK-OUT SYSTEM WHEN 
SERVICING.''
    (3) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''

PART 189--INSPECTION AND CERTIFICATION

    101. The authority citation for Part 189 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2113, 3306, 3307; E.O. 
12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 277; E.O. 12777, 56 FR 
54757, 3 CFR, 1991 Comp., p. 351; Department of Homeland Security 
Delegation No. 0170.1.

    102. In Sec.  189.25-20, revise the section heading and Table 
189.25-20(a)(2) to read as follows:


Sec.  189.25-20  Fire extinguishing equipment.

* * * * *

                          Table 189.25-20(a)(2)
------------------------------------------------------------------------
         Type system                              Test
------------------------------------------------------------------------
Foam.........................  Systems utilizing a soda solution must
                                have such solution replaced. In all
                                cases, ascertain that powder is not
                                caked.
Carbon dioxide...............  Weigh cylinders. Recharge cylinder if
                                weight loss exceeds 10% of weight of
                                charge. Test time delays, alarms, and
                                ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed carbon
                                dioxide systems must be tested or
                                renewed, as required by 46 CFR 147.60
                                and 147.65.
Halon 1301 or halocarbon.....  Recharge or replace if weight loss
                                exceeds 5% of weight of charge or if
                                cylinder has a pressure gauge, recharge
                                cylinder if pressure loss exceeds 10%,
                                adjusted for temperature. Test time
                                delays, alarms, and ventilation
                                shutdowns with carbon dioxide, nitrogen,
                                or other nonflammable gas as stated in
                                the system manufacturer's instruction
                                manual. Inspect hoses for damage or
                                decay. Ensure that nozzles are
                                unobstructed. Cylinders must be tested
                                and marked, and all flexible connections
                                to Halon 1301 and halocarbon cylinders
                                must be tested or renewed, as required
                                by 46 CFR 147.60 and 147.65 or 147.67.
                                Note that Halon 1301 system approvals
                                have expired, but that existing systems
                                may be retained if they are in good and
                                serviceable condition to the
                                satisfaction of the Coast Guard
                                inspector.
Inert gas....................  Recharge or replace cylinder if cylinder
                                pressure loss exceeds 5% of specified
                                gauge pressure, adjusted for
                                temperature. Test time delays, alarms,
                                and ventilation shutdowns with carbon
                                dioxide, nitrogen, or other nonflammable
                                gas as stated in the system
                                manufacturer's instruction manual.
                                Inspect hoses for damage or decay.
                                Ensure that nozzles are unobstructed.
                                Cylinders must be tested and marked, and
                                all flexible connections on fixed inert
                                extinguishers must be tested or renewed
                                as required by 46 CFR 147.60 and 147.66.
Water mist...................  Maintain system in accordance with the
                                maintenance instructions in the system
                                manufacturer's design, installation,
                                operation, and maintenance manual.
------------------------------------------------------------------------

* * * * *
    103. Revise Sec.  189.55-5(d)(4) to read as follows:


Sec.  189.55-5  Plans and specifications required for new construction.

* * * * *
    (d) * * *
    (4) Details of extinguishing systems, including fire mains, carbon 
dioxide, clean agent, foam, and sprinkling systems.
* * * * *

PART 190--CONSTRUCTION AND ARRANGEMENT

    104. The authority citation for Part 190 continues to read as 
follows:

    Authority: 46 U.S.C. 2113, 3306; E.O. 12234, 45 FR 58801, 3 CFR, 
1980 Comp., p. 277; Department of Homeland Security Delegation No. 
0170.1.

    105. Revise Sec.  190.15-5(i) to read as follows:


Sec.  190.15-5  Vessels using fuel having a flashpoint of 110 [deg]F or 
lower.

* * * * *
    (i) Provisions must be made for closing all cowls or scoops when 
the fixed carbon dioxide or clean agent system is operated.

PART 193--FIRE PROTECTION EQUIPMENT

    106. The authority citation for Part 193 continues to read as 
follows:

    Authority: 46 U.S.C. 2213, 3102, 3306; E.O. 12234, 45 FR 58801, 
3 CFR, 1980 Comp., p. 277; Department of Homeland Security 
Delegation No. 0170.1.

