[Federal Register Volume 72, Number 50 (Thursday, March 15, 2007)]
[Notices]
[Pages 12223-12227]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: E7-4752]


-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION


Notice of Opportunity To Comment on Model Safety Evaluation and 
Model License Amendment Request on Technical Specification Improvement 
Regarding Relocation of Departure From Nucleate Boiling Parameters to 
the Core Operating Limits Report for Combustion Engineering Pressurized 
Water Reactors Using the Consolidated Line Item Improvement Process

AGENCY: Nuclear Regulatory Commission.

ACTION: Request for comment.

-----------------------------------------------------------------------

SUMMARY: Notice is hereby given that the staff of the U. S. Nuclear 
Regulatory Commission (NRC) has prepared a model license amendment 
request (LAR), model safety evaluation (SE), and model proposed no 
significant hazards consideration (NSHC) determination related to 
changes to Standard Technical Specifications (STSs) for Combustion 
Engineering Pressurized Water Reactors (PWRs), NUREG-1432, Revision 
3.1. This change would allow the numerical limits located in technical 
specification (TS) 3.4.1, ``RCS Pressure, Temperature, and Flow 
[Departure from Nucleate Boiling (DNB)] Limits'' to be replaced with 
references to the Core Operating Limits Report (COLR). Associated 
changes are also included for the TS 3.4.1 Bases, and TS 5.6.3 ``Core 
Operating Limits Report (COLR).'' The Technical Specifications Task 
Force (TSTF) proposed these changes to the TS in TSTF-487 Revision 0, 
``Relocate DNB Parameters to the COLR.''
    The purpose of the model SE, LAR, and NSHC is to permit the NRC to 
efficiently process amendments to incorporate these changes into plant-
specific TSs for Combustion Engineering PWRs. Licensees of nuclear 
power reactors to which the models apply can request amendments 
conforming to the models. In such a request, a licensee should confirm 
the applicability of the model LAR, model SE and NSHC determination to 
its plant. The NRC staff is requesting comments on the model LAR, model 
SE and NSHC determination before announcing their availability for 
referencing in license amendment applications.

DATES: The comment period expires 30 days from the date of this 
publication. Comments received after this date will be considered if it 
is practical to do so, but the Commission is able to ensure 
consideration only for comments received on or before this date.

[[Page 12224]]


ADDRESSES: Comments may be submitted either electronically or via U.S. 
mail.
    Submit written comments to: Chief, Rulemaking, Directives, and 
Editing Branch, Division of Administrative Services, Office of 
Administration, Mail Stop: T-6 D59, U.S. Nuclear Regulatory Commission, 
Washington, DC 20555-0001. Hand deliver comments to: 11545 Rockville 
Pike, Rockville, Maryland 20852, between 7:45 a.m. and 4:15 p.m. on 
Federal workdays. Submit comments by electronic mail to: [email protected].
    Copies of comments received may be examined at the NRC's Public 
Document Room, One White Flint North, Public File Area O1-F21, 11555 
Rockville Pike (first floor), Rockville, Maryland.

FOR FURTHER INFORMATION CONTACT: Ross Telson, Mail Stop: O-12H2, 
Division of Inspection and Regional Support, Office of Nuclear Reactor 
Regulation, U.S. Nuclear Regulatory Commission, Washington, DC 20555-
0001, telephone (301) 415-2256.

SUPPLEMENTARY INFORMATION:

