[Federal Register Volume 65, Number 206 (Tuesday, October 24, 2000)]
[Corrections]
[Pages 63677-63678]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: C0-19723]



  Federal Register / Vol. 65, No. 206 / Tuesday, October 24, 2000 / 
Corrections  

[[Page 63677]]



DEPARTMENT OF ENERGY

Office of Energy Efficiency and Renewable Energy

10 CFR Part 431

[Docket No. EE-RM/TP-99-460]
RIN 1904-AA97


Energy Efficiency Program for Certain Commercial and Industrial 
Equipment: Test Procedures and Efficiency Standards for Commercial Air 
Conditioners and Heat Pumps

Correction

    In proposed rule document 00-19723 beginning on page 48828 in the 
issue of Wednesday, August 9, 2000, make the following correction:


Sec. 431.271  [Corrected]

    On page 48837 and 48838, in Sec. 431.271, Tables 1 and 2 should 
read as follows:

                                   TABLE 1.--Minimum Cooling Efficiency Levels
----------------------------------------------------------------------------------------------------------------
            Product                   Category       Cooling capacity     Subcategory      Efficiency Level \1\
----------------------------------------------------------------------------------------------------------------
Small Commercial Packaged Air    Air Cooled, 3      65,000 Btu/h.....  Split System.....  SEER = 10.0
 Conditioning and Heating         Phase.                               Single Package...  SEER = 9.7
 Equipment.
                                 Air Cooled.......  65,000  All..............  EER = 8.9
                                                     Btu/h and
                                                     135,000 Btu/h.
                                 Water Cooled       65,000 Btu/h.....  All..............  EER = 9.3
                                  Evaporatively     65,000  All..............  EER = 10.5
                                  Cooled, and        Btu/h and
                                  Water-Source.      135,000 Btu/h.
Large Commercial Packaged Air    Air Cooled.......  135,00  All..............  EER = 8.5
 Conditioning and Heating                            0 Btu/h and
 Equipment.                                          240,000 Btu/h.
                                 Water-Cooled, and  135,00  All..............  EER = 9.6
                                  Evaporatively      0 Btu/h and
                                  Cooled.            240,000 Btu/h.
Packaged Terminal Air            All..............  7,000 Btu/h......  All..............  EER = 8.88
 Conditioners and Heat Pumps.                       7,000                      EER = 10.0-(0.16  x
                                                     Btu/h and 15,000                         thousands of Btu/h at
                                                     Btu/h.                                95 deg. outdoor dry-
                                                    >15,000 Btu/h....                      bulb temperature])
                                                                                          EER = 7.6
----------------------------------------------------------------------------------------------------------------
\1\ All EER values must be rated at 95 deg.F outdoor dry-bulb temperature for air-cooled products and
  evaporatively-cooled products and at 85 deg.F entering water temperature for water-source and water-cooled
  products.


[[Page 63678]]


                                   TABLE 2.--MINIMUM HEATING EFFICIENCY LEVELS
----------------------------------------------------------------------------------------------------------------
            Product                   Category       Cooling capacity     Subcategory      Efficiency Level \2\
----------------------------------------------------------------------------------------------------------------
Small Commercial Packaged Air    Air Cooled, 3      65,000 Btu/h.....  Split System.....  HSPF = 6.8
 Conditioning and Heating         Phase.                               Single Package...  HSPF = 6.6
 Equipment.
                                 Water-Source.....  135,000 Btu/h....  Split System and   COP = 3.8
                                                                        Single Package.
                                 Air Cooled.......  65,000  All..............  COP = 3.0
                                                     Btu/h and
                                                     135,000 Btu/h.
Large Commercial Packaged Air    Air Cooled.......  135,00  Split System and   COP = 2.9
 Conditioning and Heating                            0 Btu/h and        Single Package.
 Equipment.                                          240,000 Btu/h.
Packaged Terminal Heat Pumps...  All..............  All..............  All..............  COP = 1.3+(0.16  x
                                                                                           the applicable
                                                                                           minimum cooling EER
                                                                                           prescribed in Table
                                                                                           1--Minimum Cooling
                                                                                           Efficiency Levels)
----------------------------------------------------------------------------------------------------------------
\2\ All COP values must be rated at 47 deg.F outdoor dry-bulb temperature for air-cooled products and
  evaporatively-cooled products and at 70 deg.F entering water temperature for water-source products.


[FR Doc. C0-19723 Filed 10-23-00; 8:45 am]
BILLING CODE 1505-01-D