Pt. 63, Subpt. DDDDD, Table 1
Table 1 to Subpart DDDDD of Part 63—Emission Limits for New or Reconstructed Boilers and Process Heaters
As stated in § 63.7500, you must comply with the following applicable emission limits:

[Units with heat input capacity of 10 million Btu per hour or greater]
If your boiler or process heater is in this subcategory . . .
For the followingpollutants . . .
The emissions must not exceed the following emission limits, except during startup and shutdown . . .
Or the emissions must notexceed the following alternative output-based limits, except during startup and shutdown . . .
Using this specified sampling volume or test run duration . . .
1. Units in all subcategories designed to burn solid fuel.
a. HCl
2.2E-02 lb per MMBtu of heat input
2.5E-02 lb per MMBtu of steam output or 0.28 lb per MWh
For M26A, collect a minimum of 1 dscm per run; for M26 collect a minimum of 120 liters per run.

b. Mercury
8.0E-07 a lb per MMBtu of heat input
8.7E-07 a lb per MMBtu of steam output or 1.1E-05 a lb per MWh
For M29, collect a minimum of 4 dscm per run; for M30A or M30B, collect a minimum sample as specified in the method; for ASTM D6784 b collect a minimum of 4 dscm.

2. Units designed to burn coal/solid fossil fuel
a. Filterable PM (or TSM)
1.1E-03 lb per MMBtu of heat input; or (2.3E-05 lb per MMBtu of heat input)
1.1E-03 lb per MMBtu of steam output or 1.4E-02 lb per MWh; or (2.7E-05 lb per MMBtu of steam output or 2.9E-04 lb per MWh)
Collect a minimum of 3 dscm per run.

3. Pulverized coal boilers designed to burn coal/solid fossil fuel
a. Carbon monoxide (CO) (or CEMS)
130 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (320 ppm by volume on a dry basis corrected to 3 percent oxygen, 30-day rolling average)
0.11 lb per MMBtu of steam output or 1.4 lb per MWh; 3-run average
1 hr minimum sampling time.

4. Stokers designed to burn coal/solid fossil fuel
a. CO (or CEMS)
130 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (340 ppm by volume on a dry basis corrected to 3 percent oxygen, 30-day rolling average)
0.12 lb per MMBtu of steam output or 1.4 lb per MWh; 3-run average
1 hr minimum sampling time.

5. Fluidized bed units designed to burn coal/solid fossil fuel
a. CO (or CEMS)
130 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (230 ppm by volume on a dry basis corrected to 3 percent oxygen, 30-day rolling average)
0.11 lb per MMBtu of steam output or 1.4 lb per MWh; 3-run average
1 hr minimum sampling time.

6. Fluidized bed units with an integrated heat exchanger designed to burn coal/solid fossil fuel
a. CO (or CEMS)
140 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (150 ppm by volume on a dry basis corrected to 3 percent oxygen, 30-day rolling average)
1.2E-01 lb per MMBtu of steam output or 1.5 lb per MWh; 3-run average
1 hr minimum sampling time.

7. Stokers/sloped grate/others designed to burn wet biomass fuel
a. CO (or CEMS)
620 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (390 ppm by volume on a dry basis corrected to 3 percent oxygen, 30-day rolling average)
5.8E-01 lb per MMBtu of steam output or 6.8 lb per MWh; 3-run average
1 hr minimum sampling time.

b. Filterable PM (or TSM)
3.0E-02 lb per MMBtu of heat input; or (2.6E-05 lb per MMBtu of heat input)
3.5E-02 lb per MMBtu of steam output or 4.2E-01 lb per MWh; or (2.7E-05 lb per MMBtu of steam output or 3.7E-04 lb per MWh)
Collect a minimum of 2 dscm per run.

8. Stokers/sloped grate/others designed to burn kiln-dried biomass fuel
a. CO
460 ppm by volume on a dry basis corrected to 3 percent oxygen
4.2E-01 lb per MMBtu of steam output or 5.1 lb per MWh
1 hr minimum sampling time.

b. Filterable PM (or TSM)
3.0E-02 lb per MMBtu of heat input; or (4.0E-03 lb per MMBtu of heat input)
3.5E-02 lb per MMBtu of steam output or 4.2E-01 lb per MWh; or (4.2E-03 lb per MMBtu of steam output or 5.6E-02 lb per MWh)
Collect a minimum of 2 dscm per run.