    107. Revise Sec.  193.05-10 to read as follows:


Sec.  193.05-10  Fixed fire extinguishing systems.

    (a) Approved fire extinguishing systems must be installed in all 
lamp and paint lockers, oil rooms, and similar spaces.
    (b) A fixed carbon dioxide or clean agent fire extinguishing system 
complying with 46 CFR subparts 95.15 and 95.16 must be installed for:
    (1) Internal combustion engine installations;
    (2) Gas turbine installations;
    (3) Enclosed spaces containing gasoline engines;
    (4) Chemical storerooms;
    (5) Any space containing auxiliaries with an aggregate power of 
1,000 brake horsepower (b.h.p.) or greater, or their fuel oil units, 
including purifiers, valves, and manifolds, on vessels of 1,000 gross 
tons and over; and

[[Page 8458]]

    (6) Enclosed ventilating systems installed for electric propulsion 
motors or generators.
    (c) On vessels of 1,000 gross tons and over, a fixed carbon dioxide 
or clean agent fire extinguishing system complying with 46 CFR subparts 
95.15 and 95.16 or a foam system complying with 46 CFR subpart 95.17 
must be installed for any space containing main or auxiliary oil fired 
boilers or their associated fuel oil units, valves, or manifolds in the 
line between the settling tanks and the boilers.
    (d) Systems for spaces containing explosives and other dangerous 
articles or substances must also comply with 46 CFR Part 194.
    108. In Sec.  193.10-5, revise the section heading and paragraph 
(h) to read as follows:


Sec.  193.10-5  Fire main system, details.

* * * * *
    (h) On vessels with main or auxiliary oil fired boilers or vessels 
with internal combustion propulsion machinery, when two fire pumps are 
required, the boilers or machinery must be located in separate spaces, 
and the arrangement, pumps, sea connections, and sources of power must 
be such as to ensure that a fire in any one space will not put all of 
the fire pumps out of operation. However, when it is shown to the 
satisfaction of the Commandant that it is unreasonable or impracticable 
to meet this requirement due to the size or arrangement of the vessel, 
or for other reasons, the installation of a total flooding system using 
carbon dioxide or a clean agent complying with 46 CFR subpart 95.16 may 
be accepted as an alternate method of extinguishing any fire that could 
affect the powering and operation for the required fire pumps.
* * * * *
    109. Revise the heading to subpart 193.15 to read as follows:

Subpart 193.15--Carbon Dioxide and Clean Agent Extinguishing 
Systems, Details

    110. Add a new Sec.  193.15-16 to read as follows:


Sec.  193.15-16  Lockout valves.

    (a) A lockout valve must be provided on any carbon dioxide 
extinguishing system protecting a space over 6,000 cubic feet in volume 
or a space 6,000 cubic feet or less in volume that does not have a 
horizontal escape.
    (b) The lockout valve must be a manually operated valve located in 
the discharge manifold prior to the stop valve or selector valves. When 
in the closed position, the lockout valve must provide complete 
isolation of the system from the protected space or spaces, making it 
impossible for carbon dioxide to discharge in the event of equipment 
failure during maintenance.
    (c) The lockout valve design or locking mechanism must make it 
obvious whether the valve is open or closed.
    (d) A valve is considered a lockout valve if it has a hasp or other 
means of attachment to which, or through which, a lock can be affixed, 
or it has a locking mechanism built into it.
    (e) The lockout valve must be locked in the closed position 
whenever maintenance is performed on the extinguishing system. The 
master must ensure that the lockout valve is locked in the open 
position when maintenance is complete and the system is returned to 
operable condition.
    (f) Lockout valves added to existing systems must be approved by 
the Commandant for use in the system.
    (g) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the lockout valve requirements of this section not later than 
[DATE 5 YEARS AFTER EFFECTIVE DATE OF RULE].
    111. Add a new Sec.  193.15-17 to read as follows:


Sec.  193.15-17  Olfactory additives.