Background

    Regulatory Issue Summary 2000-06, ``Consolidated Line Item 
Improvement Process [CLIIP] for STSs Changes for Power Reactors,'' was 
issued on March 20, 2000. The CLIIP is intended to improve the 
efficiency and transparency of NRC licensing processes. This is 
accomplished by processing proposed changes to the TS in a manner that 
supports subsequent license amendment applications. The CLIIP includes 
an opportunity for the public to comment on proposed changes to the TS 
following a preliminary assessment by the NRC staff and finding that 
the change will likely be offered for adoption by licensees. At the 
conclusion of the notice for comment period the NRC staff will evaluate 
any comments received for the proposed TS change and either reconsider 
the change or proceed with announcing the availability of the change 
for proposed adoption by licensees. Those licensees opting to apply for 
the subject change to TSs are responsible for reviewing the NRC staff's 
evaluation, referencing the applicable technical justifications, and 
providing any necessary plant-specific information. Following the 
public comment period, the model LAR and model SE will be finalized, 
and posted on the NRC web page. Each amendment application made in 
response to the notice of availability will be processed and noticed in 
accordance with applicable NRC rules and procedures.
    This notice involves the replacement of the departure from nucleate 
boiling (DNB) parameter limits in TS 3.4.1 with references to the 
defined formal COLR for the values of these limits. With this 
alternative, reload license amendments for the sole purpose of updating 
the cycle specific DNB parameter limits will be unnecessary. This 
change would allow licensees of Combustion Engineering PWRs to 
recalculate DNB parameter limits in the COLR using NRC-approved 
methodologies. By letter dated June 20, 2005, the TSTF proposed these 
changes for incorporation into the STSs as TSTF-487, Revision 0. These 
changes are based on the NRC Generic Letter 88-16 ``Removal of Cycle-
Specific Parameter Limits from Technical Specifications.'' This 
document is accessible electronically from the Agency-wide Documents 
Access and Management System's (ADAMS) Public Electronic Reading Room 
on the Internet (ADAMS Accession No. ML041830597) at the NRC Web site 
http://www.nrc.gov/reading-rm/adams.html. Persons who do not have 
access to ADAMS or who encounter problems in accessing the documents 
located in ADAMS should contact the NRC Public Document Room Reference 
staff by telephone at 1-800-397-4209, 301-415-4737, or by e-mail to 
[email protected].

Applicability

    These proposed changes will revise LCO 3.4.1, SR 3.4.1, the Bases 
associated with TS 3.4.1, and TS 5.6.3 for Combustion Engineering PWRs. 
To efficiently process the incoming license amendment applications, the 
NRC staff requests that each licensee applying for the changes 
addressed by TSTF-487 Revision 0, using the CLIIP submit an LAR that 
adheres to the following model. Any variations from the model LAR 
should be explained in the licensee's submittal. Variations from the 
approach recommended in this notice may require additional review by 
the NRC staff, and may increase the time and resources needed for the 
review. Significant variations from the approach, or inclusion of 
additional changes to the license, will result in NRC staff rejection 
of the submittal. Instead, licensees desiring significant variations 
and/or additional changes should submit a LAR that does not claim to 
adopt TSTF-487.

Public Notices

    This notice requests comments from interested members of the public 
within 30 days of the date of this publication. Following the NRC 
staff's evaluation of comments received as a result of this notice, the 
NRC staff may reconsider the proposed change or may proceed with 
announcing the availability of the change in a subsequent notice 
(perhaps with some changes to the model LAR, model SE or model NSHC 
determination as a result of public comments). If the NRC staff 
announces the availability of the change, licensees wishing to adopt 
the change will submit an application in accordance with applicable 
rules and other regulatory requirements. The NRC staff will, in turn, 
issue for each application a notice of consideration of issuance of 
amendment to facility operating license(s), a proposed NSHC 
determination, and an opportunity for a hearing. A notice of issuance 
of an amendment to operating license(s) will also be issued to announce 
the revised requirements for each plant that applies for and receives 
the requested change.

    Dated at Rockville, Maryland this 7th day of March, 2007.

    For The Nuclear Regulatory Commission.
Timothy J. Kobetz,
Chief, Technical Specifications Branch, Division of Inspection and 
Regional Support, Office of Nuclear Reactor Regulation.

