Pt. 63, Subpt. UUUUU, Table 1
Table 1 to Subpart UUUUU of Part 63—Emission Limits for New or Reconstructed EGUs
As stated in § 63.9991, you must comply with the following applicable emission limits:

If your EGU is in this subcategory
For the following pollutants
You must meet the following emission limits and work practice standards
Using these requirements, as appropriate (e.g., specified sampling volume or test run duration) and limitations with the test methods in Table 5
1. Coal-fired unit not low rank virgin coal
a. Filterable particulate matter (PM)
9.0E-2 lb/MWh 1
Collect a minimum of 4 dscm per run.

OR
OR

Total non-Hg HAP metals
6.0E-2 lb/GWh
Collect a minimum of 4 dscm per run.

OR
OR

Individual HAP metals:
Collect a minimum of 3 dscm per run.

Antimony (Sb)
8.0E-3 lb/GWh

Arsenic (As)
3.0E-3 lb/GWh

Beryllium (Be)
6.0E-4 lb/GWh

Cadmium (Cd)
4.0E-4 lb/GWh

Chromium (Cr)
7.0E-3 lb/GWh

Cobalt (Co)
2.0E-3 lb/GWh

Lead (Pb)
2.0E-2 lb/GWh

Manganese (Mn)
4.0E-3 lb/GWh

Nickel (Ni)
4.0E-2 lb/GWh

Selenium (Se)
5.0E-2 lb/GWh

b. Hydrogen chloride (HCl)
1.0E-2 lb/MWh
For Method 26A, collect a minimum of 3 dscm per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

OR

Sulfur dioxide (SO2) 3
1.0 lb/MWh
SO2 CEMS.

c. Mercury (Hg)
3.0E-3 lb/GWh
Hg CEMS or sorbent trap monitoring system only.

2. Coal-fired units low rank virgin coal
a. Filterable particulate matter (PM)
9.0E-2 lb/MWh 1
Collect a minimum of 4 dscm per run.

OR
OR

Total non-Hg HAP metals
6.0E-2 lb/GWh
Collect a minimum of 4 dscm per run.

OR
OR

Individual HAP metals:
Collect a minimum of 3 dscm per run.

Antimony (Sb)
8.0E-3 lb/GWh

Arsenic (As)
3.0E-3 lb/GWh

Beryllium (Be)
6.0E-4 lb/GWh

Cadmium (Cd)
4.0E-4 lb/GWh

Chromium (Cr)
7.0E-3 lb/GWh

Cobalt (Co)
2.0E-3 lb/GWh

Lead (Pb)
2.0E-2 lb/GWh

Manganese (Mn)
4.0E-3 lb/GWh

Nickel (Ni)
4.0E-2 lb/GWh

Selenium (Se)
5.0E-2 lb/GWh

b. Hydrogen chloride (HCl)
1.0E-2 lb/MWh
For Method 26A, collect a minimum of 3 dscm per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

OR

Sulfur dioxide (SO2) 3
1.0 lb/MWh
SO2 CEMS.

c. Mercury (Hg)
4.0E-2 lb/GWh
Hg CEMS or sorbent trap monitoring system only.

3. IGCC unit
a. Filterable particulate matter (PM)
7.0E-2 lb/MWh 4
9.0E-2 lb/MWh 5
Collect a minimum of 1 dscm per run.

OR
OR

Total non-Hg HAP metals
4.0E-1 lb/GWh
Collect a minimum of 1 dscm per run.

OR
OR

Individual HAP metals:
Collect a minimum of 2 dscm per run.

Antimony (Sb)
2.0E-2 lb/GWh

Arsenic (As)
2.0E-2 lb/GWh

Beryllium (Be)
1.0E-3 lb/GWh

Cadmium (Cd)
2.0E-3 lb/GWh

Chromium (Cr)
4.0E-2 lb/GWh

Cobalt (Co)
4.0E-3 lb/GWh

Lead (Pb)
9.0E-3 lb/GWh

Manganese (Mn)
2.0E-2 lb/GWh

Nickel (Ni)
7.0E-2 lb/GWh

Selenium (Se)
3.0E-1 lb/GWh

b. Hydrogen chloride (HCl)
2.0E-3 lb/MWh
For Method 26A, collect a minimum of 1 dscm per run; for Method 26, collect a minimum of 120 liters per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

OR

Sulfur dioxide (SO2) 3
4.0E-1 lb/MWh
SO2 CEMS.

c. Mercury (Hg)
3.0E-3 lb/GWh
Hg CEMS or sorbent trap monitoring system only.

4. Liquid oil-fired unit—continental (excluding limited-use liquid oil-fired subcategory units)
a. Filterable particulate matter (PM)
3.0E-1 lb/MWh 1
Collect a minimum of 1 dscm per run.