9. Fluidized bed units designed to burn biomass/bio-based solids
a. CO (or CEMS)
230 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (310 ppm by volume on a dry basis corrected to 3 percent oxygen, 30-day rolling average)
2.2E-01 lb per MMBtu of steam output or 2.6 lb per MWh; 3-run average
1 hr minimum sampling time.

b. Filterable PM (or TSM)
9.8E-03 lb per MMBtu of heat input; or (8.3E-05 a lb per MMBtu of heat input)
1.2E-02 lb per MMBtu of steam output or 0.14 lb per MWh; or (1.1E-04 a lb per MMBtu of steam output or 1.2E-03 a lb per MWh)
Collect a minimum of 3 dscm per run.

10. Suspension burners designed to burn biomass/bio-based solids
a. CO (or CEMS)
2,400 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (2,000 ppm by volume on a dry basis corrected to 3 percent oxygen, 10-day rolling average)
1.9 lb per MMBtu of steam output or 27 lb per MWh; 3-run average
1 hr minimum sampling time.

b. Filterable PM (or TSM)
3.0E-02 lb per MMBtu of heat input; or (6.5E-03 lb per MMBtu of heat input)
3.1E-02 lb per MMBtu of steam output or 4.2E-01 lb per MWh; or (6.6E-03 lb per MMBtu of steam output or 9.1E-02 lb per MWh)
Collect a minimum of 2 dscm per run.

11. Dutch Ovens/Pile burners designed to burn biomass/bio-based solids
a. CO (or CEMS)
330 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (520 ppm by volume on a dry basis corrected to 3 percent oxygen, 10-day rolling average)
3.5E-01 lb per MMBtu of steam output or 3.6 lb per MWh; 3-run average
1 hr minimum sampling time.

b. Filterable PM (or TSM)
3.2E-03 lb per MMBtu of heat input; or (3.9E-05 lb per MMBtu of heat input)
4.3E-03 lb per MMBtu of steam output or 4.5E-02 lb per MWh; or (5.2E-05 lb per MMBtu of steam output or 5.5E-04 lb per MWh)
Collect a minimum of 3 dscm per run.

12. Fuel cell units designed to burn biomass/bio-based solids
a. CO
910 ppm by volume on a dry basis corrected to 3 percent oxygen
1.1 lb per MMBtu of steam output or 1.0E+01 lb per MWh
1 hr minimum sampling time.

b. Filterable PM (or TSM)
2.0E-02 lb per MMBtu of heat input; or (2.9E-05 a lb per MMBtu of heat input)
3.0E-02 lb per MMBtu of steam output or 2.8E-01 lb per MWh; or (5.1E-05 lb per MMBtu of steam output or 4.1E-04 lb per MWh)
Collect a minimum of 2 dscm per run.

13. Hybrid suspension grate boiler designed to burn biomass/bio-based solids
a. CO (or CEMS)
1,100 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average; or (900 ppm by volume on a dry basis corrected to 3 percent oxygen, 30-day rolling average)
1.4 lb per MMBtu of steam output or 12 lb per MWh; 3-run average
1 hr minimum sampling time.

b. Filterable PM (or TSM)
2.6E-02 lb per MMBtu of heat input; or (4.4E-04 lb per MMBtu of heat input)
3.3E-02 lb per MMBtu of steam output or 3.7E-01 lb per MWh; or (5.5E-04 lb per MMBtu of steam output or 6.2E-03 lb per MWh)
Collect a minimum of 3 dscm per run.

14. Units designed to burn liquid fuel
a. HCl
4.4E-04 lb per MMBtu of heat input
4.8E-04 lb per MMBtu of steam output or 6.1E-03 lb per MWh
For M26A: Collect a minimum of 2 dscm per run; for M26, collect a minimum of 240 liters per run.

b. Mercury
4.8E-07 a lb per MMBtu of heat input
5.3E-07 a lb per MMBtu of steam output or 6.7E-06 a lb per MWh
For M29, collect a minimum of 4 dscm per run; for M30A or M30B, collect a minimum sample as specified in the method; for ASTM D6784 b collect a minimum of 4 dscm.