    FOR INCLUSION ON THE TECHNICAL SPECIFICATION WEB PAGE THE 
FOLLOWING EXAMPLE OF AN APPLICATION WAS PREPARED BY THE NRC STAFF TO 
FACILITATE THE ADOPTION OF TECHNICAL SPECIFICATIONS TASK FORCE 
(TSTF) TRAVELER TSTF-487, REVISION 0 ``RELOCATE DNB PARAMETERS TO 
THE COLR.'' THE MODEL PROVIDES THE EXPECTED LEVEL OF DETAIL AND 
CONTENT FOR AN APPLICATION TO ADOPT TSTF-487, REVISION 0. LICENSEES 
REMAIN RESPONSIBLE FOR ENSURING THAT THEIR ACTUAL APPLICATION 
FULFILLS THEIR ADMINISTRATIVE REQUIREMENTS AS WELL AS NRC 
REGULATIONS.
U. S. Nuclear Regulatory Commission, Document Control Desk, 
Washington, DC 20555.
SUBJECT: PLANT NAME, DOCKET NO. 50-[xxx,] RE: APPLICATION FOR 
TECHNICAL SPECIFICATION IMPROVEMENT TO ADOPT TSTF-487, REVISION 0, 
``RELOCATE DNB PARAMETERS TO THE COLR''
Dear Sir or Madam:
    In accordance with the provisions of Section 50.90 of Title 10 
of the Code of Federal Regulations (10 CFR), [LICENSEE] is 
submitting a request for an amendment to the technical 
specifications (TS) for [PLANT NAME, UNIT NOS.]. The proposed 
changes would allow [PLANT NAME] to replace the DNB numeric limits 
in TS with references to the core operating limits report (COLR).
    The changes are consistent with NRC-approved Industry Technical 
Specification Task Force (TSTF) Standard Technical Specification 
Change Traveler, TSTF-487 Revision 0. The availability of this TS 
improvement was announced in the Federal Register on [DATE] ([ ]FR[ 
]) as part of the consolidated line item improvement process 
(CLIIP).

[[Page 12225]]

    Enclosure 1 provides a description and assessment of the 
proposed changes, as well as confirmation of applicability. 
Enclosure 2 provides the existing TS pages and TS Bases marked-up to 
show the proposed changes. Enclosure 3 provides final TS pages and 
TS Bases pages. [LICENSEE] requests approval of the proposed license 
amendment by [DATE], with the amendment being implemented [BY DATE 
OR WITHIN X DAYS]. In accordance with 10 CFR 50.91, a copy of this 
application, with enclosures, is being provided to the designated 
[STATE] Official.
    I declare under penalty of perjury under the laws of the United 
States of America that I am authorized by [LICENSEE] to make this 
request and that the foregoing is true and correct. [Note that 
request may be notarized in lieu of using this oath or affirmation 
statement]. If you should have any questions regarding this 
submittal, please contact [ ].
Sincerely,

Name, Title

Enclosures:
    1. Description and Assessment of Proposed Changes
    2. Proposed Technical Specification Changes and Technical 
Specification Bases Changes
    3. Final Technical Specification and Bases pages

cc: NRR Project Manager
    Regional Office
    Resident Inspector
    State Contact
    ITSB Branch Chief

1.0 DESCRIPTION

    This letter is a request to amend Operating License(s) [LICENSE 
NUMBER(S)] for [PLANT/UNIT NAME(S)]. The proposed changes would 
revise Technical Specification (TS) 3.4.1, ``RCS Pressure, 
Temperature, and Flow [Departure from Nucleate Boiling (DNB)] 
Limits,'' the Bases for TS 3.4.1, and TS 5.6.3 ``Core Operating 
Limits Report (COLR),'' to allow [PLANT NAME] to place the DNB 
numeric limits with references to the COLR.
    Technical Specification Task Force (TSTF) change traveler TSTF-
487, Revision 0 ``Relocate DNB Parameters to the COLR'' was 
announced for availability in the Federal Register on [DATE] as part 
of the consolidated line item improvement process (CLIIP).

