[From the U.S. Government Printing Office, www.gpo.gov]













             NONPOINT SOURCE POLLUTION CONTROL PROGRAM


                     SEPTAGE DISPOSAL SITE INSPECTIONS


                                         AND


             PRIVATE SEWAGE DISPOSAL SYSTEM INSPECTIONS


                                 OCONTO COUNTY


                              1993 PROJECT REPORT



















                                   NOVEMBER 19, 1993
           TD
           424.8
           Z34                       BY: JEFF ZAHM
           1993











                                     TABLE OF CONTENTS


           Preface  ...................................................   Page 1

           Acknowledgement   ...........................................  Page 1
           Introduction  ...............................................  Page 2
           Objective ..................................................   Page 2
           Program Development   .......................................  Page 3

           Program Implementation   ....................................  Page 4

           Results  ....................................................  Page 5

           Conclusion ....................................   ............ Page 5

           Recommendations   ...........................................  Page 7


                                         APPENDIX


           Information from DNR
              List of district Approved Landspreading Sites
              Section 6, Handling Complaints
              Section 7, Enforcement Procedures
              Section 10, Site Inspections
              Violations-that Warrant Citations
              Pumpers News Letter

           Wisconsin Administrative Code 113.08 (3) (b) 16. Table 4

           List of Oconto County Approved Landspreading Sites

           Licensed Septage Pumpers that work in Oconto County
   010     Septage Site Owner Contacts and Inspection Reports

           Community Inspection Reports, Tallies, and Areas Covered















          PREFACE


               With the population continuing to escalate at an increasing
          rate the cities are becoming over crowded and more people are
          moving to the country. This results in a potential for an increase
          in groundwater and surface water contamination due to increasing
          development.   In response to this increased development, Oconto
          County established a NonPoint Source Pollution Control Program in
          1990, 1991, and is presently expanding it in 1993.     This program
          was aimed at eliminating NonPoint Source Pollution which results
          from failing private sewage disposal systems and the landspreading
          of septage.

               This report will detail Oconto County's efforts to control
          NonPoint Source Pollution generated from Private Sewage Disposal
          Syctems and the land Spreading sites where the septage generated
          from these systems is being periodically disposed.

          ACKNOWLEDGEMENT


               Funding for the County's NonPoint Source Pollution Control
          Program was made possible through a grant from the National Oceanic
          and Atmospheric Administration's Office of Ocean and Coastal
          Resource Management.     The Coastal Management Section of the
          Wisconsin Department of Administration regulates the Wisconsin
          Coastal Management Program.
               The Wisconsin Coastal Management Program was established in
          1978 to direct comprehensive attention to the state's 820 miles of
          Lake Michigan and Lake Superior coastline. The WCMP analyzes and
          develops state policy on a wide range of issues concerning the
          Great Lakes and their adjacent tributaries.  They provide the state
          and local government agencies with grants to  locate and rectify the
          NonPoint Source Pollution problem along the state's coastal
          waterways and their tributaries. The overall goal of the WCMP is
          to preserve,   protect arrd develop the existing resources of
          Wisconsin's coastal areas from further degradation.       This will
          allow for a cleaner and healthier environment for this and future
          generations to come.












           INTRODUCTION


                The Oconto County Zoning office, recognizing there was a
           serious need to rectify the problem of NonPoint Source Pollution,
           started a NonPoint Source Pollution Control Program in 1990. This
           program was designed to focus on NonPoint Source Pollution
           generated from failing private sewage disposal systems in the
           Little River Watershed Area.

                The NonPoint Program was expanded in 1991 to include the
           Bayshore from one end of the county to the other. It was also to
           include the landspreading sites where the septage generated from
           Holding Tanks and Septic Tanks is periodically being spread. The
           program was to be put on hold in 1992 but was continued in 1993.

                The 1993 NonPoint Program included the inspection of 28
           septage sites which were used for landspreading. These inspections
           led to many of the sites being removed from the DNR's list of
           approved sites.     The program also expanded      'the area where
           inspections for failing private sewage disposal systems were to be
           conducted.   This expansion resulted in the targeting of Abrams,
           Brookside, Lakewood, Mountain, Chute Pond, Moody Lake, Anderson
           Lake, Little Suamico, and the newly formed Pensaukee Sanitary
           District. These new areas resulted in over 1,164 inspections with
           more than 380 enforcement orders being issued.

                In order to correct these problems, more than 250 new Holding
           Tanks and over 125 new mounds would have to be installed. It is
           Oconto County's belief that Holding Tanks are not a corrective
           measure in that the effluent from the tank still has to be treated.
           The effluent is treated either by taking it to Municipal treatment
           plants or is being spread on approved fields where the soil treats
           the effluent.     Holding Tanks also have a rather short life
           expectancy which results in the problem having to be corrected
           again at a future date.

                The 1993 program was.also to police up the areas targeted by
           the 1990 and 1991 programs.       This was done by doing onsite
           investigations and if need be issuing new enforcement orders with
           a more stringent action taken against those who have not yet
           complied with the previous enforcement orders.

           OBJECTIVE


                Landspreading of septage and sludge is becoming a more serious
           problem in Oconto County as well as other counties throughout the
           state. This is due to municipal waste water treatment plants not
           accepting the septage generated from private sewage systems. The
           treatment plants, due to population increases, are reaching their
           peak capacities and can not handle any more inputs. The only other
           alternative in many counties is landspreading of the sludge and
           septage.   This in turn results in the issuing of several new

                                            2









            licensed sites for the spreading of septage yearly.

                 Landspreading of septage can lead to several serious problems
            if it is spread on unsuitable sites or improperly spread. It can
            lead to the contamination of ground water and surface water which
            could have devastating effects.         It is the County's aim to
            eliminate the potential for ground water and surface water
            contamination through properly inspecting all licensed sites within
            the county.

                 The contamination from private sewage disposal systems is also
            a nroblem that the county is giving serious attention to.           This
            results from old systems that could be failing and systems which
            have been improperly installed. The septage generated from private
            sewage systems, when not treated by a working soil absorption
            system, has to still be treated. The septage then is just being
            displaced and results in the need for more septage sites licensed
            for landspreading. it is the intention of the Oconto County Zoning
            Office to correct the initial problem of non-point source
            pollution, thus eliminating the need for a larger number of
            landspreading sites.

            PROGRAM DEVELOPMENT

                 The Non-Point Program was to focus on Private Sewage Systems
            in 1990 and to give priority attention to the sites listed for
            landspreading in 1991.     The 1993 program, working under similar
            time constraints, will encompass both of these objectives in it's
            final project goal.

                 The first step was to contact the Department of Natural
            Resources and obtain a list of licensed sites for the spreading of
            septage.    It is the responsibility of the DNR to license and
            regulate septic haulers as well as the sites where the septage is
            to be landspread. The DNR sent us a list of all the licensed sites
            in Oconto County as well as some of the guidelines they follow when
            issuing approval for sitea. They also sent some of their criteria
            which would warrant potential violations. (See Appendix)

                 It was the intention of the Oconto County Zoning Office to do
            an onsite evaluation of each site properly licensed by the DNR.
            Once the inforination was received from the DNR it was cross
            referenced with the 1991 list and the inspections done at that
            time.   Several of the sites remain the same and the files were
            updated to show the changes which took place. Several of the sites
            were only partially inspected in 1991. This was due to limitations
            such as crops affecting the ability to properly do soil borings.
            The 1993 program started the inspections in May, thus avoiding many
            of the limitations which were previously encountered. The owners
            of each site were contacted prior to the inspection and invited to
            be present at the time the inspection was to take place.


                                               3









                The inspection report sheet developed specifically for septage
          sites in 1991 was to be used for the site inspections.     The sites
          were to be evaluated based on the criteria of NR 113 Wisconsin
          Administrative Code.    These criteria were followed precisely to
          eliminate the potential for variation and ensure uniformity between
          all the evaluations.

               Once the landspreading sites where evaluated and the results
          complete we  were to start inspections of private sewage systems.
          There were several communities targeted under the 1993 program.
          The private sewage systems were evaluated based on six main
          cr3teria which delineate a failing septic system.         These six
          criteria are: Discharging sewage to Surface Water, Groundwater,
          Drain Tiles, Zones of Bedrock, Zones of Seasonally Saturated Soils,
          and the Surface of the Ground. The guidelines for soil borings are
          set in DIHLR 83 and 85 Wisconsin Administrative Code. A three foot
          separation from system elevation to Groundwater, Bedrock, or Zones
          of Seasonally Saturated soils is required.

          PROGRAM IMPLEMENTATION


               The list received from the DNR had 33 sites licensed for
          septage disposal in Oconto County.     (See appendix)   Of these 33
          sites, 5 were Municipal Wastewater Treatment Plants and the
          remaining 28 were privately owned sites for the landspreading of
          public septage.     Each privately owned site was verified for
          ownership in the Tax Listing Office. It was found out that several
          of the licensed sites had changed ownership and the DNR list was in
          need of revision.        Jim Friedrich, Septage and Laboratory
          Specialist, from the Department of Natural Resources was contacted
          in order to inform us of the qualifications needed to remove sites
          from the list of approved sites.       He informed me that it was
          necessary to have the site owner request in writing to be removed.
          After learning this, a letter for owner request was mailed to each
          [email protected] which was to be signed and dated as to their intent.     (See
          Appendix)   It took approximately two weeks to receive all the
          letters from the land owners. After they were received copies were
          sent to Jim Friedrich requesting the removal of the sites whose
          owners no longer wished to remain as an active site. This removed
          10 sites before field inspections started.

               The remain 4ng 18 sites were to then be field inspected based
          on the criteria of Chapter NR 113 of the Wisconsin Administrative
          Code. Soil borings were conducted as well as site inspections to
          verify their conformity to NR 113. The number of horings for each
          f ield was based on acreage as stated in Table 5 of NR 113.
          Pictures were taken at each site to document the findings in all
          cases and used as proof in cases where it was necessary to request
          removal from the DNR's list of active sites.

               Having the septage sites evaluated, the remaining time was
          focused on Private Septic Systems. The location of targeted areas

                                           4










           were decided on by the Planning and Zoning Committee. When a town
           has been targeted a boundary was drawn up by the Zoning
           Administrator and then a trip to the area was made to take down
           fire numbers from all the houses in the area. These numbers were
           compared to Tax Listing's numbers and- inspection reports which
           contained owner and physical description where filled out.         The
           results of all the inspections were entered into the computer and
           a print out of percent passing and failing, along with reasons why,
           was mailed to the Town Chairman.      A copy was also given to the
           Zoning Administrator and made available for anyone wishing to know
           the results. (See Appendix)

           RESULTS


                of the 18 sites where field evaluations were conducted, 10
           sites were deemed suitable for landspreading as they stand. Two
           sites were allowed to remain as active sites with limitations set
           as to what parts or what time of the year these two fields could be
           utilized. The 6 sites that were removed had several limitations
           wh-4ch restricted application of septage. The main limiting factor
           was the soil conditions. All six fields failed to meet the 3 foot
           separation above Zones of Seasonally Saturated Soils or Ground
           water.   One field was re-evaluated with Jim Friedrich, from the
           DNR, and the septage pumper present. The goal in this meeting was
           to evaluate the site in a dryer part of the year to maybe allow the
           site to be used with limitations on the times of the year that the
           septage could be spread.    one of the fields had critical slopes
           measuring in the 20-30 percent range which was also a rather
           significant factor.   (Inspection Reports for all sites can be found
           in the Appendix)

                The soil inspections of Private Sewage systems resulted in
           nine targeted areas consisting of: Abrams, Brookside, Chute Pond,
           Mountain, Lakewood, Moody Lake, Anderson Lake, Little Suamico, and
           the newly formed Pensaukee Sanitary District.       These six areas
           resulted in 1164 inspections with 380 enforcement orders being
           issued. There were also 8everal complaints and personal requests
           which resulted in an additional 10 inspections, adding 10 more
           enforcement orders from non-targeted areas. The 1993 program also
           policed up the areas where previous enforcement orders were issued
           and there was no action taken to correct the problem.       In these
           cases, 15 enforcement orders were issued with a second notice.
           These were to be the final notice sent to those people with failing
           systems.  The matter was then to be referred to the Corporation
           Council where the appropriate action would be taken if the failing
           systems were not brought up to code compliant systems.        (Tallies
           of all Inspected areas and results can be found in the Appendix)

           CONCLUSION

                With municipal Treatment Plants accepting less and less
           septage, Landspreading is a common practice in Oconto County.

                                             5









          Urbanization is becoming a more and more serious problem and the
          need for licensed sites is continuing to escalate.

                The DNR is presently responsible for the regulation and
          licensing of Septage Sites for landspreading. The Lake Michigan
          District of the DNR is in charge of Oconto County and 11 other
          counties as well. This district hires one employee to administrate
          the policies of NR 113.12 of the Wisconsin Administrative Code for
          all 12 of these counties.

                The guidelines followed by the DNR in licensing and regulating
          these sites are set forth in NR113.12 Wisconsin Administrative
          Code. The pumper is responsible for submitting the data and paper
          work for each site he wants approval for. The decisions are made
          based on his information and the guidelines of NR 113.12.          The
          pumpers information is rarely field checked to verify accuracy.
          The main criteria used to determine if the site will be approved or
          not is the soil limitations. This information is taken from the
          United States Department Of Agriculture Soil Survey of Oconto
          County.

                There were 18 sites which were field inspected and 10 were
          deemed suitable for continued landspreading.       The other 8 sites
          failed   to   meet   several   criteria   of  NR   113.12    Wisconsin
          Administrative Code. The major criteria which was not met was the
          soil limitations.     These findings emphasizes the importance of
          field evaluations on all sites prior to the issuance of a license.

                Non-Point Source Pollution from private sewage disposal
          systems is a continuing problem in Oconto County.        Plumbing was
          established in many of the existing Homesteads in the early to
          middle 1950's. Oconto County has records dating back to only 1966.
          Prior to that and even in this day and time many of the systems
          have been or are being installed by the landowner. Consideration
          was not, and in several cases is still not, given to pollution of
          Groundwater or Surface Water.
                In the targeted areas-1, 164 inspections were conducted and 380
          Enforcement Orders were issued. Many of these orders were on very
          old systems which were discharging to the Ground Surface, Rivers,
          or Groundwater.      When these systems were installed the main
          consideration was given to maintaining proper discharge from the
          residence. With escalating costs associated with replacement many
          of these systems are being maintained as is. This leads to serious
          health hazards associated with the effluent from the septic tank.
          There are a large number of Pathogenic Bacteria and Viruses which
          are not properly being disposed of.       Disposal and treatment of
          these containments in the effluent as well as the effluent itself
          is a major concern of Oconto County and it's Non-Point Source
          Pollution Control Program.



                                             6











          RECOMMENDATIONS

               The final evaluation for the septage sites and private sewage
          disposal systems shows that 35% of the licensed septage sites were
          depmed unsuitable and 33% of the existing private sewage disposal
          systems in the county are failing.      If these percentages apply
          throughout Oconto County, as well as the other counties in the
          state, there could be devastating affects on Groundwater quality
          and our environment.     These impacts could not only affect our
          Groundwater and environment but also could have serious health
          effects on the population as a whole.
               To make sure the information submitted by the pumper is
          correct and that the soil conditions are adequate, field
          evaluations need be conducted on all sites. The DNR, considering
          the wide array of duties and limited personnel, is doing an
          adequate job in administering the licensing of the septage sites.
          The only alternative in making sure a site is suitable prior to the
          issuance of the license would be to establish some sort of county
          control over the program.       This sort of program would add
          significantly to the counties workload and expenditures.      Oconto
          County simply does not have the personnel or funding to properly
          administer such a program.

               The private sewage disposal systems in the county are
          controlled by the Department of Industry and Human Relations
          (DILHR) with close cooperation from the county.      DILHR does not
          have the responsibility of pointing out problems with existing
          septic systems.     When these systems fail they have stringent
          regulations which must be followed in the event of replacing it.
          The counties are responsible for dealing with the problems
          associated with existing septic systems.     To eliminate problems
          associated with failing septic systems, Oconto County has
          established a Non-Point Source Pollution Control Program. The goal
          of this program is to eliminate the potential for Groundwater and
          surface water contamination.      Through this program and close
          cooperation with DILHR the impact on groundwater and surface water
          contamination from failing private sewage disposal systems is
          slowly being corrected.

                In the future there needs to be a greater emphasis on control
          at the county level to properly control the effects of Non-Point
          Source Pollution generated from landspreading sites and private
          sewage disposal systems. This will ensure consistent corrective
          measures which will help maintain high quality groundwater and
          create a healthier environment for our generation and those who
          follow.









                                           7



 I
 I
 I
 I
 I
 I
 I                 APPENDLX
 I
 I
 I
 I
 I
 I
 I
 I
 I
 I
 I
 I









                  Page No.       8
                  09111192
                                                                                                   DISTRICT  APPROVED.SEPTAGEI                                                1993
                                                                                                     LANDSPREADING SITES

                                                                                              SORTED BY COUNTY OF SITE LOCATION                                      Zon'ng Office
                                                                                                                                                                  Oconto Counly, Wl



                  LICENSEE                           LICENSE  LIC.     SITE     SITE                         LEGAL                               TOWNSHIP         SITE                DATE
                                                     NUMBER   CTY.     NO.      OWNER                        DESCRIPTION                         RANGE      ACRES COUNTY INSP.        APPVD.



                  SAUER SEPTIC SERVICE (RADANDT)Z1946         MAN      29       HALVERSON, LESTER            E/NW & NW/NE-S35                    19-22      75    MAN     NO          09/09/92
                  SAUER SEPTIC SERVICE (RADANDTA1946          MAN      30       HALVERSON, DICK              SWISE-S27 & W/NE-S34                19-22      55    MAN     NO          09/09/92
                  FIVE DIS  TRUCKING                 00759    MAR      01       KOUSKI, ROBERT               SW/SW-S4                            32-20      30    MAR     NO             /   /
                  FIVE DIS  TRUCKING                 00759    MAR      02       SCHROEDER, CARL    III       SE-S20 & SW-S21                     33-21      160   MAR     NO             /   /
                  FIVE DIS  TRUCKING                 00759    MAR      03       SIERACKI, MAX                NEINW-S18                           32-18      20    MAR     NO             /   /
                  FIVE DIS  TRUCKING                 00759    MAR      04       SANSA, FRANK                 SE/SE-S14 & NE/NE-S23               32-19      20    MAR     NO             /   /
                  FIVE DIS  TRUCKING                 00759    MAR      05       BODUCH, LOUIS                CENTE@/N-S`15                       32-19      90    MAR     NO             /   /
                  FIVE D'S  TRUCKING                 00759    MAR      06       KOUSXI, RONALD               E/NE/NW-S9                          32-20      15    MAR     NO             /   /
                  FIVE DIS  TRUCKING                 00759    MAR      07       RYNEN(?), GERY               NE/NE-S20                           33-20      15    MAR     NO             /   /
                  JOEL P. OLECK    SEPTIC PUMPING    01958    MAR      01       MAVES, JOHN                  W/Sw-S19                            32-20      45    MAR     NO          02/05/92
                  JOEL P. OLECK    SEPTIC PUMPING    01958    MAR      02       STARZER, JOSEPH              NW & W/NE   - S6                    31-20      55    MAR     NO          02114/92
                  JOEL P. OLECK    SEPTIC PUMPING    01958    MAR      03       MANKUSKi, MILES              NW/SE-Sl                            31-19      4     MAR     NO          03/02/92
                  JOEL P. OLECK    SEPTIC PUMPING    01958    MAR      04       TORZALA, JULIUS              SW/SE & SE/SW     S8                31-20      40    MAR     NO          03/12/92
                  OLECK PUMPING    (GRUSZINSKI)      00820    MAR      02       ANTCZAK, EDWARD              NE/SE-S12                           32-20      40    MAR     NO
                  OLECK PUMPING    (GRUSZINSKI)      00820    MAR      03       HIGHVIEW GOLF COURSE         SE/NE-S23                           32-19      20    MAR     NO
                  OLECK PUMPING    (GRUSZINSKI)      00820    MAR      04       LOVEGREN, WALMER             CENTER/S-S24                        32-20      10    MAR     NO
                  OLECK PUMPING    (GRUSZINSKI)      00820    MAR      05       WYMAN, EUGENE                N-s23                               32-20      80    MAR     NO
                  QUALITY PLUMBING & HEATING         01294    MAR      03       HARPER, MIKE&CAROLYN         W/SE/S9                             30-22      40    MAR     NO
                  ROCHON PLUMBING   & HEATING        00765    MAR      02       PLEMEL, DErl                 SE/SE/S30                           37-19      5     MAR
                  ROC'H'ON PLUMBING & HEATING        00765    MAR                      k      T?- I-              - @,L 2+ 5   1 - !5 1;?        '@?                      V,
                                                                                              i              WiSE /S-53                                    'S    '4Q      NO
                  ROCKON PLUMBING   & HEATING        00765    MAR      07       CAREY, JIM                   W/SE/S24                            37-19      20    MAR     NO
                  ROCHON PLUMBING   & HEATING        00765    MAR      08       W & R PARTNERSHIP            S/SW/S27                            36-20      35    MAR     NO
                  ROCHON PLUMBING   & HEATING        00765    MAR      09       GRAY, ELMER                  SW/S14                              36-20      100   MAR     NO
                  ROSS PLUMBING -   MICHIGAN         01791    OTS      01       MC CLELLAN, RALPH            SE/SE/Sl                            35-21      20    MAR     NO
                  ROSS PLUMBING -   MICHIGAN         01791    OTS      02       MC CLELLAN,   RALPH          E/NE/S12                            35-21      30    MAR     NO
                  BLUE SPRUCE BALLROOM (EBBEN)       01393    OCO      02       ARNDT, INC.                  SE/NW/S33                           29-20      40    Oco     NO
                  BLUE SPRUCE BALLROOM (EBBEN)       01393    oco      03       ARNDT, INC.                  SE/NE/S24                           29-19      40    Oco     NO
                  GEITER & SON                                NWD               NIGG, JOHN  J.               N/NE-S23                            32-15      So    OCO     YES









                  Page No.       9
                  09/11/92

                                                                                                  DISTRICT APPROVED SEPTAGE

                                                                                                      LANDSPREADING SITES



                                                                                              SORTED BY COUNTY OF SITE LOCATION




                  LICENSEE                           LICENSE LIC.       SITE    SITE                          LEGAL                              TOWNSHIP          SITE                DATE
                                                     NUMBER   CTY.      NO.     OWNER                         DESCRIPTION                        RANGE      ACRES  COUNTY INSP.        APPVD.



                  KIMMER SEPTIC SERVICE              01111    LNG       00      MOERICKE, MARIE               NW/NE-Sl3                          31-16      40     0CO     NO              / /
                  KOUNTRY PUMPER (KEN MATUSZAK)      01552    OCO       02      NASGOVITZ, MARVIN             W/SW/S19                           30-19      20     OCO     NO              / /
                  KOUNTRY PUMPER (KEN MATUSZAK)      01552    OCO       03      FONFEREK, JOE                 W/SW/S24                           30-17      30     OCO     NO              / /
                  KOUNTRY PUMPER (KEN MATUSZAK)      01552    OCO       04      FISHER, LYLE                  N/NW-S27                           30-17      30     OCO     NO              / /
                  KOUNTRY PUMPER (KEN MATUSZAK)      01552    OCO       05      BIEBER, FERRIS                E/SE-SlO                           29-20      80     OCO     NO              / /
                  PAL'S SEPTIC SERVICE (ZACHOW)      00655    oco       02      KONITZER, JOHN                N/SW/S34                           27-20      80     Oco     NO              / /
                  PAL'S SEPTIC SERVICE (ZACHOW)      00655    0CO       03      KACZMAROWSKI, JULIUS          SW/Nw/S2l                          27-19      25     OCO     NO              / /
                  PAL'S SEPTIC SERVICE (ZACHOW)      00655    OCO       06      KUSSOW, THOMAS                W/NW/S24                           26-20      80     OCO     NO              / /
                  PAL'S SEPTIC SERVICE (ZACHOW)      00655    Oco       09      PETERSON, ARNOLD              NE/SW-sl6                          29-20      80     Oco     NO              /
                  R.T.S. SANITATION (SOPER)          01864    SHA       02      GREENWOOD, DOROTHY            SE/SE-S9                           28-19      40     OCO     NO              /
                  R.T.S. SANITATION (SOPER)          01864    SHA       04      YOUNG, ROBERT                 SE-S35                             29-18      70     0CO     NO              /
                  R.T.S. SANITATION (SOPER)          01864    SHA       05      SCHAAL, DAVID                 S/NE-S20                           28-18      60     0CO     NO              /
                  R.T.S. SANITATION (SOPER)          01864    SHA       06      PATZER, ED. JR.               N 1/2 - S33                        28-18      100    0CO     NO          03/23/92
                  R.T.S. SANITATION (SOPER)          01864    SHA       07      FIFIELD, TIM                  SW/NE & NW/SE     S6               28-17      10     OCO     NO          03/30/92
                  SHORELAND SAN. SER. (MELLAND)      01610    OCO       02      WEIGELT, GERALD               SW/NE/s27                          28-21      10     0CO     NO
                  SHORELAND SAN. SER. (MELLAND)      01610    OCO       04      RADZINSKI, JOAN               N/NE-S34                           28-21      10     oco     YES         09/09/91
                  SUTRICK  SEPTIC(EDMOND   SUTRICK)  00300    OCO       01      LUTHER, MARTIN                SE/NW-S21                          28-19      27     OCO     NO
                  SUTRICK  SEPTIC(EOMOND   SUTRICK)  00300    OCO       02      SOLOMON, VINCENT              NE/SE-Sl                           27-19      9      OCO     NO
                  SUTRICK  SEPTIC(EDMOND   SUTRICK)  00300    OCO       07      SHEPHERD, JOHN                NE/NW/S7                           27-19      21     0CO     NO
                  SUTRICK  SEPTIC(EDMOND   SUTRICK)  00300    OCO       08      KONITZER, FRANK               SE/NE/S2                           27-19      15     OCO     NO
                  SUTRICK  SEPTIC(EDMOND   SUTRICK)  00300    OCO       10      SOLOMON, VINCENT              SE/NW-Sl                           27-19      20     0CO     NO
                  SUTRICK  SEPTIC(EDMOND   SUTRICK)  00300    OCO       11      SHALLOW, OLIVER JR.           SE/NE-S25                          29-20      8      OCO     NO (PHONE       /
                  WARSCHKOW, JACK                    01503    oco       02      WARSCHKOW, JACK               E/NE/S30                           29-19      120    OCO     YES             /
                  WARSCHKOW, JACK                    01503    OCO       03      KAUFMAN, BERLIN               S/SE/S28                           29-19      75     OCO     YES             /
                  DALE'S SEPTIC SERVICE              00539    OUT       03      KRAKE, ROBERT                 E/NW-S15    E/SE/SW-SlO            22-15      12     OUT     YES             /
                  DALE'S SEPTIC SERVICE              00539    OUT       04      TEWS, WALTER                  SE/NW/S7                           22-15      35     OUT     NO
                  FLUSH, INC.-(JEROME O'BRIGHT)      01030    WIN       02      JENNERJOHN, N.J.              S/S/S5                             21-16      50     OUT     NO
                  FLUSH, INC. (JEROME O'BRIGHT)      01030    WIN       03      JENNERJOHN, N.J.              E/SE/S26                           22-15      40     OUT     NO






                                             SECTION                3 1-93

                  HANDLING COMPLAINTS                           Zoning Office
                                                              oconto County, W1

                  Tom Nelson's advice to haulers to avoid complaints from property owners
                  surrounding disposal sites is:

                  1.   Inject the septage. This disposal Tnethod reduces odor and if
                       adjacent property owners don't see septage, they won't be so apt to
                       complain about the use of the site.

                  2.   Keep vehicles clean.

                  3.   Don't use a disposal site day after day. Concerns are likely to
                       develop if a hauler is scen continually' on one site.

                  Vhen a complaint is received, enter the information in the complaint
                  log.

                  1.   Be responsive. Return phone messages promptly and get action from
                       hauler (if necessary) as soon as possible.

                  2.   Suggest the complainant talk to the hauler. Haulers don't want to
                       irritate landowners and might be willing to change disposal prac-
                       tices.


                  3.   Involve county officials (zoning administrdtors and/or county
                       sanitarians).

                  4.   Get specific information from complaintant as to location of
                       problem, extent of problem, concerns involved, hauler suspected,
                       etc.


                  5.   Give hauler benefit of the doubt, i.e. call and find out their side
                       of the story. Before calling, check file to see if truck color and
                       description match those in complaint.      If possible, check legal
                       description of area described in landspreading complaint against
                       sites listed on annual license renewal forms. Also, check soil
                       types for specific sites in soil survey if available, so you're
                       fully informed when confronting the hauler.

                  6.   For "dumping" co-mplaints, ask the complaintant if the truck is
                       moving while waste is running out of the back.       If so, how fast is
                       it moving, and is the field being evenly covered? How much
                       distance is being allowed to houses, wells, property lines, etc.?
                       Explain code requirements after the questions are answered.