    (a) Each carbon dioxide extinguishing system must have an approved 
odorizing unit to produce the scent of wintergreen, the detection of 
which will serve as an indication that carbon dioxide gas is present in 
a protected area and any other area into which the carbon dioxide may 
migrate.
    (b) Vessels in operation on [EFFECTIVE DATE OF RULE] must comply 
with the requirements of this section not later than [DATE 5 YEARS 
AFTER EFFECTIVE DATE OF RULE].
    112. Add a new Sec.  193.15-50 to read as follows:


Sec.  193.15-50  Clean agent systems.

    A clean agent system complying with 46 CFR subpart 95.16 may be 
used as an alternative to a carbon dioxide fire extinguishing system.

PART 194--HANDLING, USE, AND CONTROL OF EXPLOSIVES AND OTHER 
HAZARDOUS MATERIALS

    113. The authority citation for Part 194 continues to read as 
follows:

    Authority: 46 U.S.C. 2103, 2113, 3306; 49 U.S.C. App. 1804; E.O. 
12234, 45 FR 58801, 3 CFR, 1980 Comp., p. 277; Department of 
Homeland Security Delegation No. 0170.1.

    114. Revise Sec.  194.20-7(a) to read as follows:


Sec.  194.20-7  Fire protection.

    (a) Each chemical storeroom must be protected by a fixed automatic 
extinguishing system using carbon dioxide or a clean agent complying 
with 46 CFR subpart 95.16, installed in accordance with 46 CFR subpart 
193.15.
* * * * *

PART 196--OPERATIONS

    115. The authority citation for Part 196 continues to read as 
follows:

    Authority: 33 U.S.C. 1321(j); 46 U.S.C. 2213, 3306, 5115, 6101; 
E.O. 12777, 56 FR 54757, 3 CFR, 1991 Comp., p. 351; E.O. 12234, 45 
FR 58801, 3 CFR, 1980 Comp., p. 277; Department of Homeland Security 
Delegation No. 0170.1.

    116. Add a new Sec.  196.37-8 to read as follows:


Sec.  196.37-8  Carbon dioxide warnings.

    Each entrance to a space storing carbon dioxide cylinders, a space 
protected by carbon dioxide systems, or any space into which carbon 
dioxide might migrate must be conspicuously marked as follows:
    (a) Spaces storing carbon dioxide--``CARBON DIOXIDE GAS CAN CAUSE 
INJURY OR DEATH. VENTILATE THE AREA BEFORE ENTERING. A HIGH 
CONCENTRATION CAN OCCUR IN THIS AREA AND CAN CAUSE SUFFOCATION.''
    (b) Spaces protected by carbon dioxide--``CARBON DIOXIDE GAS CAN 
CAUSE INJURY OR DEATH. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS 
DETECTED, DO NOT ENTER UNTIL VENTILATED. LOCK[dash]OUT SYSTEM WHEN 
SERVICING.''
    (c) Spaces into which carbon dioxide might migrate--``CARBON 
DIOXIDE GAS CAN CAUSE INJURY OR DEATH. DISCHARGE INTO NEARBY SPACE CAN 
COLLECT HERE. WHEN ALARM OPERATES OR WINTERGREEN SCENT IS DETECTED 
VACATE IMMEDIATELY.''
    117. Revise Sec.  196.37-9 to read as follows:


Sec.  196.37-9  Carbon dioxide and clean agent alarms.

    Each extinguishing system using carbon dioxide or clean agent 
complying with 46 CFR subpart 95.16 must be conspicuously marked in an 
adjacent location: ``WHEN ALARM SOUNDS VACATE AT ONCE. CARBON DIOXIDE 
OR CLEAN AGENT BEING RELEASED.''
    118. Revise Sec.  196.37-13 to read as follows:

[[Page 8459]]

Sec.  196.37-13  Fire extinguishing system controls.

    The control cabinets or spaces containing valves, manifolds or 
controls for the various fire extinguishing systems must be marked in 
conspicuous red letters at least 2 inches high: ``[CARBON DIOXIDE/CLEAN 
AGENT/FOAM--as appropriate] FIRE APPARATUS.''

    Dated: February 12, 2010.
J.G. Lantz,
Director of Commercial Regulations and Standards.
[FR Doc. 2010-3094 Filed 2-23-10; 8:45 am]
BILLING CODE 9110-04-P