[Federal Register Volume 73, Number 251 (Wednesday, December 31, 2008)]
[Notices]
[Pages 80437-80440]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: E8-31163]


=======================================================================
-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION

[Docket No. 50-499]


STP Nuclear Operating Company Notice of Consideration of Issuance 
of Amendment to Facility Operating License, Proposed No Significant 
Hazards Consideration Determination, and Opportunity for a Hearing

    The U.S. Nuclear Regulatory Commission (the Commission) is 
considering issuance of an amendment to Facility Operating License No. 
NPF-80, issued to STP Nuclear Operating Company (the licensee), for 
operation of the South Texas Project (STP), Unit 2, located in 
Matagorda County, Texas.
    The proposed amendment would extend the Allowed Outage Time (AOT) 
for Technical Specification (TS) 3.7.1.7, ``Main Feedwater System.'' 
This AOT extension is requested to facilitate repairs to the Unit 2 
Train D Main Feedwater Isolation Valve (MFIV).
    The Action Statement for TS 3.7.1.7 requires that, with one MFIV 
inoperable in MODES 1 and 2 but open, operation may continue provided 
the inoperable valve is restored to OPERABLE status within 4 hours; 
otherwise, the Unit must be placed in HOT STANDBY within the next 6 
hours. There is no action required for an inoperable MFIV that is 
closed.
    The Unit 2 Train D MFIV is currently operable, but degraded. The 
degraded condition is a nitrogen leak of the tubing to the valve 
accumulator. Temporary repairs have reduced the tube leak such that 
operator action is maintaining the nitrogen accumulator pressure, 
assuring the MFIV operability. The licensee states that, although these 
actions are sufficient at the present time, it is

[[Page 80438]]

unknown if the leak will degrade to a point where operator action would 
not be able to assure operability of the Unit 2 Train D MFIV. In that 
case, Unit 2 must be shut down in accordance with the Action Statement.
    The licensee has proposed to repair the Unit 2 Train D MFIV 
nitrogen tubing. The licensee estimates that the repair of the tubing 
leak will render the MFIV inoperable for approximately 8 hours, which 
exceeds the 4-hour AOT. Therefore, the licensee requests a one-time 
extension of AOT to 24 hours to permit repair of the MFIV valve without 
shutting the Unit down. The licensee requests that the amendment be 
approved on an exigent basis to assure that further degradation of the 
Unit 2 Train D MFIV will not result in a Unit shutdown.
    Before issuance of the proposed license amendment, the Commission 
will have made findings required by the Atomic Energy Act of 1954, as 
amended (the Act) and the Commission's regulations.
    Pursuant to 10 CFR 50.91(a)(6) for amendments to be granted under 
exigent circumstances, the NRC staff must determine that the amendment 
request involves no significant hazards consideration. Under the 
Commission's regulations in 10 CFR 50.92, this means that operation of 
the facility in accordance with the proposed amendment would not (1) 
involve a significant increase in the probability or consequences of an 
accident previously evaluated; or (2) create the possibility of a new 
or different kind of accident from any accident previously evaluated; 
or (3) involve a significant reduction in a margin of safety. As 
required by 10 CFR 50.91(a), the licensee has provided its analysis of 
the issue of no significant hazards consideration, which is presented 
below:

    1. Does the proposed change involve a significant increase in 
the probability or consequences of an accident previously evaluated?
    Response:
    No. The proposed change extends the action completion time for 
Unit 2 Train D MFIV from 4 hours to 24 hours. Extending the 
completion time is not an accident initiator and thus does not 
change the probability that an accident will occur. However, it 
could potentially affect the consequences of an accident if an 
accident occurred during the extended unavailability of the [ MFIV, 
which is inoperable]. The increase in time, that the MFIV is 
unavailable, is small and the probability of an event occurring 
during this time period, which would require isolation of the main 
feedwater flow paths, is low.
    Therefore, the proposed change does not involve a significant 
increase in the probability or consequences of an accident 
previously evaluated.
    2. Does the proposed change create the possibility of a new or 
different kind of accident from any accident previously evaluated?
    Response:
    No. The proposed change does not involve any physical alteration 
of plant equipment and does not change the method by which any 
safety-related structure, system, or component performs its function 
or is tested. Closure of the MFIVs is required to mitigate the 
consequences of the Main Steam Line Break and Main Feedwater Line 
Break accidents.
    Therefore, the proposed change will not create the possibility 
of a new or different kind of accident from any accident previously 
evaluated.
    3. Does the proposed change involve a significant reduction in a 
margin of safety?
    Response:
    No. The proposed change [ ] does not adversely affect existing 
plant safety margins or the reliability of the equipment assumed to 
operate in the safety analysis. There are no changes being made to 
safety analysis assumptions, safety limits or safety system settings 
that would adversely affect plant safety [margins] as a result of 
the proposed change.
    Therefore, the proposed change does not involve a significant 
reduction in a margin of safety.

    The NRC staff has reviewed the licensee's analysis and, based on 
this review, it appears that the three standards of 10 CFR 50.92(c) are 
satisfied. Therefore, the NRC staff proposes to determine that the 
amendment request involves no significant hazards consideration.
    The Commission is seeking public comments on this proposed 
determination. Any comments received within 14 days after the date of 
publication of this notice will be considered in making any final 
determination.
    Normally, the Commission will not issue the amendment until the 
expiration of the 14-day notice period. However, should circumstances 
change during the notice period, such that failure to act in a timely 
way would result, for example, in derating or shutdown of the facility, 
the Commission may issue the license amendment before the expiration of 
the 14-day notice period, provided that its final determination is that 
the amendment involves no significant hazards consideration. The final 
determination will consider all public and State comments received. 
Should the Commission take this action, it will publish in the Federal 
Register a notice of issuance. The Commission expects that the need to 
take this action will occur very infrequently.
    Written comments may be submitted by mail to the Chief, Rulemaking, 
Directives and Editing Branch, TWB-05-B01M, Division of Administrative 
Services, Office of Administration, U.S. Nuclear Regulatory Commission, 
Washington, DC 20555-0001, and should cite the publication date and 
page number of this Federal Register notice. Documents may be examined, 
and/or copied for a fee, at the NRC's Public Document Room, located at 
One White Flint North, Public File Area O1 F21, 11555 Rockville Pike 
(first floor), Rockville, Maryland.
    The filing of requests for hearing and petitions for leave to 
intervene is discussed below.
    Within 60 days after the date of publication of this notice, the 
person(s) may file a request for a hearing with respect to issuance of 
the amendment to the subject facility operating license and any 
person(s) whose interest may be affected by this proceeding and who 
wishes to participate as a party in the proceeding must file a written 
request via electronic submission through the NRC E-filing system for a 
hearing and a petition for leave to intervene. Requests for a hearing 
and a petition for leave to intervene shall be filed in accordance with 
the Commission's ``Rules of Practice for Domestic Licensing 
Proceedings'' in 10 CFR Part 2. Interested person(s) should consult a 
current copy of 10 CFR 2.309, which is available at the Commission's 
PDR, located at One White Flint North, Public File Area O1F21, 11555 
Rockville Pike (first floor), Rockville, Maryland. Publicly available 
records will be accessible from the Agencywide Documents Access and 
Management System's (ADAMS) Public Electronic Reading Room on the 
Internet at the NRC Web site, http://www.nrc.gov/reading-rm/doc-collections/cfr. If a request for a hearing or petition for leave to 
intervene is filed by the above date, the Commission or a presiding 
officer designated by the Commission or by the Chief Administrative 
Judge of the Atomic Safety and Licensing Board Panel, will rule on the 
request and/or petition; and the Secretary or the Chief Administrative 
Judge of the Atomic Safety and Licensing Board will issue a notice of a 
hearing or an appropriate order.
    Each contention must consist of a specific statement of the issue 
of law or fact to be raised or controverted. In addition, the 
petitioner/requestor shall provide a brief explanation of the bases for 
the contention and a concise statement of the alleged facts or expert 
opinion which support the contention and on which the petitioner 
intends to