OR
OR

Total HAP metals
2.0E-4 lb/MWh
Collect a minimum of 2 dscm per run.

OR
OR

Individual HAP metals:
Collect a minimum of 2 dscm per run.

Antimony (Sb)
1.0E-2 lb/GWh

Arsenic (As)
3.0E-3 lb/GWh

Beryllium (Be)
5.0E-4 lb/GWh

Cadmium (Cd)
2.0E-4 lb/GWh

Chromium (Cr)
2.0E-2 lb/GWh

Cobalt (Co)
3.0E-2 lb/GWh

Lead (Pb)
8.0E-3 lb/GWh

Manganese (Mn)
2.0E-2 lb/GWh

Nickel (Ni)
9.0E-2 lb/GWh

Selenium (Se)
2.0E-2 lb/GWh

Mercury (Hg)
1.0E-4 lb/GWh
For Method 30B sample volume determination (Section 8.2.4), the estimated Hg concentration should nominally be <1/2 the standard.

b. Hydrogen chloride (HCl)
4.0E-4 lb/MWh
For Method 26A, collect a minimum of 3 dscm per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

c. Hydrogen fluoride (HF)
4.0E-4 lb/MWh
For Method 26A, collect a minimum of 3 dscm per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

5. Liquid oil-fired unit—non-continental (excluding limited-use liquid oil-fired subcategory units)
a. Filterable particulate matter (PM)
2.0E-1 lb/MWh 1
Collect a minimum of 1 dscm per run.

OR
OR

Total HAP metals
7.0E-3 lb/MWh
Collect a minimum of 1 dscm per run.

OR
OR

Individual HAP metals:
Collect a minimum of 3 dscm per run.

Antimony (Sb)
8.0E-3 lb/GWh

Arsenic (As)
6.0E-2 lb/GWh

Beryllium (Be)
2.0E-3 lb/GWh

Cadmium (Cd)
2.0E-3 lb/GWh

Chromium (Cr)
2.0E-2 lb/GWh

Cobalt (Co)
3.0E-1 lb/GWh

Lead (Pb)
3.0E-2 lb/GWh

Manganese (Mn)
1.0E-1 lb/GWh

Nickel (Ni)
4.1E0 lb/GWh

Selenium (Se)
2.0E-2 lb/GWh

Mercury (Hg)
4.0E-4 lb/GWh
For Method 30B sample volume determination (Section 8.2.4), the estimated Hg concentration should nominally be <1/2 the standard.

b. Hydrogen chloride (HCl)
2.0E-3 lb/MWh
For Method 26A, collect a minimum of 1 dscm per run; for Method 26, collect a minimum of 120 liters per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

c. Hydrogen fluoride (HF)
5.0E-4 lb/MWh
For Method 26A, collect a minimum of 3 dscm per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

6. Solid oil-derived fuel-fired unit
a. Filterable particulate matter (PM)
3.0E-2 lb/MWh 1
Collect a minimum of 1 dscm per run.

OR
OR

Total non-Hg HAP metals
6.0E-1 lb/GWh
Collect a minimum of 1 dscm per run.

OR
OR

Individual HAP metals:
Collect a minimum of 3 dscm per run.

Antimony (Sb)
8.0E-3 lb/GWh

Arsenic (As)
3.0E-3 lb/GWh

Beryllium (Be)
6.0E-4 lb/GWh

Cadmium (Cd)
7.0E-4 lb/GWh

Chromium (Cr)
6.0E-3 lb/GWh

Cobalt (Co)
2.0E-3 lb/GWh

Lead (Pb)
2.0E-2 lb/GWh

Manganese (Mn)
7.0E-3 lb/GWh

Nickel (Ni)
4.0E-2 lb/GWh

Selenium (Se)
6.0E-3 lb/GWh

b. Hydrogen chloride (HCl)
4.0E-4 lb/MWh
For Method 26A, collect a minimum of 3 dscm per run.

For ASTM D6348-03 2 or Method 320, sample for a minimum of 1 hour.

OR

Sulfur dioxide (SO2) 3
1.0 lb/MWh
SO2 CEMS.

c. Mercury (Hg)
2.0E-3 lb/GWh
Hg CEMS or Sorbent trap monitoring system only.

1 Gross electric output.
2 Incorporated by reference, see § 63.14.
3 You may not use the alternate SO2 limit if your EGU does not have some form of FGD system (or, in the case of IGCC EGUs, some other acid gas removal system either upstream or downstream of the combined cycle block) and SO2 CEMS installed.
4 Duct burners on syngas; gross electric output.
5 Duct burners on natural gas; gross electric output.
[78 FR 24087, Apr. 24, 2013]