                  7.   Complaintants have the right t   o remain anonymous.    However, caution
                       them that if they don't identify themselves, then we can't call
                       them back to tell them how their complaint was resolved. They may
                       want to leave their first name and phone number and request that
                       this information not be made    part of the file.    This data can be
                       kept in a diary, card file, etc. and be destroyed after the
                       complaint is resolved. Do not put their name in the complaint log
                       if they wish to remain ancnymous, as this log is public record.
                                                                                          4/87

                                                        A-3











                                 WISCONSIN DEPARTMENT OF NATURAL RESOURCES
                                     ENVIRONMENTAL ENFORCEMENT PROGRAM



                program staff  ---------  VIOLATION IDENTIFICATION    -------- ADVISE LOCAL WARDEN
                                                     ,
                program staff  ----------  NOTICE OF NONCOMPLIANCE   --------- ADVTSE LOCAL WARDEN


                                                 (follow-up)        (yes)         Close-out

                                                        (no)


                program staff -------- REQUEST SECONDARY ENFORCEMENT -----ADVISE LOCAL WARDEN





          environmental enforcement   -----  NOTICE OF VIOLATION   --------- ADVISE LOCAL WARDEN
                                  
          program staff                           (follow-up)      (yes)         Close-out




          environmental enforcement ---    ENFORCEMENT CONFERENCE   -------- ADVISE LOCAL WARDEN


          program staff  ------------  (participation  and follow-up)      (yes)     Close-out

                                                         (no)


          environmental enforcement ----    ADMINISTRATIVE ORDER (OPTIONAL) ADVISE LOCAL WARDEN


          program staff  ---------------   (review and  follow-up)       (yes) Close-out
                                                         (no)


          environmental enforcement   ----------  REFERRAL   TO LOCAL DISTRICT ATTORNEY
                                                              (LONG FORM CIVIL COMPLAINT FORM)

          program staff  --------  (review, participate, and follow-up)






                                                       A-3. 1
 






                                         SECTION 7




               ENFORCEMENT - See the Environmental Enforcement Handbook (4190.5),
               Chapters 10 and 20 for more information.

               Stepped Enforcement - Object is to gain compliance with state or federal
               laws.
                    Primary Enforcement:      informal contacts
                                              Notice of Noncomrliance (sent by program
                                              staff)

                    Secondary Enforcement:    Notice of Violation (sent by district
                                              enforcement staff) - should be issued
                                              within 30-60 days of violation
                                              Enfoz-cei,ient C@,nference


               NON   subject line = Notice of Noncompliance.  Informs the violator of
               the roncom?liance with the statuces or codes, and identifies the specif-
               ic viclation.  A response is usually rcquested within a specific time
               period as to how the problem will be solved.

               NOV - subject line = Notice of Violation.  Sent by district enforcement
               specialist by Certified Mail.  Objectives:

               1.   Document specific violations of the law, citing statutory authori-
                    ty.
               2.   States the Department is aware of the violation.
               3.   Advises of possible prosecution and forfeitures.
               4.   Requests a written response within a specified time period.
               5.   Requests remedial action within a specified time period.
               6.   Requests additional information, including a schedule for regaining
                    compliance within a specified time period.
               7.   Schedule an enforcement conference.


               All letters must be documented in files.


               Routine letters are not enforcement actions.  These would include
               letters that request information, transmit forms, reminders of incorrect
               fees, incomplete forms, ete.

               Enforce ment Conference - A formal meeting with the violator. The
               enforcement specialist takes the lead role. Meeting agenda includes the
               following:


               1.   Gather information about the violation.
               2.   Provide an opportunity for the violator to explain the reason
                    and/or cause of the violation.
               3.   Explain the Department's intended actions if the violation is not
                    resolved.
               4.   Obtain a commitment from the violator to achieve compliance.









                                                 A -4











          If agreements are reached at the conference, a Compliance Agreement
          should be written to document the commitments. The agreement should
          include:


          1.   The facts of the violation.
          2.   The legal basis of the Department's actions.
          3.   The actions which the violator agreed to take to correct the
               V.Lolation, including a compliance schedule.

          Issuance of Citations - See memo to District Wardens describing vio-
          lations they might see in the field,.Pad what to cite under..

          E-nf,)rcenien,: '1'h.romh -1-b P. Co-,nr_Y Lis tr -.i cc t. At toriey - The Bur-2-au c, f Legal
          Counsel Hs decided that violations of s.146.20 will not be handled
          through the Department of Justice. Prosecution of NR 113 violations
          should be sought through the County District Attorney, and may be done
          by county officials as well as DNR employees.

          Documentation and ENTRACK - All violations and enforcement actions must
          be documented in area, district and Central Office files.

          Actions beginning with Nocices of Noncompliance through referrals are
                    0                                          0
          entered in the enforcement tracking system (ENTRACK). Janet Hopke
          enters this information.


          Closing Out Violations - When a violation is resolved and no further
          enforcement is planned, the violation must be closed out. The staff
          person who signed the most recent enforcement letter should draft a
          letter to the violator that no further action will be taken, but that a
          future violation may subject them to enforcement again.

                                                                           4/87

















                                           A-4.1







                                               SECTION 10




                   SITE INSPECTIONS


                   When requests for septage landspreading site aoprcval are received, the
                   district does as much preliminary work in the 'office as possible.      A sk
                   for an aerial photo and soil mapping to be submitted.
                                                         0

                   The Landspreading Site Evaluate Checklisr is very useful for site
                   investigations.   Use the legai description for the site location line.
                   The soil survey shows the soil types, series, and land use. This
                                                       r,
                   information provides the slope, depth to groundwater, and depth to
                   bedrock.   After the above information is obtained, the site T.-.a,! nct be
                   approvable.   In that case, a site visit has been avoided.      Inform the
                   haliler requesting approval that the site is not acceptable for land-
                   spreading.   The Agricultural Site Evaluation Fotm for Land Appl'cat-*on
                   (Form 3400-122)  can be used for notification of approval/denial.      The
                   standard conditions for municipal sludge application listed on the back
                   of the form zlosely follo-; sepLace landspreading rules.
                                                      C,            - a


                   If a site inspection is warrantes:, take a soil auger to check soil
                   te-xture, color, evidence of around-,zater, etc.   Also, while on site check
                   for:


                   1.    location of nearby residences, public and private wells,

                   2.    also, watch out for old wells and hand pumps in the field that are
                         not properly abandoned and are most likely of substandard
                         construction,

                   3.    lo-,,7 areas subject to flooding or ponding,

                   4.    location of surface waters,

                   5.    evidence of rock outcroppings and sink holes,

                   6.    de-ree and extent of slopes,

                   7.    drainage patterns  and how they will affect surround4n- land areas,

                   8.    condition of field; has it been used for crops recently or is it in
                         continuously, unharvested sod? Are there any truck ruts, burned
                         vegetation, eroded gullys, or obvious "dumping" soots?

                   9.    Decide if field has obvious evidence of being used for      septage
                         application.   Inquire as to frequency of use to see if hauler's
                         response matches evidence on field.     Hauler may say it's used
                         frequently when you actually don't see any evidence of it.      In that
                         case, suspect that they're heavily using a bad site, but showing a
                         good site that's seldom used.    Ask them to show you their most
                         heavily used site also.

                   10.   While on site, point out good and bad points about site to the
                         hauler, as well as all precau6ions for use.

                                                                                         4/87
                                                        A-5











                                   VIOLATIONS THAT WARRANT CITATIONS




                   A).  VIOLATIONS OF THE CODE REGARDLESS OF LICENSING STATUS:

                         -Discharging of septage less than 200 feet from a ditch, dry run,
                           pond, lake , stream, flowage or floodplain.
                              *NR 113.07(3)(c)3., s.s.29.29.

                        --Discharging of septage into or on any ditch, dry run, pond, lake,
                           stream, flowage, floodplain, cave, sinkhole, mine, gravel pit or
                           quarry.
                              *NR 113.07(4)., s.s.29.29.

                        --Allowing the spreading vehicle to remain motionless while
                           discharging the septage from the vehicle.
                              *NR 113.07(3)(c)7.
                        --Allowing the septage to become pon&d after spreading.     Ponding
                           is defined as an accumulation of liquids to form standing water.
                           (The limitation from the revised NR 113 is that no free liquid of
                           3 square feet or more be visible 2 hours after application of the
                           septage).
                              *NR 113.07(3)(c)7.

                        --Discharging of septage within 200 feet of any private well.
                              *NR 113.07(3)(c)S.

                        --Discharging of septage within 500 feet of any place of habitation
                           or business or area used for recreational purposes.
                              *NR 113.07(3)(c)6.

                        --Use of a sumip pump and hose to pump out tanks and dispose of the
                           wastes.  This is evidenced be a hose coming out of the tank and
                           discharging the wastes to the ground surface.   Also included is
                           the alteration of the tanks, whereby a hole is punched in the
                           tank and a buried pipe connected to.the tank discharges the
                           wastes to the ground surface.
                              *NR 113.07(3)(c)l.-7.











                                                    A-6










  :4.






                        B)    VIOLATIONS OF THE CODE WHICH ARE SPECIFIC TO THE LICENSING STATUS:


                         "PRIVATE HOMEOWNER VIOLATIONS:

                              --Persons who are servicing their own tanks without being
                                registered as a private pumper.
                                   *NR 113.04, s.s.146.20(3)(d).

                              --Operating a vehicle used for servicing without having "Not For
                                Hire" prominently displayed on both sides of the servicing
                                vehicle. They should also have the vehicle certification sticker
                                displayed on the rear of the servicing vehicle.
                                   *NR 113.06(3)(1)4.







                         **COMMERCIAL PUMPER VIOLATIONS:

                              --Persons who are servicing tanks for others without being licensed
                                as a commercial hauler/pumper.
                                   *NR 113.04., s.s.146.20(3).

                              --Operating a vehicle used for servicing without having the valid
                                vehicle certification sticker displayed on the rear of the tank.
                                They are also required to have the words "Wisconsin Sanitary
                                Licensee" and "License No. " painted on both sides of the
                                servicing vehicle.  Licensed Plumbers may have their plumber's
                                license number painted on the vehicle instead of their Sanitary
                                License number.
                                   *NR 113.06(3)(1)1.,2., s.s.146.20(3)(c).















                                                    A-7
















                   Septage         
			 Newsletter



          Vol. 3, No. 6                 PUBL-WWOO6                     April, 1993


          TO:      Licensed Pumpers                      RECEIVED
                   County Zoning Administrators
                   Municipalities                         MAY. 10 1993
          FROM:    Robert J. Steindorf, P.E.                 Zoning Office
                   Municipal Wastewater Section            Oconto County. WI


                                 TOPICS IN THIS ISSUE


                                   Certificate Renewal Dates
                                    Continuing Education
					Draft Schedule for NR 113 Revisions
						Federal 503 Regulations
					How Are We Doing On Certification?
					     Septage Hauler's Decals



                           CERTIFICATE RENEWAL DATES


          All certificates are being issued for a two-year period, as required by NR 114. Some concerns have
          been raised about the dates we have selected for issuing the certificates. The concern is that people
          who took the exams early are being disadvantaged because they will have less time to accumulate the
          required 12 hours of continuing education credits before their certificate needs to be renewed.

          The procedure we used to set certification dates is as follows. The first three exams were given on
          January 12, 1991; August 17, 1991; and January 25, 1992. The revisions to NR 114 that affect
          septage operator certification went into effect on March 1, 1992. We didn't feel we could certify
          anyone for a date before the rule went into effect, so for anyone who passed the exams on those first
          three dates, we arbitrarily selected an effective date of May 1, 1992. This date was selected because
          it was after the rule went into effect and because the renewals would fit in reasonably well with other
          Department workloads.

          For anyone passing a test on a later date, we made the effective date the date of the test. This is
          partly based on our need to balance out the workload of certificate renewals. We will probably have
          about 1,000 certified operators in the future, and we cannot handle the kind of workload that would
          come if we had 1,000 renewals coming in at about the same time, once every two years. In addition,
                                           A-8
 





                                                                   2

                NR 114.08 says that we should issue the certification "upon satisfactory fulfillment of 'the
                qualifications required by this chapter." We take this to mean that the certificate should be issued
                once the test has been passed.

                Part of the confusion may come from NR 114.16, which says "septage servicing operators who are
                performing septage servicing as of March 1, 1992 shall have one year from that date to become
                certified." Some people are interpreting this to mean that we would issue all of the certificates to be
                effective on March 1, 1993. We have interpreted this to be a deadline that people could not go
                beyond, and not the date that the certificates would be issued on.

                If you have any questions or comments on these certification dates, please call John Cain at
                (608) 266-9259.



                                                                      EDUCATION


                After you have successfully passed your septage certification exams, it will be time for you to
                consider your responsibilities regarding "continuing education" and the renewal of your certification
                within two years. As you know, you will no longer have to take certification exams to retain your
                certificate. However, as new developments in the septage industry emerge, you will need to keep
                abreast of them by taking at least 12 hours of training every two years.

                Before the expiration date on your wallet card, certified vehicle operators and operators-in-charge will
                need to receive 12 hours of training in order to have their septage servicing certification renewed.
                Training opportunities will soon be available and they will be announced by the Department and other
                organizations involved in scheduling and delivering training.

                In the past, the Wisconsin Liquid Waste Carriers Association has been a primary septage training
                delivery organization in Wisconsin. They will likely continue to deliver training at their two
                conferences each year. In the future, the Department of Natural Resources, the Vocational Tr        g
                and Adult Education system, and vendors in the septage industry will likely provide training
                opportunities in Wisconsin. This training will likely be conducted in numerous locations in the state
                convenient to your business or place of work.

                Since new regulations, such as the Federal 503 regulations, will be impacting the septage industry in
                the next few years, it is important that you organize your training plans to receive information on
                these new developments. Training opportunities will be announced as often as possible in this
                publication so that you are aware of them far enough in advance to fit them into your busy business
                schedule.



                                DRAJff SC IMULE FOR NR 113 REVIRONS

                Following is the latest projected schedule for revisions to Chapter NR 113 of the Wisconsin
                Administrative Code. This is a draft schedule and, as such, is subject to change. You will be kept
                informed of any significant changes.

                I .   Complete an initial draft of proposed rule changes.                              October 31, 1993
                2.    Develop a Technical Advisory Committee (TAC).                                 November 12, 1993
                3.    Start TAC review/input on the draft rule changes.                              December 10, 1993
                                                                   A-8. I






                                                                      3

                 4.     Complete TAC review/input on the draft rule changes.                                  April 1, 1994
                 5.     Natural Resources Board authorization to go out for public
                        hearings on draft rules.                                                                  May,   1994
                 6.     Public hearings on draft rules, in four locations.                                July/August,   1994
                 7.     Evaluate comments, develop responsiveness document, revise
                        draft codes.                                                                    September 30,    1994
                 8.     Natural Resources Board approves administrative rule.                               November,    1994
                 9.     Rules sent to legislature (two standing committees).                                   January,  1995
                 10.    Final administrative rule published.                                                 March 1,    1995
                 11.    Effective date of administrative rules.                                                 July 1,  1995


                                              I IERAL 503 REGULATIONS


                 The long-awaited federal 503 sludge and septa@ge regulations were printed in final form in the Federal
                 Register on February 19, 1993. The total package of regulations that apply to both sludge and
                 septage is quite lengthy and complex. However, I will summarize a simpler version that can be used
                 for landspreading septage provided two conditions are met:

                 1.     The application must be to non-public contact sites; and,

                 2.     The septage must be from strictly domestic sources.

                 Non-public sites are sites which are not frequently used by the general public, such as agricultural
                 fields, forest land, and reclamation sites. Strictly domestic means that there are no commercial or
                 indvstrial wastes, such as grease trap wastes, mixed in with the septage. It does not exclude totally
                 domestic septage from commercial or industrial sources where the septage is kept completely separate
                 from other wastewaters. If you meet these criteria, the federal regulations require you to comply with
                 the following:

                 (NOTE - YOU MUST ALSO REMAIN IN COMPLIANCE WITH CHAPTER NR 113. WHERE
                 THERE IS A DIFFERENCE BETWEEN THE STATE AND FEDERAL REQUIREMENTS, YOU
                 MUST FOLLOW THE MORE RESTRICrfVE ONES.)

                 1.     Deadlines For Achieving Compliance

                        a.    Monitoring, record keeping, and reporting - by 7/20/93.

                        b.    With all other requirements - by 2/19/94; or if construction is necessary to achieve
                              compliance - by 2/19/95.

                 2.     Records That Must Be Kept For At Least Five Years

                        a.    Location of the site where septage is applied.

                        b.    Number of acres to which septage is applied at each site.

                        C.    The date and time of each septage application.

                        d.    The nitrogen requirement for the crop grown on each site during the year. While not
                              required, you should also indicate the expected crop yield.

                        e.    The number of gallons which are applied to the site during the specified 365 day period.
                                                                    A-9






                                                                      4

                       f.     Certification by the hauler that he has met the pathogen and vector attraction reduction
                              requirements.

                       g,     A description of how the pathogen requirements were met.

                       h.     A description of how the vector attraction reduction requirements were met

                3.     Determining The Maximum Volume Of Application

                       The maximum volume of septage which may be applied to any site depends on the amount of
                       nitrogen required by the planned crop and yield. (See Appendix for table of typical nitrogen
                       uptake rates for various crops grown in Wisconsin.)


                                 Annual Application Rate (AAR)               Pounds of Nitrogen -Required
                                 (gallons/acre/year)                       ----For the Crop & @'ield
                                                                                         0.0026


                FOR EXAJAPLE: If your crop needs 100 pounds of nitrogen per acre, you would calculate:


                                            AAR                          100 pounds/acre

                                                                              0.0026

                                            AAR                     38,500 gallons/acre/year


                4.     Pathogen Reduction, Site Restriction Requirements - These can be satisfied by complying with
                       either "a" or "b" below.

                       a.     Raise the pH of the septage to 12 or higher by alkali addition and, without the addition
                              of more alkali, maintain it at 12 or higher for 30 minutes; gnd meet crop restrictions Mv
                              under "c" below.


                       b.     Apply septage to the site without treatment but meet crop restrictions i-vi under "c" and
                              site restriction i under "d" below.


                       C.     Crop Restrictions

                              L      Food crops with harvested parts that touch the septage/soU mixture and are totally
                                     above ground shall not be harvested from the land for 14 months after application.

                              ii.    Food crops with harvested parts below the surface shall not be harvested for 20
                                     months after application when the septage remains on the surface for four months
                                     or longer prior to incorporation.

                              iii.   Food crops with harvested parts below the surface shall not be harvested for 38
                                     months after application when the septage remains on the surface for less than
                                     four months prior to incorporation.

                              iv.    Feed, fiber and other food crops shall not be harvested for 30 days after
                                     application.

                                                                        A-9 . 1






                                                                    5

                             V.     Animals shall not be allowed to graze on the land for 30 d4ys afte.r application.

                             vi,    Turf grown on land where septage is applied shall not be harvested for one year
                                    after application when the harvested turf is placed on either a lawn or other land
                                    with potential for public exposure.

                       d.    Site Restriction

                             L      Public access to land with a low potential for public exposure shall be restricted
                                    for 30 days after application. Examples of restricted access include remoteness,
                                    posting and/or simple fencing.

                5.     Vector Attraction Reduction - This can be satisfied by doing one of -the following: either "a",
                       "b", or "CH.

                       a.    Immediately inject the septage below the surface of the land.

                       b.    Incorporate the septage into the soil surface plow layer within six hours after application.

                       C.    Raise the pH of the septage to 12 or higher by alkali addition and, without the addition
                             of more alkali, maintain it at 12 or higher for 30 minutes.

                6.     Comply With The Following Management Practices

                       a.    Do not apply in areas where there is potential for harming threatened or endangered
                             species of plant, fish, or wildlife or their habitat.

                       b.    Do not apply to flooded or saturated soil.

                       C.    Do not apply to frozen or snow-covered land such that the septage will enter a wetland
                             or other waters of the U.S.


                       d.    Do not apply septage to land that is 10 meters (33 feet) or less from the waters of the
                             U.S.


                REM]EM[13ER, the above restrictions apply only to the disposal of sgptage from strictly domestic
                sources to non:public contact sites. If you do not meet both of these criteria, you must comply with
                the more elaborate requirements contained in the regulations. In any case, you must also be in
                compliance with the requirements contained in Chapter NR 113, Wisconsin Administrative Code,
                whenever they may be more restrictive than the federal regulations. If you have any questions, please
                contact Bob Steindorf at (608) 266-0449.

                                                              APPENDIX


                                          Nitrogen Uptake by Various Crops in pounds/acre*
                                      CROP -TYIELD PER ACRET-@,77iAKE aM/ACRE)
                                  Corn              120 bu                    150
                                                    140 bu                    185
                                  Corn silage       32 tons                   200
                                  Soybeans          50 bu                     257**
                                                                   A-10





                                                                   6


                                                    60 bu                     336**
                                 Grain sorghum      8000 lbs                  250
                                 Wheat              60 bu                     125
                                                    90 bu                     186

                                 Oats               100 bu                    150
                                 Barley             100 bu                    150
                                 Alfalfa            8 tons                    450**
                                 Orchard grass      6 tons                    300
                                 Brome grass        5 tons                    166
                                 Tall fescue        3.5 tons                  135
                                 Bluegrass          3 tons                    200


                       These numbers are approximate. For more specific information on crop needs in your area,
                       contact your local agricultural extension agent.

                       Legumes get most of their nitrogen ftom the air so additional nitrogen sources are not
                       normally needed.


                                HOW ARE WE DOWG ON U                                       ATION?

                Many septage servicing operators and septage servicing business owners have been making good
                progress toward getting certified in time to meet the two deadlines given in NR 114. Anyone
                operating a septage servicing vehicle after March 1, 1993, must be certified as a Grade 1 operator.
                In order for a business license to be renewed for the July 1, 1993 to June 30, 1994 period, the owner
                must designate a Grade 2, operator in charge. The owner does not have to be the operator in charge,
                but it must be someone that is actively involved in the business. To become a Grade 2 Operator, you
                must pass both the Grade I and the Grade 2 exams.

                So far, exams have been offered eight times in the past two years. Three of these times, the exams
                were offered at six locations throughout the state. In addition, exams have been offered to some of
                the larger businesses near their headquarters to save travel time for their employees.

                As of the February 27, 1993 exam, 910 people have taken at least one exam and many people have
                taken both. Of these 910 people, 780 have passed the Grade I exam and 484 have also passed the
                Grade 2 exam.


                One thing that was pretty surprising was that, so far, 20 people have recorded perfect scores on the
                Grade 1 exam and 2 people have recorded perfect scores on the Grade 2 exam. In addition, a
                number of people have scored in the 90's on both exams. This shows that there are a lot of haulers
                who have really done their homework and really know their business. Anyone passing the exam
                should be proud, but anyone getting scores that high should be especially proud.

                The percent of people passing each exam varies a little each time the exam is offered. Also, the
                exams have been changed slightly between offerings, to improve the quality of the exams and for
                security reasons. Over all of the offerings, the pass rate for the Grade 1 exam has been slightly over
                70 percent and the pass rate for the Grade 2 exam has been slightly under 70 percent. Most people
                who take both exams score higher on the Grade I than on the Grade 2.
                                                                    A-10. 1






                                                                        7

                 Unfortunately, we still have 187 people who have taken one or both exams and- still have not passed
                 at least one of them. Hopefully many of these people will be able to retake these exams on May 12,
                 and get a passing grade. A number of people who did not pass an exam on the first try came back
                 and passed on a second or third try.

                 We are in the process of sending out certificates to everyone who is ready to be certified. If you
                 have passed a test and still not received your certificate, it may be that we are holding it. For anyone
                 who has indicated they want to become a Grade 2 Operator, but has only passed one of the two
                 exams, we are holding off on issuing a certificate until both exams are passed. If you applied to take
                 both tests but only passed the Grade 1 test, you're eligible to be certified as a Grade I Operator.
                 However, you should let us know so we can issue your certificate. If you passed the Grade 2 test,
                 but not Grade 1, you are not eligible to be certified as a Grade 2 Operator until you pass the Grade 1
                 test.


                 If you passed both tests you will be certified as a Grade 2 Operator. It is understood that anyone
                 having a Grade 2 Certification has passed both tests. You will not get both a Grade I and a Grade 2
                 Certificate.


                 If you have any questions on certification, please call Tom Mickelson at (608) 266-8907.


                                               SEFTAGE HAUl"'S DECAIS

                 Starting on July 1, all septage servicing vehicles should display a new decal. Ile color for 1.993-94
                 will be yellow. The decal should be displayed on the back of the vehicle. Also, each vehicle should
                 have the business owner's license number displayed on both sides.

                 If you have any questions about whether or not a vehicle is properly licensed, you should check with
                 the septage coordinator in your district. The six coordinators are:

                  Jim Perry                    Southem District                         Madison               608/275-3325
                  Tom Nelson                   Southeast District                       Milwaukee             414/263-8635
                  Jim Friedrich                Lake Michigan District                   Green Bay             414/492-5877
                  Dan Boardman                 North Central District                   Rhinelander           715/369-8972
                  Lyle Gast                    Westem District                          Eau Claire            715/839-3749
                  Jim Hansen                   Northwest District                       Park Falls,           7151762-3204




















                                                                        A-11




                                 DEPARTMENT OF NATURAL RESOURCES        366-9
                                                                NR 113

                                           TABLE 3
                               MAXIMUM METAL LOADINGS TO A SITE
                                    Maximum Site Loading based on Soil Cation Exchange Capacity
                                                       (meq/100g) in lbs/ac
                                       Less than 5                    5-10                   10-15             Greater than 15
                  Cadmium                   4.5                       9.0                    13.5                    1.0
                    Lead                  445                       890                    1335                   1750
                    Zinc                  225                       445                     670                    890
                    Copper                110                       220                     335                    445
                    Nickel                 45                        90                     135                    180
                  16. The minimum separation distances and maximum slope require-
              ments for different septage application alternatives are listed in Table 4.

                                                                   TABLE 4

                                                                 Surface
                                                                 Spreading            Incorporation                 Injection
              Minimum depth from surface to                        3.0 ft                  3.0 ft                      3.0 ft
              bedrock and groundwater
              Maximum allowable slope                              6.0%                    9.0%                       12.0%
              (nonwinter)
              Maximum allowable slope                              2.0%                    4.0%                        6.0%
              (winter-site unmanaged)
              Maximum allowable slope                              4.0%                    N/A                         N/A
              (winter-site managed)
              Minimum distance to a                                1000 ft                 1000 ft                    1000 ft
              community well
              Minimum distance to a private or                      200 ft                  200 ft                     200 ft
              noncommunity well
              Minimum distance to a residence,                     1000 ft                  500 ft                     500 ft
              business or recreational area
              Minimum distance to a residence                       500 ft                  200 ft                     200 ft
              or business with written
              permission from the owner or
              occupant to spread closer than
              usual
              Minimum distance to a stream,                          N/A                    100 ft                     100 ft
              river, pond, lake, sinkhole,
              flowage, ditch or wetland (greater
              than 6% to 12% slope)
              Minimum distance to a stream,                         100 ft                   50 ft                      50 ft
              river, pond, lake, sinkhole,
              flowage, ditch or wetland (0% to
              6% slope)
              Minimum distance to a dry run                          50 ft                   25 ft                      25 ft
              and a property line
                 (C) Special Site criteria for land application of septage. 1. Septage may be
              landspread seasonally on or into soils with a seasonal high groundwater
              level at a depth of greater than 2 feet but less than 3 feet from the surface
              if it is demonstrated that the soil has an available water capacity greater
              than 5 inches for the soil above the high groundwater level.
                2. Septage may not be surface applied on fields where crops are grown
              which will be grazed by or fed to dairy cows within one month after
 







                    OCONTO COUNTY SEPTAGE SITES 1993

              County Site        Acres        Owner                     Licensed Pumper

              OCSS  1            40           Marie Moericke            Bostwick Septic
              OCSS  2            80           John Nigg                 Geiter & Son
              OCSS  6            100          Ed Patzer                 RTS Sanitation
              OCSS  7            60           David Schaal              RTS Sanitation
              OCSS  9            10           Joan Radzinski            Shoreland Sanitation
              OCSS  10           27           Martin Luther             Sutrick Septic
              OCSS  12           9            Vincent Solomon           Sutrick Septic
              OCSS  13           20           Vincent Solomon           Sutrick Septic
              OCSS  14           15           Frank Konitzer            Sutrick Septic
              OCSS  16           40           Frank Konitzer            Sutrick Septic
              OCSS  17           75           Berlin Kaufman            Warschkow, Jack
              OCSS  18           120          Jack Warschkow            Warschkow, Jack



                    28 Sites were on the origional DNR approved list


                    16 Sites were removed


                    12 Sites remain open
































                                                       A-13









           SEPTIC PUMPERS THAT FREQUENTLY WORK IN OCONTO COUNTY



           Bartz Septic Service                  Stordeur Sanitation
           2331 Cedar Lane                       3110 Glendale Avenue
           Green Bay, WI 54313                   Green Bay, WI 54313
           414-434-1085                          414-434-2888
           WDNR License #726                     WDNR License #704

           Bostwick Septic Service               Robert Sutrick
           W1425 Rose Lake                       d/b/a Sutrick's Septic Service
           White Lake, WI 54491                  359 South Washington Street
           715-484-3683                          Oconto Falls, WI 54154
           WDNR License #1930                    414-846-2378
           Fox Valley Portables                  WDNR License #300
           AAA Sanitation, Inc.                  Jack Warschkow
           1448 West Frontage Road               d/b/a Jack's Septic
           DePere, WI 54115                      9308 County A West
           414-336-5409                          Lena, WI 54139
           WDNR License #1191                    414-829-5273
           Gelter Construction, Inc.             WDNR License #15.03
           1775 Ogden Ave                        Willems Sanitation
           Wabeno, WI 54566                      812 North Duluth Place
           715-473-3901                          Sturgeon Bay, WI 54235
           WDNR License #18                      414-743-8047
                                                 WDNR License #1952
           Dan LaBrosse
           Kountry Pumper                        William Zachow
           8188 County CC                        d/b/a Pal's Septic Service
           Oconto Falls, WI 54154                3085 Sot Road
           1-800-236-2339                        Abrams, WI 54101
           414-846-2117                          414-826-5844
           WDNR License #1552                    WDNR License #655


           John Melland
           d/b/a Shoreland Sanitation
           1005 McDonald Street
           Oconto, WI 54153
           414-834-2563
           WDNR License #1610

           Randy and Tim Soper
           d/b/a R.T. Sanitation
           Route 3, Box 470
           Pulcifer, WI 54164
           WDNR License #1864









                                                           A-14                                       Rev. 2/92







                        COUNTY OF OCONTO



                                OFFICE OF


                       ZONING ADMINISTRATOR


                           Phone: 414-834-6827


                                   February 23, 1993.