2.0 PROPOSED CHANGES

    Consistent with NRC-approved TSTF-487 Revision 0, the following 
changes are proposed:
     Revise the limiting conditions for operation and 
surveillance requirements in TS 3.4.1 to replace the DNB numeric 
limits for reactor coolant pressure, temperature, and flow with 
references to limits for those parameters calculated in the COLR.
     Revise the bases associated with TS 3.4.1 to reflect 
that the DNB numeric limits are contained in the COLR.
     Revise TS 5.6.3 to add the methodology requirements for 
calculating the DNB numeric limits in the COLR,

3.0 BACKGROUND

    The background for this application is as stated in the model SE 
in NRC's Notice of Availability published on [DATE] ([ ] FR [ ]), 
the NRC Notice for Comment published on [DATE] ([ ] FR [ ]), and 
TSTF-487, Revision 0.

4.0 TECHNICAL ANALYSIS

    [LICENSEE] has reviewed Generic Letter 88-16, and the model SE 
published on [DATE] ([ ] FR [ ]) as part of the CLIIP Notice for 
Comment. [LICENSEE] has applied the methodology in Generic Letter 
88-16 to develop the proposed TS changes. [LICENSEE] has also 
concluded that the justifications presented in TSTF-487, Revision 0 
and the model SE prepared by the NRC staff are applicable to [PLANT, 
UNIT NOS.], and justify this amendment for the incorporation of the 
changes to the [PLANT] TS.

5.0 REGULATORY ANALYSIS

    A description of this proposed change and its relationship to 
applicable regulatory requirements and guidance was provided in the 
NRC Notice of Availability published on [DATE] ([ ] FR [ ]), the NRC 
Notice for Comment published on [DATE] ([ ] FR [ ]), and TSTF-487, 
Revision 0.

6.0 NO SIGNIFICANT HAZARDS CONSIDERATION

    [LICENSEE] has reviewed the proposed no significant hazards 
consideration determination published in the Federal Register on 
[DATE] ([ ] FR [ ]) as part of the CLIIP. [LICENSEE] has concluded 
that the proposed determination presented in the notice is 
applicable to [PLANT] and the determination is hereby incorporated 
by reference to satisfy the requirements of 10 CFR 50.91(a).

7.0 ENVIRONMENTAL EVALUATION

    [LICENSEE] has reviewed the environmental consideration included 
in the model SE published in the Federal Register on [DATE] ([ ] FR 
[ ]) as part of the CLIIP. [LICENSEE] has concluded that the staff's 
findings presented therein are applicable to [PLANT] and the 
determination is hereby incorporated by reference for this 
application.
    Proposed Safety Evaluation, U.S Nuclear Regulatory Commission, 
Office of Nuclear Reactor Regulation.
    Consolidated Line Item Improvement Technical Specification Task 
Force (TSTF).
    Change TSTF-487, Revision 0, RELOCATE DNB PARAMETERS TO THE 
COLR.

1.0 INTRODUCTION

    By application dated [Date], (Ref. 7.1), the [Name of Licensee] 
(the licensee) requested changes to the Technical Specifications 
(TS) for the [Name of Facility].
    The proposed changes would revise TS 3.4.1, the associated bases 
of TS 3.4.1, and TS 5.6.3 to replace the departure from nucleate 
boiling (DNB) parameters limits in Technical Specifications (TSs) 
with references to the Core Operating Limits Report (COLR). These 
changes would allow the licensee to recalculate the DNB parameter 
limits using NRC-approved methodologies without the need for a 
license amendment request (LAR).
    The proposed changes include the following:
     Change TS 3.4.1, ``RCS Pressure, Temperature, and Flow 
[Departure from Nucleate Boiling (DNB)] Limits,'' Limiting 
Conditions for Operation (LCO) 3.4.1 and the associated Surveillance 
Requirements (SRs) to replace the specific limit values of RCS 
pressurizer pressure, cold leg temperature, and RCS total flow rate 
with ``the limits specified in the COLR.''
     Change the Bases for LCO 3.4.1 to reflect that the DNB 
limits are specified in the COLR.
     Change Section 5.6.3 of TS, ``Core Operating Limits 
Report (COLR)'' to include the NRC approved methodologies and 
requirements used to calculate the DNB limits.
    Generic Letter (GL) 88-16 titled ``Removal of Cycle-Specific 
Parameter Limits from Technical Specifications'' (Ref. 7.2) is the 
regulatory guidance for this change.