15. Units designed to burn heavy liquid fuel
a. CO
130 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average
0.13 lb per MMBtu of steam output or 1.4 lb per MWh; 3-run average
1 hr minimum sampling time.

b. Filterable PM (or TSM)
1.3E-02 lb per MMBtu of heat input; or (7.5E-05 lb per MMBtu of heat input)
1.5E-02 lb per MMBtu of steam output or 1.8E-01 lb per MWh; or (8.2E-05 lb per MMBtu of steam output or 1.1E-03 lb per MWh)
Collect a minimum of 3 dscm per run.

16. Units designed to burn light liquid fuel
a. CO
130 ppm by volume on a dry basis corrected to 3 percent oxygen
0.13 lb per MMBtu of steam output or 1.4 lb per MWh
1 hr minimum sampling time.

b. Filterable PM (or TSM)
1.1E-03 a lb per MMBtu of heat input; or (2.9E-05 lb per MMBtu of heat input)
1.2E-03 a lb per MMBtu of steam output or 1.6E-02 a lb per MWh; or (3.2E-05 lb per MMBtu of steam output or 4.0E-04 lb per MWh)
Collect a minimum of 3 dscm per run.

17. Units designed to burn liquid fuel that are non-continental units
a. CO
130 ppm by volume on a dry basis corrected to 3 percent oxygen, 3-run average based on stack test
0.13 lb per MMBtu of steam output or 1.4 lb per MWh; 3-run average
1 hr minimum sampling time.

b. Filterable PM (or TSM)
2.3E-02 lb per MMBtu of heat input; or (8.6E-04 lb per MMBtu of heat input)
2.5E-02 lb per MMBtu of steam output or 3.2E-01 lb per MWh; or (9.4E-04 lb per MMBtu of steam output or 1.2E-02 lb per MWh)
Collect a minimum of 4 dscm per run.

18. Units designed to burn gas 2 (other) gases
a. CO
130 ppm by volume on a dry basis corrected to 3 percent oxygen
0.16 lb per MMBtu of steam output or 1.0 lb per MWh
1 hr minimum sampling time.

b. HCl
1.7E-03 lb per MMBtu of heat input
2.9E-03 lb per MMBtu of steam output or 1.8E-02 lb per MWh
For M26A, Collect a minimum of 2 dscm per run; for M26, collect a minimum of 240 liters per run.

c. Mercury
7.9E-06 lb per MMBtu of heat input
1.4E-05 lb per MMBtu of steam output or 8.3E-05 lb per MWh
For M29, collect a minimum of 3 dscm per run; for M30A or M30B, collect a minimum sample as specified in the method; for ASTM D6784 b collect a minimum of 3 dscm.

d. Filterable PM (or TSM)
6.7E-03 lb per MMBtu of heat input; or (2.1E-04 lb per MMBtu of heat input)
1.2E-02 lb per MMBtu of steam output or 7.0E-02 lb per MWh; or (3.5E-04 lb per MMBtu of steam output or 2.2E-03 lb per MWh)
Collect a minimum of 3 dscm per run.

a If you are conducting stack tests to demonstrate compliance and your performance tests for this pollutant for at least 2 consecutive years show that your emissions are at or below this limit, you can skip testing according to § 63.7515 if all of the other provisions of § 63.7515 are met. For all other pollutants that do not contain a footnote “a”, your performance tests for this pollutant for at least 2 consecutive years must show that your emissions are at or below 75 percent of this limit in order to qualify for skip testing.
b Incorporated by reference, see § 63.14.
c If your affected source is a new or reconstructed affected source that commenced construction or reconstruction after June 4, 2010, and before January 31, 2013, you may comply with the emission limits in Tables 11, 12 or 13 to this subpart until January 31, 2016. On and after January 31, 2016, you must comply with the emission limits in Table 1 to this subpart.
[78 FR 7193, Jan. 31, 2013]