          To     Mr. Lyle Fisher
                  10449 Central Road
                 Suring, Wisconsin 54174

          Dear Mr. Fisher:

          This letter is in regards to the septage site update, conducted by
          the Oconto County Zoning Office, which I previously discussed with
          you on the phone. If you will sign and date the statement below,
          your name will be removed from the list of active sites printed by
          the Department of Natural Resources.
               1              4 JV- @@ ZDate:             would like my name
               rehioytd from the DNR's list so my site7-s will no longer be
               rega.'eded as active for the spreading of public septage.

          Please return this letter in the post paid, self addressed envelope
          at your earliest convenience.

          Thank you for your cooperation in helping us update our records.

          Sin er y,


            ffrey    Zahm
          NonPoint Source Pollution Specialist








                                                               -E C E I V

                                                                  F EB 2 6 1993
            We
               r Y'



            ffr ey   Zal




















                                                                   Zoning Office
                                                                  oconto S22a, W1
                                           A-15








                          COUNTY OF OCONTO



                                 OFFICE OF
                        ZONING ADMINISTRATOR

                            Phone: 414-834-6827


                                     February 23, 1993

          To





          Dear Mr.


          This letter is in regards to the septage site update, conducted by
          the Oconto County Zoning Office, which I previously discussed with
          you on the phone. If you will sign and date the statement below,
          your name will be removed from the list of active sites printed by
          the Department of Natural Resources.
                  I                        Date:4/7/1993 would like my name
                  removed from the DNR's list so my site/s will no longer be
                  regarded as active for the spreading of public septage.

          Please return this letter in the post paid, self addressed envelope
          at your earliest convenience.

          Thank you for your cooperation in helping us update our records.

          Sincerely,


          Jeffrey L. Zahm
          NonPoint Source Pollution Specialist
                         



         








                                              A-16
 











                 
                           COUNTY OF OCONT0



                                   OFFICE OF

                          ZONING ADMINISTRATOR

                              Phone: 414-834-6827


                                       February 23, 1993

           To      Mr. Marvin Nasgovitz
                   10584 Marl Lake Road
                   Pound, Wisconsin 54161

           Dear Mr.    Nasgovitz:

           This letter is in regards to the septage site update, conducted by
           the Oconto County Zoning Office, which I previously discussed with
           you on the phone. If you will sign and date the statement below,
           your name will be removed from the list of active sites printed by
           the Department of Natural Resources.
                I                           Date: 2-24-93 would like my name
                removed from the DNR's list so my site/s will no longer be
                regarded as active for the spreading of public septage.

           Please return this letter in the post paid, self addressed envelope
           at your earliest convenience.

           Thank you for your cooperation in helping us update our records.

           Sincerely,

           Jeffrey L. Zahm
           NonPoint Source Pollution Specialist
             
                   
                








										           RECEIVED
                                                                       FEB 26 1993
                                                                     Zoning 0ffices
                                                                    Oconto County, WI   
                                                                       
                                                 A-17
 







                        COUNTY OF OCONTO



                               OFFICE OF

                      ZONING ADMINISTRATOR


                          Phone: 414-834-6827


                                  February 23, 1993

         To:     Mr. Joseph Fonferek
                 Route 1
                 Suring, Wisconsin 54174

         Dear Mr. Fonferek:

         This letter is in regards to the septage site update, conducted by
         the Oconto County Zoning office, which I previously discussed with
         you on the phone. If you will sign and date the statement below,
         your name will be removed from the list of active sites printed by
         the Department of  Natural Resources.
              I                      Date: Feb 25-93 would like my name
              removed from the DNR's list so my site/s will no longer be
              regarded as active for the spreading of public septage.

         Please return this letter in the post paid, self addressed envelope
         at your earliest convenience.

         Thank you for your cooperation in helping us update our records.

         Sincerely



         Jeffrey L. Zahm
         NonPoint Source Pollution Specialist









                                                             RECEIVED    

                                                            FEB 26 1993
            							
									     Zoning Office
									   Oconto County, WI
                 












                                                                  
                                           A-18
 







                         COUNTY OF OCONTO



                                OFFICE OF

                       ZONING ADMINISTRATOR

                           Phone:. 414-834-6827


                                   February 23, 1993

         To     Mr. Robert Young, Jr.
                10172 Highway G
                Gillett, Wisconsin 54124

         Dear Mr. Mr. Young:

         This letter is in regards to the septage site update, conducted by
         the Oconto County Zoning Office, which I previously discussed with
         you on the phone. If you will sign and date the statement below,
         your name will be removed from the list of active sites printed by
         the Department of Natural Resources.
                
               I                            Date: 2-24-93 would like my name
               removed from the DNR's list so my site/s will no longer be
               regarded as active for the spreading of public septage.

         Please return this letter in the post paid, self addressed envelope
         at your earliest convenience.

         Thank you for your cooperation in helping us update our records.

         Sincerely,


         Jeffrey L. Zahm
         NonPoint Source Pollution Specialist






                                                         RECEIVE

                                                        MAR 1 1993
                                         
								       Zoning Office
									Oconto County, WI
           

                                                              




                                                     



                                            A-19
 






                         COUNTY OF OCONTO



                                 OFFICE OF

                        ZONING ADMINISTRATOR

                            Phone: 414-834-6827


                                    February 23, 1993

          To     Mr. Ned Buhrandt
                 6759 Settlement Road
                 Gillett, Wisconsin 54124

          Dear Mr.    Buhrandt:

          This letter is in  regards to the septage site update, conducted by
          the Oconto County Zoning Office, which I previously discussed with
          you on the phone. If you will sign and date the statement below
          your name will be  removed from the list of active sites printed by
          the Department of  Natural Resources.
               I Ned Buhrandt     Date: 2/26/93 would like my name
               removed from the DNR's list so my site/s will no longer be
               regarded as active for the spreading of public septage.

          Please return this letter in the post paid, self addressed envelope
          at your earliest convenience.

          Thank you for your cooperation in helping us update our records.
          
          Sincerely,



               
          Jeffrey L. Zahm 
          NonPoint Source Pollution Specialist




                                                RECEIVED

                                                  MAR 1    1993


                                                   Zoning Office
                                                  Oconto county, WI
                                             










                                             A-20
 






                        COUNTY OF OCONTO



                               OFFICE OF
                                                             E C E I V E
                       ZONING ADMINISTRATOR                   MAR 1 7 1993
                           Phone: 414-834-6827                  bmng Office
                                                               ocanto COU*. M
                                  February 23, 1993

         To     Ms. Alegra LaPoint
                Mr. Milo Soper
                1566 West 9th Avenue
                Oshkosh, Wisconsin 54901
         Location     SE114 SEI/4, Sec. 9, T28N, R19E, Town of Oconto Falls (40 acres)



         Dear Mr. Soper and Ms. LaPoint:

         The Oconto County Zoning Office has been updating all the licensed
         septage sites in the county. According to the records sent to us
         by the Department of Natural Resources,    .your property has been
         licensed as a septage disposal site.       In order to update our
         records we need to know if you would like to have your site/s
         remain active or not. Please check the appropriate box below.

                    Yes, I would like my- site/s to remain on the list of
                F-1 active sites.

                    No, I would  like my site/s removed from the list of
                    active sites.

         if you checked no please sign and date the enclosed fo= stating
         you would like your name removed from the DNR-;s list.

         Please send your reply in the post paid, self addressed envelope at
         your earliest convenience.

         If you have any questions feel free to contact me at the Oconto
         County Zoning Office. (414) 834-6832.

         Sin r y,


           ffrey L. Zahm
         NonPoint Source Pollution Specialist
                 Y'
                 _@p
         :f Vfrrev;L.1


                                          A-21







                          COUNTY OF OCONTO


                                 OFFICE OF                deceived
                       ZONING ADMINISTRATOR                    MAR 1 7 1993
                           Phone: 414-834-6827
                                                                 Zoning Office
                                    February 23, 1993    1993      Oconto  County, wi
                                     I Alegra La Point date 2/27/93      would like  my name
         removed from the DNR's list so my site/s will no 'Longer be regarded
         as active f or the spreading of public septage.

         If you would like your site to remain open please return the form
         with the approiate box checked. If you no longer want your site to
         remain active please sign and date this f orm and return it to our
         office.

         Sincerely,


         Jeffrey L Zahm
         NonPoint Source 'Pollution Specialist
            
            								A-22











                                            


             COURTHOUSE-300 WASHINGTON STREET-OCONTO, WI 54153-1621







                         COUNTY OF OCONTO


                                                              received                                                                         
                                 OFFICE OF                        
                       ZONING ADMINISTRATOR                       MAR - 51993

                           Phone: 414-834-6827
                                                                    Zoning Office
        To      Arndt, Inc.         February 23, 1993			Oconto County, WI		
                7512 Arndt Road
                Lena, Wisconsin 54139

        Dear Mr. Arndt:

        This letter is in regards to the septage site update, conducted by
        the Oconto County Zoning office, which I previously discussed with
        you on the phone. If you will sign and date the statement below,
        your name will be removed from the list of active sites printed by
        the Department of Natural Resources.
                     I Michtell R Arndt, Pres Date: 2/28/93 would like my name
              r                   DNR' s list so 'my sites will no longer be
              regarded as active for the spreading of public septage.

        Please return this letter in the post paid, self addressed envelope
        at your earliest convenience.

        Thank you for your cooperation in helping us update our records.

        Sincerely,
        Jeffrey L Zahm
        NonPoint Source Pollution Specialist
         
           
                 
                     






















                                             A-23


             COURTHOUSE-300 WASHINGTON STREET-OCONTO, WI 54153-1621












                            SEPTAGE SITE INSPECTION REPORT
                             OCONTO COUNTY ZONING OFFICE

         PUMPER:                        May, 1993
         R.T.S. Sanitation(Soper)       PHOTOS TAKEN? Yes
         Route 3, Box 470               SOIL MAP: Oeb,Sd,Co,FsC,OeE,KvB
         Pulcifer, WI 54164             WETLAND MAP: T3K
                                        FLOODPLAIN: clear

         LANDOWNER:                     LOCATION:- Town of Gillett
         Ed Patzer, Jr.                 N 1/2, section 33
         5292 Patzer Ln                 T28N, R18E
         Gillett, WI 54124              100 acres approved

         TAX PARCEL: 016-33-330011A     SITE NUMBER: OCSS 6
         016-33-3300412, 016-33-330052, 016-33-3300621

         INSPECTED BY: Jeffrey L.- Zahm

         SOIL INSPECTION:


              SEE ATTACHED SHEET








         SITE INSPECTION:

           lDcation of nearby residences: <  1,000 ft
           location of nearby wells: > 200 ft
           low areas subject to flooding or ponding: Yes, about 1 acre
           location of surface waters: none
           evidence of rock outcroppings: none
           degree and extent of slope: 6-12%
          ,drainage patterns: none evident
           condition'of field: Hay and recently worked for crops

           evidence of septage application: none
           public access: No, remote 1 ocation

         COMMENTS:
          Spreads on 5 fields all being used for crop production
          Site inspection criteria based on Wisconsin Admininstrative Code
         NR 113.08 (3)(b) 16. Table 4


         RECOMMENDATIONS: Limit spreading to areas with smaller slopes.and
         avoid low areas. If limitations are followed may continue use.





                                         A-24















                                    OCSS 6    Ed Patzer


         BORINGS:

               1: 0-13" Med Bn 1, 13-17" R-Bn sil, 17-26" GY-R sicl, 26-371,
                   Brt R c, flf motts at 37"

               2: 0-101, med Bn 1, 10-16" R-Bn 1, 16-24" R-gy cl, > 241, R c,
                 flf motts at 40"

             # 3: 0-100 med Bn 1, 10-22" R scl, 22-36" R cl, > 36ff lt Bn scl

             # 4: 0-101, med Bn 1, 10-201, R. cl, flf motts at 2011, 20-261, R c,
                 > 26" till


             # 5: 0-12" dk Bn 1, 12-17" Bn scl, 17-39" lt Bn fs, sat at 39,,

             # 6: 0-141, dk Bn 1, 14-26" R scl, 26-31" R c, 31-40" R s, sat at
                  36", > 40" R c

             # 7: 0-14" dk Bn 1, 14-24" R scl, 24-30" R c, 30-39" R s,, sat at
                 38", >  39" R c

             # 8: 0-12"  dk Bn sil, 12-23" lt Bn s, c2p motts at 20", sat at
                 22-, >  23" till

             # 9:  0-12" dk Bn 1, 12-16 lt Bn scl, 16-25" R cl, 25-33" R c, >
                 33" till

             # 10: 0-12" dk Bn sil, 12-40" R s, > 400 R sc

             # 11: 0-121, dk Bn 1, 12-331, R lsf 33-400 R cl

























                                             A-25





                 hff


                                                  -1






                                                               MA













                               SEPTAGE SITE INSPECTION REPORT
                                OCONTO COUNTY ZONING OFFICE


          PUMPER:                      MAY , 1993
          Bostwick Septic              PHOTOS TAKEN? Yes
          W 1425 Rose Lake             SOIL MAP:MnB, MnC, PsD, PkC
          White Lake, WI 54491         WETLAND MAP: < 5acres (2)
                                       FLOODPLAIN: clear


          LANDOWNER:                   LOCATION: Town of Armstrong
          Marie Moericke               NW1/4, NE1/4, Section 13
          13727 Silver Hill Rd         T31N, R16E
          Mountain, WI 54149           40 acres approved

          TAX PARCEL:                  SITE NUMBER: OCSS 1
          .004-13-1301512

          INSPECTED BY: Jeffrey L.     Zahm

          SOIL INSPECTION:'
          BORINGS:
             # 1: 0-1011med   En sil, 10-19" R ms, 19-47" Brt R s, 47-57" Bn s

             # 2: 0-12" Dk    Bn 1, 12-18" R ls, 18-45" R s, 45-60" Lt Bn s

             #  3: 0-10" Bn'  sil, 10-18" Rls, 18-47" R s, 4    7-60" Lt Bn s

             #  4: 0-1011 Dk  Bn sil, 10-1911 R s,. 19-4811 Brt R s, 48-60 Lt Bn s

             #  5: 0-1011 Dk  Bn sil, 10-20" R scl, 20-48" R s, 48-60" Bn s


          SITE  INSPECTION:

            location of nearby residences: < 1,000 ft
            location of nearby wells: > 200 ft
            low areas subject to flooding or ponding: None
            location of surface waters: None
            evidence of rock outcroppings: None
            degree and extent of slope: 3%
            drainage patterns: None evident
            condition of field: Hay

            evidence of septage application: Yes, some puddling
            public access: Yes, From public road

          COMMENTS:

           Site inspection criteria based on Wisconsin Admininstrative Code
           NR 113.08 (3)(b) 16. Table 4


          RECOMMENDATIONS: May continue use of this field



                                               A-27









                                                            AA













                                                                                              'Air
                                                                               apt                               "im,


                                                                                                         it



                                                                                                                                  4w
                                                                                                                               114







                                                                                                           4 4







                                         -%r-g
                                                                                                                              I",,. I J@il





                                                                                                                                  fill














                            SEPTAGE SITE INSPECTION REPORT
                             OCONTO COUNTY ZONING OFFICE

         PUMPER:                         MAY , 1993
         R.T.S. Sanitation (Soper)       PHOTOS TAKEN? Yes
         Route 3, Box 470                SOIL MAP: Es, OeB, OeC2, SoA
         Pulcifer, WI 54164              WETLAND MAP: S3K
                                         FLOODPLAIN: 245, clear

         LANDOWNER:                      LOCATION: Town of Gillett
         David Schaal                    S112, NE1/4, Section 20
         10063 Schaal  Rd                T28N, R18E
         Gillett, WI 54124               60 acres approved

         TAX PARCEL:,,016-20-2000313     SITE NUMBER: OCSS 7
          016-20-2000414


         INSPECTED BY: Jeffrey L. Zahm

         SOIL INSPECTION:


              SEE ATTACHED SHEET










         SITE INSPECTION:

           location of nearby residences: < 1,000 ft
           location of nearby Wells: > 200 ft
           low areas subject to flooding or ponding: None
           location of surface waters: None
           evidence of rock outcroppings: None
           degree and extent of slope: 2-6%
           d--ainage patterns: None evident
           condition of field: Recently worked for planting

           evidence of septage application:. None
           public access: Yes, off public road    John Lane


         C014MENTS:
          should only use middle of field to meet setbacks to residences
          Site inspection criteria based on Wisconsin Admininstrative,Code
          NR 113.08 (3)(b) 16. Table 4

         RECOMMENDATIONS: May continue use of this site



                                          A-29













                               OCSS 7 ( DAVID SCHAAL)


         BORINGS:

            # 1: 0-7" Bn sil, 7-21" Bn 1, 21-38" R scl

            # 2: 0-8" Bn sil, 8-22" Bn 1, 22-40" R scl
            # 3: 0-23" Bn scl, 23-39" R sc

            # 4: 0-14" Bn sil, 14-22" R sl, 22-31" R s, 31-38" R sl

            # 5: 0-8" Bn sil, 8-21" Bn 1, 21-40" R scl,

            # 6: 0-12" Bn sil. 12-23" Bn 1, 23-40" R scl

            # 7: 0-7" Bn sil, 7-22" Bn 1, 22-40" R scl













































                                         A-30










                                                                                                                                                                                                   .1. fj@
                                                                                                                                                 WS
                                                                                                                                                                                                                                                         to


                                                                                                                                                                                                                                                             T1,
                                                                                                                                                                      Of
                                                          ki'll, All:                                                                             0,
                                                                                                                                                                                                                       _;.4i




                                                                                                                                                                       f 0




                                                                                                                                                                                 14'




                                                                                                                                                                     All                -top
                                                j. #I
                                                                                                                               V.                             ii-Y 'A."i

                                                                                  :1







                                                                                                                             vt
                                               14                   "'A


                                                                                                                                 sly v




                                                                                                                                                                               rr. ol







                         COUNTY OF OCONTO



                                OFFICE OF

                       ZONING ADMINISTRATOR

                           Phone: 414-834-6827


                                   February 23, 1993

          To    Frank Konitzer
                7727 Konitzer Road
                Oconto Falls, Wl 54154


          Location    T27N, R19E
                      SE1/4, NE1/4 Section 2
                      15 acres


          Dear Mr.

          The Oconto County Zoning Office has been updating all the licensed
          septage sites in the county.   According to the records sent to us
          by the Department of Natural Resources, your property has been
          licensed as a septage disposal site.      In order to update our
          records we need to know if you would like to have your site/s
          remain active or not. Please check the appropriate box below.

                    Yes, I would like my site/s to remain on the list of
                    act  ive sites.

                    No, I  would like my site/s removed from the list of
                    active  sites.

          If you checked no please sign and date the enclosed form stating
          you would like your name removed from the DNR's list.

          Please send your reply in the post paid, self addressed envelope at
          your earliest convenience.

          If you have any questions feel free to contact me at the Oconto
          County Zoning Office. (414) 834-6832.

          S' c ely,
                                                           E    E
                      C @", 4
           e re      Zahm.
          NonPoint Source Pollution Specialist               MAR 1 6 In-
             c  e
                                                              E @IV
         e r We

                                                               zl)ning office
                                                              (N)Conto countvy'


                                          A-32














                              SEPTAGE SITE INSPECTION REPORT
                               OCONTO COUNTY ZONING OFFICE


           PUMPER:                         MAY , 1993
           Sutrick Septic Service          PHOTOS TAKEN? Yes
           359 South Washington St         SOIL MAP: SfB, WfK
           Oconto Falls, WI 54154          WETLAND MAP: T3K
                                           FLOODPLAIN: 270, small floodplain

           LANT)OWNER:                     LOCATION: Town of Morgan
           Frank Konitzer                    SE1/4, NE1/4, Section 2
           7727 Konitzer Rd                  T27N, R19E
           Oconto Falls, WI  54154           15 acres approved

           TAX PARCEL: 028-02-0200414      SITE NUMBER: OCSS 14



           INSPECTED BY: Jeffrey L. Zahm

           SOIL INSPECTION:
           BORINGS:
                1: 0-10" med Bn s, 10-34" R ms, 34-39" lt Bn s, >39" Lt Bn
                   sl.
                2: 0-10" med  Bn s, 10-36" R s, 36-42" lt Bn s, >42" lt Bn sl

                3: 0-10" Bn ls, 10-36 R s, 36-441, lt Bn s

                4: 0-10" Bn  ls, 10-34 R s, 34-441, lt Bn s





           SITE INSPECTION:


             location of nearby residences: > 1,000 ft
             location of nearby wells: > 260 ft
             low areas subject to flooding or ponding: None
            -
             location of surface waters: None
             evidence of rock outcroppings: None
             degree and extent of slope: 0-2%
             drainage patterns: None evident
             condition of field: Hay

             evidence of septage application: Yes
             public access: No, remote


           COMMENTS:

            Site inspection criteria based on Wisconsin Admininstrative Code
            NR 113.08 (3)(b) 16. Table 4.

           RECOMMENDATIONS: Good soil conditions - May continue use



                                             A-33




























                                                                                                                                       Tq,@q



                                                                                                                         MM


                                                                                                                                    IMP
                                                                         ;;zpf"
                                                                                                                                               'I'T  ;,7
                                                                          rM
                                                                                                                                  W-1
                                                                                                                        e       W15W-K       -Nul"A
                                                                                                                                          G
                                                                                                                                                 aq
                                                                                                                                             'ON
                                                                                                                                                                'A.




                                                                          k.,

                                                                      pin
                                                                              n
                                                                        wq
                                                                                                                                         @Wr
                                                                                                                                                 g4
                                                                                                                                                         RA






                                                                                                                                                    -j,
                                                                                                                       linvai














                              SEPTAGE SITE INSPECTION REPORT
                                OCONTO COUNTY ZONING OFFICE


            PUMPER:                         MAY , 1993
            Sutrick Septic Service          PHOTOS TAKEN?
            359 South Washington St         SOIL MAP:
            Oconto Falls, WI 54154          WETLAND MAP:
                                            FLOODPLAIN:


            LANDOWNER:                      LOCATION: Town of Oconto Falls
            Martin Luther                   SE1/4, NW1/4, Section 21
            10502 Town Hall Rd              T28N, R19E
            Gillett, WI 54124               27 acres approved

            TAX PARCEL: 032-21-2100924      SITE NUMBER: OCSS 10



            INSPECTED BY: Jeffrey L. Zahm

            SOIL INSPECTION:


                 SEE ATTACHED SHEET













            SITE INSPECTION:


              location of nearby residences: > 1,000 ft
              location of nearby wells: > 200 ft
              low areas subject to flooding or ponding: None
              location of surface waters: None
              evidence of rock outcroppings: None
              degree and extent of slope: 2-6 %
              drainage patterns: None evident
              condition of field: Recently worked to plant

              evidence of septage application: None
              public access: No, Back end of 80 acre field



            COMMENTS:
            Make sure setbacks are maintained at southn end of field
             Site inspection criteria based on Wisconsin Admininstrative Code
             NR 113.08 (3)(b) 16. Table 4

            RECOM14ENDATIONS: May continue use of this f ield



                                              A-35















                                OCSS 10 ( MARTIN LUTHER )


            BORINGS


              #1: 0-14" Dk Bn  1, 14-25" R scl, 25-35" R sic, > 35" till, f1f
                 motts at 36 


              #2: 0-15" Dk Bn  sil, 15-23" R scl, 23-37" R sc > 37till, f1p
                  motts at 35"


              #3: 0-14" med Bn 1, 14-27"   Lt Bn scl, 27-36" R c, > 36" till,
                  f1f motts at  38"


              #4: 0-14" med Bn-1, 14-24"  Lt Bn sil, 24-38" R c, > 38", till,
                  c1p motts at 37"

              #5: 0-14" med Bn 1, 14-25" R scl, 25-36" R sic, > 36" till, f1f
                  motts at 36"


              #6: 0-15" Bn sil, 15-24" Lt Bn scl, 24-37" R c, > 37", till, f1p
                  motts at 36"












































                                           A-36






    ow







                         COUNTY OF OCONTO

                                 OFFICE OF

                        ZONING ADMINISTRATOR


                            Phone: 414-834-6827




                                      May 17, 1993

           To: Ferris Bieber
               9049 Hwy 141 N
               Lena, WI 54139

           Dear Mr. Bieber,

           The Oconto County Zoning Office is conducting field evaluations of
           all the DNR approved septage spreading sites in the county.

           A field inspection was conduct  ed at your site on May 13, 1993.
           This site was evaluated based on Wisconsin Administrative Code NR
           113.03(3) (b)16 Table 4.   This site fails to meet the following
           criteria of NR 113:

                (1) Minimum of 3 ft separation from the surface of the ground
                    to high groundwater or zones of seasonally saturated
                    soils.

                (2) minimum distance to residence - 1,000 ft

           Based on these findings, this site may no longer be used as a land
           spreading site for septage.

           Enclosed is a'copy of the  inspection report and a copy of NR 113
           which the decision was based on.              Sincerely,


                                                         James V. M   y
                                                         Zoning A inistrator












                                           A-38














                            SEPTAGE SITE INSPECTION REPORT
                              OCONTO COUNTY ZONING OFFICE


          PUMPE@-@:                      MAy , 1993
          Sutrick's Septic Service       PHOTOS TAKEN? Yes
          359 South Washington St        SOIL YiAP:Es,OeB,SoA,OeC2,OmB
          Oconto Falls, WI 54154         WETLAND MAP: < 5 acres
                                         FLOODPLAIN: #200,clear


          LANDOWNER:                     LOCATION: Town Lena
          Ferris Bieber                  El/2, SE1/4, section 10
          9049 Hwy 141 N                 T29N, R20E
          Lena, WI 54139                 80 acres approved

          TAX PARCEL:020-10-1002444      SITE NUMBER: OCSS 1.5
          020-10-1002041, 020-10-1002141A

          INSPECTED BY: Jeffrey L. Zahm

          SOIL INSPECTION:


               SEE ATTACHED SHEET






                                                                0







          SITE INSPECTION:


            location of nearby residences: < 1,000 ft
            location of nearby wells: > 200 ft
            low areas subject to flooding or ponding: Yes
            location of surface waters: None
            evidence of rock outcroppings: None
            degree and extent of slope: 0-2%
            drainage patterns:None evident
            condition of field: old corn stubble

            evidence of septage application: None
            public access: Remote - have to go through yard

          CO=NTS:

           Site inspection criteria based on Wisconsin Admininstrative Code
           NR 113.08 (3) (b) 16. Table 4
           Low areas have some standing water at this time

          RECOMMENDATIONS: Discontinue use of this field



                                           A-39











                                    OCSS 15 - Ferris Bieber


                  BORINGS:
            Boring 1: 0-12", Dk Bn 1, 12-21" med Bn sil, flf motts at 21", 21-
                        26" med R grvly cl, c2p motts at 23", sat at 26.

            Boring 2:   0-12",Dk Bn 1, 12-17" Br sil, 17-21"Br sl, flf motts at
                        21", 21-30" R sc, c3p motts at 26."

            Boring 3:   0-10" Dk Bn 1,   10-17" Bn sil, 17-32" R grvly sl, c3p
                        motts at 28",   sat at 32".

            Boring 4:   0-11" Dk Bn 1, 11-17" Bn sil, 17-32" R grvly sl c2p motts
                        at 28", sat at 32".

            Boring 5:   0 - 13 11" Dk Bn 1, 13-22" med Bn sl, flp motts at 21", 22-33",
                        grvly fs, c3p   motts at 32".

            Boring 6:   0-11" Dk Bn 1,  11-19" cs, 19-26" fs, 26-32" grvly sc, m2p
                        motts at 28",   sat at 32".

            Boring 7:   0-12" Dk Bn 1, 12-20", med R sil, 20-29" sl, f2p motts at
                        28, 29-34" grvly fs, sat at 32".

            Boring 8:   0-11", med Bn 1, 11-16" Bn sil, 16-28" cs, 28-36" gy ls,
                        c2p motts at 30", sat at 32".

            Boring 9:   0-12" Dk Bn 1, 12-18", med Bn sil, 18-30" cs, 30-36", gy
                        ls, f2p motts at 32", sat at 34" .

            Boring 10: 0-12" Dk Bn 1, 12-21" med Bn sl, flf motts at 21", 21-
                        26", med R grvly cl, c2p motts at 23", sat at 26.





























                                               A-40






















































                  Lill






                                                              AM'















                                             OFFICE OF

                                 ZONING ADMINISTRATOR


                                         Phone: 414-834-6827


                                      May 17, 1993

           To: John Nigg
               14992 Island Lake Rd
               Mountain, WI 54149

           Dear Mr. Nigg,

           The Oconto County Zoning Office is conducting field evaluations of
           all DNR approved septage spreading sites in the county.

           A field inspection on your site listed to be in the N1/2, NE 1/4,
           of section 23 was conducted on May 11, 1993. This visit found the
           majority of the acreage listed to be planted in trees and the
           remaining part may continue to be used for land spreading of
           septage.

           Based on these findings, the open portion of this site may continue
           to be used as a spreading site for septage.
           Enclosed is a copy of the inspection report and the findings.

                                                         Sincerely,


                                                         James V. Mabry
                                                         Zoning Administrator





















                                           A-42















                              SEPTAGE SITE INSPECTION REPORT
                               OCONTO COUNTY ZONING OFFICE


           PUMPER:                         MAY , 1993
           Geiter Construction, Inc        PHOTOS TAKEN? Yes
           1775 Oaden Av                   SOIL MAP:PaB,PkB
           Wabeno, WI S4566                WETLAND MAP:Clear
                                           FLOODPLAIN:Clear


           LANDOWNER:                      LOCATION: Town Doty
           John Nigg                       N1/2, NE1/4, Section 23
           14992 Island Lake Rd            T32, R15
           Mountain, WI 54149              80 acres approved

           TAX PARCEL:014-41-2300111       SITE NUMBER: OCSS 2
           014-41-2300212


           INSPECTED BY: Jeffrey L.   Zahm.

