[Federal Register Volume 59, Number 11 (Tuesday, January 18, 1994)]
[Unknown Section]
[Page 0]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 94-1098]


[[Page Unknown]]

[Federal Register: January 18, 1994]


-----------------------------------------------------------------------

NUCLEAR REGULATORY COMMISSION
[Docket No. 50-333]

 

Power Authority of the State of New York; Consideration of 
Issuance of Amendment to Facility Operating License, Proposed No 
Significant Hazards Consideration Determination, and Opportunity for a 
Hearing

    The U.S. Nuclear Regulatory Commission (the Commission) is 
considering issuance of an amendment to Facility Operating License No. 
DPR-59 issued to the Power Authority of the State of New York (the 
licensee) for operation of the James A. FitzPatrick Nuclear Power Plant 
located in Oswego County, New York.
    The proposed amendment would add Limiting Conditions for Operation 
(LCO) and Surveillance Requirements to Tables 3.12.1, ``Water Spray/
Sprinkler Protected Areas'', and 4.12.1, ``Water Spray/Sprinkler System 
Tests'' and clarify the associated Bases to reflect the installation of 
a new full area fire suppression system in the east and west cable 
tunnels. This new full area fire suppression system was installed 
because the previous sprinkler system did not provide coverage to some 
cable trays and the sprinkler head orientation did not provide full 
coverage of the cable trays where it was installed. The proposed 
amendment would also correct other portions of Tables 3.12.1 and 4.12.1 
for consistency with changes made to reflect the east and west cable 
tunnel modification.
    Before issuance of the proposed license amendment, the Commission 
will have made findings required by the Atomic Energy Act of 1954, as 
amended (the Act) and the Commission's regulations.
    The Commission has made a proposed determination that the amendment 
request involves no significant hazards consideration. Under the 
Commission's regulations in 10 CFR 50.92, this means that operation of 
the facility in accordance with the proposed amendment would not: (1) 
Involve a significant increase in the probability or consequences of an 
accident previously evaluated; or (2) create the possibility of a new 
or different kind of accident from any accident previously evaluated; 
or (3) involve a significant reduction in a margin of safety. As 
required by 10 CFR 50.91(a), the licensee has provided its analysis of 
the issue of no significant hazards consideration, which is presented 
below:

    Operation of the FitzPatrick plant in accordance with the 
proposed Amendment would not involve a significant hazards 
consideration as defined in 10 CFR 50.92, since it would not:
    1. Involve a significant increase in the probability or 
consequences of an accident previously evaluated.
    The proposed changes revise the Technical Specifications to 
incorporate a modification to the James A. FitzPatrick Fire 
Protection System and to make existing Technical Specifications 
consistent with the specifications proposed for the modification. 
The modification will improve the ability of the plant's fire 
protection system to detect and suppress fires. The modified system 
has been designed, analyzed and constructed in accordance with fire 
protection system requirements. These changes to the Technical 
Specifications assure that the modified system is operable by 
periodic surveillance and that required actions are taken if it is 
not available. The surveillance requirements meet or exceed past 
requirements.
    2. Create the possibility of a new or different kind of accident 
from those previously evaluated.
    The only potential for a new or different type of accident 
arises from different failure mechanisms of the system. An analysis 
of flooding has demonstrated that there are no associated failures 
of shutdown equipment. The new system has been designed and 
constructed so that there is no damage to safety related equipment 
due to missiles or water spray. The modification to the first 
protection system provides additional protection for possible fires 
in the east and west cable tunnels through increased spray coverage. 
There are no changes to plant operations or operating procedures 
other than Surveillance Requirements. The Surveillance Requirements 
are consistent with past plant practices and industry codes and 
standards.
    3. Involve a significant reduction in the margin of safety.
    The piping has been designed and constructed to prevent damage 
to safety related equipment due to missiles or water spray during a 
seismic event. The modification improves the plant's capability to 
detect and suppress fires. The potential for flooding or water 
damage has been evaluated and does not result in failure of shutdown 
equipment. The LCO and Surveillance Requirements meet or exceed past 
practice. This change results in no reduction in the margin of 
safety.