2.0 REGULATORY EVALUATION

    The Commission's regulatory requirements related to the content 
of Technical Specifications are specified in Title 10 CFR (Code of 
Federal Regulations), Section 50.36, ``Technical Specifications.'' 
10 CFR 50.36(c)(2)(i) defines that limiting conditions for operation 
are the lowest functional capability or performance levels of 
equipment required for safe operation of the facility. For the DNB 
parameters, 10 CFR 50.36(c)(2)(ii)(B) Criterion 2 applies, which 
requires that TS LCOs be established for each process variable, 
design feature, or operating restriction that is an initial 
condition of a design basis accident or transient analysis that 
either assumes the failure of or presents a challenge to the 
integrity of a fission product barrier.
    LARs are required for each fuel cycle design that results in 
changes to parameter limits specified in TS. To meet 10 CFR 
50.36(c)(2)(ii) requirements and alleviate the need for LARs to 
update parameter limits every fuel cycle, the NRC issued GL 88-16 
with specific guidance for replacing the limit values for cycle-
specific parameters in the TSs with references to an owner-
controlled document, namely, the COLR. The guidance in GL 88-16 
includes the following three actions:
    1. The addition of the definition of a named formal report 
(i.e., Core Operating Limits Report) in TS that includes the values 
of cycle-specific parameter limits that have been established using 
an NRC-approved methodology and consistent with all applicable 
limits of the safety analyses.
    2. The addition of an administrative reporting requirement (in 
TS 5.6.3) to submit the formal report on cycle-specific parameter 
limits to the Commission for information.
    3. The modification of individual TS to note that the specific 
parameters shall be maintained within the limits provided in the 
defined formal report (COLR).
    The proposed change has been evaluated against GL 88-16 and 
found to be consistent with that regulatory guidance.

3.0 TECHNICAL EVALUATION

    TS LCO 3.4.1 specifies the limit values of the DNB parameters to 
assure that the pressurizer pressure, the RCS cold leg

[[Page 12226]]

temperature, and RCS flow rate during operation at rated thermal 
power (RTP) will be maintained within the limits assumed in the 
safety analyses in the final safety analysis report (FSAR). The 
safety analyses of anticipated operational occurrences (AOOs) and 
accidents assume initial conditions within the envelope of normal 
steady state operation at the RTP to demonstrate that the applicable 
acceptance criteria, including the specified acceptable fuel design 
limits (such as DNB ratio) and RCS pressure boundary design 
conditions, are met for each event analyzed. The TS limits placed on 
the DNB-related parameters ensure that these parameters, when 
appropriate measurement uncertainties are applied, will be bounded 
by those assumed in the safety analyses, and thereby provide 
assurance that the applicable acceptance criteria will not be 
violated should a transient or accident occur while operating at the 
RTP.
    It is essential to safety that the plant is operated within the 
DNB parameter limits. This change retains the requirement to 
maintain the plant within the DNB parameter limits in LCO 3.4.1 
along with the SR verification for each of the DNB parameters. As 
these parameter limits are calculated using NRC-approved 
methodologies and are consistent with all applicable limits of the 
plant safety analyses, this change does not affect nuclear safety.
    TS 5.6.3, ``Core Operating Limits Report (COLR),'' specifies 
that the core operating limits shall be determined such that all 
applicable limits of the safety analyses are met, and that the 
analytical methods used to determine the core operating limits shall 
be those previously reviewed and approved by the NRC. This change 
modifies the list of NRC approved methodologies in TS 5.6.3 to 
include those used to calculate the DNB limits on pressurizer 
pressure, RCS cold leg temperature, and RCS total flow rate. The 
limit values of these parameters in the COLR will comply with 
existing operating fuel cycle analysis requirements, and are initial 
conditions assumed in safety analyses. Replacing of the DNB 
parameter values with references to the COLR does not lessen the 
requirement for compliance with all applicable limits.
    Any revisions to the safety analyses that require prior NRC 
approval will be identified by the 10 CFR 50.59 review process. TS 
5.6.3 also specifies that the COLR, including any midcycle revisions 
or supplements, shall be provided upon issuance for each reload 
cycle to the NRC. This will allow NRC staff to continue trending the 
information even though prior NRC approval of the changes to these 
limits will not be required.
    Section 50.36 requires LCOs to contain the lowest functional 
capability or performance levels of equipment for safe operation of 
the facility. The NRC staff finds that the proposed change to LCO 
3.4.1 referencing the specific values of the DNB parameter limits in 
TS in the COLR continues to meet the regulatory requirement of 10 
CFR 50.36(c)(2)(ii)(B) (Criterion 2), and follows the guidance 
described in GL 88-16. The NRC staff, therefore, concludes that this 
change is acceptable.
    For safety analyses of transients or accidents, various sections 
of Chapter 15 of the Standard Review Plan (Ref. 7.3) specify that 
the reactor is initially at the RTP plus uncertainty, and the RCS 
flow is at nominal design flow including the measurement 
uncertainty. If one or more DNB parameter limits change, and these 
changes do not support the RTP, a license amendment would be 
required to either reduce the RTP or limit the plant operation at a 
level below the RTP. 10 CFR 50 Appendix K requires that the loss of 
coolant accident analysis be performed at 102% of the RTP. Other 
plant-specific analyses can contain an initial condition to be 
performed at RTP. To insure a clear understanding of this 
requirement the following statement has been added to TS 5.6.3: 
``The maximum thermal power from the COLR shall be equal to or 
greater than the RTP defined in TS 1.1.''