           SOIL INSPECTION:


                NO BORINGS TAKEN -   FIELD APPROVED BY JIM FRIEDRICH, FROM AN
                ONSITE VISIT













           SITE INSPECTION:

             location of nearby residences:> 1,000 ft
             location of nearby wells:> 200 ft
             low areas subject to flooding or ponding: None
             location of surface waters: None
             evidence of rock outcroppings: None
             degree and extent of slope: 3%
             drainage patterns:None visible
             condition of field: Dormant, now planted with trees

             evidence of septage application: None
             public access: Yes, access from public roads on each side

           COMMENTS:


            Site inspection criteria based on Wisconsin Admininstrative Code
            NR 113. 08 (3) (b) .16. Table 4

           RECOMMENDATIONS: May continue use of this     site


                                            A-43









                         COUNTY OF OCONTO

                                 OFFICE OF

                        ZONING ADMINISTRATOR


                            Phone: 414-834-6827





                                      May 17, 1993



          To: Arne Peterson
               6336 Goatsville Road
               Lena, WI 54139

          Dear Mr. Peterson,

          The Oconto County Zoning Office is conducting field evalutations of
          all DNR approved septage spreading sites in the county.

          A visit was made to your home on May 14, 1993. Your wife indicated
          that your site was only used for waste generated on your farm and
          no public septage would be spread there.

          This office was informed by Jim Friedrich, Septage and Labratory
          Specialist - WDNR, that a site used for farm generated waste does
          not need to be on their list of approved sites. Based on this, the
          county has made a request to have your site removed from the list
          of active sites used for the spreading of public septage.

                                                     Sincerely,



                                                     James V. M
                                                     Zoning.   inistrator
                                                  @
                                                       'Inc er




                                                      m s
                                                     Ja e
                                                     Zon ing






















                                            A-45


                                                                           7ML=M;77M-*T-A "@M




                                                              RECEIVED

                                                                 JUN 1 1993
                         COUNTY OF OCONTO                                                                                      Zoning Office
                     
                                                                     Zoning Office
                                                                   Oconto County WI



               
                                OFFICE OF

                        ZONING ADMINISTRATOR


                            Phone: 414-834-6827
          To    Mr. Arne Peterson  February 23, 1993
                6336 Goatsville Road
                Lena, WI 54139

          Dear Mr.  Mr. peterson:

          This letter is in regards to the septage site update, conducted by
          the Oconto County Zoning office, which I previously discussed with
          you on the phone.   If you will sign and date the statement below,
          your name will be removed from the list of active sites printed by
          the Department of Natural Resources.
               I               Date: 5/25/93 would like my name
               removed from the DNR's list so my site/s will no longer be
               regarded as active for the spreading of public septage.

          Please return this letter in the post paid, self addressed envelope
          at your earliest convenience.          none enclosed.

          Thank you for your cooperation in helping us update our records.

          Sincerely



          Jeffrey L Zahm
          NonPoint Source  Pollution Specialist
           
           
           
               
          























                                             A-46







                         COUNTY OF OCONTO



                                 OFFICE OF

                        ZONING ADMINISTRATOR

                           Phone: 414-834-6827

                                       May 24, 1993
          To: John Shepherd'
               9531 CCC Road
               Oconto Falls,  WI 54154

          Dear Mr. Shepherd,

          The Oconto County Zoning Of f ice is conducting f ield evaluations of
          all the DNR approved septage spreading sites in the county.

          A field inspection was conducted at your site on May 24, 1993.
          This site was evaluated based,on Wisconsin Administrative Code NR
          113.08(3)(b)16 Table 4.     This site fails to meet the following
          criteria of NR 113:

                (1) Minimum of 3 ft separation from the surface of the ground
                   to high groui-.Ldwater or zones of seasonally saturated
               soils.


                (2) Minimum distance to residence - 1,000 ft

          Based on these findings this site should no longer be used as a
          land spreading site for septage.

          Enclosed is a copy of the. inspection report and a copy of NR 113
          which the decision was based on.

                                                     Sincerely,



                                                     James V. Ma
                                                     Zoning A    nistrator
                                                     Sinc ere ly


                                                         s
                                                         1
                                                     J  e  V - Ma
                                                    Z 4on i n gA nistrat(





                                            A-47













                                SEPTAGE SITE INSPECTION REPORT
                                 OCONTO COUNTY ZONING OFFICE


           PUMPER:                            May, 1993
           Sutrick Septic Service             PHOTOS TAKEN? No
           359 South Washington St            SOIL MAP: OeB,OeC2,OcB,OcD
           Oconto Falls, WI 54154             WETLAND MAP: clear
                                              FLOODPLAIN:265,330,clear

           LANDOWNER:                         LOCATION: Town of Morgan
           John Shepherd                      Nel/4, Nw1/4, section 7
           9531 CCC Road                      T27N, R19E
           Oconto Falls,    WI 54154          21 acres approved

           TAX PARCEL: 028-07-0700521         SITE NUMBER: OCSS 11



           INSPECTED BY: Jeffrey L. Zahm


           SOIL INSPECTION:
           BORINGS:

               # 1:  0-10" dk Bn sil, 10-33" R sc, f2p motts at 26", sat at 33"

               # 2:  0-10" dk Bn sil, 10-36" R sc, c3p motts at 3011, sat at 341,

               # 3:  0-11" dk  Bn sil, 11-36" R-Bn sc, c2d motts at 3011, sat at
                     341,

               # 4:  0-101, dk Bn sil, 10-30" R sc, 30-36" R c, f3p motts at 341,

               # 5:  0-10" dk  Bn 1, 10-14" Bn scl, 14-34" R sc, c2p motts at
                     30", sat  at 33"
           SITE INSPECTION:

             location of nearby residences: < 1,000 ft
             location of nearby wells: > 200 ft
             low areas subject to flooding or ponding: None
             location of surface waters: None
             evidence of rock outcroppings: None
             degree and extent of slope: 0-2%
             drainage patterns: None evident
             condition of field: Hay field

             evidence of septage application: None
             public access: Yes, from CCC Rd

           COMMENTS:
            Site inspection criteria based on Wisconsin Admininstrative Code
            NR 113.08 (3)(b) 16. Table 4

           RECOMMENDATIONS: site should no longer be used due to poor soils



                                                A-48






                           COUNTY OF OC01@1!m                     I V

                                                            MAR 2 6 1993
                                   OFFICE OF          I
                                                              Zon:ng tfice
                         ZONING ADMINISTRATOR                Ocanto County, wj

                              Phone: 414-834-6827


                                      February 23, 1993

           To    Joan Radzinski
                 3491 Airport Road
                 Oconto, W1 54153


           Location : T28N, R21E, N1/4; NE1/4
                       Section 34, Town of Oconto
                        10 acres


           Dear Ms. Radzinski,

           The Oconto County   Zoning Office has been updating all the licensed
           septage sites in the county.     According to the records sent to us
           by the Department of Natural Resources,        your property has been
           licensed as a septage disposal site.          In order to update our
           records we need to know if you would like to have your site/s
           remain active or   not. Please check the appropriate box below.

                      Yes, I would like my site/s to remain on the list of
                      active  sites.


                      No, I   would like my site/s removed from the list of
                      active  sites.

           If you checked no please sign and date the enclosed form stating
           you would like your name removed from the DNR's list.

           Please send your reply in the post paid, self addressed envelope at
           your earliest convenience.

           If you have any questions feel free to contact me at the Oconto
           County Zoning Office. (414) 834-6832

           Sin r     t


           Jeffrey   . Zah-m
           NonPoint Source Pollution Specialist
            - Mn   y
                 r

            @f f rev 1@/ Z,





                                               A-49














                             SEPTAGE SITE INSPECTION REPORT
                               OCONTO COUNTY ZONING OFFICE


          PUMPER:                          May, 1993
          John Melland                     PHOTOS TAKEN? Yes
          d/b/a Shoreland Sanitation       SOIL MAP: MoB,IsA,RsB,WaA
          1005 McDonald Street             WETLAND MAP: clear
          Oconto, WI 54153                 FLOODPLAIN: clear


          LANDO',VNER:                     LOCATION:Town of Oconto
          Joanne Radzinski                 Nl/2,NEl/4, section 34
          3491 Airport Rd                  T28N, R21E
          Oconto, WI 54153                 10 acres approved

          TAX PARCEL: 030-32-3400212       SITE NUMBER: OCSS 9

          INSPECTED BY: Jeffrey L. Zahm.

          SOIL INSPECTION:


          BORINGS:


             1:  0-10" Dk Bn ls, 10-31" R s, 31-47" Lt Bn s, m3p motts at 4411,
                 sat at 46"


             2:  0-10" Dk Bn ls, 10-30" R s, 31-48"Lt Bn s, m3p motts at 4511,
                 sat at 46"


             3:  D-10" Dk Bn ls, 10-31" R s, 31-45" Lt Bn s, m3p motts at 45"




          SITE   INSPECTION:


            location of nearby residences: > 1,000 ft
            location of nearby wells: > 200 ft
            low areas subject to flooding or ponding: None
            location of surface waters: None
            evidence of rock outcroppings: None
            degree and extent of slope: Nearly level
            drainage patterns: None evident
            condition of field: Hay field

            evidence of septage application: Yes, piles and truck tracks
            public access: No, remote

          COMMENTS:

           Site inspection criteria based on Wisconsin Admininstrative Code
           NR 113.08 (3)(b) 16. Table 4

          RECOMMENDATIONS: May continue use of this field



                                            A-50















                                                                                                                 INN
                                                                                                                                     11 7
                                                                                                               lim q@













                                                                                                     Iti














                              SEPTAGE SITE INSPECTION REPORT
                               OCONTO COUNTY ZONING OFFICE


           PUMPER:                         May, 1993
           Jack Warschkow                  PHOTOS TAKEN? Yes
           9308 County A                   SOIL MAP: Wd,ShA,OeB,MoB,MoD
           Lena, Wi 54139                  WETLAND MAP: 83K
                                           FLOODPLAIN: 260, clear

           LANDOWNER:                      LOCATION: Town of Spruce
           Jack Warschkow                  E1/2, NE1/4, section 30
           9308 County A                   T29N, R19E
           Lena, WI 54139                  120 acres approved

           TAX PARCEL: 038-19-1902144      SITE NUMBER: OCSS 18
           038-30-3000111, 038-30-3000414

           INSPECTED BY: Jeffrey L. Zahm

           SOIL INSPECTION:


                SEE ATTACHED SHEET













           SITE INSPECTION:


             location of nearby residences: >'1,000 ft
             location of nearby wells: > 200 ft
             low areas subject to flooding or ponding: none
             location of surface waters: none
             evidence of rock outcroppings-: none
             degree and extent of slope: 2-6%
             drainage patterns: none evident
             condition of field: Hay field

             evidence of septage application: Yes, truck tracks
             public access: No, remote


           COMMENTS:

            Site inspection criteria based on Wisconsin Admininstrative Code
           NR 113.08 (3)(b) 16. Table 4


           RECOMMENDATIONS: May continue use of this    site



                                            A-52
















                                   OCSS 18 - Jack Warschkow


             BORINGS:


                 1: 0-10" dk Bn 1, 10-18" med Bn sil, 18-24" R c, f2p motts at
                    24"1 , 24-29" R scl, c2p motts at 26" sat at 29"

                 2:  0-10 dk Bn sil, 10-25" med Bn 1, 25-33" med Bn scl, 33-50"
                     ls

                 3:  0-10", dk Bn sil, 10-20" med Bn 1, 20-36" R c, f1p motts at
                     34", > 36", gy till

                 4:  0-10", dk Bn sil, 10-19" Bn 1, 19-37" R sic, f1p motts at
                  34", > 37", gy till

                 5: 0-11", dk Bn  sil, 11-16", med Bn 1, 16-32" R sic, 32-43" R
                     scl

               # 6: 0-11", dk Bn  sil, 11-16", med Bn 1, 16-22" med Bn fs, 22-36",
                    R cs, 36-40"  gy sic

               # 7: 0-11", dk. Bn sil, 11-16" Bn 1, 16-24" med Bn fs, 24-36" R
                    cs, 36-44" gy sic

               # 8: 0-10", dk Bn sil,   10-16", med Bn 1, 16-24" R cl, 24-30" med
                     Bn sic, 30-36" med Bn sicl, > 36" gravel

               # 9:  0-10" dk Bn sil, 10-16", med Bn 1, 16-24" R cl, 24-32", med
                    Bn sic, 32-36' med Bn sicl, > 36" gravel

               # 10: 0-10", dk Bn sil, 10-16", med Bn 1, 16-26" R cl, 26-32", med
                      Bn sic, 32-39" med Bn grvly sicl

                 11: 0-18" dk Bn 1, 18-22" B1 sl, 22-50" R ms, > 50", R cs

                 12: 0-16" dk. Bn 1, 16-22" Bl sl, 22-50" R s, > 50", R cs

                 13: 0-16" dk Bn sil, 16-22" B1 sl, 22-50" R s, > 50" r cs

















                                                A-53












                                                          MOM*




                           75R


                                     A-Z


                                                   rx:
                            X7
                                                             ,.I
                                                     No






                                      OWN                           pa
                                          Ow
                            E0   M       mg,
                                                        P

                          Am
                                      SON
                                                               X.-d
                                                                  FRE7-, N


                                                                  AIM.

                                               Nq

                                                          MI,


                                                Ig








































                                                               :\4J















                              SEPTAGE SITE INSPECTION REPORT
                               OCONTO COUNTY ZONING OFFICE


           PUMPER:                         May, 1993
           Pals Septic Service             PHOTOS TAKEN? Yes
           3085 Sot Rd                     SOIL MAP:.Es,OeB,MoB,SoA,Sd
           Abrams, WI 54101                WETLAND MAP: S3K < 5 acres
                                           FLOODPLAIN: # 330, clear

           LANDOWNER:                      LOCATION: Town of Morgan
           Julius Kaczmarowski,            SW1/4, NW1/4, section 21
           8667 Morgan Marsh Rd            T27N, R19E
           Oconto Falls, WI 54154          40 acres approved

           TAX PARCEL: 028-21-2101222      SITE NUMBER: Ocss 3



           INSPECTED BY: Jeffrey L. Zahm

           SOIL INSPECTION:


                REMOVED FROM DNR LIST BY JIM FRIEDRICH DUE TO PAPER FOR FIELD
                APP'2,OVAL NOT BEING SUBMITTED


                SOIL INSPECTION ON ATTACHED SHEET









           SITE INSPECTION:

             location of nearby residences: > 1,000 ft
             location of nearby wells: > 200 ft
             low areas subject to flooding or ponding: Yes, about 1 acre
             location of surface waters: Wetland, < 200 ft
             evidence of rock outcroppings: None
             degree and extent of slope: 0-2%
             drainage patterns: None evident
             condition of field: recently worked for planting

             evidence of septage application: None
             public access: Yes, from public road

           COMMENTS:
           Owner stated that the higher parts of the field are used
           Site inspection criteria based on Wisconsin Admininstrative Code
           NP 113.08 (3) (b) 16. Table 4
           Should only use about 15 acres in the center of the field

           RECOMMENDATIONS: Discontinue use, site was removed from list



                                            A-55













                BORINGS:
          Boring 1: 0-10" med Bn 1, 10-161, gy scl, 16-22" R grvly sc, 22-36"
                     R c, f2p motts at 26, c3p motts at 34, > 361, till

          Boring 2:  0-10 med Bn 1,  10-401, R ms, f1f motts at 40'

          Boring 3:  0-10" med Bn 1, 10-26" R ms, 26-45" grvly cs, > 45 till,
                     sat at 45"


          Boring 4:  0-10' med Bn 1, 10-22" R s, 22-28" lt. Bn scl, 28-37" R s,
                    37-48" R qscl, >  48" R c, m3qp motts at 48"

          Boring 5: 0-1q0" med Bn 1,   10-4211 R s, > 42 Bn s

          Boring 6: 0-10" med Bn 1,   10-34" R s, 34-40" R scl















































                                            A-56
 




















                                                                                                                                        5


                                                                                                                                                                     - K;'r,


























                                                                                                                                                                           RN
                                                                                                                    Ir4











                I T
                           COUNTY OF OCONTO



                                  OFFICE OF

                         ZONING ADMINISTRATOR


                            Phone: 414-834-6827



                                        May 17, 1993



           To    Berlin Kaufman
                 7798 Pagel Lane
                 Lena, WI 54139

           Dear Mr. Kaufman,

           The Oconto County Zoning Office is conducting field evaluations of
           all the DNR approved septage spreading sites in the county.

           A field inspection was conducted at your site on May 13, 1993.
           This site was evaluated based on Wisconsin Administrative Code NR
           113.08(3) (b)16,Table 4.    The portion of this site, presently in
           hay, fails to meet the following criteria of NR 113:
                 (1) Slope requirements - 6% for surface spreading
                                          - existing slopes measured 10-15%

                 (2) Minimum distance to residence (1,000 ft)

                 (3) Minimum distance to stream, lake, flowage ditch, pond, or
                     wetland with greater than 6 to 12 % Slope.

                 (4) Soils in low areas do not have the required 3 ft
                     seperation from seasonally high groundwater.

           Based on  these findings, this part of the site may no longer be
           used as a land spreading site for septage. The portion of the site
           presently under cultivation may continue to be used as a spreading
           site.   This site may remain open only if these limitations are
           followed. Failure to obide by these limitations will result in the
           closure of the entire site.

           Enclosed is a copy of the inspection report and a copy of Wisconsin
           Administrative Code NR 113 which the decision waw based on.

                                                       Si cerely


                                                        ames V. ab
                                                           e@re
                                                       Si c    ly
                                                       j  e    - 2@@bis
                                                          I q
                                                65@    Zoning Adm' istrator


                                             A-58














                             SEPTAGE SITE INSPECTION REPORT
                              OCONTO COUNTY ZONING OFFICE


          PUMPER                    May, 1993
          Jack Warschkow            PHOTOS TAKEN? Yes
          d/b/a Jack's Septic       SOIL MAP: OeB, OeC2
          9308 County A West        WETLAND MAP:< 5 acres (2)
          Lena, WI 54139            FLOODPLAIN: 260, Clear

          LANDOWNER:                LOCATION: Township Lena
          Beriin Kaufman            S1/2, SE1/4 - Section 28
          7798 Pagel Ln             T29N, R19E
          Lena, WI 54139            75 Acres approved

          TAX PARCEL:               SITE NUMBER: OCSS 17
          038-28-2801844


          INSPECTED BY: Jeffrey L.  Zahm

          SOIL INSPECTION:


               SEE ATTACHED SHEET









          SITE INSPECTION:

            location of nearby residences: < 1000 ft
            location of nearby wells: > 200 ft
            low areas subject to flooding or ponding: Yes, Center of field
            location of surface waters: Wetland, Center of field
            evidence of rock outcroppings: None
            degree and extent of slope: 10 - 15%
            drainage patterns: Not evident
            condition of field: Hay field and part was recently worked for
            planting.

            evidence of septage application: None
            public access: Yes, Public road along side field

          COMMENTS:
           Site inspection criteria based on Wisconsin Admininstrative Code
           NR 113.08 (3)(b) 16. Table 4
           To great of slope to spread on
           Soils do not meet the 3 foot criteria

          RECOMMENDATIONS: Limit spreading to acreage that is presently in
          corn. Site may remain open if limitations are followed.




                                           A-59





                BORNINGS:        OCSS 17 - Berlin Kaufman

           Borning 1:  0-11" Drk Bn sil, 11-22" Bn sl, 22-32" R scl, 32-401,
                       Grvly ls, flf motts at 40".

                    2: 0-12" Drk Bn sil, 12-20" Bn sl, 20-30" R sic, f1f motts,
                       at 28", >30" R c m3p motts at 34".

                    3: 0-11" Drk Bn sil, 11-24" Bn sl, 24-30" R scl, 30-38" med
                       R c, f lf motts at 3 8

                    4: 0-12" Drk Bn sil, 12-181, med Bn sl, 18-32" R sicl, c2p
                       motts at 26", > 32"gry c, m3p motts at 32".

                    5- 0-211 Drk med Bn sl, 2-20" R scl, 20-29" R sl, 29-421,
                       grvly ls, f2p motts at 41".

                    6: 0-8" Bn 1, 8-161, grvly ls, > 16" grvly sl - could not
                       auger past 18".

                    7: 0-10" med Bn sil, .10-2111 lt Bn scl, 21-30" R sl, 30-421,
                       R scl










































                                             A-60

















                                                                                                                                                           d4a -W
                                                                                                                                @4 4j
                                                                                                                                                sm
                                                                                                                                                               WM'j"W
                                                                                                                                                 @oll WE
                                                                                                                                                                                                                                                                p'-
                                                                                                                                                                                                                                                                       re ir
                                                                                                                                    ,Nm                           ME       1 aw      -
                                                                                                                            I Rl
                                                                                                                                                                                       wt



                                                                                                                                          . . . . . . . . . . . . .


                                                                                                                                                                                                                                                              -4t4p ',av
                                                                                                                                                                                                                                                         " MMW@








                                                                                                                                                     RWA



                                                                                                                     'ga
                                                                                                                                                                                                                                                                             , 4i
                                                                                                                                                                                                                                                                                        ,jw
                                                                                                                                                                                                                                                                                   WEII







                         COUNTY OF OCONTO



                                OFFICE OF
                                                                C E 2- ------
                        ZONING ADMINISTRATOR               U
                            Phone: 414-834-6827                MAR - 8ISS3

                                                                 Zoning office
                                   February 23, 1993               county, W1

          To     Mr. Vincent Soloman
                 7497 Konitzer Road
                 Oconto Falls, Wisconsin 54154


          Location      SEIA NWI/4, Sec. 1, T27N, R19E, Town of Morgan (20 acres)
                        NEIA SEIA, Sec. 1, T27N, R19E, Town of Morgan (9 acres)


          Dear Mr. Soloman:

          The Oconto County Zoning  Office has been updating all the licensed
          septage sites in the county. According to the records sent to us
          by the Department of Natural Resources, your property has been
          licensed as a septage disposal site.       In order to update our
          records we need to know if you would like to have your site/s
          remain active or  not. Please check the appropriate box below.

                    Yes, I would like my site/s to remain on the list of
                    active  sites.

                    No, I   would like my site/s removed from the list of
                    active  sites.

          if you checked no please   sign and date the enclosed form.   stating
          you would like your name  removed from the DNR's list.

          Please send your reply in the post paid, self addressed envelope at
          your earliest convenience.

          If you have any questions feel free to contact me     at the Oconto
          County Zoning Office. (414) 834-6832.

          Si   r


            effrey     a
          NonPoint Source Pollution Specialist
                     Z







                                           A-62














                               SEPTAGE,SITE INSPECTION REPORT
                                OCONTO COUNTY ZONING OFFICE


           PUMPER:                          May, 1993
           Sutrick Septic                   PHOTOS TAKEN? No
           359 South Washington St          SOIL MAP: MnB,MnD,WaA
           Oconto Falls, WI 54154           WETLAND MAP: T3K
                                            FLOODPLAIN: #265, small floodplain

           LANDOWNER:                       LOCATION: Town of Morgan
           Vincent Solomon                  SE1/4, NW1/4, Section 1
           7497 Konitzer Rd                 T27N, R19E
           Oconto Falls, WI   54154         20 Acres approved

           TAX PARCEL: 028-01-0101424       SITE NUMBER: Ocss 13



           INSPECTED BY: Jeffrey L. Zahm


           SOI-.@'J INSPECTION:
           BORINGS:


                 1: 0-8" Bn 1, 8-16" med Bn Is, 16-34" R sl, > 34" R s

                 2: 0-8" Bn 1, 8-22" Bn Is, 22-38" R ms

                 3: 0-10" Bn sil, 10-19" Bn 1, 19-32" R sl, 32-40" R s

                 4: 0-8" Bn 1, 8-22" Bn sl, 22-40" R Is

                 5: 0-8" Bn 1, 8-16" med Bn sl, 16-30" R Is, 30-42" R


           SITE  INSPECTION:

              location of nearby residences: > 1,000 ft
              location of nearby wells: > 200 ft
              low'areas subject to flooding or ponding: None
              location of surface waters: None
              evidence of rock outcroppings: None
              degree and extent of slope: 0-2%
              drainage patterns: None evident
              condition of field; Hay field

              evidence of septage application: None
              public access: No, Remote field


           COMMENTS:

            Site inspection criteria based on Wisconsin Admininstrative Code
            NR 113.08 (3)(b) 10'. Table 4

           RECOMMENDATIONS: May continue use of this site



                                               A-63













                                 SEPTAGE SITE INSPECTION REPORT
                                  OCONTO COUNTY ZONING OFFICE


            PUMPER:                            MAY , 1993
            Sutrick Septic                     PHOTOS TAKEN?    Yes
            359 South Washington St            SOIL MAP:MnB,    MnD, WaA
            Oconto Falls, WI 54154             WETLAND MAP:     T3K
                                               FLOODPLAIN:      270,    adjacent       to
                                                                 floodplain.
            LANDOWNER:                         LOCATION:Town    of Morgan
            Vincent Solomon                    NEI/4, SE1/4,    Section 1
            7497 Konitzer Rd                   T27N, R19E
            Oconto Falls, WI    54154          9 acres approved

            TAX PARCEL:                        SITE NUMBER: OCSS 12
             028-01-0102241


            INSPECTED BY: Jeffrey L. Zahm

            SOIL INSPECTION:


            BORINGS:


                  1: 0-8" Bn s, 8-22" R s,    22-34" Lt Bn s, 34-41 R s, >41" Bn s

                4 2: 0-8" Bn s,   8-20" R s,  20-36" Lt Bn s, 36-42"R s, >42" Bn s







            SITE INSPECTICN:


              location of nearby residences: > 1,000 ft
              location of nearby wells: > 200 ft
              low areas subject to flooding or ponding: None
              location of surface waters: None
              evidence of rock outcroppings: None
              degree and extent of slope: 0-2%
              drainage patterns: None evident
              condition of field: Hay field

              evidence of septage application: Yes, paper and truck tracks
              public access: No, remote



            COMMENTS:
             Good soil conditions
             Site inspection criteria based on Wisconsin Admininstrative Code
             NR 113. 08 (3) (b) 16. Table 4

            RECOMMENDATIONS: May continue use of this site



                                                 A-64
















                              SEPTAGE SITE INSPECTION REPORT
                                OCONTO COUNTY ZONING OFFICE


           PUMPER:                          May, 1993
           John Melland                     PHOTOS TAKEN? No
           d/b/a Shoreland Sanitation       SOIL MAP: OeB,SoA,MoB,RsB,MnC, Wf
           1005 McDonald Street             WETLAND MAP: T3KW
           Oconto, WI 54153                 FLOODPLAIN  290, 295 small floodplain

           LANDOWNER:                       LOCATION: Town of Oconto
           Gerald Weigelt                   SW114, NE114, section 27
           3163 Airport Road                T28N, R21E
           Oconto, WI 54153                 10 acres approved

           TAX PARCEL:                      SITE NUMBER: OCSS 8
                 030-25-270126A
                 030-25-2701578


           INSPECTED BY: Jeffrey L. Zahm.

           SOIL INSPECTION:


                 NO SOIL INSPECTION CONDUCTED SINCE SITE HAS ALREADY BEEN
                 OVERLOADED.







           SITE INSPECTION:


             location of nearby residences:
             location of nearby wells:
             low areas subject to flooding or ponding:
             location of surface waters:
             evidence of rock outcroppings:
             degree and extent of slope:
             drainage patterns:
             condition of field:

             evidence of septage application:
             public access:

           COMMENTS:


            Site inspection criteria based on Wisconsin Admininstrative Code
            NR 113.08 (3)(b) 16. Table 4
            1990 - 1991 pumping reports indicate this field has already been
            overloaded.


           RECOMMENDATIONS: Removal from list of approved sites



                                             A-66









                A.
                        COUNTY OF OCONTO
           a 100



                               OFFICE OF


                       ZONING ADMINISTRATOR


                         Phone: 414-834-6827




                                     May 28, 1993

         To: Gerald Weigelt
              3163 Airport Rd
              Oconto, WI 54153

         D ear Mr. Weigelt,

         The Oconto County Zoning Office is conducting field evaluations of
         all the DNR approved septage spreading sites in the county.

         The county will be requesting the removal of your site from the
         DNR's list of approved sites. This decision is based on 1990-1991
         pumping reports sent to us from the DNR indicating that your site
         has already been overloaded.

         Until this site is officially removed from the DNR's list we ask
         that you refrain from dumping any more septage.


                                                  Sincerely,




                                                  James V. Mab
                                                  Zoning Admi istrator
                                                  Sincere ly'
                                                  J  escrV-Za]b@
                                                            i
                                             e@@ @=ninA        strator





                                          A-67












                e
                         COUNTY OF OCONTO


                                OFFICE OF

                        ZONING ADMINISTRATOR

                           Phone: 414-834-6827



                                      May 28, 1993



          To: Thomas Kussow
               5239 County S
               Little Suamico, WI 54141


          Dear Mr. Kussow,

          The Oconto County Zoning Office is conducting field evaluations of
          all the DNR approved septage spreading sites in the county.

          A field inspection was conducted at your site on May 26, 1993.
          This site was evaluated based on Wisconsin Administrative Code NR
          113.08(3)(b) 16, table 4.    This site fails to meet the following
          criteria of NR 113:

                (1) Minimum of 3 ft separation from the surface  of the ground
                    to high groundwater or zones of seasonally saturated
                    soils.


                (2) Minimum distance to residence - 1,000 ft

          Based on  these findings the county will be requesting the removal
          of this site from the DNRI-s list of approved land spreading sites.
          Until this site is officially removed, we ask that you refrain from
          dumping septage on it.