    The NRC staff has reviewed the licensee's analysis and, based on 
this review, it appears that the three standards of 10 CFR 50.92(c) are 
satisfied. Therefore, the NRC staff proposes to determine that the 
amendment request involves no significant hazards consideration.
    The Commission is seeking public comments on this proposed 
determination. Any comments received within 30 days after the date of 
publication of this notice will be considered in making any final 
determination.
    Normally, the Commission will not issue the amendment until the 
expiration of the 30-day notice period. However, should circumstances 
change during the notice period such that failure to act in a timely 
way would result, for example, in derating or shutdown of the facility, 
the Commission may issue the license amendment before the expiration of 
the 30-day notice period, provided that its final determination is that 
the amendment involves no significant hazards consideration. The final 
determination will consider all public and State comments received. 
Should the Commission take this action, it will publish in the Federal 
Register a notice of issuance and provide for opportunity for a hearing 
after issuance. The Commission expects that the need to take this 
action will occur very infrequently.
    Written comments may be submitted by mail to the Rules Review and 
Directives Branch, Division of Freedom of Information and Publications 
Services Office of Administration, U.S. Nuclear Regulatory Commission, 
Washington, DC 20555, and should cite the publication date and page 
number of this Federal Register notice. Written comments may also be 
delivered to room P-223, Phillips Building, 7920 Norfolk Avenue, 
Bethesda, Maryland, from 7:30 a.m. to 4:15 p.m. Federal workdays. 
Copies of written comments received may be examined at the NRC Public 
Document Room, the Gelman Building, 2120 L Street, NW., Washington, DC 
20555.
    The filing of requests for hearing and petitions for leave to 
intervene is discussed below.
    By February 17, 1994, the licensee may file a request for a hearing 
with respect to issuance of the amendment to the subject facility 
operating license and any person whose interest may be affected by this 
proceeding and who wishes to participate as a party in the proceeding 
must file a written request for a hearing and a petition for leave to 
intervene. Requests for a hearing and a petition for leave to intervene 
shall be filed in accordance with the Commission's ``Rules of Practice 
for Domestic Licensing Proceedings'' in 10 CFR part 2. Interested 
persons should consult a current copy of 10 CFR 2.714 which is 
available at the Commission's Public Document Room, the Gelman 
Building, 2120 L Street, NW., Washington, DC 20555 and at the local 
public document room located at Penfield Library, State University 
College of New York, Oswego, NY 13126. If a request for a hearing or 
petition for leave to intervene is filed by the above date, the 
Commission or an Atomic Safety and Licensing Board, designated by the 
Commission or by the Chairman of the Atomic Safety and Licensing Board 
Panel, will rule on the request and/or petition; and the Secretary or 
the designated Atomic Safety and Licensing Board will issue a notice of 
hearing or an appropriate order.
    As required by 10 CFR 2.714, a petition for leave to intervene 
shall set forth with particularity the interest of the petitioner in 
the proceeding, and how that interest may be affected by the results of 
the proceeding. The petition should specifically explain the reasons 
why intervention should be permitted with particular reference to the 
following factors: (1) The nature of the petitioner's right under the 
Act to be made party to the proceeding; (2) the nature and extent of 
the petitioner's property, financial, or other interest in the 
proceeding; and (3) the possible effect of any order which may be 
entered in the proceeding on the petitioner's interest. The petition 
should also identify the specific aspect(s) of the subject matter of 
the proceeding as to which petitioner wishes to intervene. Any person 
who has filed a petition for leave to intervene or who has been 
admitted as a party may amend the petition without requesting leave of 
the Board up to 15 days prior to the first prehearing conference 
scheduled in the proceeding, but such an amended petition must satisfy 
the specificity requirements described above.
    Not later than 15 days prior to the first prehearing conference 