4.0 STATE CONSULTATION

    In accordance with the Commission's regulations, the [----------
------] State official was notified of the proposed issuance of the 
amendment. The State official had [(1) no comments or (2) the 
following comments--with subsequent disposition by the staff].

5.0 ENVIRONMENTAL CONSIDERATION

    The amendment[s] change[s] a requirement with respect to the 
installation or use of a facility component located within the 
restricted area as defined in 10 CFR Part 20 or surveillance 
requirements. The NRC staff has determined that the amendment 
involves no significant increase in the amounts, and no significant 
change in the types, of any effluents that may be released offsite, 
and that there is no significant increase in individual or 
cumulative occupational radiation exposure. The Commission has 
previously issued a proposed finding that the amendment involves no 
significant hazards consideration and there has been no public 
comment on such finding published [DATE] ([ ] FR [ ]). Accordingly, 
the amendment meets the eligibility criteria for categorical 
exclusion set forth in 10 CFR 51.22(c)(9). Pursuant to 10 CFR 
51.22(b), no environmental impact statement or environmental 
assessment need be prepared in connection with the issuance of the 
amendment.

6.0 CONCLUSION

    The NRC staff has reviewed this proposed change to replace the 
values of the DNB parameters in TS with references to the COLR. This 
change will allow the licensee the flexibility to manage operating 
and core design margins associated with the DNB parameters without 
the need for cycle-specific LARs. Any future revisions to safety 
analyses that require prior NRC approval will be identified by the 
10 CFR 50.59 review process. Based on this evaluation the NRC staff 
concludes that this change meets the regulatory requirements of 10 
CFR 50.36, follows the guidance described in GL 88-16, and is 
acceptable.

7.0 REFERENCES

    7.1 License Amendment Request dated [MMM, DD, YYYY], [Title of 
Amendment Request], ADAMS Accession No. [MLXXXXXXXXX].
    7.2 Generic Letter 88-16 dated October 4, 1988, ``Removal of 
Cycle-Specific Parameter Limits from Technical Specifications,'' 
ADAMS Accession No ML041830597.
    7.3 NUREG-0800, ``Standard Review Plan.''