          Enclosed is a copy of the inspection report and a copy of NR 113
          which the decision was  based on.
                                                  @
                                                    Sincerely,



                                                     ames V. Ma
                                                    Zoning Administrator
                                                     in er@ely
                                                       c     '--7 *
                                                       es V.  a@
                                                    7












                                           A-68







                        COUNTY OF OCONTO



                               OFFICE OF

                       ZONING ADMINISTRATOR
                           Phone: 414-834-6827             E C E    V
                                  February 23, 1993          MAR - 8 1993

         To     Mr. Thomas Kussow                              Zoning office
                5239 County S                                r@nntn CauntV. M
                Little Suamico, Wisconsin 54141


         Location    W11, NW14, Sec. 24, 40 acres in Town of Little Suamico




         Dear Mr. Kussow:

         The Oconto County Zoning Office has been updating all the licensed
         septage sites in the county. According to the records sent to us
         by the Department of Natural Resources,    .your property has been
         licensed as a septage disposal site.       In order to update our
         records we need to know if you would like to have your site/s
         remain active or  not. Please check the appropriate box below.
                   -<es, I would like my site/s to remain on the list of
                   active  sites.

                   No, I   would like my site/s removed from the list of
                   active  sites.   -

         If you checked no please sign and date   the enclosed form stating
         you would like your naine removed from the DNR's list.

         Please send your reply in the post paid, self addressed envelope at
         your earliest convenience.

         If you have any questions feel free to contact me at the Oconto
         County Zoning Office. (414) 834-6832.

         Si ce ly,



          ef e L. Za.
         NonPoint Source Pollution Specialist
                                                                    V









         W
            ce



           f
          ee    @L- T15M


                                          A-69














                               SEPTAGE SITE INSPECTION REPORT
                                OCONTO COUNTY ZONING OFFICE


            PUMPER:                         May, 1993
            Pals Septic Service(Zachow)     PHOTOS TAKEN? No
            3085 Sot Rd                     SOIL MAP: FsB, ShA, Wf
            Abrams, WI 54101                WETLAND MAP: T3K
                                            FLOODPLAIN: 365, small floodplain

            LANDOWNER:                      LOCATION: Town of Little Suamico
            Thomas Kussow                   W1/2, NW1/4, Section 24
            5239 County S                   T26N, R20E
            Little Suamico, WI 54141        40 acres approved

            TAX PARCEL: 024-18-2402323      SITE NUMBER: OCSS 4
            024-18-2402422


            INSPECTED BY: Jeffrey L. Zahm

            SOIL INSPECTION:


                 SEE ATTACHED SHEET













            SITE INSPECTION:


              location of nearby residences: < 1,000 ft
              location of nearby wells: > 200 ft
              low areas subject to flooding or ponding: Yes, several in field
              location of surface waters: ponding in field
              evidence of rock outcioppings: None
              degree and extent of slope: 0-2%
              drainage patterns: None evident
              condition of field: old coin stubble

              evidence of septage application: None
              public access: Yes, off county S and Fox Rd

            COMMENTS:
            Site has standing water in places
            site inspection criteria based on Wisconsin Admininstiative code
            NR 113 .08 (3) (b) 16. Table 4


            RECOMMENDATIONS: Discontinue use of this site



                                            A-70
















                                    OCSS 14 - Thomas Kussow


            BORINGS:


               1:  0-711 med Bn ls, 7-2811 R ms, c3p motts at 2611, > 2811 It Bn s,
                   sat at 3211


               2:  0-811 med Bn ls, 8-28" R ms, c2d motts at 2411, > 2811 lt Bn s,
                   sat at 3211


               3:  0-811 med Bn Is, 8-2611 R ms, c3p motts at 26", > 26" It Bn s,
                   sat at 3211


               4:  o-g,, dk Bn  1, 9-1911 lt Bn s, c2d motts at 1111,   sat at 1911

               5:  0-911 dk Bn  1, 9-21" It Bn s, m2d motts at 1311,    sat at 1911

               6:  0-911 dk Bn  1, 9-18" It Bn s, c2d motts at 1111,    sat at 1911

               7:  0-911 dk Bn  sl, 9-20" R ms, c2d motts at 1811, >    2011 It Bn s,
                   sat at 2311


               8:  0-911 dk Bn  sl, 9-2311 R ms, f2d motts at 2011, >2311 It Bn s,
                   sat at 2411


               9:  0-9" Bn sl,  9-2011 R s, flf motts at 1811, > 20 It Bn s, sat at
                   2311


               10: 0-711 med Bn Is, 7-281! R ms, f2d motts at 2611, > 2811 It Bn s,
                    sat at 3211































                                               A-71












                        COMMUNITY OF ABRAMS - SOIL INSPECTIONS

          130 Sites inspected as of June 16, 1993

                88 systems fail due to High Ground Water, Zones of Seasonally
                Saturated Soil, and direct discharge to Wetlands or the
                Surface of the Ground.

                42 Systems Pass due to:

                     13 are existing Holding Tanks

                     5 are existing Mounds

                     4 are New Conventional

                     20 are existing conventional systems which meet the soil
                     requirements.


                68% of the systems are failing

                32% of the systems are passing, including systems which have
                already been brought up to code.


          Percent failure and passing with the systems up to code, HTS,
          Mounds, and New Conventional, removed.

                82% of the systems are failing

                18% of the existing conventional systems are passing




























                                           A-72




















                                      ABRAMS COMMUNITY
                                  ON-SITE INSPECTION REPORT


       Physical. Address    Owner            Passed Failed Reasons

      5916 County D         Abrams Feed & Grain         x   < 3ft from GW or ZSSS
      5810 Maple Street     Abrams School               X   < 3ft from GW or ZSSS
      5875 Maple St         Allen, Calvin               x   < 3ft from GW or ZSSS
      5852 Oak Orchard Rd   Ambrosius, Gary             x   < 3ft from GW or ZSSS
      3156 Wiedenheft LA    Athey, Thomas               x    Holding Tank
      5827 County D         Bakran, John        x            New conventional 1990
      2959 W. Railroad St   Bakran, John                x   < 3ft from GW or ZSSS
      2945 W.Railroad St    Bakran, John                x   < 3ft from GW or ZSSS
      3009 Chandler St      Bartz, Marie                x   < 3ft from GW or ZSSS
      3179 Sot Rd           Beckendorf, Donald          x   < 3ft from GW or ZSSS
      5783 Oak Orchard Rd   Berg, Calvin        x            Soils meet 3ft sep
      5814 Maple Street     Betts, Denis                x   < 3ft from GW  or ZSSS
      3225 Wiedenheft LA    Blazer, Patrick     x            Holding Tank
      5867 County D         Bohl, Louis                 x   < 3ft from GW  or ZSSS
      2939 W. Railroad St   Bonk, Genevieve             x   < 3ft from GW  or ZSSS
      5732 County D         Borkovek, David             x   < 3ft from GW  or ZSSS
      5738 County D         Bostedt, Clyde              x   < 3ft from GW  or ZSSS
      5949 Pine St          Brehmer, Darell     x            Mound in 1992
      2991 Sot Rd           Bristol, Robert     x            Soils meet 3ft sep
      3185 Sot Rd           Byng, Bruce         x            Mound in 1988
      5781 County  D        Byng, Carol                 x   < 3ft from GW or ZSSS
      6042 CeOax St         Byng, George                x   < 3ft from GW or ZSSS
      5968 County D         Byng, Hazel         x            Soils meet 3ft sep
      6000 County D         Byng, William       x            Soils meet 3ft ser)
      3125 Wiedenheft LA    Calvery Luth Church         x   < 3ft from GW or ZSSS
      5716 County D         Calvery Luth Church         x   < 3ft from GW or ZSSS
      5993 County D         Coron, Wilfred      x            Soils meet 3ft sep
      5823 County D         Damp, James         x            Mound
      5791 County D         Delzer, Frederick           x   < 3ft from GW or ZSSS
      3148 Wiedenheft LA    Demeny, Donald      x            New Convectional 1992
      3177 Wiedenheft LA    Deprey, Willard             X   < 3ft from GW  or ZSSS
      3109 Wiedenheft LA    Dessart, John               x   < 3ft from GW  or ZSSS
      5865 Maple St         Dorn, Timothy               X   < 3ft from GW  or ZSSS
      5801 County D         Duddek, David               x   < 3 f tfrom GW or ZSSS
      3235 Sot Rd           Duffy, James                x   < 3ft from GW  or ZSSS
      3223 Sot Rd           Duffy, Edward               x   < 3 f tfrom GW or ZSSS
      3239 Sot Rd           Duffy, James                x   < 3 f tfrom GW or ZSSS
      5861 Oak Orchard Rd   Eichman, Marilyn X               Soils meet 3ft sep
      5836 County D         Erdmann, Mark       x            Soils meet 3ft sep
      3191 Sot Rd           Falk, Eugene                x   < 3ft from GW or ZSSS
      5932 County  D        Falk, Winfred               X   < 3ft from 'GW or ZSSS
      5951 County  D        Falk, Gordon                x   < 3ft from GW or ZSSS



                                              A-73










     2913 W. Railroad St   Faulds, Morva              x    < 3ft from GW or  ZSSS
     5970 Cedar St         Ferdon, Douglas            x    < 3ft from GW or  ZSSS
     3189 Wiedenheft LA    Freyslaben, Muriel X             Mound in 1992
     5895 County D         Gauthier, Jeri             x    < 3ft from  GW or ZSSS
     2953 Chandler St      Gokey, Alfred              x    < 3ft from  GW or ZSSS
     2990 E. Railroad St   Gokey, Timothy             x    < 3ft from  GW or ZSSS
     3015 W. RAilroad St   Griebeler, Wenda           x    < 3ft from  GW or ZSSS,SG
     5881 Maple St         Griebeler, Wenda           x    < 3ft from  GW or ZSSS
     3163 Wiedenheft LA    Haffeman, Curt             x    < 3ft from  GW or ZSSS
     5878 County D         Hanop, Laverne             x    < 3ft from  GW or ZSSS
     5962 County D         Hansen, Randall            x    < 3ft from  GW or ZSSS
     5780 Oak Orchard Rd   Heider, Judith     x             Soils meet 3ft sep
     2982 Marion St        Heider, Ruby               x    < 3ft from GW or ZSSS
     5784 Oak Orchard Rd   Heider, Shelly     x             New Conventional 1989
     2922 Woodward  St     Hermsen, David     x             Holding Tank
     5994 Cedar St         Herr, Norbert              x    < 3ft from GW` or ZSSS,SG
     3157 Sot Rd           Houston, Patricia          x    < 3ft from GW  or ZSSS
     2908 Woodward  St     International Ark  X             Holding Tank
     2918 Woodward  St     International Ark  X             Holding Tank
     5899 County  D        Isable, LeMeryl            x    < 3ft from GW  or ZSSS
     5857 County  D        Jaeger, Gerald             x    < 3ft from GW  or ZSSS
     5833 County  D        Jendrusiak, Margaret       x    < 3ft from GW  or ZSSS
     5850 County  D        Jensen, Nancy              x    < 3ft from GW  or ZSSS
     5746 County  D        John, Louis        x             Soils meet 3ft sep
     5937 County  D        Kane, Ronald       x             Soils meet 3ft sep
     5825 Maple ST         Kennin, Donald             x    < 3ft from GW or ZSSS
     2970 Wocdward  St     Kennin, Donald             X    < 3ft from GW or ZSSS
     5762 Oak Orchard Rd   Kennin, Stella     x             Holding Tank
     5872 County D         Konitzer, John     x             Holding Tank
     5838 Maple St         Kozlowski, Dennis          x    < 3ft from GW or ZSSS
     5754 Oak Orchard Rd   Kozlowski, John    x             Soils meet 3ft sep
     2979 Elm Street       Kozlowski, Thomas          x    < 3ft from GW or ZSSS
     2941 Sot Rd           Krause, Mitchell   X             Soils inspected 1992
     5990 County D         Kusch, Elsie       x             Soils meet 3ft sep
     3079 Wilson  Rd       Kutska, Keith      x             Soils meet 3ft sep
     6049 Cedar St         Lefevre, Virginia          x    < 3ft from GW or ZSSS
     2985 Sot Rd           Leja, Kenneth      x             Soils meet 3ft sep
     3048 Sot Rd           Leja, Kenneth              x    < 3ft from GW or ZSSS
     5741 County  D        Leia, Lillian      x             Soils meet 3ft sep
     2979 W. Railroad St   Lingsine, Lionel           x    < 3ft from GW  or ZSSS
     5969 Pine St          Longsine, Richard  X             Holding Tank
     2916 Sot Rd           Lotter, Robert     x             Holding tank
     5891 County D         Machurick, James           x    < 3ft from  GW or ZSSS
     5732 Oak Orchard Rd   McCaughn, Michael          x    < 3ft from  GW or ZSSS
     2921 W. Railroad ST   McDe=id, James             x    < 3ft from  GW or ZSSS
     5818 County D         McDermid, James            x    < 3ft from  GW, or ZSSS
     2998 Walnut St        McDermid, James            x    < 3ft from  GW or ZSSS
     5863 County D         Naze, Michael              x    < 3ft from  GW or ZSSS
     5778 County D         Nicholas, Bernice          X    < 3ft from  GW or ZSSS
     5871 County D         Norwest Bank               x    < 3ft from  GW or ZSSS
     5938 Cedar St         Olejnickzak, Keith         x    < 3 f tfrom GW or ZSSS
     5747 County D         Pagel, Grant       x             Soils meet 3ft sep
     5862 County D         Pogrant, Jeffrey           x    < 3ft from GW or ZSSS
     2940 Chandler  St     Robenhorst, Ardie  X             Holding Tank



                                            A-74









     5860  Maple St        Rovinski, Max             X    < 3ft from GW  or ZSSS
     3083  Wiedenheft LA   Ryczek, Ernest            X    < 3ft from GW  or ZSSS,SG
     5926  Pine St         Samsa, Michael            X    < 3ft from GW  or ZSSS
     5876  County D        Schenkoski, Marlin        X    < 3ft from GW  or ZSSS
     3022  Sot Rd          Schneider, Terrance       X    < 3ft from GW  or ZSSS
     5817  County  D       Schroeder, Byron          X    < 3ft from GW  or ZSSS
     2951  W. Railroad St  Shutelt, Marion           X    < 3ft from GW  or ZSSS
     5845  County D        Sot, Audrey        X            Soils meet 3ft sep
     5993  Cedar St        Steinhausen, Joan         X    < 3ft from GW or  ZSSS
     5852  Maple St.       St. Louis Cong.    X            Mound in 1992
     5945  County D        Stock, Karen              X    < 3ft from GW  or ZSSS
     2991  W. Railroad St  Stoll, Joseph             X    < 3ft from GW  or ZSSS
     5858  County D        Sutrick, Jerome           X    < 3ft from GW  or ZSSS
     5746  County D        Swearing, Hal Jay         X    < 3ft from GW  or ZSSS
     2971  W. Railroad St. Tappa, Bernard            X    < 3ft from GW  or ZSSS
     2997  Walnut St       Tappa, Chris              X    < 3ft from GW  or ZSSS
     2925  Woodward St     Tepolt, Robert     X             Holding Tank
     2980  Elm Street      United Methodist Church   X    < 3ft from GW  or ZSSS
     5842  County D        Van, Earle                X    < 3ft from GW  or ZSSS
     5809  County D        Van Pay, Ronald           X    < 3ft from GW  or ZSSS
     5866  County D        Volk, Merlin              X    < 3ft from GW  or ZSSS
     3049  Sot Rd          Weaver, Harold            X    < 3ft from GW  or ZSSS
     2985  W. Railroad St  Westcott, Linwood         X    < 3ft from GW  or ZSSS
     5870  Maple St        Weycker, Patrick          X    < 3ft from GW  or ZSSS
     2917  Woodward St     whistler, Michael  X            Holding Tank
     3111  Wilson Rd       White, Edward             X    < 3ft from GW  or ZSSS
     5853  Oak Orchard Rd  Wickman, Willis    X            Soils meet 3ft sep
     2931  W.Railroad St   Wieber, Michael           X    < 3ft from GW or ZSSS
     5839  County D        Wieser, William    X            New convectional 1989
     5979  Pine St         Winans, Darrell           X    < 3ft from GW or ZSSS
     5792  County D        Wolf, Richard      X            Soils meet 3ft seo
     5974  Pine St         Woodworth, Arlene         X    < 3ft from GW or ZSSS
     2911  Woodward St     Woosencraft, Peter X            Holding Tank
     3124  Wiedenheft LA   Zimmerman, Olive X              Soils meet 3ft sep


























                                             A-75







                                                                                                     1/7 0
                      C04
                                                                                                     C/
                                                                                                                   ab
                                                                                                                        /7
                                                Awl
                                                                                     7 -q
                                                                           rb
                           61 i@
                              r
                                                 C!  Ui/.                                            lb      4s
                                                                                                                   01
                          So                                                                                           A


                                                                                                I W.I.
                                                                                                                        N
                                    k6
                                         0


                                                                                                1V6 r[i
                        .46
                         11     -     )  .
                        Ll
                                                 4@a
                                                                                                         aflair
                                                                                                     4-T
                                 I AIP-111of /1            01



                                                           ai





                                     bl


                                                    (7D
                                                        C)

                            oo-

                                                                         lop



















                      COMMUNITY OF BROOKSIDE - SOIL INSPECTIONS


          37 Sites inspected as of June 22, 1993

                    16 systems fail due to High Ground Water, Zones of
                    Seasonally Saturated Soils,and direct discharge to
                    Wetlands, Surface Water, or the Surface of the Ground.

                    21 systems pass due to:

                             2 are existing Holding Tanks

                             6 are existing Mounds

                             2 are new In-Ground Pressure


                             11 are existing conventional svstems which meet
                             the soil requirements.

                             43% of the systems are failing

                             57% of the systems are pasS411g' including
                             systems which have already been brought up
                             to code.


         Peicent failure and passing with the systeams up to code, HTS,
         Mounds, and New Conventional, removed.

                    60% of the systems are failing

                    40% of the existing conventional systems are
                    passing






















                                          A-77













                                          BROOKSIDE COM = ITY
                                      ON-SITE INSPECTION REPORT


            Physical Address     Owner          Passed Failed   Reasons

            3682 County i        Barke, David              x    < 3ft from GW or ZSSS
            3576 County i        Bloom, Harvey             x    < 3ft from   GW or ZSSS
            4658 Brookside Rd    Brabant, Bruce    X            New Mound
            4531 Brookside Rd    Enderby, Allan    X            Soils meet   3ft sep
            4885 Hwy 41          Erdman, Gary              x    < 3ft from   GW or ZSSS
            4879 Hwy 41          Erdman, Gary      x            New Mound
            4881 Hwy 41          Erdman, Helen             x    < 3ft from   GW or ZSSS
            4741 Brookside Rd    Foster,Jack       x            Soils meet   3ft sep
            4681 Brookside Rd    Hellmann, Edna    X            Soils meet   3ft sep
            4621 Brookside Rd    Hellmann, Myron   X            New Mound
            3673 County J        Jessel,Charles    X            Soils meet   3ft sep
            3661 County J        Konkel, George            x    < 3ft from   GW or ZSSS
            3530 Moody Rd        Lafortune, Don    X            New In-Ground Pres
            4671 Brookside  Rd   Lamirande, Bonnie         x    Discharge to Wetland
            4740 Brookside  Rd   Matravers, Alice          x    < 3ft from GW or ZSSS
            4680 Brookside  Rd   Matravers, Ruth           x    < 3ft from GW or ZSSS
            4680 Brookside  Rd   Matravers, Ruth           x    < 3ft from GW or ZSSS
            4705 Brookside  Rd   Melotte, Gerald   X            Soils meet 3ft sep
            4586 Brookside  Rd   Migel, Ed                 x    Discharge to SG
            4830 Brookside  Rd   Neuberg, William X             Holding Tank
            3590 County i        Noel, George      x            Soils meet 3ft seo
            4620 Brookside  Rd   Olson, Leroy              x    < 3ft from GW or zSSS
            3481 County J        Pagel, Roger      x            New Mound
            4710 Brookside  Rd   Pensaukee, Town   X            Holding Tank
            3624 County J        Pensaukee, Town           x    < 3ft from   GW or ZSSS
            362S County J        Peters, Rosella           x    < 3ft from   GW or ZSSS
            4770 Brookside  Rd   Riley, Ralph              x    < 3ft from   GW or ZSSS
            4872 Brookside  Rd   Sterrett, Jackson   X          New Mound
            3588 Moody Rd        Sutrick, Julia X               Soils meet   3ft sep
            4753 Brookside  Rd   Thompson, Raymond         x    < 3ft from   GW or ZSSS
            4609 Brookside  Rd   VandenLangenherg,D X           Soils meet   3ft sep
            3526 Moody Rd        Watts, Brian      x            New In-Ground Pres
            3541 'Hoody Rd       Watts, Brian      x            Soils meet 3ft sep
            472S Brookside  Rd   Wittkopf, Roger   X            Soils meet 3ft sep
            4767 Brookside  Rd   Zima, John        x            No system
            4750 Brookside  Rd   Zima, John        x            New Mound
            3749 County J        Zimanek, Albert           x      3ft from GW or ZSSS















                                              A-78






                                                                               0.
                                           7,9                  a-1,7
                 M,                                                      PA  A'OW 4
                    Clef            T
                                                       ]e f
                                     rc
                                                                       C)
                                                      ra   @,nrync@

                                                           4n
             rl           67
           f                   (D t             ru



                                                             WID.
                                     b
              (D   M017 C@ 7L te-- Wa
                                                        0
                   74@,. 96
                            t?D.
            oo              rl
                                                        Wlf   iv)n



                                                       Drhzn f,
            -Dia6          t
                           6
          Wa- -/; @t  W@-
                                            /07

          'Let-
                                                                       ar

                      A                               q) N            r
                                                        (b
                                                       o-
                                     rb 0
         (b                                                 f'Q
                                                          TC@Yloul(@zyj  :b,
                                                                               0
                 JC)h17           -D4017ald                                   14-
                [email protected]       Re-  t-17701717
                                             /71
                   7710                                                       lic







                                                OCONTO
                                                         COUNTY
                                                                        



                                               OFFICE OF

                                  ZONING ADMINISTRATOR


                                          Phone: 414-834-6827

                                        August 6, 1993
                                                                           93-130




          Mr. Wilbur Dilley, Chairman
          Town of Lakewood
          144918 Resort Lane
          Lakewood, Wisconsin 54138

          Mr. Dilley:

          We have completed our inspections for the Non-Point Source
          Pollution Program relating to failing septic systems.

          Enclosed is a detailed report. Although a 20% failure rate may not
          seem abnormal, what is most significaqnt to me is that about 75% of
          the tested area does not have sufficient area to replace the
          systems when they do fail.

          I encourage the Town of Lakewood to proceed with their Sanitary
          District p1ans.   Please refer this report to the district.    I Will
          be available to meet and discuss the report and its use to justify
          the district, grants, aids, etc.

          If you have questions on this matter please call me.

                                          Sincerely,



                                          James V. Mabry
                                          Zoning Administrator

          JVM:sM


          Enc.
                                       
                                              




                                                   
                                          
                                              




                                            A-80
 






                                            C) c7' <D r-J rr' <D



                           . . . . . . . . . . . .



                                         OFFICE OF
                               ZONING ADMINISTRATOR                PHONE (414) 834. 6827
                                       COURT HOUSE

                                   300 WASHINGTON STREET

                                  OCONTO, WISCONSIN 54153



                                      August 23, 1993
                                                                       93-154



         Mrs. Joanne Roy, Clerk
         Town of Lakewood
         P. 0. Box 40
         Lakewood, Wisconsin 54138


         Mrs. Roy:

         We have completed our inspections      for the Non-Point Source
         Pollution Program relating to failing  septicsystems.

         Enclosed is a detailed report. Although a 20% failure rate may not
         seem abnormal, what is-most significant to me is that about 75% of
         the tested area does not have sufficient area to replace the
         systems when they do fail.

         I encourage zhe Town of Lakewood to proceed with their Sanitary
         District plans. Please refer this report to the district. I will
         be available to meet and discuss the report and its use to justify
         the district, grants, aids , etc.

         If you have cruestions on this matter please call me.

                                        Sincerely,




                                         ames V. Mab
                                        Zoning Administrator

         JVM:sm


         Enc.
                                           e s
                                        Z:ning









                                          A-81


















                        COMMUNITY OF LAKEWOOD    SOIL INSPECTIONS

          147 Sites inspected as of August 5, 1993

                26 systems fail due to High Ground Water, Zones of
                Seasonally Saturated Soil, and direct discharge to
                Wetlands or the Surface of the Ground.

                121 Systems Pass due to:

                     6 are existing Holding Tanks

                     1 is a existing Mound

                     5 are New Conventional

                     2 are Houses without systems

                     107 are existing conventional systems which meet the
                     soil requirements.


                18 % of the systems are failing

                82 % of the systems are passing, including systems which
                have already been brought up to code.


          Percent failing and passing with the systems up to code, HTS,
          Mounds, and New Conventional, removed.

                20 % of the systems are failing

                80 % of the existing conventional systems are passing


          NOTE: About 110 or 75% of the sites tested would have insuf f icient
          area for replacement systems in the case of future failure or
          business expansion.     This would result in the costly monthly
          expense of Holding Tanks being incorporated. The County's view is
          that the addition of Holding Tanks does not solve the problem in
          that the effluent from these tanks still has to be treated and is
          therefore just being displaced, therefore causing two problems out
          of one problem.









                                            A-82




















                                                                    LAKEWOOD COMY-UNITY
                                                             ON-SITE INSPECTION REPORT


                    Physical Address                     Owner                               Pass Fail           Reasons

                    15650        Hwy 32                  Anderson, Ravmond                               x       < 3ft       from     ZSSS
                    15112        County F                Anderson,Raymond                      x                 Soils       meet     3ft sep
                    15298        Long St                 Andrews, Howard                       x                 Soils       meet     3ft sep
                    15698        H@vy 3 2                Anglemyer, Richard                              X       < 3ft       from     ZSSS
                    15217        Brook Lane              Bailey, Cliff:,Sr.                    X                 Solis       meet     3 f t-  sep
                    15236        Brook Lane              Bailey, Clif-ford                     x                 Soils       meet     3ft     sep
                    15242        Brook Lane              Bailey, Clifford                      x                 Soils       meet     3ft     sep
                    15335        Hwy 32                  Bartels, Don                          x                 Soils       meet     3ft     sep
                    15-121       Long St                 Bartels, Lynn                         x                 Soils       meet     3 f t   sep
                    15265        County F                Bartels,Theodore                      x                 Soils       meet     3ft     sep
                    15630        Hwy 32                  Bennett, Wayne                                  x       < 3ft       from     ZSSS
                    17256        Circle        Dr        Bezold,Lawrence                       x                 Soils       meet     3ft sep
                                                                             M4
                    15288        Tugs Road               Birkholz,              @chael         X                 Soils       meet     3ft     sen
                    15264        Brook Lane              Bodoh, Timot',--Y                               x       < 3ft       from     ZSSS
                    15436        Hwy 32                  Boehm, Merrill                        x                 Soils       me e -L  3ft sep
                    17165        Evergreen               Bogan, Wayne                          x                 Soils       meet     3ft sea
                    15329        Hwy 32                  Bohl, Kenneth                                   x       < 3ft       from     ZSSS
                    15331        Hwy 32                  Bohl, Kenneth                         x                 Soils       meet     3ft sep
                    15300        Hw-y 32                 DeCaster, Donald                      x                 Holding Tanks
                    17245        Circle        Dr        Dobbs, Rudy                           x                 Soils       meet 3ft         sep
                    15198        Brook Lane              Driesen,William                       x                 Soils       meet 3ft         sep
                    17218        Circle Dr               Dunlap, Richard                       x                 Soils       meet     3 f t   sep
                    15398        H@@ry 3 2               Dunlap.. Richard                      x                 Soils       meet     3ft     sep
                    15108        County        F         Dunsirn, Lola                         x                 Mound       in 1991
                    17159        Evergreen               Elbe, Thomas                          x                 Soils       meet 3ft         sep
                    17342        North Rd                Ellingson, Robert                     X                 Soils       meet 3ft         sep
                    15255        Hwy 32                  Exferd, Helen                         x                 Soils       meet     3ft     sep
                    17310        North Rd                Fahnstrom,Francis                               x       < 3 f tbf rom GW or          ZSSS
                    17302        North Rd                Farrell, Terence                      x                 Soils meet 3ft               sep
                    15267        Hwy 32                  Fisher, Leonard                       x                 Soils meet 3ft               sep
                    15268        Hwy 32                  Flynn, Douglas                        X                 Soils       meet     3ft     sep
                    17146        Wilson        Rd        Flynn, Douglas                        x                 New Conventional
                    15264        County        F         Flynn, Michael                        x                 Soils meet 3ft sep
                    17238        Circle        Dr        Fritsch, Terry                        x                 Soils meet 3ft sep
                    15295        Wilson        Rd        Gardebrecht, Allan                    X                 New Conventional
                    15636        Hvry 3 2                Geiger, Gerald                        x                 System not           in use
                    15301        Long St                 Giese, Lynn                           x                 Soils meet           3ft sep
                    15386        Hwy 32                  Ginder, Charles                                 x       < 3ft from           ZSSS
                    15276        Brook Lane              Glander,Darlene                                 x       < 3ft from           ZSSS
                    15294        Long St                 Goetz, Christopher                    X                 Soils meet           3ft sep
                                                                          W4
                    15203        County F                Greasby, illiam.                      x                 Soils meet           3ft sep
                    15496        HAry 3 2                Gryboski, Thomas                      x                 New Conventional