scheduled in the proceeding, a petitioner shall file a supplement to 
the petition to intervene which must include a list of the contentions 
which are sought to be litigated in the matter. Each contention must 
consist of a specific statement of the issue of law or fact to be 
raised or controverted. In addition, the petitioner shall provide a 
brief explanation of the bases of the contention and a concise 
statement of the alleged facts or expert opinion which support the 
contention and on which the petitioner intends to rely in proving the 
contention at the hearing. The petitioner must also provide references 
to those specific sources and documents of which the petitioner is 
aware and on which the petitioner intends to rely to establish those 
facts or expert opinion. Petitioner must provide sufficient information 
to show that a genuine dispute exists with the applicant on a material 
issue of law or fact. Contentions shall be limited to matters within 
the scope of the amendment under consideration. The contention must be 
one which, if proven, would entitle the petitioner to relief. A 
petitioner who fails to file such a supplement which satisfies these 
requirements with respect to at least one contention will not be 
permitted to participate as a party.
    Those permitted to intervene become parties to the proceeding, 
subject to any limitations in the order granting leave to intervene, 
and have the opportunity to participate fully in the conduct of the 
hearing, including the opportunity to present evidence and cross-
examine witnesses.
    If a hearing is requested, the Commission will make a final 
determination on the issue of no significant hazards consideration. The 
final determination will serve to decide when the hearing is held.
    If the final determination is that the amendment request involves 
no significant hazards consideration, the Commission may issue the 
amendment and make it immediately effective, notwithstanding the 
request for a hearing. Any hearing held would take place after issuance 
of the amendment.
    If the final determination is that the amendment request involves a 
significant hazards consideration, any hearing held would take place 
before the issuance of any amendment.
    A request for a hearing or a petition for leave to intervene must 
be filed with the Secretary of the Commission, U.S. Nuclear Regulatory 
Commission, Washington, DC 20555, Attention: Docketing and Services 
Branch, or may be delivered to the Commission's Public Document Room, 
the Gelman Building, 2120 L Street, NW., Washington, DC 20555, by the 
above date. Where petitions are filed during the last 10 days of the 
notice period, it is requested that the petitioner promptly so inform 
the Commission by a toll-free telephone call to Western Union at 1-
(800) 248-5100 (in Missouri 1-(800) 342-6700). The Western Union 
operator should be given Datagram Identification Number N1023 and the 
following message addressed to Robert A. Capra: Petitioner's name and 
telephone number, date petition was mailed, plant name, and publication 
date and page number of this Federal Register notice. A copy of the 
petition should also be sent to the Office of the General Counsel, U.S. 
Nuclear Regulatory Commission, Washington, DC 20555, and to Charles M. 
Pratt, Power Authority of the State of New York, 1633 Broadway, New 
York, NY 10019, attorney for the licensee.
    Nontimely filings of petitions for leave to intervene, amended 
petitions, supplemental petitions and/or requests for hearing will not 
be entertained absent a determination by the Commission, the presiding 
officer or the presiding Atomic Safety and Licensing Board that the 
petition and/or request should be granted based upon a balancing of the 
factors specified in 10 CFR 2.714(a)(1) (i)-(v) and 2.714(d).
    For further details with respect to this action, see the 
application for amendment dated December 22, 1993, which is available 
for public inspection at the Commission's Public Document Room, the 
Gelman Building, 2120 L Street, NW., Washington, DC 20555 and at the 
local public document room located at Penfield Library, State 
University College of New York, Oswego, NY 13126.

    Dated at Rockville, Maryland, this 10th day of January 1994.

    For the Nuclear Regulatory Commission.
Brian C. McCabe,
Senior Project Manager, Project Directorate I-1, Division of Reactor 
Projects--I/II, Office of Nuclear Reactor Regulation.
[FR Doc. 94-1098 Filed 1-14-94; 8:45 am]
BILLING CODE 7590-01-M