[[Page 80439]]

rely in proving the contention at the hearing. The petitioner/requestor 
must also provide references to those specific sources and documents of 
which the petitioner/requestor is aware and on which the petitioner/
requestor intends to rely to establish those facts or expert opinion. 
The petitioner/requestor must provide sufficient information to show 
that a genuine dispute exists with the applicant on a material issue of 
law or fact. Contentions shall be limited to matters within the scope 
of the amendment under consideration. The contention must be one which, 
if proven, would entitle the petitioner/requestor to relief. A 
petitioner/requestor who fails to satisfy these requirements with 
respect to at least one contention will not be permitted to participate 
as a party.
    Those permitted to intervene become parties to the proceeding, 
subject to any limitations in the order granting leave to intervene, 
and have the opportunity to participate fully in the conduct of the 
hearing.
    If a hearing is requested, the Commission will make a final 
determination on the issue of no significant hazards consideration. The 
final determination will serve to decide when the hearing is held. If 
the final determination is that the amendment request involves no 
significant hazards consideration, the Commission may issue the 
amendment and make it immediately effective, notwithstanding the 
request for a hearing. Any hearing held would take place after issuance 
of the amendment. If the final determination is that the amendment 
request involves a significant hazards consideration, any hearing held 
would take place before the issuance of any amendment.
    All documents filed in NRC adjudicatory proceedings, including a 
request for hearing, a petition for leave to intervene, any motion or 
other document filed in the proceeding prior to the submission of a 
request for hearing or petition to intervene, and documents filed by 
interested governmental entities participating under 10 CFR 2.315(c), 
must be filed in accordance with the NRC E-Filing rule, which the NRC 
promulgated on August 28, 2007 (72 FR 49139). The E-Filing process 
requires participants to submit and serve all adjudicatory documents 
over the internet, or in some cases to mail copies on electronic 
storage media. Participants may not submit paper copies of their 
filings unless they seek a waiver in accordance with the procedures 
described below.
    To comply with the procedural requirements of E-Filing, at least 
ten (10) days prior to the filing deadline, the petitioner/requestor 
must contact the Office of the Secretary by e-mail at 
[email protected], or by calling (301) 415-1677, to request (1) a 
digital ID certificate, which allows the participant (or its counsel or 
representative) to digitally sign documents and access the E-Submittal 
server for any proceeding in which it is participating; and/or (2) 
creation of an electronic docket for the proceeding (even in instances 
in which the petitioner/requestor (or its counsel or representative) 
already holds an NRC-issued digital ID certificate). Each petitioner/
requestor will need to download the Workplace Forms ViewerTM 
to access the Electronic Information Exchange (EIE), a component of the 
E-Filing system. The Workplace Forms ViewerTM is free and is 
available at http://www.nrc.gov/site-help/e-submittals/install-viewer.html. Information about applying for a digital ID certificate is 
available on NRC's public Web site at http://www.nrc.gov/site-help/e-submittals/apply-certificates.html.
    Once a petitioner/requestor has obtained a digital ID certificate, 
had a docket created, and downloaded the EIE viewer, it can then submit 
a request for hearing or petition for leave to intervene. Submissions 
should be in Portable Document Format (PDF) in accordance with NRC 
guidance available on the NRC public Web site at http://www.nrc.gov/site-help/e-submittals.html. A filing is considered complete at the 
time the filer submits its documents through EIE. To be timely, an 
electronic filing must be submitted to the EIE system no later than 
11:59 p.m. Eastern Time on the due date. Upon receipt of a 
transmission, the E-Filing system time-stamps the document and sends 
the submitter an e-mail notice confirming receipt of the document. The 