                                                                                     A-83









                    15261       Brook Lane             Harris, Theodore                              x       < 3ft       from ZSSS or BR
                    17175       Gage St                Haskins, Robert                               x       < 3ft       from     ZSS)S
                    15155       Brook Lane             Havenstine,George                   X                 Soils       meet     3ft sep
                    15138       County F               Hickinbotham,james                  X                 Soils       meet     3ft sep
                    15305       Hwy 32                 Hixon, James                        x                 Soils       meet     3ft sep
                    17314       North Rd               Hoffman, Ervin                                x       < 3ft       from     ZSSS
                    15408       Hwy 32                 Hogan, Iva                                    x       < 3ft       from     ZSSS
                    15261       Hwy 32                 Holl, Walter                        x                 Soils       meet     3ft sep
                    17280       Circle       Dr        Horn, Marvin                        x                 Soils       meet     3ft sep
                    15257       Brook Lane             Huffer, Robert                                x       < 3ft       from ZSSS        or GW
                    15250       Long St                Jarvais, Eugene                     x                 Soils, meet          3ft     sep
                    15289       County F               Jeranek, Elliott                    x                 Soils meet           3 f t   sep
                    17-188      St Mary's Rdjeranek, Elmer                                 x                 Soils,meet           3ft     sep
                    17408       Rugg Road              Jones,Russell                       x                 Soils       meet     3ft     sep
                    17105       Evergreen              juedes, Brian                       x                 Soils       meet     3ft     sep
                    17276       Circle Dr              Kasperek, Kenneth                   X                 Soils       meet     3ft     sep
                    17194       St Mary's RdKempsen, Robert                                x                 Soils       meet     3 f t   sep
                    15421       Hwy 32                 Kennard, Marvel                     x                 Soils       meet     3ft     sep
                    15251       Hwy 32                 Kennedy, Ruth                       x                 Soils       meet     3 f t   sep
                    15260       Long St                Kerscher, Anton                     x                 Soils       meet     3ft     sep
                    15293       County F               Kerscher, Anton                     x                 Soils       meet     3 f t   sep
                    15249       County F               Kilman, Willard                     x                 Soils       meet     3 f t   se
                    15680       Hwy 32                 Kitche=aster,Veryle                     X             Soils       meet     3ft     sep
                    15163       Brook Lane             Koch, Louis                         x                 Soils       meet     3 f t   sep
                    15315       Hwy 32                 Kolakowski, Thomas                            x       Broken Tile
                    15553       Hwy 32                 Krueger, john.                      x                 Soils       meet     3 f t   sep
                    15552       Hwy 32                 Lakewood Fst.              Pres.X                     Soils       meet     3ft     sep
                    17 17 3     Evergreen              Linssen, Gary                                 x       < 3ft       from     ZSSS
                    15620       Hwy 3 2                Lowery, Neil                                  x       < 3ft       from     ZSSS
                    15207       Brook Lane             Lyons, Eugene                       x                 Soils       meet     3ft sep
                    15686       Hwy 32                 Mahnke, jack                                  x       < 3ft       from     ZSSS
                    17243       Rugg Road              Marquardt,C-erald                   x                 Soils       meet     3 f t   sep
                    17156       Wilson St              Marshall, Kevin                     x                 Soils       meet     3 f t   sep
                    17369       North St               Mason, Karl                         x                 Soils       meet     3ft     sep
                    15487       Commercial             Mayer, Gary                         x                 Soils       meey     3ft     sep
                    17293       Circle Dr              Mazur, John                         x                 Soils       meet     3 f t   sep
                    15297       Hwy 32                 McMahon, Roy                        x                 Soils       meet     3 f t   sep
                    17141       Evergreen              Mc.Nutt,'Mark                       x                 Soils       meet     3 f t   sep
                    17265       Circle Dr              Mellen, Richard                     x                 Soils       meet     3 f t   sep
                    17205       Circle Dr              Mermuys, Thomas                     x                 Soils       meet     3ft     sep
                    17299       Circle Dr              Meylmans, Raymond                   X                 Soils       meet     3ft-    sep
                    15199       Brook :,ane            Mikula, Robert                      x                 Soils       meet     3ft     sep
                    1-5220      County F               Mills, Leola                        x                 Soils       meet     3 f t   sep
                    15194       Brook Lane             Nelis, James                        x                 Soils       meet     3ft     sep
                    17374       Rugg Road              Nelson, Loren                       x                 Soils       meet     3 f t   sep
                    17249       Rugg Road              Niccioli,Gene                       x                 Soils       meet     3 f t   sep
                    15253       Long St                Northwoods Bible                              x       < 3ft       from     ZSSS
                    15290       Long St                Northwoods Bible                    x                 Soils       meet     3ft sep
                    15678       Hwy 32                 Northern Hoff Aspen X                                 No system
                    17317       North Rd               Ohlfs, Henry                        x                 Soils meet           3ft sep
                    17177       Sherman St             Padjen, Thomas                      x                 New conventional
                    15213       County F               Peterson, Charles                             x       Discharge to SGJ
                    15219       County F               Peterson, Charles                   X                 Soils meet 3ft sep
                    15664       Hwy 32                 Peterson, Marlene                             x       < 3ft from ZSSS



                                                                                  A-84









              17195    Evergreen        Pleshek, Michael          x            Soils meet 3ft Sep
              17255    Circle Dr        Pohl, Marvin              X            Soils meet 3ft Sep
              15337    Hwy 32           Rank, Terrence            x            Holding Tank
              15345    Hwy 32           Rank, Terrence            x            Holding Tank
              Is Z12 3 Redinger Av      Redinger, David           x            Soils meet 3ft Sep
              15249    Hwy 32           Redinger Trust            x            Soils meet 3ft Sep
              15346    Long St          Reitzner, Joan            x            New Conventional
              15684    Hwy 32           Rickel, Patrick                  x     < 3ft   from   ZSSS
              17174    St Mary's RdRiebe, Jane                    x            Soils   meet   3ft Sep
              15302    Long St          Roche, Maurice            x            Soils   meet   3ft Sep
              15392    Hwy 32           Roy, Robert                      x     < 3ft   from   ZSSS
              17349    Rugg Road        Rugg, Leslie              x            Soils   meet   3ft  Sep
              15188    Brook Lane       Ruh, Melvin               x            Soils   meet   3ft  Sep
              15306    Long St          Scheuerman, Dale          x            Soils   meet   3 f tSep
              15225    Hwy 32           Schmidt,    George        x            Soils   meet   3ft  Sep
              15309    Hwy 32           Schmidt,    Randall       x            Soils   meet   3ft  Sep
              17184    Wilson    St     Schokey,    Raoul         x            Soils   meet   3ft  Sep
              17270    Circle    Dr     Schultz,    Richard       x            Soils   meet   3ft  Sep
              15177    Brook Lane       Sherman,    Thomas        x            Soils   meet   3ft  Sep
              15291    County F         Sports Card Center        X            Holding Tank
              15290    Hwy 32           State Bank Wabeno         X            Soils meet 3ft      Sep
              15351    Hwy 32           St. Louis, Thomas                x     < 3ft from ZSSS
              15232    County    F      ST. Mary's Church         X            Soils   meet   3ft Sep
              15695    Hwy 32           Strommen, David           x            Holding Tanks
              15292    Brook Lane       Swan, Leon                x            Soils meet     *3ft Sep
              15285    Hwy 32           Tebo, Michael             x            No System
              152819   Hwy 32           Tebo, Michael             x            Soils meet 3ft      Sep
              17193    Wilson    St     Tebo, Michael             x            Soils meet     3ft  Sep
              17290    Circle    Dr     Therrien, Mark            X            Soils meet     3ft  Sep
              15115    County    F      Thielke, Gerald           x            Soils meet     3ft  s eo
              15335    Long St          Thomas, Viola             x            Soils meet     3ft  Sep
              1S374    Hwy 32           Thomas, Warren                   x     Add Locks and Chains
              15491    Commercial       Thomas, Warren            x            Soils meet 3ft      Sep
              15293    Hwy 32           Thyssen, Earl             x            Soils meet 3ft      Sep
              15271    Hwy 32           Tipler Well Drill         X            Soils meet     3ft  Sep
              17258    North Road       Town of Lakewood          x            Soils meet     3ft  Sep
              15397    Hwy 3 2          Town of--Lakewood         x            Soils meet     3ft  sep
              15235    Hwy 32           Town of Lakewood          x            Holding Tank
              15283    Hwy 32           Valley Trust Co.          x            Soils meet 3ft      Sep
              17108    Evergreen        VanDenBloomer, R.         x            Soils meet 3ft      Sep
              15275    Brook Lane       Verboomen, Norbert        X            Soils meet     3ft  Sep
              15425    Hwy 32           Wachtendonk, John         X            Soils meet     3ft  Sep
              15268    Long St          Wankowski, Elizabeth         X         Soils meet     3ft  Sep
              15260    Brook Lane       Welter, Dawn                     x     < 3 f t From GW or  ZSSS
              17173    ST.Mary's RdWeyers, James                         x     < 3FT   From   ZSSS
              15381    Hwy 32           Wimberger, Richard        x            Soils   meet   3ft  Sep
              15266    Tugs Road        whiting, Theresa          x            Soils   meet   3ft  Sep
              1S248    Tugs Road        Wurzer, Henry             x            Soils   meet   3ft  Sep
              15272    Hwy 32           Wurzer, Thomas            x            Soils   meet   3ft  Sep
              171S3    Evergreen        Yingling, Todd            x            Soils   meet   3ft  Sep
              17381    Rugg Road        Zabinske, Erwin           x            Soils   meet   3ft  Sep






                                                             A-85



                                            1?@IeJ7 0    rl-e,,i-                                          jera-
                                             Ma,5017     GH
                                                         /VaSO/7
                                                            4,0
                                                                                   7
                                 RO/70-/d                             o/70-/d
                                 1*--IC -DO f 7 aild                    /7
                                                             r-,r@
                                                             @ Q                                           w11c
                                   do



                                                                    A CRE s


                                                                      <1
                                                    K.   759
                                                                                LIT.      BEAR
  9INDEO                                    -4-0                                        L IV A

                                                 AZ

                                                                                                         7


   @,, @ng

                                                                                           tQ,

                                                                                                           A6.


                       to                                                                               IT
                                           c-'s.
                                                                           @S?411










                                                       Le 5,
                                                                                                          zr

                                                                                                            F


                                                       Qpq
         ov
                                                                    T
                                      <
                                                                                                         Tcz ei,< -
                                                                                                        kci
                                                                                                  ,@. W.,rcAx.

                                                                                           L
                                                                                           [c
                                                                                           r














                    ...........                                                    L.C,       LIS
                              4m                                                                  43
                                                         A
                           N                     a)                                        C C/7
                                                                                 IZ
                     RIBALD I-X. RD. @O












                        COMMUNITY OF MOUNTAIN - SOIL INSPECTIONS

           100 sites inspected as of August 27, 1993

                15 systems fail due to High Ground Water or Zones of
                Seasonally Saturated Soil.

                85 Systems pass due to:

                      12 are Holding Tanks

                      15 are New Conventional

                      58 are existing conventional systems which meet the soil
                      requirements.

                15 %  of the systems are failing

                85 %  of the systems are passing, including systems which have
                already been brought up to code.

           Percent failing and passing with the systems up to code, HTS and
           New Conventional, removed.

                20 % of the systems are failing

                80 % of the existing conventional systems' are passing

































                                             A-87












                                    MOUNTAIN COMMUNITY
                                 ON-SITE INSPECTION REPORT



           Physical Address   Owner               Pass Fail  Reasons

           13953 Hwy 32 & 64  Anderson, Arnold     x         Holding tank
           14007 Hwy 32 & 64  Auto Financial Ser   X         Holding Tank
           13984 Hwy 32 & 64  Baldwin, Rodney      x         Holding tank
           14270 Spring CrRd  Ballering, William   X         Soils meet 3ft sep
           14324 County W     Bartz, Ircel         x         Soils meet 3ft sep
           14336 Main Ln      Bartz, Wayne         x         Soils meet 3ft sep
           14218 County W     Bauman, Linda        x         Holding Tank
           14008 Emily Rd     Berglin, Jack             x    2 share 1 system
           13994 Emily Rd     Berglin,'Kenneth     X         Soils meet 3ft  sep
           13946 Hwy 32 &  64 Beth, Michael        x         Holding tank
           14318 County W     Bowman, Bernard      x         Soils meet  3ft sep
           14345 Main Ln      Cannon, Janeth       x         Soils meet  3ft sep
           14040 Emily Rd     Chickering, James    X         Soils meet  3ft sep
           14337 County W     Chickering, James    X         Soils meet  3ft sep
           14345 County W     Chickering, James    x         Soils meet  3ft sep
           14340 County W     Chickering, Vivien   x         Soils meet  3ft sep
           14353 County W     Christian, Jack      x         New conventional
           14092 Hwy 32 &  64 Coleman, Harvey      x         Soils meet 3ft sep
           14176 Doran Rd     Debauche, Clifford   X         New conventional
           14158 Doran Rd     Dekatch, Bernadette X          New conventional
           14013 Hwy 32 &  64 Deltgen, James       x         Holding Tanks
           14010 Emily Rd     Dewitt, Philip       x         Soils meet 3ft sep
           14024 Emily Rd     Diestler, Raymond    X         Soils meet 3ft sep
           14244 County W     Dunlap, Lloyd        x         Holding tanks
           14344 County W     Eldin, Diane         x         Soils meet 3ft sep
           14438 Elbe Lane    Elbe, Paul           x         Soils meet 3ft sep
           14446 Elbe Lane    Elbe, Peter                    New conventional
           14439 Elbe Ln      Elbe, Steven         x         Soils meet 3ft sep
           13.c4l Hwy 32 & 64 Fire Dept. Park      x         Vaulted Privy
           14312 County  W    Flynn, Kelly         x         New conventional
           14050 Old 32       Forrest, Leslie      x         Soils meet  3ft sep
           14062 Silver  Hill Foster, Diane        x         Soils meet  3ft sep
           14294 County  W    Frisch, Nora         x         Soils meet  3ft sep
           14281 Church  Rd   Haefs, David         x         Soils meet  3ft sep
           14288 Ridge St     Hagen, Barbara       x         Soils meet  3ft sep
           13993 Hwy 32 & 64  Haase, Mary          X         Soils meet  3ft sep
           14075 Hwy 32 & 64  Heuser, Ronald       x         Holding tank
           13985 Railroad Av  Hitchcock, Roy            x    < 3ft from ZSSS
           14032 Old 32       Hoerres, Mary        x         Soils meet 3ft sep
           14249 County  W    Hubatch, Raymond          x    SG,< 3ft from ZSSS
           13927 Silver  Hill Isaacson, Oswald          x    < 3ft from ZSSS
           14308 County  W    Jacquet, Harrison    X         Soils meet 3ft sep
           14048 Hwy 32  & 64 Janssen, Paul        x         Soils meet 3ft sep
           14054 Hwy 32  & 64 Janssen, Paul        x         Soils meet 3ft sep
           13890 Hwy 32  & 64 Jazwiecki, Leonard   X         New conventional
           13938 Silver  Hill Jensen, Mary         x         Soils meet 3ft sep
           14201 County  W    Johnston, Alfred          x    < 3ft from ZSSS
           14316 Main Ln      Johnson, Tom              x    < 3ft from ZSSS



                                              A-88






             14159  Doran Rd-      Kalk, Roger            x          New Conventional
             14256  Spring CrRd    Kingston, Leona        x          Soils meet    3ft sep
             14180  County W       Kramer, Earl           x          No system
             14190  County W       Kramer, Earl                 x    < 3ft  from   ZSSS
             13-052 Railroad   Av  Lambrecht, Shyrl             x    < 3ft  from   ZSSS
             14205  County W       Lapaige, Carol               x    < 3ft  from   ZSSS
             14098  Hwy 32 &   64  Larsen, Willard        x          Soils  meet   3ft sep
             14057  Hwy 32 &   64  Leonard, Richard,      X          Soils  meet   3ft sep
             13910  Emily Rd       Meggers, Bonnie        x          Soils  meet   3ft sep
             13960  Hwy 32 &   64  Menting, Edward        x          Vacant house
             14035  Dewey St       Metzler, Arlene        x          Soils meet 3ft    sep
             14104  Hwy 32   & 64  McLain, Marylain       x          Soils meet 3ft    sep
             14295  County   W     Mountain church        x          Soils  meet   3ft sep
             14108  Silver   Hill  Napier, Ronald         x          Soils  meet   3ft sep
             14202  County   W     Niemann, Douglas       x          New conventional
             13954  Hwy 32   & 64  Miemann, Douglas       x          Holding tank
             13937  Silver   Hill  Norwest Bank           x          Soils meet 3ft sep
             14206  County   W     Olson, Jan                   x    < 3ft from ZSSS
             13992  Hwy 32   & 64  Olson, Jan             x          Holding tank
             14259  Spring   CrRd  Olson, Ruth            x          Soils  meet   3ft sep
             14269  Spring   CrRd  Pagel, Bernice         x          Soils  meet   3ft sep
             13940  Silver   Hill  Patula, Raymond        x          Soils  meet   3ft sep
             14241  County   W     Peterson, Darrell            x    < 3ft  from   ZSSS
             13934  Silver   Hill  Pfaff, Elaine          x          Soils  meet   3ft sep
             13245  Spring   CrRd  Rakowski,Virgil        x          Soils  meet   3ft sep
             14235  County   W     Rasmussen, Viola             x    < 3ft from Gw or  ZSSS
             14066  Hwy 32   & 64  Royce, Gerald          x          Soils meet 3ft sep
             14339  Main Ln        Rushton, A.R.          x          Soils meet 3ft sep
             14022  Doran Rd       Saffran, Norman              X    < 3ft from BR or  ZSSS
             14282  Church Rd      Schaal, Cyril          x          New conventional
             14268  Church Rd      Schaal, Cyril          x          Soils meet 3ft sep
             14267  Church Rd      Schaal, Stewart        x          Soils meet 3ft sep
             14173  Doran Rd       Schindler, John        x          New conventional
             14330  County W       School Dist. # 1       x          Soils meet 3ft sep
             14327  Main Ln        Schwartz, Raymond      X          Soils meet 3ft sep
             14275  Ridge St       Spreeman, James        x          Soils meet 3ft sep
             14302  County W       Sorenson, Harold       x          New conventional
             14164  Doran Rd       Stout, Susan           x          New conventional
             14290  ArmstrongSt    Strebe, Kenneth        x          Soils meet 3ft sep
             14162  Church Rd      Tabor Luthern                x    < 3ft from ZSSS
             14153  Church Rd      Tabor Luthern          x          Holding tank  '
             14184  Doran Rd       Tesch, Arlis                 x    < 3 f t from GW or ZSSS
             13986  Silver Hill    Tetzlaff, Arlan        x          Soils meet 3ft sep
             13965  Hwy 32 & 64    Town of Mountain       x          No soil abs. system
             14170  Doran Rd       Trepanier, Wilbert     X          New conventional
             14056  Old 32         Trepanier, Wilbert     X          Soils meet 3ft sep
             14290  County W       Trever, Lois           x          Soils meet 3ft sep
             14082  Old 32         Trever, Melvin         x          Soils meet 3ft sep
             14284  Spring   CrRd  Vogeltanz, Robert      X          Soils meet 3ft sep
             14283  Doran St       Wasurick, Al           x          New conventional
             14152  Doran St       Willemon, Mike         x          New conventional
             13945  Hwy 32 & 64    Yokeum, David          x          Holding tank





                                                   A-89




                                                                                                   16

                                                                                                 /9.

                    7r-
                        TAS: A)
                                           Q3                                          4670



                                                40

                                           rN
    Tell                                                                                                           106.7
                                     /e, r-
  U/C177a,17                       In

   arve
                 64                 21-5
  'I-

                                                          O'e/17Y
                             r,                                                    Q33


                                                                                       r7
       C,        Ou
                                                                      H- L                                 E40
                                                                                           RD.


                                                                                       5
                                                                                M.,q.,e
               mar                                                                  No r r     C'-7

   14A

                                                                                              (,7-aLJ


                                                                                                    RO.
                                                                                         . .. .........
     ,,3h c (c(cn                                                                                      :::,: - i
                                                                      V/171
                                    Car
                                                             76E
                                     Nar
     A57                              41-
                   4o a Jqa@5 If      union               gel    k.
                                     Mal,
               cawarc.       Zcfl-
                                                                A-
              @-Diano-          5     rue@luY'
                                            v
   to
                               4a












                           COMMUNITY OF PENSAUKEE - SOIL INSPECTIONS

                103 Sites inspected as of May 5, 1993

                      90 systems fail due to High Ground Water, Zones of Seasonally
                      Saturated Soil, and Direct Discharge to the Surface of the
                      Ground or Wetlands.

                      13 systems pass due to being Holding Tanks


                90 %  of the systems are failing

                10 % of the systems are passing, including systems which have
                already been brought up to code.


           Percent failure and passing with the systems up to code       HTS, removed.

                100 % of the systems are failing

                None of the existing systems are passing






































                                              A-91











                                     PENSAUKEE SANITARY DISTRICT
                                           SOIL INSPECTIONS

            Physical Address     Owner           Passed Failed Reasons

            2614  County  S      Alsteen, Milton           x      Surface ponding
            3181  County  SS     Bartz, Darrell            x     < 3ft from GW or ZSSS
            3173  County  SS     Bartz, Darrell     x             Holding Tank
            4260  Old St. Rd     Breed, Jacob              x     < 3ft from GW or ZSSS
            3271  Snyder Ln      Bredell, Dennis    x             Holding Tank
            3112  County  S      Campbell, Daryl           x     <  3ft from  GW,BR,ZSSS
            2546  County         Darr, Alphonsus           x     <  3ft from  GW or ZSSS
            2465  County  S      Darr, Clair               x     <  3ft from  GW or ZSSS
            2673  Rocky Ledge    Darr, Lula Mae            x     <  3ft from  GW or ZSSS
            2663  Rocky Ledge    Darr, Lula Mae            x     <  3ft from  GW or ZSSS
            3205  Dienberg Ln    DeWindt, Paul             x     <  3ft from  GW or ZSSS
            4066  Pen Bay Sh     Doeren, Sebastian         x     <  3ft from  GW,SG,ZSSS
            4095  Pen Bay Sh     Donlevy, Brian            x     <  3ft from  GW or ZSSS
            3090  Fish HouseRd   DonLevy, John             x     <  3ft from  GW or ZSSS
            3288  Drolette Rd    Drolette, Mabel           x     <  3ft from  GW or ZSSS
            3163  County SS      Duffy, Randall            x     <  3ft from  GW or ZSSS
            2728  KunzE@r Beach  Duquaine, Ed              x     <  3ft from  GW or ZSSS
            4133  Pen Bay Sh     Dworshok, Donald          x     <  3ft from  GW or ZSSS
            3272  Snyder Ln      Eichman, Carl             x     <  3ft from  GW or ZSSS
            2812  Kunzer Beach   Elliott, Terri            x     <  3ft from  GW,BR,ZSSS
            3104  County S       Flanagan, Charles         x     <  3ft from  GW,BR,ZSSS
            4072  Frease Ln      Frease, Terry             x      Discharge   to SW, SG
            2971  Fish HouseRd   Fritz, Jacob              x     < 3ft from   GW or ZSSS
            3065  Old St Rd      Frisque, Gordon           x     < 3ft from   GW or ZSSS
            3196  County S       Gevers, M.J.              x     <  3ft from  BR or ZSSS
            3145  Wood Rd        Gogat, Genevieve          x      Discharge   to SG,SW
            2824  Kunzer Beach   Goodletson, Tom           x     < 3ft from   GW or ;@SSS
            4364  Old 41         Grohall, Louise           x     < 3ft from   GW or ZSSS
            3096  County  S      Haessly, Eugene           x     <  3ft from  GW,BR,ZSSS
            3488  County  S      Hanes, Ronald      x             Holding Tank
            4143  Pen Bay Sh     Hansen, Albert            x     < 3ft from GW or ZSSS
            2704  Kunzer Beach   Herber,.Peter      x             Holding Tank
            3290  County S       Honish, John       x             Holding tank
            4132  Pen Bay Sh     Jessel, Charles           x     Discharge to SW,SG,GW
            3178  County S       Johnson, Willis           x     < 3ft from BR or ZSSS
            3336  Drolette Rd    Kasbaum, Ann Marie        x     Discharge to SW,SG,GW
            3188  County S       Kimber, Allan             x     < 3ft from BR   or ZSSS
            3296  County S       Koch, Harold              x     < 3ft from BR   or ZSSS
            2830  Kunzer Beach   Kramer, King       x             Holding Tank
            3074  Fish HouseRd   Krutzik, Merlin           x     < 3ft from GW   or ZSSS
            2624  County S       Kunzer, Adeline           x     < 3ft from GW   or ZSSS
            2782  kunzer Beach   Kutner, Mary              x     < 3ft from BR   or GW
            4191  Lower St Rd    Lipp, Donna               x     Discharge to SG,GW
            3019  Fish HouseRd   Livermore, Duane          x     < 3ft from GW or ZSSS
            3073  Wood Rd        Metzler, Bernard          x     Discharge to SW
            4199  Lower St Rd    Miller, James      x             Holding Tank
            4428  Old 41         Mocco, Wilfred            x     < 3ft from GW or ZSSS
            2538  County S       Nelis, Calvin             x     Discharge to SG, SW
            2988  County  S      Nier, Edward              x     < 3ft from GW or ZSSS



                                                 A-92











           4084 Pen Bay Sh     O'Connor, Richard        x     Discharge to SW,SG,GW
           2752 Kunzer Beach   Osten, Ruth              x     < 3ft from GW or ZSSS
           3152 County SS      Peterson, Dorothy        x     < 3ft from GW or ZSSS
           2742 Kunzer Beach   Posey, Gary              x     < 3ft. from GW or ZSSS
           3065 Wood Rd        Rasmussen, Allen         x     Discharge yo SG,ZSSS
           2589 County S       Renard, F@ank            x     < 3ft from GW or ZSSS
           4168 Old 41         Drolette, Donald         x     < 3ft from GW or ZSSS
           2929 Fish HouseRd   Schilling Fish Co        x     < 3ft from GW or ZSSS
           2946 Fish HouseRd   Schilling Fish Co        x     Discharge to SW, ZSSS
           2960 Fish HouseRd   Scott, David             x     Discharge to SW
           4272 Old St Rd      Snyder, Bruce            x     Discharge to GW,SG
           3291 Snyder Ln      Snyder, Michael          x     < 3ft from BR or ZSSS
           3527 County S       Snyder, Roger      x            Holding Tank
           4115 Pen Bay Sh     Sohrweide, Roger         x     < 3ft from GW or ZSSS
           4153 Pen Bay Sh     Stoegbauer, Pat          x     < 3ft from GW or ZSSS
           3143 County SS      Swaer,  Art              x     Discharge to SG,SW,GW
           4109 Pen Bay Sh     Swaer,  David            x     < 3ft from GW or ZSSS
           3214 County SS      Swaer,  Dean             x     < 3ft from GW or ZSSS
           30GO Fish HouseRd   Swaer,  Dean             x     < 3ft from GW or ZSSS
           2985 Fish HouseRd   Swaer,  Dean             x     Discharge to SW,GW
           3001 Fish HouseRd   Swaer,  Dean             x     Discharge to SW,GW
           4146 Pen Bay Sh     Swaer,  Francis          x     < 3ft from  GW or ZSSS
           3050 Fish HouseRd   Swaer,  Norbert          x     < 3ft from  GW or ZSSS
           3426 County S       Swaer,  Orpha            x     < 3ft from  GW or ZSSS
           4193 Topel Rd       Thompson, Lavern X              No System
           4162 County SS      Thompson, Lavern         x     < 3ft from  GW or ZSSS
           3184 County SS      Thompson, Lavern         x     < 3ft from  GW or ZSSS
           3090 County S       Tonon, Francie           x     < 3ft from  BR
           4120 Pen Bay Sh     Topel, Barry             x     Discharge to SW,SG,GW
           4295 Old St Rd      Topel, Fred "            x     < 3ft from GW  or ZSSS
           3312 Drolette  Rd   Topel, Russell           x     < 3ft from GW  or ZSSS
           3116 County S       Urban, Robert            x     < 3ft from  BR
           3262 County S       VanderBloomen,  Ellen    x     < 3ft from  BR
           3070 County S       VanEss, Walter           x     < 3ft from  GW or ZSSS
           3446 County S       Weber, Jeff        X.           Holding Tank
           3306 County S       Weigelt, Harold    X            Holding Tank
           4203 Topel. Rd      Weinandt, Robert         x     < 3ft from GW  or ZSSS
           2620 Kunzer Beach   Westfahl,Gilbert   X            Holding Tank
           2650 Kunzer Beach   Whiting, David     x            Holding Tank
           3341 County -SS     ziesmer, Raymond         x     < 3ft from GW  or ZSSS


















                                              A-93




                                       SEE PAGE             12                                                                                                             "9
                                                                                                                                         A3

                                                                                                                                                                          'K
                 c                                                Oconto
                                                                    Coun@(,
                                 Bond,                                                                           2/x*e
                                                                                                                                    -Donald
                                                                                                                 @au
                                                                             C FL.                            V/7 e-5                '51 lvna             1@
                               143                        2.30 74                                                                  1(5?4. 4,9                34      A
                           Con,5tal7cc                             OF
                                                                                           G.
                                                        U                                   40                   etal

                                     '9"    /a
                                                                                           7,
                                     /-CU                                    200                    41                        A                 0

                                                                                                                                                       A
                                                                    Vfle@,ncn                                                al c;@
                                                                                                   L           7@7-J       0xs >/7,
                                               T@ome         .11f _r     -j&                                                         ela/
                                                        do                   40  .40                    &7.,57         -c@ 57
    16. 0


                                       /-u c
               5
                                       Ord                                            @u
                                     -bu/11-   ICS. 77, @0@'Vz'c         S
                                                                         d3                                                                                           2900
                                            -10         8                         !"K. z
                                         rl                                     --  --     -      cs:::::
                                                          ('r&/nes
                                                          Z7(:Wn(2-          Lakd
                's.                                     Cr7lun 0j&r5C-.'7
                                                        40 -;t 7 3L@' ;
                            CIV                         v
                                                            -0    '0  Lit 7-T- PD.