Proposed No Significant Hazards Consideration Determination

    Description of Amendment Request: [Plant name] requests adoption 
of an approved change to the standard technical specifications (STS) 
for Combustion Engineering Pressurized Water Reactor (PWR) Plants 
(NUREG-1432) and plant-specific technical specifications (TS), to 
allow replacing the departure from nucleate boiling (DNB) parameter 
limits with references to the core operating limits report (COLR) in 
accordance with Generic Letter 88-16, ``Removal of Cycle Specific 
Parameter Limits from Technical Specifications,'' dated October 4, 
1988. The changes are consistent with NRC approved Industry/
Technical Specification Task Force (TSTF) Standard Technical 
Specification Change Traveler, TSTF-487.
    Basis for proposed no-significant-hazards-consideration 
determination: As required by 10 CFR 50.91(a), an analysis of the 
issue of no-significant-hazards-consideration is presented below:
    Criterion 1: Does the Proposed Change Involve a Significant 
Increase in the Probability or Consequences of an Accident 
Previously Evaluated?
    Response: No.
    The proposed amendment replaces the limit values of the reactor 
coolant system (RCS) DNB parameters (i.e., pressurizer pressure, RCS 
cold leg temperature, and RCS flow rate) in TS with references to 
the COLR, in accordance with the guidance of Generic Letter 88-16, 
to allow these parameter limit values to be recalculated without a 
license amendment. The proposed amendment does not involve operation 
of any required structures, systems, or components (SSCs) in a 
manner or configuration different from those previously recognized 
or evaluated. The cycle-specific values in the COLR must be 
calculated using the NRC-approved methodologies listed in TS 5.6.5, 
``Core Operating Limits Report (COLR).'' Replacing the RCS DNB 
parameter limits in TS with references to the COLR will maintain 
existing operating fuel cycle analysis requirements. Because these 
parameter limits are determined using the NRC-approved 
methodologies, the acceptance criteria established for the safety 
analyses of various transients and accidents will continue to be 
met. Therefore, neither the probability nor consequences of any 
accident previously evaluated will be increased by the proposed 
change.
    Therefore, operation of the facility in accordance with the 
proposed amendment does not involve a significant increase in the 
probability or consequences of an accident previously evaluated.
    Criterion 2: Does the Proposed Change Create the Possibility of 
a New or Different Kind of Accident from any Previously Evaluated?
    Response: No.

[[Page 12227]]

    The proposed amendment to replace the RCS DNB parameter limits 
in TS with references to the COLR does not involve a physical 
alteration of the plant, nor a change or addition of a system 
function. The proposed amendment does not involve operation of any 
required SSCs in a manner or configuration different from those 
previously recognized or evaluated. No new failure mechanisms will 
be introduced by the proposed change.
    Therefore, the proposed amendment does not create the 
possibility of a new or different kind of accident from any accident 
previously evaluated.
    Criterion 3: Does the Proposed Change Involve a Significant 
Reduction in the Margin of Safety?
    Response: No.
    The proposed amendment to replace the RCS DNB parameter limits 
in TS with references to the COLR will continue to maintain the 
margin of safety. The DNB parameter limits specified in the COLR 
will be determined based on the safety analyses of transients and 
accidents, performed using the NRC-approved methodologies that show 
that, with appropriate measurement uncertainties of these parameters 
accounted for, the acceptance criteria for each of the analyzed 
transients are met. This provides the same margin of safety as the 
limit values currently specified in the TS. Any future revisions to 
the safety analyses that require prior NRC approval are identified 
per the 10 CFR 50.59 review process.
    Therefore, the proposed amendment would not involve a 
significant reduction in a margin of safety.
    Based on the staff's review of the licensee's analysis, the 
staff concludes that the proposed amendment presents no significant 
hazards consideration under the standards set forth in 10 CFR 
50.92(c) and, accordingly, a finding of ``no significant hazards 
consideration'' is justified.

[Lit. face SIG]
    Dated at Rockville, Maryland this ------ day of ------ , 2007.

    For The Nuclear Regulatory Commission.

Project Manager
Plant Licensing Branch [ ]
Division of Operating Reactor Licensing
Office of Nuclear Reactor Regulation
[FR Doc. E7-4752 Filed 3-14-07; 8:45 am]
BILLING CODE 7590-01-P