EIE system also distributes an e-mail notice that provides access to 
the document to the NRC Office of the General Counsel and any others 
who have advised the Office of the Secretary that they wish to 
participate in the proceeding, so that the filer need not serve the 
documents on those participants separately. Therefore, applicants and 
other participants (or their counsel or representative) must apply for 
and receive a digital ID certificate before a hearing request/petition 
to intervene is filed so that they can obtain access to the document 
via the E-Filing system.
    A person filing electronically may seek assistance through the 
``Contact Us'' link located on the NRC Web site at http://www.nrc.gov/site-help/e-submittals.html or by calling the NRC electronic filing 
Help Desk, which is available between 8 a.m. and 8 p.m., Eastern Time, 
Monday through Friday. The electronic filing Help Desk can be contacted 
by telephone at 1-866-672-7640 or by e-mail at [email protected].
    Participants who believe that they have a good cause for not 
submitting documents electronically must file a motion, in accordance 
with 10 CFR 2.302(g), with their initial paper filing requesting 
authorization to continue to submit documents in paper format. Such 
filings must be submitted by: (1) First class mail addressed to the 
Office of the Secretary of the Commission, U.S. Nuclear Regulatory 
Commission, Washington, DC 20555-0001, Attention: Rulemaking and 
Adjudications Staff; or (2) courier, express mail, or expedited 
delivery service to the Office of the Secretary, Sixteenth Floor, One 
White Flint North, 11555 Rockville Pike, Rockville, Maryland 20852, 
Attention: Rulemaking and Adjudications Staff. Participants filing a 
document in this manner are responsible for serving the document on all 
other participants. Filing is considered complete by first-class mail 
as of the time of deposit in the mail, or by courier, express mail, or 
expedited delivery service upon depositing the document with the 
provider of the service.
    Documents submitted in adjudicatory proceedings will appear in 
NRC's electronic hearing docket which is available to the public at 
http://ehd.nrc.gov/ehd_proceeding/home.asp, unless excluded pursuant 
to an order of the Commission, an Atomic Safety and Licensing Board, or 
a Presiding Officer. Participants are requested not to include personal 
privacy information, such as social security numbers, home addresses, 
or home phone numbers in their filings. With respect to copyrighted 
works, except for limited excerpts that serve the purpose of the 
adjudicatory filings and would constitute a Fair Use application, 
Participants are requested not to include copyrighted materials in 
their submissions.
    Non-timely requests and/or petitions and contentions will not be 
entertained absent a determination by the Commission, the presiding 
officer, or the Atomic Safety and Licensing Board that the petition 
and/or request should be granted and/or the contentions should be 
admitted, based on a balancing of the factors specified in 10 CFR 
2.309(c)(1)(i)-(viii).
    For further details with respect to this exigent license 
application, see the application for amendment dated December 19, 2008, 
which is available

[[Page 80440]]

for public inspection at the Commission's Public Document Room (PDR), 
located at One White Flint North, Public File Area O1 F21, 11555 
Rockville Pike (first floor), Rockville, Maryland. Publicly available 
records will be accessible electronically from the Agencywide Documents 
Access and Management System's (ADAMS) Public Electronic Reading Room 
on the Internet at the NRC Web site http://www.nrc.gov/reading-rm.html. 
Persons who do not have access to ADAMS or who encounter problems in 
accessing the documents located in ADAMS should contact the NRC PDR 
Reference staff by telephone at 1-800-397-4209, or 301-415-4737, or by 
e-mail to [email protected].

    Dated at Rockville, Maryland, this 23rd day of December 2008.

    For the Nuclear Regulatory Commission.
Mohan C. Thadani,
Senior Project Manager, Plant Licensing Branch LPL IV, Division of 
Operating Reactor Licensing, Office of Nuclear Reactor Regulation.
[FR Doc. E8-31163 Filed 12-30-08; 8:45 am]
BILLING CODE 7590-01-P