                                -Z@


                                       40
             IT                     40
                                                        0Q           ZI&SI77                  C
        /7                                                                   A52
          Se/7                                 Q                                        @@   (k

                                                          IQ

                           xg                           0 10
      .73                                   Del7nis
                                            Z /'/7/-7c2 a
                          O&Z's          a     Clok                          k0a                        4
                                                                             I?
                                                                a                f
                                                                             IE

                         Gr                                                                                                  3300
                                                                 -7@ tj      7;@
                        Gcorqe                          Q,
                                                                                                                            R. 2 2 E.
                                                                                                                                                         N
                                                                                                                            SEE PA GE /3
                     G,c,-7
                                                        VeI7                                                     1;9.
                                            @57e                                                                                                                               CI
                        Is /7                                                             c                                       I_7oSCp17 C
                      -;t@                                              Cal@y @
                                                                                                      ARD
                                                                                            4                           @z
             60      G              30                               7-&-/77C
                                                                   14al 7,5
                                                                                                                                         U's
                                                                                                                                          &O-N.
                           Gl-&
                                            77( '2r                          YDER
                                                                               LA




    V7

                                                        VII
                         Z11770r7C-A',                                                     Mass
                                                                                                                               C0rr9ocrV,,?y po)n-ts')q"c';q"
                                                                                                                   2900                                  2)00
           e3o                   D*                     am -4
       a               a
                                                        vIn
                                               (5/k/770-/
                                                        e fur
                                                              7
                             /Iboet
                                               .40
                          (51,9
                                               RD.
         U
                                            Cb(7

        tj
       -Z
                                                           A/
                                            LAS
                                                             z-7 la

















                             CHUTE POND    SOIL INSPECTIONS


          336 Sites inspected as of October 8, 1993

                61 systems fail due to High Ground Water, Zones of Seasonally
               Saturated Soil, or Illegal Systems.

                275 systems pass due to:

                     16 are existing Holding Tanks

                     7 are existing Mounds

                     11 are New Conventional

                     2 are Houses without systems

                     239 are existing conventional systems which meet the soil
                    requirements.

                18 % of the systems are failing

                82 % of the systems are passing, including systems which have
               already been brought up to code.

          Percent failing and   passing with the systems up to code, HTS,
          Mounds, and New Conventional, removed.

                20 % of the systems are failing

                80 % of the existing conventional systems are passing























                                           A-95












                                    CHUTE POND COMMUNITY
                                 ON-SITE INSPECTION REPORT



           Physical Address    Owner               Pass Fail  Reasons

           12505 W Shore Dr    Aerts, Russell       x         Soils meet 3ft sep
           13276 Hwy 64        Allen, Patrick       x         Soils meet 3ft sep
           13445 Joppa Ln      Athey, John          x         Soils meet 3ft. sep
           12175 S Shore Dr    Athey, Raymond            x    < 3ft from ZSSS
           12334 S Shore Dr    Awe, Margaret        x         Mound System
           12954 Bauman Ln     Bacheller, Evelyn    X         Soils meet  3ft sep
           12338 S Shore Dr    Badeau, David        x         Soils meet  3ft sep
           13763 Lake Sh Ln    Baeten, Clyde        x         Soils meet  3ft sep
           12836 W Shore Dr    Baeten, Robert       X         Soils meet  3ft sep
           13412 Hillside Dr   Baier, Earl          x         Soils meet  3ft sep
           12667 E Shore Dr    Bartingal, Robert    X         Soils meet  3ft sep
           12748 W Shore Dr    Bartz, Robert        x         Soils meet  3ft. sep
           12332 W Shore Dr    Bast, Helen          x         No System
           13774 Bonita Ln     Basten, Norbert           x    < 3ft from  ZSSS
           12970 Bauman Ln     Bauman, James        x         Soils meet  3ft sep
           12930 Bauman Ln     Bauman, James        x         Soils meet  3ft sep
           12546 W Shore Dr    Bauman, Richard      x         Soils meet  3ft sep
           12627 E Shore Dr    Baumgartner,Gerald   X         Soils meet  3ft sep
           13-'06 Hillside Dr  Beck, Frank Joe           x    < 3ft from BR & ZSSS
           12566 W Shore.Dr    Beckman, Orville     x         Soils meet  3ft sep
           12777 E Shore Dr    Bermke, Kenneth      x         New Mound
           13758 Bonita Ln     Bernston, Paul       x         Soils meet  3ft sep
           13811 Bonita Ln     Beyer, Darrell            x    < 3ft from  ZSSS
           13663 Lake Sh Ln    Bohrmueller, Melvin X          Soils meet  3ft sep
           13683 Lake Sh Ln    Bohrmueller, Melvin   X        Soils meet  3ft sep
           13286 Hwy 64        Borah, William       x         Soils meet  3ft sep
           12342 W Shore Dr    Bowen, Margaret      x         New Mound
           12582 W Shore Dr    Boyle, Kenneth       x         Soils meet  3ft sep
           13380 Hillside Dr   Blecke, Joan         x         Soils meet  3ft sep
           12870 W Shore Dr    Bray, Donald         x         New Conventional
           12789 E Shore Dr    Brennecke, Jane      x         Soils meet 3ft sep
           13416 Hillside Dr   Brock, Milton        x         New Conventional
           13667 S Sh Hts Ln   Brodhaaen, Kenneth   X         Soils meet 3ft sep
           12338 W Shore Dr    Brown, Henry              x    < 3ft from ZSSS
           13376 Hillside Dr   Bryfczynski, Donald X          Soils meet 3ft sep
           12576 Berry Dr      Buck, Allan          X         Soils meet 3ft sep
           13007 L Bgly Rpds   Buelow, Leonard           x    < 3 f t from Gw or ZSSS
           13664 S Sh Hts Av   Burns, Michael       x         Soils meet 3ft  sep
           12760 W Shore Dr    Capelle, Lloyd       x         Soils meet 3ft  sep
           12271 Sunset Ln     Cerk, Kenneth        x         Holding Tank
           12783 E Shore Dr    Check, Joyce         x         Soils meet  3ft sep
           13091 L Bgly Rpds   Choren, Anthony      x         Soils meet  3ft sep,
           13810 Bonita Ln     Christie, Bernice    x         Soils meet  3ft sep
           12765 E Shore Dr    Coppus, Joseph       x         Soils meet  3ft sep
           12578 W Shore Dr    Craig, Grantland     x         Soils meet  3ft sep
           13122 Hwy 64        Czerwinski, Dennis   X         Soils meet  3ft sep
           12630 W Shore Dr    Dauer, George        x         Soils meet  3ft sep
           13458 Joppa Ln      Deau, Larry          x         Soils meet  3ft sep



                                              A-96









              13779  Lake Sh Ln      Delcore, Francis         X            Soils   meet  3ft sep
              12575  W Shore Rd      Depner, Lyman                   X     < 3ft   from  ZSSS
              14195  Kingston Rd     Devroy, Richard          X            Soils   meet  3ft   sep
              12415  Poquette Ln     Dillon, Edward           X            Soils   meet  3ft   sep
              12421  Poquette        Dillon, Edward           X            Soils   meet  3ft   sep
              13690  S Sh Hts Ln     Dishaw, James            X            Soils   meet  3ft   sep
              13284  Hwy 64          Ditiege, Bonnie          X            Soils   meet  3ft   sep
              12577  Berry Dr        Donovan, Mabel           X            Soils   meet  3ft   sep
              12489  W Shore Rd      Dorn, Robert             X            Soils   meet  3ft   sep
              13368  Hillside Dr     Duchateau, Wayne         X            Soils   meet  3ft   sep
              12562  W Shore Dr      Edquist, Gary            X            New conventional
              12936  Bauman Ln       Ellenbecker, Larry       X            Soils meet 3ft sep
              12234  S Shore Dr      Ellington, Diane         X            Soils meet 3ft sep
              12360  W Shore Dr      Eslien, Howard           X            Soils   meet  3ft   sep
              12275  Sunset Ln       Ferry, Wilbert           X            Holding Tank
              13@74  Woodland Ln     Flynn, Patrick                  X     < 3ft   from BR &   ZSSS
              13821  Bonita Ln       Fox, Jerome              X            Soils   meet 3ft    sep
              13370  Woodland Ln     Fox, Gerald              X            Mound   System
              12574  W  Shore Dr     Frechette, Harold               X     < 3ft   from  ZSSS
              12771  E  Shore Dr     Frisch, Roy              X            Soils   meet  3ft sep
              12233  S  Shore Dr     Gaab, Mark               X            Soils   meet  3ft   sep
              12226  S  Shore Dr     Gagan, Robert            X            Soils   meet  3ft   sep
              12977  L  Bgly Rpds    Gajdostik, Anthony       X            Soils   meet  3ft   sep
              12814  W. Shore Dr     Gennrich, Robert         X            Soils   meet  3ft   sep
              13340  Woodland Ln     Gerou, C.M.                     X     < 3ft   from  ZSSS
              13735  Lake Sh Ln      Gerrits, Harold          X            Soils   meet  3ft sep
              13701  Lake Sh Ln      Gerskow, Melvin                 X     Privy   & Plumbing
              12388  S Shore Dr      Geurts, Fred                    X     Add Lock and Chain
              12597  Waupee Rvr      Giese, Allen             X            Soils meet 3ft sep
              13320  Hillside Dr     Giese, Delbert           X            Holding Tank
              13350  Woodland Ln     Gilbertson, Leroy        X            Holding Tank
              13378  Woodland Ln     Gilson, Darold                  X     < 3ft from BR & ZSSS
              13025  L Bgly Rpds     Giuliani, Joseph                X     < 3 f t from GW or ZSSS
              12362  W Shore Dr      Golden, Martin           X            New conventional
              12345  W Shore Dr      Golden, Peter            X            New Mound
              123S4  S Shore Dr      Gore, Norman             X            Soils meet 3ft sep
              12604  Berry Dr        Grey, Harry              X            Soils meet 3ft sep
              14167  Kingston Rd     Gunkel, David            X            Soils meet 3ft sep
              12617  E Shore    Dr   Gutnecht, Donald         X            Soils meet 3ft sep
              12244  S Shore    Dr   Hagen, Jerome                   X     < 3 f t from GW or ZSSS
              12558  W Shore    Dr   Hansche, Charles         X            New conventional
              13441  Cresent    Dr   Hansen, Roger            X            Soils meet 3ft sep
              12314  S Shore    Dr   Hanson, Leslie                  X     Add Locks And Chain
              12330  S Shore    Dr   Hardekopf, Fred                 X     < 3ft from ZSSS
              13668  S Sh Hts Ln     Hartman, Francis         X            Soils meet 3ft sep
              12561  Balsam La.      Hartwell, Richard        X            Soils meet 3ft sep
              12217  S Shore Dr      Heilman, Robert          X            Soils meet 3ft sep
              13430  Joppa Ln        Helmarth, Theresia.      X            Soils meet 3ft sep
              12316  W Shore Dr      Hendricks, Kenneth       X            New Conventional
              12960  Bauman Ln       Hendricks, William       X            Soils meet 3ft sep
              12660  W Shore Dr      Hengel, Donald           X            Soils meet 3ft sep
              12675  E Shore Dr      Henke, James             X            Soils meet 3ft sep
              12336  W Shore Dr      Hergert, Paul                   X     < 3 f t from BR, GW, ZSSS
              12392  S Shore Dr      Hermus, John                    X     < 3 f t from SW or ZSSS



                                                        A-97










            13763  Bonita Ln      Hewett, John                x    < 3ft from ZSSS
            12261  Sunset Ln      Heyrman, Clifford           x    < 3ft from BR
            13543  S Sh Hts Ln    Hietpas, Lee          x          Soils meet 3ft sep
            13850  Bonita Ln      Hintz, Norbert              x    < 3ft from GW or ZSSS
            13826  Bonita Ln      Hockers, Francis      x          Soils  meet  3ft sep
            12583  E Shore Dr     Hoehne, Eileen        x          Soils  meet  3ft sep
            13678  S Sh Hts Av    Hoffman, Robert       x          Soils  meet  3ft sep
            12@29  Poquette Ln    Horkman, Donald             x    < 3ft  from  ZSSS
            12479  W Shore Dr     Huiting, Donald       x          Soils  meet  3ft  sep
            13189  Hwy 64         Hulchiy, Michael      x          Soils  meet  3ft  sep
            13433  Cresent Dr     Huska, Robert         x          Soils  meet  3ft  sep
            13366  Woodland Ln    Ison, Leslie                x    < 3ft  from  BR
            12577  E Shore Dr     Jahnke, Leroy         x          Soils  meet  3ft  sep
            12586  W Shore Dr     Jandrey, Henry        x          Soils  meet  3ft  sep
            12805  E Shore Dr     Janquart, Julie       k          Soils  meet  3ft  sep
            13490Chute Dam Ln     Jans, Ron             x          Soils  meet  3ft  sep
            14173  Kingston Rd    Jasculca,   Richard   X          Soils  meet  3ft  sep
            13680  S Sh Hts Ln    Jindra, Dan           x          Soils  meet  3ft  sep
            12595  E Shore Dr     Johnson, Richard      x          Soils  meet  3ft  sep
            12650  W Shore Dr     Johnson, Violet       x          Soils  meet  3ft  sep
            12795  E Shore Dr     Jolly, William        x          Soils  meet  3ft  sep
            12725  E Shore Dr     Jost, Roger           x          New Conventional
            14175  Kingston Rd    Kamper, Herbert       x          Soils meet 3ft sep
            13280  Hillside Dr    Karnitz, Dane         x          Holding Tank
            12589  W Sh HeightsKerscher, Paul           x          Soils meet 3ft    sep
            13651  S Sh Hts Av    Kersten, Clarence     X          Soils meet 3ft    sep
            12324  W Shore Dr     Kersten, Robert       x          Holding Tank
            13693  Lake Sh Ln     Kester, Willert       x          Soils meet 3ft    sep
            12342  S Shore Dr     Kielbasa, Frank             x    < 3f t from GW or ZSSS
            135212 Hillside Dr    Kiernan, Patrick      x          Soils meet 3ft    sep
            13360  Woodland Ln    Kiffe, James                x    < 3ft from ZSSS
            12659  E Shore Dr     King, Donald          X          Soils meet 3ft sep
            13805  Bonita Ln      King, Paul                  x    Add lock and chain
            13324  Hillside Dr    Kitzman, Robert       x          Holding Tank
            13769  Lake Sh Ln     Klawitter, Kevin      x          Soils meet 3ft sep
            12245  Sunset Ln      Klobuchar, Robert           x    Add locks and chains
            12223  Sunset Ln      Koehnke, Ralph              x    < 3ft from   BR
            13369  Hillside Dr    Kollman, Milton       x          Soils meet   3ft sep
            13410  Joppa Ln       Konczyk, B.. J.       x          Soils meet   3ft sep
            12618  W Shore Dr     Kratcheck, Edward     X          Soils meet   3ft sep
            12220  S Shore Dr     Kros, Joseph          x          Soils meet   3ft sep
            12322  S Shore Dr     Krueger, Edward             x    Disconnect   Plumbing
            13296  Hillside Dr    Kuble, Thomas         x          Soils meet   3ft sep
            13276  Hillside Dr    Kuehl, Gerald         x          Holding Tank
            13384  Woodland Ln    Lakso, Eugene         x          Soils meet 3ft sep
            13778  Bonita Ln      Lamers, Harold              x    < 3ft from ZSSS
            12305  S Shore Dr     Lamers, William             x    Add Lock And Chain
            12592  W Shore Dr     Lanser, Cyril         x          Soils meet 3ft    sep
            13354  Woodland Ln    Lardinois, Laverne    X          Holding Tank
            12643  E Shore Dr     Lautenschlager, G.    X          Soils meet 3ft    sep
            12990  Bauman Ln      LeBlanc, Jerome       x          Soils meet 3ft    sep
            13647  S Sh Hts Av    Lecomte, Donna        x          Soils meet 3ft    sep
            13684  S Sh hts Av    Lemense, Danny        x          Soils meet 3ft    sep
            13518  Hillside Dr    LeMere, Gerald        x          Soils meet 3ft    sep



                                                 A-98









            12COl  E Shore  Dr Lepkowski, Robert       X         Soils meet 3ft sep
            12173  S Shore Dr Lewis, Orville                X    < 3ft from ZSSS
            12692  W Shore Dr Linstad, Gary            X         Soils meet 3ft sep
            12301  S Shore Dr Litscher, Thomas         X         Soils meet 3ft sep
            13486  Chute Dam LnLoritz, J.              X         Soils meet 3ft sep
            13697  Lake Sh Ln    Lubenske, John             X    Direct Discharge SG
            12506  W Shore Dr    Luck, Wallace         X         Soils meet 3ft sep
            12229  S Shore Dr    Luedeman, Alvin       X         Soils meet 3ft sep
            12318  S Shore Dr    Maccaux, Edward            X    < 3ft from ZSSS
            13498  Hillside Dr   Macco, James          X         Soils meet 3ft sep
            12400  S Shore Dr    Madsen, David              X    Add lock and chain
            13622  S Sh Hts Av   Magnin, Dean          X         Soils  meet 3ft sep
            13725  Lake Sh Ln    Makholm, C.M.              X    Privy  & Plumbing
            13640  S Sh Hts Ln   Mancusi, Nancy        X         Soils  meet  3ft sep
            13394  Woodland Ln   Mantz, Lyle           X         Soils  meet  3ft sep
            12609  E Shore Dr    Marquardt, Randis     X         Soils  meet  3ft sep
            12989  L Bgly Rpds   Martin,.Herbert       X         Soils  meet  3ft sep
            12613  Berry Dr      Maas, Lawrence        X         Soils  meet  3ft sep,
            12470  Hwy 32 & 64   McDonald, Ardyth      X         Soils  meet  3ft sep
            13408  Hillside Dr   McGlinn, Harold            X    Privy  & Plumbing
            12681  E Shore Dr    McKellep, Jane        X         Soils  meet  3ft sep
            12830  W Shore Dr    Mecikaliski, Leroy    X         Soils  meet  3ft sep
            12687  E Shore Dr    Melnarik, Edward      X         Soils  meet  3ft sep
            13610  S Sh Hts Ln   Melotte, Richard      X         Soils  meet  3ft sep
            12942  Bauman Ln     Merkley, R. C.        X         Soils  meet  3ft sep
            13256  Hwy 64        Mertz, John           X         Soils  meet  3ft sep
            13838  Bonita   Ln   Messmer, Harold            X    < 3ft from GW, SW, ZSSS
            13510  Hillside Dr   Midler, John          X         Soils meet 3ft   sep
            12540  W Shore Dr    Miller, Mark          X         Soils meet 3ft   sep,
            13492  Hillside Dr   Mix, Vivian           X         Soils  meet  3ft sep
            13451  Waupee Rvr    Moede, Daniel         X         Soils  meet  3ft sep
            12246  Sunset Ln     Moore, Harvey         X         Holding Tank
            12672  W Shore Dr    Moore, Richard        X         Soils  meet  3ft sep
            13528  Hillside Dr   Morgan, Joseph        X         Soils  meet  3ft sep
            12772  W Shore Dr    Mueller, Robert       X         Soils  meet  3ft sep
            12608  W Shore Dr    Muench, Elizabeth     X         Soils  meet  3ft sep
            12366  S Shore Dr    Murray,.Joseph        X         Soils  meet  3ft sep
            13822  Bonita Ln     Musolf, Roy           X         Soils  meet  3ft sep
            14034  W Shore Dr    Nackers, LeRoy        X         Soils  meet  3ft sep
            12999  L Bgly Rpds   NernBerger, Lee            X    < 3ft from GW or ZSSS
            13644  S Sh Hts Ln   Netols, Kenneth       X         Soils meet 3ft sep
            12786  W Shore Dr    Nickel, Erwin         X         Holding Tank
            13502  Hillside Dr   Nield, Thomas         X         Holding Tank
            13427  Cresent Dr    Northam, James        X         New Conventional
            12605  Berry Dr      Olson, John           X         Soils  meet  3ft sep
            13 '2@ 3 7Cresent Dr Olson, Judith              X    < 3ft  from  ZSSS
            12617  Waupee Rvr    Owen, Sue             X         Soils  meet  3ft sep
            12581  W Sh HeightsOzarowicz, Robert       X         Soils  meet  3ft sep
            12862  W Shore Dr    Paul, Dorothy         X         Soils  meet  3ft sep
            13290  Hillside Dr Paulik, Gerald               X    < 3ft  from  ZSSS
            13656  S Sh Hts Ln   Peacock, Robert       X         Soils  meet  3ft sep,
            13420  Joppa Ln      Pekarske, Joseph      X         Holding Tank
            12636  Waupee Rvr    Penney, Lee           X         New Conventional
            13484  Chute Dam LnPeot, J. H.             X         Soils meet 3ft sep



                                                 A-99









           13745  Lake Sh Ln   Perarske, Donald     x        Soils meet 3ft sep
           12640  W Shore Dr   Pirlot, Larry        x        Soils meet 3ft sep
           12651  E Shore Dr   Plamann, Melvin      x        Soiuls meet 3ft sep
           12778  W Shore Dr   Pomprowitz, Ronald        x   To close to SW
           12614  Berry Dr     Popp, Donald         x        Soils meet   3ft sep
           13205  Hwy 64       Poradek, Bernard     x        Soils meet   3ft sep
           12441  Hwy 32       Pritzl, Julius            x   < 3ft from   BR
           12538  W Shore Dr   Property Owners      x        No System
           13842  Bonita Ln    Pungarcher, DouglasX          Soils  meet  3ft sep
           13140  Hwy 64       Quandt, Orville      x        Soils  meet  3ft sep
           13165  Hwy 64       Radtke, Allan        x        Soils  meet  3ft sep
           12360  S Shore Dr   Radtke, Allen        x        Soils  meet  3ft sep
           13673  Lake Sh Ln   Radtke, Robert       x        Soils  meet  3ft sep
           13663  S Sh Hts Av  Radue,melvin         x        Soils  meet  3ft sep
           13689  S Sh Hts Av  Reinhard, Norbert    X        Soils  meet  3ft sep
           12620  Waupee Rvr   Rekitzke, Harold     x        Soils  meet  3ft sep
           13655  S Sh Hts Ln  Rezachek, Charles    X        Soils  meet  3ft sep
           1291-0 Bauman Ln    Ritger, Raymond      x        Soils  meet  3ft sep
           13618  S Sh Hts Ln  Rheingans, Chester   X        Soils  meet  3ft sep
           13388  Woodland Ln  Robach, Scott        x        Soils  meet  3ft sep
           13657  S Sh Hts Av  Robedeaux, John      x        Soils  meet  3ft sep
           13685  S Sh hts Av  Roeser, Robert       X        Soils  meet  3ft sep
           12449  Hwy 32       Rogers, Patrick           x   Add Locks & Chains
           12730  W Shore Dr   Rohatsch, Antoinette   X      Soils meet 3ft sep
           13815  Bonita Ln    Rohloff, Carl        x        Soils meet 3ft sep
           12352  W Shore'Dr   Romenesko, Richard   X        New Conventional
           12525  W Shore Dr   Ross, Carolyn        x        Soils  meet 3ft  sep
           13123  Hwy 64       Rummel, Clifford     x        Soils  meet 3ft  sep
           12950  Bauman Ln    Runge, Richard       x        Soils  meet 3ft  sep
           12374  S Shore Dr   Sallis, Dort.hy      x        Soils  meet 3ft  sep
           12304  S Shore Dr   Schabel, David       x        Mound  System
           13632  S Sh Hts Ln  Schaefer, Gerald     x        Soils  meet  3ft sep
           13660  S Sh Hts Ln  Schenkoske, Richard X         Soils  meet  3ft sep
           13614  S Sh Hts Ln  Schnetzer, James     x        Soils  meet  3ft sep
           13846  Bonita Ln    Schommer, Joseph     x        Soils  meet  3ft sep
           12551  Hwy 32 & 64  School, Katherine    X        Soils  meet  3ft sep
           12753  E Shore Dr   Schmidt-, Alice      x        Soils  meet  3ft sep
           12510  W Shore Dr   Schmidt, Arthur      x        Soils  meet  3ft sep
           12514  W Shore Dr   Schmidt, Kenneth     x        Soils  meet  3ft sep
           12741  E Shore Dr   Schmidt, Ralph       x        Soils  meet  3ft sep
           13404  Hillside Dr  Schoepke, Duane      x        Soils  meet  3ft sep
           12240  Sunset Ln    Schuette, Mark            x   < 3ft  from  BR
           12236  Sunset Ln    Schuette, Paul            x   Home made System
           12237  Sunset Ln    Schuette, Paul            x   < 3ft from ZSSS
           12348  S Shore Dr   Schuetpelz, Lee      x        Soils meet 3ft sep
           12684  W Shore Dr   Schuh, Keith         x        Soils  meet  3ft sep
           12717  E Shore Dr   Schumacher, Alfred   X        Soils  meet  3ft sep
           12711  E Shore Dr   Schuster, Allan      x        Soils  meet  3ft sep
           13659  S Sh Hts Ln  Sell, Leroy               x   Homemade System
           12215  Sunset Ln    Sherwood, Glen       x        Soils meet 3ft sep
           12766  W Shore Dr   Simanson, Sharon     x        Soils meet 3ft sep
           13331  Cresent Dr   Simen, Cathy         x        Holding Tank
           12756  W Shore Dr   Smith, Carol              x   < 3 f t from GW or ZSSS
           12510  Knollwood RdSmith, Wilmer         x        Soils meet 3ft sep



                                              A-100









           13115  L Bgly Rpds   Spanbauer, William   X         Soils meet 3ft sep
           12167  S Shore Dr    Staszak, Harry            x    < 3ft from ZSSS
           13033  L Bgly Rpds   SteinDrenner, Russ        x    < 3ft from GW or ZSSS
           13832  Bonita Ln     Stemper, Gordon      x         Soils meet 3ft sep
           13789  Lake Sh Ln    Sterling Tool MFG    X         Soils meet 3ft   sep
           12494  Hwy 32 & 64   ST. Michael's Cong   X         Soils  meet 3ft  sep
           13649  S Sh Hts Ln   Swanson, Carl        x         No System
           12386  S Shore Dr    Swiechowski, EdwardX           Soils meet.3ft   sep
           12346  W Shore Dr    Swoboda, Nancy       x         New Mound
           12852  W Shore Dr    Terry, Daniel        x         Soils meet 3ft   sep
           12559  Hwy 32 & 64   Thielke, Gerald      x         Holding Tanks
           13751  Lake Sh  Ln   Thompson, Gary       x         Soils meet 3ft   s ep
           13755  Lake Sh  Ln   Thompson, Gary       x         Soils meet 3ft   sep
           12380  W Shore  Dr   Thompson, Philip     x         Soils meet 3ft   sep
           12380  S Shore  Dr   Thompson, Philip     x         Soils meet 3ft   sep,
           12587  E Shore  Dr   Ullrich, Richard     x         Soils meet 3ft   sep
           12326  S Shore  Dr   Ulman, Theodore           x    < 3ft f rom. GW or ZSSS
           13348  Hillside Dr   Vanbeek, Denis            x    < 3ft  from BR
           13356  Hillside Dr   Vanbeek, Denis            x    Privy  and Plumbing
           13360  hillside Dr   Vanbeek, Kathryn     x         Soils  meet 3ft  sep
           12703  E Shore Dr    Vandehey, Robert     x         Soils  meet 3ft  sep
           12233  Sunset Ln     VanDenBogart, William     x    < 3ft  from BR
           13633  S Sh Hts Ln   VandenBush, Ralph X            Soils  meet 3ft  sep
           12515  W Shore Dr    Vander Heyden, Andrew          Soils  meet 3ft  sep
           12407  S Shore Dr    Vander Heyden, Peter   X       Soils  meet 3ft  sep
           12824  W Shore Dr    Vanderloop, Char     x         Soils  meet 3ft  sep
           12916  Bauman Ln     VanderVelden,joyce X           Soils  meet 3ft  sep
           12320  W Shore Dr    VanevenHoven, Kieth    X       Holding Tanks
           14033  W Shore Dr    Van Hout, Marlene    X         Soils meet 3ft   sep
           13609  S Sh Hts Ln   Vanlankvelt, Peter   X         Soils meet 3ft   sep
           13155  Hwy 64        Van Pay, Terrance    X         Soils  meet 3ft  sep
           13049  L Bgly Rpds   Voight, Bonnie            x    < 3ft  from BR
           12369  S Shore Dr    Vollmar, James       x         New Conventional
           12370  Bonita Ln     Vollmar, James       x         Soils meet  3ft sep
           12566  Waupee Rvr    Vorpahl, Pearl       x         Soils meet  3ft sep
           13652  S Sh Hts Ln   Voster, Vern         x         Soils  meet 3ft  sep
           12735  E Shore Dr    Walters, Robert      x         Soils  meet 3ft  sep
           12240  S Shore Dr    Wargin, Ro4er             x    Disconnect  Plumbing
           12493  W Shore Dr    Warmbrunn, Frank     x         Soils  meet 3ft  sep
           12759  E Shore Dr    Wasmund, Clarence    X         Soils  meet 3ft  sep
           13456  Balsam Ln     Wasmund, Micheal     x         Soils  meet 3ft  sep
           12225  Sunset Ln     Watermolen, Richard.X          Soils  meet 3ft  sep
           12387  S Shore Dr    Watt, Joseph         x         Soils  meet 3ft  sep
           13671  S Sh Hts Av   Webb, Alice          x         Soils  meet 3ft  sep
           13069  L Bgly Rpds   Weege, Lynford            x    < 3ft  from BR
           12695  E Shore Dr    Weidner, Daniel      x         Soils  meet 3ft  sep
           12554  W Shore Dr    Weinhold, Lori       x         No System
           12607  W Shore Dr    Weinhold, Otis       x         Soils  meet 3ft  sep
           12534  W Shore Dr    Wendt, Maynard       x         Soils  meet 3ft  sep
           12409  Poquette Ln   Westphal, Harriet         x    < 3ft  from ZSSS
           12573  Waupee Rvr    White, Barbara       x         Soils  meet 3ft sep
           12SSO  Hwy 32 & 64   White, Barbara       x         Soils  meet 3ft sep
           12431  Poquette Ln   Wichman, Donald           x    < 3ft  from ZSSS
           12401  Poquette Ln   Wichman, Evan        x         Soils  meet 3ft sep



                                              A-101







           12980  Bauman Ln      Widowski, Anthony      X         New Conventional 1992
           12602  W Shore Dr     Widowski, Ronald       x         Soils meet  3ft. sep
           14183  Kingston Rd    Wilson, Calvin         x         Soils meet  3ft-sep
           13762  Bonita Ln      Wilson, D.             x         Soils meet  3ft  sep
           12526  W Shore Dr     Wippert, George        x         Soils meet  3ft  sep
           13168  Hwy 64         Wirth, David           x         Soils meet  3ft  sep
           13206  Hwy 64         Wirth, Donald          x         Soils meet  3ft  sep
           13194  Hwy 64         Wirth, Gary            x         Soils meet  3ft. sep
           12492  W Shore Dr     Wisnewski, T.J.        x         Soils meet  3ft  sep
           12496  W Shore Dr     Wisniewski, Carl       x         Soils meet  3ft. sep
           12678  W Shore Dr     Witt, Laverne          x         Soils meet  3ft  sep
           13514  Hillside Dr    Wochinski, Antone      X         Holding Tank
           13715  Lake Sh Ln     Wochinski, Daniel      X         Soils meet 3ft.  sep
           12225  S Shore Dr     Woelz, Donald          x         Soils meet 3ft.  sep
           12924  Bauman Ln      Wolf, Leo              x         Soils meet  3ft. sep
           13325  Cresent. Dr    Woulf, Carol           x         Mound System
           12880  W Shore Dr     Yakel, Jay             x         Soils meet 3ft   sep
           12727  E Shore Dr     Yuenger, Cynthia       x         Soils meet 3ft.  sep


































                                                   A-102








                                          (G; R ALA-           7
                                                L

  Ao                        p
                    99A 6 L. RD.           UT                          -0 lz
                                                        S14. o co
             BA G L
                           @@ x         . (Z zi
               P/0
    0              OUND     Q
                             c          C.- (@@                         qj Q
                             a      ki
        OW BA GL@Cy        7z@ Qj
         PIDS R           'l-jAl:r-jc
          ...     Li 15 P.                                  77
                                        ID                             Li.
                                             4-
                    480                     E39.6
                                   MA .. :


                 N          RD.
                                    Nie     400
                    BernIce-                                         547.74
                    --u,3

                                                   Ila
                                TRS-              u
                                                                  3  0

                                                                      Ll   IC,

                                                  ro         ......
                                D A
                                                         ZL                    ux

     ............
                                            ure                              LA.
                                                          ef

       zi.                                                  cill


                                                                        Lt'






                         (@runcf-l


                                             Nis.
                 20
    EE PAGE
 IS                     13900                                             ap    jk
                                                                              I I cj













                    COMMUNITY OF LITTLE SUAMICO - SOIL INSPECTIONS

          60 Sites inspected as of October 21, 1993

               36 Systems fail due to High Ground Water, Zones of
               Seasonally Saturated Soil, and Direct Discharge to
               Wetlands and the Surface of the Ground.


               24 Systems pass due to:

                    7 are existing Holding Tanks

                    10 are existing Mounds

                    3 are New Conventional

                    4 are existing conventional systems which meet the soil
                    requirements.

               60 % of the systems are failing

               40 % of the systems are passing, including systems which have
               already been brought up to code.


          Percent failure and passing with the systems up to code, HTS,
          Mounds, and New Conventional, removed.

               90 % of the systems are failing

               10 % of the existing conventional systems-are passing




























                                          A-104











                                 COMMUNITY OF LITTLE SUAMICO
                                  ON-SITE INSPECTION REPORT



           Physical Address     Owner               Pass Fail  Reasons

           5337  Allen  Road    Alberts, Gary             X    Discharge to SG
           5412  Allen  Road    Allen, Clifford           x    Discharge to SG
           5021  Allen  Road    Allen, Debra         X         New Mound
           5587  Allen  Road    Allen, Douglas            x    < 3ft from ZSSS, SG
           5423  k1len  Road    Allen, Violet             x    < 3ft from ZSSS
           5673  Allen  Road    Allen, William            x    Direct Discharge SG
           5151  Allen  Road    Baribeau, Kenneth         x    < 3ft from ZSSS
           5496  Bram.  Road    Belanger, Michael         x    Discharge to SG
           5188  Allen  Road    Bergh, Colin         x         Soils meet  3ft sep
           5318  Allen  Road    Bergh, George        x         New Mound
           5524  Bram.  Road    Bramschreiber, Martha     x    < 3ft from  ZSSS,  SG
           5387  Birch  Creek   Charapata, James          x    < 3ft from  ZSSS
           5338  Allen  Road    Cole, Jane                x    < 3ft from  ZSSS
           5388  Birch  Creek   Coopman, James            x    < 3ft from  ZSSS
           5348  Allen  Road    Debauch, Roger            x    < 3ft from  ZSSS
           5408  County S       Detiege, David       x         New Conventional
           5169  Bram. Road     Falk, Patrick        x         Holding Tank
           5391  County S       Follett, Harold           x    < 3ft  from ZSSS
           5409  County S       Follett, Harold      x         Soils  meet 3ft sep
           5659  County S       Galkowski, Alice          x    < 3ft  from ZSSS
           5488  Bram. Road     Hall, Janice              x    < 3ft  from ZSSS,  SG
           5352  Bram. Road     Helmle, Amy               x    < 3ft  from ZSSS
           5400  Allen Road     Hoglund, Meta             x    < 3ft  from ZSSS,  SG
           5004  Allen Road     Johnson, Robert      x         New Mound
           5420  Bram. Road     King, Robert              x    < 3ft from  ZSSS
           5390  County S       Klarkowski, NlorbertX          Soils  meet 3ft sep
           5210  County S       Komorowski, Bill          x    < 3ft  from ZSSS
           51S3  County S,      Kozloski, Daniel     x         New Mound
           5226  Allen Road     Krumerauer, Enid     x         Holding Tank
           5108  County S       Kussow, Ben               X    < 3ft from ZSSS
           5239  County S       Kussow, Thomas            x    < 3ft from ZSSS,   SG
           5220  County S       Kwiatkowski, John         x    < 3ft  from ZSSS
           5200  County S       Kwiatkowski, John         x    < 3ft  from ZSSS
           5365  Bram.  Road    Leanna, Daniel       x         New Conventional
           5372  Bram.  Road    Leclair, David            x    <,3ft from ZSSS
           5026  Allen  Road    Lefeber, Eugene      x         Holding Tanks
           5374  Allen  Road    Lindsley, Kari       x         New Mound'
           5274  Bram.  Road    Losch, Robert             x    < 3ft from ZSSS
           5350  Birch  Creek   Marchand, Rodney     x         New Mound
           5519  Bram.  Road    Matuszewski, John         x    < 3ft from ZSSS, SG
           5340  Bram.  Road    Noack, Milo          x         Holding Tank
           5375  Allen  Road    Peters, Muriel            x    < 3ft from  ZSSS,SG
           5409  Bram.  Road    Peters, Roger             x    < 3ft from  ZSSS
           5419  County S       Piontek,Ervin             x    < 3ft from  ZSSS
           5193  Race Lane      Race, Frank          x         Soils meet  3ft.  sep
           5320  Allen Road     Robertson, Roy       x         New Mound
           5460  Bram. Road     Rosek, Roger              x    < 3ft from  ZSSS
           5474  Bram. Road     Rosek, Roger              X    < 3ft from  ZSSS




                                               A-105








          5168 Allen Road     Schaden, Richard          x   < 3ft from ZSSS
          5487 County S       Shella, Cecilia           X   < 3ft from ZJSSS
          5388 Braim. Road    Travis, William     x         Holding Tanks
          5606 Allen Road     Urbaniak, Robert          X   < 3ft from ZSSS
          5362 Bram. Road     Van Lanen, FlorenceX          Holding Tank
          5579 County S       Van Lanen, Jeff     x         New Mound
          5691 Allen Road     Winter, Eugene            X   Discharge to SG
          5262 Allen Road     Wolfgram, Donald    x         New Mound
          5374 County S       Wroldewski, Stanley       x   < 3ft from ZSSS












































                                               A-106







       NORTH
        )AMD:
       ... ...                                           40                   wu


          74Z.                                                                                            --k
                                                                                                                                          z, a
                                                                                                                HOT:
                    Yt    fic                                                veiclechow
                                                         r
                                                                                     k
                                                                                69 6
                                                                                                                              41 Oki'
                                                                                n@
                                                                                               0. g "
                                                                                                               Cka                     p  r)
    -@j CROSS                                                                                    i8
                              IM                                                                               7               fvp    (5
                                                      RO   r                                                            -1111011  rm
                                                                                                                   7,)
                                                      'Eq

          2D                                                                                                              (n
                                  Rob                                                                                                6
                            ') -9
                          @'fi    Kux,-nal7,
                                  eta/
                                         @9.


                                                                                                                              Z;n
                                                             RIcharcy
         C jka                                                                                                          to
                                                                                                 Lill     A! k,



                                                 willldtn
     Q               Alcicr,5          tu I)       PlIen                           lice
                            5t3    fb                                                -"4                  ,      4      X ".)
                                                   46. - I
                                                                                                     A           606
                              k
                                    Plha
                            V
                            f,    Bfa77-';C/) -                                             r)  @4
                                                                                                                              Q
      AR
     11                                                0                    772a                                        9
     19
                                                                 W ran
                                                                ru    ,Face                 DO V/d
                                                                                                                                       r\j
                                             farm                                                  80
                                                                15@                            les
                                                 k pfSt.                                                   nk
                                                                      I CL               Wrpblew,@k;                                         ]-@t -11

                   (n
                                  rb
                                                                                                                                        on

                                                                   Ic a
          f-a/1s                            U 1.9 -a 7.88               n
                                      14                                       @50.4,3                 6ch
                                                                 141. c
     C.                                                           9/



                                                                                                  ou-

             RA
                                                                    RD.                  BLVD.
                            500                       900                         SEE PAGE        .4
                                                                                    1300                         1700                       21












                                   MOODY LAKE COMMUNITY
                                ON-SITE INSPECTION REPORT

          Phys.ical Address   Owner              Pass Fail  Reasons

          11754  Moody Lk  Dr Arndt, Kenneth      x         Soils meet  3ft sep
          11741  Moody Lk  Dr Arndt, Mark         x         Soils meet  3ft sep
          11901  Moody Lk  Dr Bandy, Leon         x         Soils meet  3ft sep
          11743  Moody Lk  Dr Bauer, Charles      x         Soils meet  3ft sep
          11838  Moody Lk  Dr Behnke, Helen       x         Soils meet  3ft sep
          13192  Campfire  Ln Carpenter, Eugene         x   Plumbing &  Privy
          11770  Moody Lk  Dr Carroll, Richard    x         Soils  meet 3ft sep
          11841  Moody Lk  Dr Conway, Daniel      x         Soils  meet 3ft sep
          11?59  Moody Lk  Dr Demerath, Jerome    x         Soils  meet 3ft sep
          11827  Moody Lk  Dr Dey, Ronald         X         Soils  meet 3ft sep
          13150  Moody Lk  Rd Eckert, Priscilla   X         Soils  meet 3ft sep
          13241  Campfire  Ln Ern, Milton         x         Soils  meet 3ft sep
          13151  Campfire  Ln Ernst, Richard      x         Soils  meet 3ft sep
          13110  Moody Lk  Rd Feranchex, Gerald   X         Soils  meet 3ft sep
          11809  Moody Lk  Dr Frank, Robert       x         Soils  meet 3ft sep
          13154  Moody Lk  Rd George, Joseph      x         Soils  meet 3ft sep
          11740  Moody Lk  Dr Hatfield, Arthur    x         Soils  meet 3ft sep
          11821  Moody Lk  Dr Heckenlaible, D.    x         Soils  meet 3ft sep
          13209  Campfire  Ln Herald, Patrick     x         Soils  meet 3ft sep
          13152  Campfire  Ln Heritage, Donald    x         Soils  meet 3ft sep
          11739  Moody Lk  Dr Herman, Robert                Soils  meet 3ft sep
          13184  Campfire  Ln Hooser, Mary        x         Soils  meet 3ft sep
          13167  Campfire  Ln Kebschull, Gary     x         Soils  meet 3ft sep
          13193  Campfire  Ln Kessler, Joseph     x         Soils  meet 3ft sep
          11900  Moody Lk  Dr Kramer, James       x         Soils  meet 3ft sep
          13120  Moody Lk  Rd Kress, Florence     x         Soils  meet 3ft sep
          11765  Moody Lk  Rd Loberger, Richard   X         Soils  meet 3ft sep
          11756  Moody Lk  Dr Lyons, Robert       x         Soils  meet 3ft sep
          11720  Moody Lk  Vw Moser, Michael      x         Soils  meet 3ft sep
          13270  Campfire  Ln Okrasinki, James    x         Soils  meet 3ft sep
          11851  Moody Lk  Dr Pennings, Leon      x         Soils  meet 3ft sep
          13157  Campfire  Ln Pfankuch, James     x         Soils  meet 3ft sep
          11836  Moody Lk  Dr Platz, Walter       x         Soils  meet 3ft sep
          11826  Moody Lk  Dr Quandt, Mark        x         Soils  meet 3ft sep
          11837  Moody Lk  Dr Santkujl, Peter     x         Soils  meet 3ft sep
          13281  Campfire  Ln Schmatzhagen, CarolX          Soils  meet 3ft sep
          11739  Moody Lk  Vw Schneider, Michael X          Soils  meet 3ft sep
          11835  Moody Lk  Dr Schott, Larry             x   < 3ft  from BR
          13200  Campfire  Ln Seamars, Kent             X   Ground Surface
          13291  Campfire  Ln Seroogy, Darcy      x         Soils meet 3ft  sep
          11745  Moody Lk  Dr Smrz, Jerold        x         Soils meet 3ft  sep
          11767  Moody Lk  Dr Splitt, Betty       x         Soils  meet 3ft sep
          11861  Moody Lk  Dr Stabbe, Gregory           x   Illegal system
          13221  Campfire  Ln Stillman, Edwin           x   < 3ft from  ZSSS
          13211  Campfire  Ln Stillman, Edwin     x         Soils meet  3ft sep
          13198  Campfire  Ln Suring, Lee         x         Soils  meet 3ft sep
          13294  Campfire  Ln Valley, Robert            x   Plumbing &  Privy
          11831  Moody Lk  Dr Volpintesta, AlbertX          Soils meet  3ft sep
          13162  Campfire  Ln Yakel, Kenneth      x         Soils meet  3ft sep



                                             A-108












                            MOODY LAKE   SOIL INSPECTIONS

          49 Sites inspected as of October 15, 1993

               6 systems fail due to High Ground Water, Zones of Seasonally
               Saturated Soil, Illegal Systems, And Direct Discharge to
          Ground Surface.

               43 systems are existing systems which meet the soil
               requirements

               12 % of the systems are failing

               88 % of the existing conventional systerns are passing















































                                         A-109






                        00
            cat                                                                                                                                                                             CHUM@P,@


      MY
      Mal.                                                                                                          L





                                                        C4
         Ri                                                                                    U                                                                                            F I
                     d f                                    f                                                                             Cl)
                    Tf.

                                                                                                                   till
                                                                                                                                                                            Ul
                                                                                                                                9 0 @'K
                                          Ljt*




                                                                                                                                                                                                       00
            7e4
                                                                                                                                                            4@.

                                                                                                                                                            C-b
                                                                                                                                         (IV


                     ia
                             3v
                                                     c Ixa       t:@k
                   v iTl
          f pt-



                                                                       JA





















                           ANDERSON LAKE - SOIL INSPECTIONS


          145 Sites inspected as of November 12, 1993

               36 Systems fail due to High Ground Water, Zones of Seasonally
               Saturated Soil, Plumbing & Privys, or Illegal Systems.

               109 Systems Pass due to:

                    29 are existing Holding Tanks

                    11 are New Conventional


                    3 are Houses without systems

                    1 is an existing mound


               25% of the systems are failing

               75% of the systems are passing, including systems which have
               already been brought up to code.


          Percent failure and passing with the systems up to code, HTS,
          Mounds, and New Conventional, removed.

               36% of the systems are failing

               64% of the existing conventional systems are passing






















                                         A-111












                                    ANDERSON LAKE COMMUNITY
                                   ON-SITE INSPECTION REPORT



            jLhysical Address    Owner                Pass Fail  Reasons

            13280  N And  Lk Ln  Anthony, Harold              X  Plumbing      Privy
            13631  Tonka  Lane   Arndt, Carl            x        Soils meet    3ft sep
            13237  N And  Lk Ln  Arnold, Florence             X  < 3ft from    ZSSS
            12192  Leo's  Rd     Basten, Gordon         x        Soils meet    3ft sep
            12226  Leo's  Rd     Baumgartner, Louis     X        Soils meet    3ft sep
            13287  N And  Lk Ln  Baumhart, Robert       x        Holding Tank
            11891  E And  Lk. Rd Bayorgeon, Dennis      x        Holding Tank
            12295  Ziereis Ln    Berendsen, John        x        Soils meet 3ft sep
            11962  Hwy 32        Bialcik, Donald        x        Soils meet 3ft    sep
            12269  Leo's Rd      Bishop, Robert         x        Soils meet 3ft    sep
            13293  N And Lk Ln.  Bockman, Leon          x        Holding Tank
            13295  N And Lk Ln   Boc1a-nan, Leon        x        Holding Tank
            12275  Ziereis Ln    Boegh, Randy           x        Soils meet 3ft    sep
            13283  N And Lk Ln   Bohrer, Alfred         x        Soils meet 3ft    sep
            13247  N And Lk Ln   Brantmeier, Michael    x        Soils meet 3ft    sep
            13238  N And Lk Ln.  Braun, Harlan                X  < 3ft from ZSSS
            13306  N*And Lk Ln   Brockman, Leon         x        Holding Tank
            13633  Tonka Lane    Burghardt, George      x        Soils meet 3ft    sep
            12042  LakeSide Dr   Buss, Robert           x        Soil-S meet 3ft   sep
            12245  Ziereis Ln    Camey, Mabel           x        Soils meet 3ft    sep
            12232  Leo's Rd      Capaletti, Michael           X  Illegal System
            12205  Leo's Rd      Capaletti, Timothy     X        Soils meet 3ft    sep
            13256  S Shore Dr    Capaletti, Timothy     X        No system
            12069  LakeSide Dr   Chaloupka, William     X        Soils meet 3ft    sep
            11871  E And Lk Rd   Cramer, Gary           x        New Conventional
            12041  LakeSide Dr   Christensen, RussellX           Soils meet 3ft sep
            12238  Leo's Road    Coel, Milton           x        Soils meet 3ft sep
            13246  S Shore Dr    Colbert, Peter         x        Soils meet 3ft    sep
            13253  S Shore Dr    Cowling, Grover        x        Soils meet 3ft    sep
            13343  N And Lk  Ln  Dejardin, Louis              X  < 3ft from ZSSS
            13273  N And Lk  Ln  DeValk,-Robert               X  Setbacks, Grey Water
            13319  N And Lk  Ln  Driedric, Andrew             X  < 3ft from ZSSS
            12107  LakeSide  Dr  Ellefson, David        x        Soils meet 3ft sep
            12261  Leo's Rd      Etheridge, Myrna       x        Soils meet 3ft sep
            12119  LakeSide  Dr  Federmeyer, Lee        x        New In-Ground Pres
            13217  N And Lk  Ln  Firgens, Colleen       x        New Conventional
            13385  N And Lk.Ln   Firgens, Hilbert       x        Holding Tank
            12212  Leo's Rd      Frederickson, Ken      x        Holding Tank
            11923  E And Lk Rd   Frederickson, Vernonx           Holding Tank
            13347  N And Lk  Ln  Freweard, Daniel       x        Mound System
            11927  And Lk Ln     Fulcer, Warren         x        Holding Tank
            11919  E And Lk Rd   Gossen, Jerry          x        Holding Tank
            13267  N And Lk Ln   Graser, Mary           x        New Conventional
            11943  E And Lk  Rd  Gulczynski, Theodorex           Holding Tank
            12148  Hwy 32        Haave, Ethel           x        Soils meet 3ft sep
            12249  Ziereis Ln.   Hackbarth, William     X        New Conventional
            11981  Hwy 32        Hackbarth, William     X        Soils meet 3ft sep
            13257  N And Lk Ln   Hansen, George         x        Soils meet 3ft sep



                                                A-112










           12210  Ziereis Ln   Harris, Glenn              X  < 3ft from ZSSS
           12176  Leo's Rd     Hayes, Clarence            X  Illegal System, SG
           13225  N And Lk Ln  Heimerl, John         x       New Conventional
           12270  Zeiries Ln   Hensberger, Alan      x       Soils meet 3ft sep
           12115  LakeSide Dr  Hintz, Edward         x       Soils meet 3ft sep
           13233  N And Lk Ln  Hoban, William             X  Illegal System
           13231  N And Lk Ln  Hochrein, John        x       Soils meet 3ft sep
           13357  N And Lk Ln  Homel, Joseph              X  < 3ft from ZSSS
           12238  Ziereis Ln   Hort, Terry           x       Soils meet 3ft sep
           12053  LakeSide Dr  Huebscher, Harold     x       Soils meet 3ft sep
           12184  Leo's Rd     Jaeger, Edgar         x       Holding Tank
           13240  S Shore Dr   Jaeger, Gregory       X       Soils meet 3ft sep
           12244  Leo's Rd     Jensen, Nels          x       New Conventional
           13294  N And Lk Ln  Johnson, Jeanne       x       Holding Tank
           12093  LakeSide Dr  Johnson, Jeanne       x       Soils meet 3ft sep
           12206  Leo's Rd     Joosten, Thomas            X  Illegal System, ZSSS
           13348  N And Lk Ln  Kammerman, Thomas     x       New Conventional
           12268  Ziereis Ln   Karwedsky, Ellen           X  Plumbing &  Privy
           13311  N And Lk Ln  Kimball, Christopher       X  < 3ft  from ZSSS
           12309  Ziereis Ln   Kohel, Gary           x       Soils  meet 3ft sep
           12202  Leo's Rd     Krings, Alan               X  < 3ft  from ZSSS
           11942  Hwy 32       Kroeing, Lenerth      x       Soils  meet 3ft sep
           13277  N And Lk Ln  Kroll, Thomas              X  < 3ft  from ZSSS
           11983  Hwy 32       Kuehl, Kenneth             X  < 3ft  from ZSSS
           11997  Hwy 32       Kuehl, Kenneth        x       Holding Tanks
           12096  LakeSide Dr  Kusters, Robert       x       Soils meet 3ft sep
           13315  N And Lk Ln  Kwiatkowski,  Daniel       X  < 3ft from ZSSS
           13314  N And Lk Ln  Kwiatkowski, Daniel        X  Disconnect  Plumbing
           13303  N And Lk Ln  Landua, Guy           x       Holding Tank
           11915  E And Lk Rd  Lemery, Gary          x       Holding Tank
           11853  E And Lk Rd  Lewandowski,  Walter       X  < 3ft from ZSSS
           11861  E And Lk Rd  Lewandowski,  Walter  X       No System
           12258  Leo's Rd     Lind, John            x       Soils meet 3ft sep
           11883  E -And Lk Rd Lisiak, Robert             X  < 3ft from GW & ZSSS
           13299  N Arid Lk Ln Liss Fa-mily Trust    x       Holding Tank
           11935  E And Lk Rd  Lucka, Richard             X  < 3ft from GW & ZSSS
           11959  E And Lk Rd  Maves, Weldon         x       Holding Tank
           12136  LakeSide Dr  McDonald, Ardyth      x       Soils meet 3ft  sep
           12075  LakeSide Dr  McGregor, Marvin      x       Soils meet 3ft  sep
           12308  Ziereis Ln   Meverden, Jerome      x       Vacant Lot
           12258  Ziereis Ln   Mier, Delmar          x       Soils meet 3ft  sep
           12276  Ziereis Ln   Mleziva, Wericil      x       Soils meet 3ft  sep
           13648  Tonka Lane   Mott, Gleen           x       New Conventional
           12267  Ziereis Ln   Muniz, Andrea         x       Soils meet 3ft sep
           11877  E And Lk Rd  Neary, Donald         x       Holding Tank
           12296  Ziereis Ln   Neuser, Donald        x       Soils meet 3ft. sep
           12084  Hwy 32       Olle, Donald          x       Soils meet 3ft  sep
           12252  Ziereis Ln   Persson, Robert       x       Soils meet 3ft  sep
           12266  Ziereis Ln   Peters, Robert             X  Plumbing & Privy
           11897  E And Lk Rd  Peterson, Marie            X  < 3ft from GW & ZSSS
           13270  S Shore Dr   Peterson, Robert           X  < 3ft from ZSSS & GW
           12213  Leo's Rd     Peterson, Roy         x       Holding Tank
           12241  Ziereis Ln   Pfankuch, Michael     x       Soils meet 3ft sep
           13278  N And Lk Ln  Phillips, Richard          X  < 3ft from ZSSS



                                              A-113









            13644  Tonka Lane    Polster, Eugene        x        Soils meet 3ft sep
            13641  Tonka Lane    Raab, Edward           X        Soils meet 3ft sep
            11911  E And Lk Rd   Radue, Harold                X  < 3ft from GW & ZSSS
            13284  N And Lk Ln   Rasmussen, Roger             X  Plumbing And Privy
            12269  Ziereis Ln    Roe, Richard           x        Soils  meet 3ft sep
            11865  E And Lk Rd   Rollins, Richard             X  < 3ft  from ZSSS
            11947  E And Lk Rd   Rudzinski, Carolyn           X  < 3ft  from GW & ZSSS
            12262  Ziereis Ln    Sabrowsky, David       x        Soils  meet 3ft sep
            12101  LakeSide Dr   Schmuhl, Russell       x        Soils  meet 3ft sep
            13247  S Shore Dr    Schreiner, Paul        x        Soils  meet  3ft sep
            13215  N And Lk Ln   Scl'luettpelz, StephenX         New Conventional
            12236  Ziereis  Ln   Schulz, Arvid          X        Soils meet 3ft sep
            12237  Ziereis  Ln   Schulz, R.L.           x        Soils meet 3ft sep,
            12234  Ziereis  Ln   Schulz, Arvid          x        Soils  meet  3ft sep,
            13252  S Shore  Dr   Siems, Kent            x        soils  meet  3ft sep,
            13260  S Shore  Dr   Sonnenberg, Don        x        No system
            13264  S Shore  Dr   Sonnenberg,   Don            X  Privy & Plumbing
            13243  N And Lk Ln   Spreeman, Leonard      x        Holding Tank
            13307  N And Lk Ln   Spreeman, Eugene       x        Holding Tank
            12277  Leo's Rd      Steeno, Gary                 X  < 3ft from   ZSSS
            11969  E And Lk  Rd  Stefanec, Ronald       x        Soils meet   3ft sep
            12211  Ziereis Ln    Thede, Claude          x        Soils meet   3ft sep
            12047  LakeSide Dr   Thermansen, Mas              X  Plumbing &   Privy
            12278  Leo's Rd      Timm, Albert           x        Soils meet   3ft sep
            12266  Leo's Rd      Timm, Cindy            x        Soils meet   3ft. sep
            11975  And Lk Ln     Thompson, Allan        x        Holding Tank
            11905  E And Lk Rd   Thompson, Robert       x        Holding Tank
            11951  E And Lk Rd   Trick, Gilbert         x        Holding Tank
            11939  E And Lk  Rd  Trost, Leonard               X  < 3ft from ZSSS
            13339  N And Lk  Ln  Uhlenbrauck, Keith     X        Holding Tank
            13377  N And Lk  Ln  Uhlenbrauck, Larry           X  < 3ft from ZSSS
            12290  Ziereis Ln    VanBeek, Arnold        x        Soils meet 3ft sep
            12303  Ziereis Ln    Van Bellinger, Ray     X        Soils meet 3ft sep
            11901  E And Lk Rd   Van Rens, Gerald       x        Holding Tank
            132-44 N And Lk Ln   Werner, David          x        Soils meet 3ft sep
            12267  Ziereis Ln    Whipp, Leonard         x        Soils meet 3ft sep
            12304  Ziereis Ln    Whipp, -Leonard        x        New Conventional
            12262  Ziereis Ln    Wickman, Lyle          x        Soils meet 3ft sep
            11963  E And Lk RD   Witthuhn, Diana        X        Holding Tank
            11931  E And Lk Rd   Woelfel, George        x        Holding Tank
            12242  Ziereis Ln    Zahn, Michael          x        Soils meet 3ft sep
            12265  Ziereis Ln    Zernicke, Harvey       x        Soils meet 3ft sep
            12198  Leo's Rd      Ziereis, Sharon              X  < 3ft from ZSSS

















                                                A-114





                 Q::
                                                    30                                                                29

                                                                                                                                   640


           32
               4
                                              @e::::          CSHORrLA.

              Zt



                                                                                   419
                                                                    LL
                                                                   ....                                                                                                        IIACI
                                         :4ck
           CH
             PO                                                                                                                         rn ....
                                                                               ...                                                                                                   IN'
                                                                                                                                                        TS
                                                                                                                 oJd            440


                                                                          civ



                                                                                                        Ilh-pi-n







                                                                                                                                                            LI;
                                      c-11 78                                                                                                    C; S@a
                                                                                                                    son
                                                    a,;.                                                                                                                          70



                                                              J2


                                       60

                                            ------                                     ------  Z7-
                                                        4J
                                                                                                                                                                        /VCU'

                                                                                                                                                                                  Aa











































































                                                            3 6668 14109 6620